# Organization of Control of the Generalized Power Quality Parameter Using Wald’s Sequential Analysis Procedure

^{1}

^{2}

^{3}

^{4}

^{*}

## Abstract

**:**

## 1. Introduction

_{2}emissions per unit of output. The need for this is due to the 2023 introduction of the carbon tax in the European Union, with goods exported to the EU from countries with high levels of atmospheric CO

_{2}emissions subject to the tax. Thus, the more visible the carbon footprint of an industrial enterprise, the less attractive it will be to consumers and investors.

- THDi < 0.1—normal situation, with no faults in the operation of electrical equipment;
- 0.1 < THDi < 0.5—significant pollution of the EPDN by harmonic components, with the danger of increasing the temperature of electrical equipment, which necessitates the transition to larger cross-sections of cable lines, as well as the use of GUs of DG facilities and backup power supply sources of higher capacity;
- THDi > 0.5—a large degree of pollution of the EPDN by harmonic components, which can lead to failures and shutdowns of electrical equipment due to overheating; requires the installation of filtering and compensation devices.

_{rated}within one or two periods of the utility frequency [14].

- Voltage sags (less than 90% of U
_{rated}in at least one phase); - Voltage interruptions (less than 5% of U
_{rated}phase voltage in all phases); - Overvoltages and surge voltages (switching and atmospheric overvoltages).

- To keep the mix and values of regulated PQPs up to date based on periodic review of regulatory requirements and accumulated statistical data, as well as requirements for the efficiency of manufacturing processes and the quality of manufactured products;
- To determine the current operating conditions of the EPDN on-line;
- To carry out continuous automated data collection and processing, analysis, and reporting on PQP deviations from their standard values;
- To create a statistical database on PQPs for information support of the operation of electric power quality management systems;
- To identify critical areas of the EPDN, where deviations of PQPs are the most significant and occur quite often, which requires the arrangement of their continuous monitoring and control;
- To identify (and contain) sources of current and voltage distortions that may cause significant damage, in order to implement measures to change their operating state or power distribution circuit to mitigate the negative impact;
- To make recommendations addressed to duty officers on the implementation of organizational and engineering measures to bring the PQPs to their standard values;
- To determine the most effective ways of load balancing to compensate harmonic components in currents and voltages generated by a nonlinear load with power electronic components;

^{2}R. These two factors accelerate the processes of reducing the rotation speed and the values of free currents in the rotors of IMs [24].

- Centralized data processing, as a rule, requires a large bandwidth of data transmission channels and significant computing power of the central computing device [28].

## 2. Materials and Methods

- The hypergeometric distribution determines the numerical value of deviations of PQPs that made it to the aggregate sample, while taking into account the decision-making during monitoring on deviations, as governed by the “acceptable/not acceptable” principle. The hypergeometric distribution from the outset assumes the process of sampling and the execution of the monitoring procedure;
- The binomial distribution is used when estimating the aggregate timed sample of a PQP (a composite parameter) when each instantaneous value has a probabilistic nature and may or may not correspond to the established standard values. The sampling-based monitoring procedure in the analysis of the binary “conform/fails to conform” relationship is modeled by the binomial distribution;
- Poisson distribution can be applied when investigating the distribution of non-conformities, including those of individual PQPs at certain time intervals. The use of this distribution to analyze the results of sampling-based monitoring of PQPs is implemented in order to mathematically simplify the relations of hypergeometric and binomial models of monitoring procedures;
- The normal distribution, as a rule, describes the cumulative result of monitoring with respect to alternative PQPs, as well as modeling the distribution of quantitative PQPs as a source of continuous random variables [27].

- Positive $(\rho >0)$, when $\left({\sigma}^{2}\left[D\right]/\left\{M\left[D\right]\times \left(1-M\left[D\right]/N\right)\right\}\right)>1$, or ${\sigma}^{2}\left[D\right]>\left\{M\left[D\right]\times \left(1-M\left[D\right]/N\right)\right\}$;
- Negative $(\rho <0)$, when $\left({\sigma}^{2}\left[D\right]/\left\{M\left[D\right]\times \left(1-M\left[D\right]/N\right)\right\}\right)<1$, or ${\sigma}^{2}\left[D\right]<\left\{M\left[D\right]\times \left(1-M\left[D\right]/N\right)\right\}$;
- Equal to zero $\left(\rho =0\right)$, when $\left({\sigma}^{2}\left[D\right]/\left\{M\left[D\right]\times \left(1-M\left[D\right]/N\right)\right\}\right)=1$, or ${\sigma}^{2}\left[D\right]=\left\{M\left[D\right]\times \left(1-M\left[D\right]/N\right)\right\}$.

## 3. Results

- To form a generalized PQP, which can be used to estimate the comprehensive impact of a set of deviations of individual PQPs on the operation of electrical loads of a particular consumer;
- To determine the ranges of acceptable deviations of the generalized PQP, within which no damage occurs to specific consumers. This problem can be solved using simulation data for various circuit/operating state situations and the operating conditions of a particular consumer, including in the main maintenance circuits of the external distribution network;
- To develop a procedure for sampling-based monitoring of PQPs on the basis of the generalized PQP for subsequent decision-making on the implementation of organizational and technical measures to bring the generalized PQP into the acceptable range.

_{j}is binary and takes the value of 1—under unacceptable PQP deviation with respect to the j-th index—or 0—under acceptable PQP deviation.

_{j}for a particular EPDN can be obtained from the results of simulation or monitoring of PQPs in various conditions of EPDN operation over a long time interval as related to its circuit and operation.

**m**is distributed as governed by the binomial distribution with the probability independent of n, the random variable $\xi $, as a linear combination of asymptotically normal quantities ${m}_{j}$ (j = 1, 2, …, k), also has an asymptotically normal distribution with the expected value ${m}_{\xi}$ and variance ${\sigma}_{\xi}^{2}$:

_{ξ}

_{set}.

_{ξ}is the true mean value, is defined by the following equality:

## 4. Discussion

_{1}… I

_{M}); a comparison unit, including comparison circuits (CC

_{1}… CC

_{N}) for each of the PCIs; a multiplication unit, consisting of N multiplication units for each of the PCIs; a group adder unit; a sequential analysis unit; and a memory unit.

_{i}are fed to the input of the sequential analysis unit. The other input of the sequential analysis unit receives arrays of acceptance a(m) and rejection b(m) numbers, whose components correspond to the setpoint values for each step of the sequential analysis procedure. Figure 3 illustrates the decision-making process in the sequential analysis aided by a generalized PQP, where the sequential analysis process ends with assuming the hypothesis of an unacceptable deviation of the generalized PQP from the standard value.

## 5. Conclusions

## Author Contributions

## Funding

## Data Availability Statement

## Conflicts of Interest

## Abbreviations

PQP | Power quality parameter |

EPDN | Electric power distribution network |

GU | Generating unit |

DG | Distributed generation |

RES | Renewable energy source |

ESS | Electricity storage system |

THDi | Total harmonic current distortion |

IM | Induction motor |

DSP | Digital signal processor |

FPGA | Field-programmable gate array |

ASIC | Application-specific integrated circuit |

PQMS | Power quality monitoring system |

SCADA | Supervisory control and data acquisition |

## References

- Zeng, B.; Wen, J.; Shi, J.; Zhang, J.; Zhang, Y. A multi-level approach to active distribution system planning for efficient renewable energy harvesting in a deregulated environment. Energy
**2016**, 96, 614–624. [Google Scholar] [CrossRef] - Ghadi, M.; Rajabi, A.; Ghavidel, S.; Azizivahed, A.; Li, L.; Zhang, J. From active distribution systems to decentralized microgrids: A review on regulations and planning approaches based on operational factors. Appl. Energy
**2019**, 253, 113543. [Google Scholar] [CrossRef] - Begovic, M.M. (Ed.) Electrical Transmission Systems and Smart Grids: Selected Entries from the Encyclopedia of Sustainability Science and Technology; Springer Science + Business Media: New York, NY, USA, 2013. [Google Scholar]
- Alberto Escalera, A.; Prodanović, M.; Castronuovo, E.D. Analytical methodology for reliability assessment of distribution networks with energy storage in islanded and emergency-tie restoration modes. Int. J. Electr. Power Energy Syst.
**2019**, 107, 735–744. [Google Scholar] [CrossRef] - Schwan, M.; Ettinger, A.; Gunaltay, S. Probabilistic reliability assessment in distribution network master plan development and in distribution automation implementation. In Proceedings of the CIGRE, 2012 Session, Paris, France, 26–30 August 2012; p. C4-203. [Google Scholar]
- Varma, R.K.; Rahman, S.A.; Vanderheide, T.; Dang, M.D.N. Harmonic impact of a 20-MW PV solar farm on a utility distribution network. IEEE Power Energy Technol. Syst. J.
**2016**, 3, 89–98. [Google Scholar] [CrossRef] - Torquato, R.; Freitas, W.; Hax, G.R.T.; Donadon, A.R.; Moya, R. High frequency harmonic distortions measured in a Brazilian solar farm. In Proceedings of the 17th International Conference on Harmonics and Quality of Power (ICHQP), Belo Horizonte, Brazil, 16–19 October 2016; pp. 623–627. [Google Scholar]
- IEEE STD 519-2014; Recommended practices and requirements for harmonic control in electrical power systems/Transmission and Distribution Committee of the IEEE Power and Energy Society. The Institute of Electrical and Electronics Engineers: New York, NY, USA, 2014.
- Filippov, S.P.; Dilman, M.D.; Ilyushin, P.V. Distributed Generation of Electricity and Sustainable Regional Growth. Therm. Eng.
**2019**, 66, 869–880. [Google Scholar] [CrossRef] - Shushpanov, I.; Suslov, K.; Ilyushin, P.; Sidorov, D. Towards the flexible distribution networks design using the reliability performance metric. Energies
**2021**, 14, 6193. [Google Scholar] [CrossRef] - Adineh, B.; Keypour, R.; Sahoo, S.; Davari, P.; Blaabjerg, F. Robust optimization based harmonic mitigation method in islanded microgrids. Int. J. Electr. Power Energy Syst.
**2022**, 137, 107631. [Google Scholar] [CrossRef] - Bahrami, M.; Eslami, S.; Zandi, M.; Gavagsaz-ghoachani, R.; Payman, A.; Phattanasak, M.; Nahid-Mobarakeh, B.; Pierfederici, S. Predictive based reliability analysis of electrical hybrid distributed generation. In Proceedings of the International Conference on Science and Technology (TICST), Pathum Thani, Thailand, 4–6 November 2015. [Google Scholar]
- Saha, S.; Saleem, M.I.; Roy, T.K. Impact of high penetration of renewable energy sources on grid frequency behavior. Int. J. Electr. Power Energy Syst.
**2022**, 145, 108701. [Google Scholar] [CrossRef] - Li, W. Risk Assessment of Power Systems: Models, Methods and Applications; John Wiley and Sons: New York, NY, USA, 2005. [Google Scholar]
- McDonald, J.D.F.; Pal, B.C. Representing the risk imposed by different strategies of distribution system operation. In Proceedings of the 2006 IEEE PES General Meeting, Montreal, Canada, 18–22 June 2006. [Google Scholar]
- Ilyushin, P.V. Emergency and post-emergency control in the formation of micro-grids. E3S Web Conf.
**2017**, 25, 02002. [Google Scholar] [CrossRef] [Green Version] - Gurevich, Y.E.; Kabikov, K.V. Peculiarities of Power Supply, Aimed at Failure-Free Operation of Industrial Consumers; ELEKS-KM: Moscow, Russia, 2005. (In Russian) [Google Scholar]
- Gurevich, Y.E.; Libova, L.E. Application of Mathematical Models of Electrical Load in Calculation of the Power Systems Stability and Reliability of Power Supply to Industrial Enterprises; ELEKS-KM: Moscow, Russia, 2008. (In Russian) [Google Scholar]
- Lacommare, K.; Eto, J. Cost of power interruptions to electricity consumers in the United States (US). Energy
**2006**, 31, 1845–1855. [Google Scholar] [CrossRef] [Green Version] - Suslov, K.V.; Solonina, N.N.; Smirnov, A.S. Distributed power quality monitoring. In Proceedings of the IEEE 16th International Conference on Harmonics and Quality of Power (ICHQP), Bucharest, Romania, 25–28 May 2014; pp. 517–520. [Google Scholar]
- Gallego, L.; Torres, H.; Pavas, A.; Urrutia, D.; Cajamarca, G.; Rondón, D. A Methodological proposal for monitoring, analyzing and estimating power quality indices: The case of Bogotá—Colombia. In Proceedings of the IEEE Power Tech 2005, St Peterburg, Russia, 27–30 June 2005. [Google Scholar]
- Gavrilov, D.; Gouzman, M.; Luryi, S. Monitoring large-scale power distribution grids. Solid-State Electron.
**2019**, 155, 57–64. [Google Scholar] [CrossRef] - Byk, F.L.; Myshkina, L.S.; Khokhlova, K. Power supply reliability indexes. In Proceedings of the International Conference on Actual Issues of Mechanical Engineering, Tomsk, Russia, 27–29 July 2017; pp. 525–530. [Google Scholar]
- Bollen, M.H.J.; Dirix, P.M.E. Simple model for post-fault motor behaviours for reliability/power quality assessment of industrial power systems. IEE Proc. Gener. Transm. Distrib.
**1996**, 143, 56–60. [Google Scholar] [CrossRef] - Ribeiro, P.F.; Duque, C.A.; Silveira, P.M.; Cerqueira, A.S. Power Systems Signal Processing for Smart Grids; John Wiley & Sons Ltd.: Hoboken, NJ, USA, 2014. [Google Scholar]
- Kulikov, A.L.; Ilyushin, P.V.; Suslov, K.V.; Karamov, D.N. Coherence of digital processing of current and voltage signals at decimation for power systems with a large share of renewable power stations. Energy Rep.
**2022**, 8, 1464–1478. [Google Scholar] [CrossRef] - Knowler, L.A.; Howell, J.M.; Gold, B.K.; Coleman, E.P.; Moan, O.B.; Knowler, W.S. Statistical Methods of Product Quality Control; McGraw-Hill Book Company: New York, NY, USA, 1989. [Google Scholar]
- Won, D.-J.; Chung, I.-Y.; Kim, J.-M.; Moon, S.-I.; Seo, J.-C.; Choe, J.-W. Development of power quality monitoring system with central processing scheme. In Proceedings of the IEEE Power Engineering Society Summer Meeting, Chicago, IL, USA, 21–25 July 2002; Volume 2, pp. 915–919. [Google Scholar]
- Marple, S.L., Jr. Digital Spectrum Analysis with Applications; Prentice Hall: Hoboken, NJ, USA, 1987. [Google Scholar]
- Won, D.-J.; Chung, I.-Y.; Kim, J.-M.; Moon, S.-I.; Seo, J.-C.; Choe, J.-W. A new algorithm to locate power-quality event source with improved realization of distributed monitoring scheme. IEEE Trans. Power Deliv.
**2006**, 21, 1641–1647. [Google Scholar] [CrossRef] - Valsan, S.P.; Swarup, K.S. Wavelet transform based digital protection for transmission lines. Int. J. Electr. Power Energy Syst.
**2009**, 31, 379–388. [Google Scholar] [CrossRef] - McGranaghan, M.F.; Santoso, S. Challenges and trends in analysis of electric power quality measurement data. EURASIP J. Adv. Signal Process.
**2007**, 2007, 057985. [Google Scholar] [CrossRef] [Green Version] - Kulikov, A.L.; Misrikhanov, M.S. Introduction to Methods of Digital Relay Protection of High-Voltage Transmission Lines; Energoatomizdat: Moscow, Russia, 2007. (In Russian) [Google Scholar]
- Kezunovic, M.; Meliopoulos, S.; Venkatasubramanian, V.; Vittal, V. Application of Time-Synchronized Measurements in Power System Transmission Networks; Springer: New York, NY, USA, 2014. [Google Scholar]
- Ilyushin, P.V.; Shepovalova, O.V.; Filippov, S.P.; Nekrasov, A.A. Calculating the Sequence of Stationary Modes in Power Distribution Networks of Russia for Wide-Scale Integration of Renewable Energy Based Installations. Energy Rep.
**2021**, 7, 308–327. [Google Scholar] [CrossRef] - NASPI. Synchrophasor Monitoring for Distribution Systems: Technical Foundations and Applications; A White Paper by the NASPI Distribution Task Team NASPI-2018-TR-001; NASPI: Tempe, AZ, USA, 2018. [Google Scholar]
- Edomah, N. Effects of voltage sags, swell and other disturbances on electrical equipment and their economic implications. In Proceedings of the 20th International Conference and Exhibition on Electricity Distribution, Prague, Czech Republic, 8–11 June 2009; pp. 1–4. [Google Scholar]
- Ilyushin, P.V.; Sukhanov, O.A. The Structure of Emergency-Management Systems of Distribution Networks in Large Cities. Russ. Electr. Eng.
**2014**, 85, 133–137. [Google Scholar] [CrossRef] - Wentzel, E.S. Probability Theory (First Steps); Mir: Moscow, Russia, 1986. [Google Scholar]
- Won, D.J.; Chung, I.Y.; Kim, J.M.; Ahn, S.J.; Moon, S.I. A modified voltage sag duration for power quality diagnosis. Proc. IFAC
**2003**, 36, 739–743. [Google Scholar] [CrossRef] - Won, D.J.; Ahn, S.J.; Moon, S.I. A modified sag characterization using voltage tolerance curve for power quality diagnosis. IEEE Trans. Power Deliv.
**2005**, 20, 2638–2643. [Google Scholar] [CrossRef] - Cowden, D.J. Statistical Methods in Quality Control; Prentice-Hall, Inc.: Englewood Cliffs, NJ, USA, 1957. [Google Scholar]
- Shor, Y.B. Statistical Methods of Analysis and Quality Control and Reliability; Soviet Radio: Moscow, Russia, 1962. (In Russian) [Google Scholar]
- Belyaev, Y.K. Probabilistic Sampling Methods; Nauka: Moscow, Russia, 1975. (In Russian) [Google Scholar]
- EN 50160:2019; Voltage Characteristics of Electricity Supplied by Public Electricity Networks. European Committee for Standards: Brussels, Belgium, 2019; 34p.
- ANSI C84.1-2020; Electric Power Systems and Equipment—Voltage Ratings (60 Hz). American National Standards Institute: Washington, DC, USA, 2020; 21p.
- Wald, A. Sequential Analysis; John Wiley and Sons: New York, NY, USA, 1947. [Google Scholar]
- Ayvazyan, S.A.; Mkhitaryan, V.S. Applied Statistics and Fundamentals of Econometrics: A Textbook for High Schools; UNITY: Moscow, Russia, 1998; 1022p. [Google Scholar]
- Suslov, K.; Shushpanov, I.; Buryanina, N.; Ilyushin, P. Flexible power distribution networks: New opportunities and applications. In Proceedings of the 9th International Conference on Smart Cities and Green ICT Systems, Prague, Czech Republic, 2–4 May 2020; Volume 1, pp. 57–64. [Google Scholar]
- Ilyushin, P.V.; Suslov, K.V. Operation of automatic transfer switches in the networks with distributed generation. In Proceedings of the 2019 IEEE Milan PowerTech, Milan, Italy, 23–27 June 2019. [Google Scholar] [CrossRef]

**Figure 1.**A transient in the EPDN of an industrial enterprise during a near-to-generator three-phase short circuit in the external distribution network.

**Figure 3.**The process of sequential decision-making regarding the deviations of the generalized PQP.

**Figure 4.**Structural diagram of the device that implements the sampling-based monitoring procedure of the generalized PQP.

**Table 1.**Values of the variables used in the sequential decision-making procedure regarding the deviations of the generalized PQP.

m | 1 | 2 | 3 | 4 | 5 | 6 | 7 | 8 | 9 |
---|---|---|---|---|---|---|---|---|---|

ξ | 149 | 151 | 154 | 155 | 148 | 160 | 156 | 154 | 150 |

${\displaystyle \sum}_{i=1}^{m}}{\xi}_{i$ | 149 | 300 | 454 | 609 | 757 | 917 | 1123 | 1287 | 1437 |

a(m) | 55 | 197.5 | 340 | 482.5 | 625 | 767.5 | 910 | 1052.5 | 1195 |

b(m) | 256.9 | 399.4 | 541.9 | 684.4 | 826.9 | 969.4 | 1111.9 | 1254.4 | 1396.9 |

Disclaimer/Publisher’s Note: The statements, opinions and data contained in all publications are solely those of the individual author(s) and contributor(s) and not of MDPI and/or the editor(s). MDPI and/or the editor(s) disclaim responsibility for any injury to people or property resulting from any ideas, methods, instructions or products referred to in the content. |

© 2023 by the authors. Licensee MDPI, Basel, Switzerland. This article is an open access article distributed under the terms and conditions of the Creative Commons Attribution (CC BY) license (https://creativecommons.org/licenses/by/4.0/).

## Share and Cite

**MDPI and ACS Style**

Kulikov, A.; Ilyushin, P.; Suslov, K.; Filippov, S.
Organization of Control of the Generalized Power Quality Parameter Using Wald’s Sequential Analysis Procedure. *Inventions* **2023**, *8*, 17.
https://doi.org/10.3390/inventions8010017

**AMA Style**

Kulikov A, Ilyushin P, Suslov K, Filippov S.
Organization of Control of the Generalized Power Quality Parameter Using Wald’s Sequential Analysis Procedure. *Inventions*. 2023; 8(1):17.
https://doi.org/10.3390/inventions8010017

**Chicago/Turabian Style**

Kulikov, Aleksandr, Pavel Ilyushin, Konstantin Suslov, and Sergey Filippov.
2023. "Organization of Control of the Generalized Power Quality Parameter Using Wald’s Sequential Analysis Procedure" *Inventions* 8, no. 1: 17.
https://doi.org/10.3390/inventions8010017