# HVAC Optimization Genetic Algorithm for Industrial Near-Zero-Energy Building Demand Response

^{1}

^{2}

^{3}

^{4}

^{*}

## Abstract

**:**

## 1. Introduction

- An original demand response optimization scheme is developed to include cost of energy and predicted mean vote (PMV) as the two criteria merged into one objective function. Along with HVAC hourly set points used as the variables of GA optimization, the developed approach constitutes a powerful assessment and decision tool which can be used to identify and ultimately apply dominant HVAC set point patterns based on actual weather conditions and preferences with regard to indoor conditions.
- The optimization algorithm coupled with the validated dynamic thermal model of the building enables the assessment of energy cost, energy savings, and thermal comfort for a wide range of temperature set point patterns and RTP schemes.
- The developed approach is designed to assess RTP schemes based on real DA market information to take advantage of price fluctuations which reflect current market operations in the optimization process.

## 2. Methodology and Infrastructure

#### 2.1. Methodology

_{HVAC}, kW), indoor air temperature (T

_{air}, °C), indoor radiant temperature (T

_{rad}, °C), and relative humidity (RH, %) for the period of interest (in this case, 2018). Fourthly, day-ahead pricing information was used to create the DARTP model required for the optimization. Day-ahead energy prices (€/MWh) for the region of central–northern Italy were used as the main component for the formulation of the energy pricing scheme used in the optimization. Additional costs related to transmission/distribution, as well as other costs and taxes, were included to define the final energy pricing profile. Fifthly, a genetic algorithm was constructed to optimize the objective function composed by (a) the daily sum of hourly cost of energy, and (b) the daily average of hourly PMV values for the working hours of the building and specifically from 9:00 a.m. to 6:00 p.m. In the GA optimization scheme, HVAC temperature set points were used as the discrete decision variables subject to upper and lower boundaries which differed between the heating and cooling seasons. Lastly, simulation of the validated building thermal model was executed in an iterative process using the set points selected by the GA until convergence criteria were met. Simulation output values of HVAC power, indoor air temperature, radiative temperature, and relative humidity were used to evaluate energy cost and the PMV at each iteration.

#### 2.2. Infrastructure

^{2}K and double-glazed windows with U-values between 1.793 and 3.194 W/m

^{2}K. It is equipped with an advanced energy management system controlling HVAC, artificial lights, energy from PV, and sensible thermal storage facilities. The building is equipped with a 236.5-kWp rooftop PV installation, a 400-m

^{3}thermal storage water tank, ground water heat pumps (heating coefficient of performance (COP) of 4.8, cooling energy efficiency ratio (EER) of 6.2–7), smart artificial light controls based on illuminance/presence sensors, and automatic rotating external window louvers. Operations are monitored and managed by MyLeaf, a state-of-the-art proprietary energy management platform customized for testing and integrating new concepts and technologies.

#### 2.2.1. GA optimisation model

- Metabolic (M) rate in W/m
^{2}; - Effective mechanical power (W) in W/m
^{2}; - Clothing insulation (Icl) in (m
^{2}K/W); - Air temperature in (°C);
- Mean radiant temperature (°C);
- Relative air velocity (m/s);
- Relative humidity (RH, %).

#### 2.2.2. Cost of energy model

## 3. Results and Discussion

^{2}and a height of 8 m, surrounded by various other spaces including offices, meeting rooms, and other facilities on two floors. Following a number of trials, the population size of the GA was set to 50, the crossover fraction was set to 0.8, and the maximum number of iterations was set to 4,600 in order to examine a wide range of different solutions. Based on the set of the results, solutions were obtained to identify the set point patterns associated with optimum levels of energy and cost savings, as well as compliance with well-established standards of thermal comfort and temperature set point drift. The approach was designed to evaluate energy cost on a 24-h time frame. Representative results for four winter days, two days for autumn, one for summer, and one for spring are presented to account for different seasonal climatic conditions, heating and cooling modes, and DA pricing profiles.

## 4. Conclusions and Future Steps

## Author Contributions

## Funding

## Conflicts of Interest

## Nomenclature

${T}_{s}{}_{i=1}^{24}$ | hourly temperature set points of the HVAC system the next day |

${w}_{c}$ | weighting coefficient for the daily operational cost of energy for the HVAC |

${w}_{pmv}$ | weighting coefficient for the daily thermal comfort |

${C}_{i}$ | day-ahead price per hour for hours 1–24 |

${P}_{i}$ | hourly average power consumption of the HVAC in kW (equivalent to kWh) |

${C}_{T}$ | total energy bill (€) |

IVA | value added tax (€) |

${C}_{E}$ | total energy charges (€) |

${C}_{T}$ | total tax charges (€) |

${C}_{S}$ | energy procurement cost (€) |

${C}_{N}$ | network services cost (€) |

${C}_{S,F}$ | energy procurement fixed cost component (€/kWh) |

${C}_{EDD}$ | daily excise duty on electricity and taxes (€) |

${C}_{v,u}$ | various costs normalized per kWh (€/Wh) |

$D{A}_{h}$ | day-ahead market prices (€/kWh) |

${C}_{F}$ | fixed cost component (€) |

${C}_{Pmax}$ | maximum power cost component (€/kW) |

${C}_{AT}$ | active energy cost component (€/kWh) |

${C}_{A-UC}$ | fixed cost for up to 4 GWh per month (€/kWh) |

$D{A}_{N,h}$ | DA price flexible factor per hour $h$ (€/kWh) |

${C}_{EDH}$ | excise duty per kWh (€/kWh) |

${C}_{FAA}$ | parameter to account for F, AT, and A-UC components (€/kWh) |

${C}_{Pmax,F}$ | maximum power fixed cost component (€/kW) |

Abbreviations | |

ADR | automated demand response |

AMI | advanced metering infrastructure |

COP | coefficient of performance |

CPP | critical peak pricing |

DA | day-ahead |

DER | distributed energy resources |

DR | demand response |

DSM | demand side management |

EER | energy efficiency ratio |

GA | genetic algorithm |

HVAC | heating, ventilation, and air conditioning |

MIP | Mixed Integer Programming |

MILP | mixed-integer linear problem |

MINLP | mixed-integer non-linear problem |

PMV | predicted mean vote |

PPD | percentage of people dissatisfied |

PV | photovoltaic |

RES | renewable energy sources |

RH | relative humidity |

RTP | real-time pricing |

R&D | Research and Development |

SDG | sustainable development goal |

ToU | time of use |

## References

- Albadi, M.H.; El-Saadany, E.F. A summary of demand response in electricity markets. Electr. Power Syst. Res.
**2008**, 78, 1989–1996. [Google Scholar] [CrossRef] - Siano, P. Demand response and smart grids—A survey. Renew. Sustain. Energy Rev.
**2014**, 30, 461–478. [Google Scholar] [CrossRef] - Mccollum, D.; Gomez, L.; Riahi, E.K.; Parkinson, S. A Guide to SDG Interactions: From Science to Implementation. 2017. Available online: http://www.icsu.org/publications/a-guide-to-sdg-interactions-from-science-to-implementation (accessed on 1 April 2019).
- Palensky, P.; Dietrich, D. Demand side management: Demand response, intelligent energy systems, and smart loads. IEEE Trans. Ind. Inf.
**2011**, 7, 381–388. [Google Scholar] [CrossRef] - Doostizadeh, M.; Ghasemi, H. A day-ahead electricity pricing model based on smart metering and demand-side management. Energy
**2012**, 46, 221–230. [Google Scholar] [CrossRef] - Li, Y.; Yang, Z.; Zhao, D.; Lei, H.; Cui, B.; Li, S. Incorporating energy storage and user experience in isolated microgrid dispatch using a multi-objective model. IET Renew. Power Gener.
**2019**, 13, 973–981. [Google Scholar] [CrossRef] - Li, Y.; Yang, Z.; Li, G.; Mu, Y.; Zhao, D.; Chen, C.; Shen, B. Optimal scheduling of isolated microgrid with an electric vehicle battery swapping station in multi-stakeholder scenarios: A bi-level programming approach via real-time pricing. Appl. Energy
**2018**, 232, 54–68. [Google Scholar] [CrossRef] [Green Version] - Good, N.; Ellis, K.A.; Mancarella, P. Review and classification of barriers and enablers of demand response in the smart grid. Renew. Sustain. Energy Rev.
**2017**, 72, 57–72. [Google Scholar] [CrossRef] [Green Version] - Vallés, M.; Reneses, J.; Cossent, R.; Frías, P. Regulatory and market barriers to the realization of demand response in electricity distribution networks: A European perspective. Electr. Power Syst. Res.
**2016**, 140, 689–698. [Google Scholar] [CrossRef] - Torriti, J.; Hassan, M.G.; Leach, M. Demand response experience in Europe: Policies, programmes and implementation. Energy
**2010**, 35, 1575–1583. [Google Scholar] [CrossRef] [Green Version] - OpenADR 2.0 Demand Response Program Implementation Guide. OpenADR Alliance
**2014**, 1–91. - Faruqui, A.; Hledik, R.; George, S.S.; Bode, J.; Mangasarian, P.; Rohmund, I.; Wikler, G.; Ghosh, D.; Yoshida, S. A National Assessment of Demand Response Potential; FERC: Washington, DC, USA, 2009.
- Shariatzadeh, F.; Mandal, P.; Srivastava, A.K. Demand response for sustainable energy systems: A review, application and implementation strategy. Renew. Sustain. Energy Rev.
**2015**, 45, 343–350. [Google Scholar] [CrossRef] - Vardakas, J.; Zorba, N.; Verikoukis, C. A Survey on Demand Response in Smart Grids. IEEE Trans. Ind. Inf.
**2015**, 11, 1–8. [Google Scholar] - Motegi, N.; Piete, M.A.; Watson, D.S.; Kiliccote, S.; Xu, P. Introduction to Commercial Building Control Strategies and Techniques for Demand Response; Lawrence Berkeley National Laboratory: Berkeley, CA, USA, 2007.
- Mathieu, J.L. Modeling, Analysis, and Control of Demand Response Resources. Ph.D Thesis, University California, Berkeley, CA, USA, 2012. [Google Scholar] [Green Version]
- Goldman, C.; Reid, M.; Levy, R.; Silverstein, A. National Action Plan for Energy Efficiency, Coordination of Energy Efficiency and Demand Response. 2010. Available online: https://www.epa.gov/sites/production/files/2015-08/documents/ee_and_dr.pdf (accessed on 7 June 2019).
- Pérez-Lombard, L.; Ortiz, J.; Pout, C. A review on buildings energy consumption information. Energy Build.
**2008**, 40, 394–398. [Google Scholar] [CrossRef] - Dounis, A.I.; Caraiscos, C. Advanced control systems engineering for energy and comfort management in a building environment—A review. Renew. Sustain. Energy Rev.
**2009**, 13, 1246–1261. [Google Scholar] [CrossRef] - Harish, V.S.K.V.; Kumar, A. A review on modeling and simulation of building energy systems. Renew. Sustain. Energy Rev.
**2016**, 56, 1272–1292. [Google Scholar] [CrossRef] - Afram, A.; Janabi-Sharifi, F. Review of modeling methods for HVAC systems. Appl. Therm. Eng.
**2014**, 67, 507–519. [Google Scholar] [CrossRef] - Afroz, Z.; Shafiullah, G.M.; Urmee, T.; Higgins, G. Modeling techniques used in building HVAC control systems: A review. Renew. Sustain. Energy Rev.
**2018**, 83, 64–84. [Google Scholar] [CrossRef] - Okochi, G.S.; Yao, Y. A review of recent developments and technological advancements of variable-air-volume (VAV) air-conditioning systems. Renew. Sustain. Energy Rev.
**2016**, 59, 784–817. [Google Scholar] [CrossRef] - Wang, S.; Ma, Z.; Wang, S. Supervisory and Optimal Control of Building HVAC Systems: A Review Supervisory and Optimal Control of Building HVAC Systems: A Review. HVAC R Res.
**2008**, 14, 3–32. [Google Scholar] [CrossRef] - Lin, H.-W.; Hong, T. On variations of space-heating energy use in office buildings. Appl. Energy
**2013**, 111, 515–528. [Google Scholar] [CrossRef] [Green Version] - Papantoniou, S.; Kolokotsa, D.; Kalaitzakis, K. Building optimization and control algorithms implemented in existing BEMS using a web based energy management and control system. Energy Build.
**2015**, 98, 45–55. [Google Scholar] [CrossRef] - Risbeck, M.J.; Maravelias, C.T.; Rawlings, J.B.; Turney, R.D. A mixed-integer linear programming model for real-time cost optimization of building heating, ventilation, and air conditioning equipment. Energy Build.
**2017**, 142, 220–235. [Google Scholar] [CrossRef] - Pombeiro, H.; Machado, M.J.; Silva, C. Dynamic programming and genetic algorithms to control an HVAC system: Maximizing thermal comfort and minimizing cost with PV production and storage. Sustain. Cities Soc.
**2017**, 34, 228–238. [Google Scholar] [CrossRef] - Serra, J.; Pubill, D.; Vázquez, M.Á.; Verikoukis, C. Experimental evaluation of an HVAC system under dynamic pricing with comfort constraints. In Proceedings of the 2014 IEEE PES Innov. Smart Grid Technol. Conf. ISGT 2014, Washington, DC, USA, 19–22 February 2014. [Google Scholar]
- Alhaider, M.; Fan, L. Mixed integer programming for HVACs operation. IEEE Power Energy Soc. Gen. Meet.
**2015**, 2015, 1–5. [Google Scholar] - Ma, K.; Yuan, C.; Yang, J.; Liu, Z.; Guan, X. Switched Control Strategies of Aggregated Commercial HVAC Systems for Demand Response in Smart Grids. Energies
**2017**, 10, 953. [Google Scholar] [CrossRef] - Lee, Y.M.; Horesh, R.; Liberti, L. Simulation and optimization of energy efficient operation of HVAC system as demand response with distributed energy resources. In Proceedings of the 2015 Winter Simulation Conference (WSC), Huntington Beach, CA, USA, 6–9 December 2015; pp. 991–999. [Google Scholar]
- Zhang, Y.; Zeng, P.; Zang, C. Multi-objective optimal control algorithm for HVAC based on particle swarm optimization. In Proceedings of the Fifth International Conference on Intelligent Control and Information Processing, Dalian, China, 18–20 August 2014; pp. 417–423. [Google Scholar]
- Kampelisa, N.; Gobakisa, K.; Vagiasa, V.; Kolokotsaa, D.; Standardib, L.; Isidorib, D.; Cristallib, C.; Montagninocd, F.M.; Paredescd, F.; Muratore, P. Evaluation of the performance gap in industrial, residential & tertiary near-Zero energy buildings. Energy Build.
**2017**, 148, 58–73. [Google Scholar] [Green Version] - EN ISO 7730. Ergonomics of the Thermal Environment—Analytical Determination and Interpretation of Thermal Comfort using Calculation of the PMV and PPD Indices and Local Thermal Comfort Criteria (ISO 7730:2005). CEN, 2006. Available online: https://www.iso.org/standard/39155.html (accessed on 7 June 2019).

**Figure 1.**Genetic algorithm (GA)-based heating, ventilation, and air conditioning (HVAC) temperature set point optimization scheme.

© 2019 by the authors. Licensee MDPI, Basel, Switzerland. This article is an open access article distributed under the terms and conditions of the Creative Commons Attribution (CC BY) license (http://creativecommons.org/licenses/by/4.0/).

## Share and Cite

**MDPI and ACS Style**

Kampelis, N.; Sifakis, N.; Kolokotsa, D.; Gobakis, K.; Kalaitzakis, K.; Isidori, D.; Cristalli, C.
HVAC Optimization Genetic Algorithm for Industrial Near-Zero-Energy Building Demand Response. *Energies* **2019**, *12*, 2177.
https://doi.org/10.3390/en12112177

**AMA Style**

Kampelis N, Sifakis N, Kolokotsa D, Gobakis K, Kalaitzakis K, Isidori D, Cristalli C.
HVAC Optimization Genetic Algorithm for Industrial Near-Zero-Energy Building Demand Response. *Energies*. 2019; 12(11):2177.
https://doi.org/10.3390/en12112177

**Chicago/Turabian Style**

Kampelis, Nikolaos, Nikolaos Sifakis, Dionysia Kolokotsa, Konstantinos Gobakis, Konstantinos Kalaitzakis, Daniela Isidori, and Cristina Cristalli.
2019. "HVAC Optimization Genetic Algorithm for Industrial Near-Zero-Energy Building Demand Response" *Energies* 12, no. 11: 2177.
https://doi.org/10.3390/en12112177