# Cooling Effectiveness of a Data Center Room under Overhead Airflow via Entropy Generation Assessment in Transient Scenarios

^{1}

^{2}

^{3}

^{*}

## Abstract

**:**

## 1. Introduction

## 2. Motivation and Goals

## 3. Mathematical Model and Numerical Implementation

- The room transfers no heat to the outside (adiabatic walls),
- Fully-contained aisle, in other words, air only flows through servers and heat exchangers,
- Heat conduction allowed through the aisle containment walls,
- Fluid flow in the turbulent regime,
- Constant server heat dissipation of 1 kW, for a total of 100 kW of required overhead cooling.

#### 3.1. Airside

#### 3.2. Server Transient Model

#### 3.3. Heat Exchanger Transient Model

#### 3.4. Entropy Generation

- Servers: heat transfer between the electronics and the cooling air; pressure drop as the air flows through the server, undergoing significant impedance
- Overhead heat exchangers: heat transfer between the chilled water and the airflow
- Airside: the temperature difference between the room and the aisle induces heat transfer through the containment walls; turbulent viscous dissipation of momentum becomes non-negligible

- ${\dot{S}}_{\mathrm{gen},\overline{\mathrm{D}}}^{\u2034}$: Entropy Generation by direct dissipation.
- ${\dot{S}}_{\mathrm{gen},{\mathrm{D}}^{\prime}}^{\u2034}$: Entropy Generation by turbulent dissipation.
- ${\dot{S}}_{\mathrm{gen},\overline{\mathrm{C}}}^{\u2034}$: Entropy Generation by heat conduction.
- ${\dot{S}}_{\mathrm{gen},{\mathrm{C}}^{\prime}}^{\u2034}$: Entropy Generation by heat transfer with fluctuating temperature gradients.

#### 3.5. Numerical Procedure

^{TM}. The velocity and pressure fields were coupled using the SIMPLE algorithm, and the nodes were interpolated via a second order upwind scheme.

^{TM}. We considered air as an ideal gas and assumed both the impedance and fan curves as a quadratic function of the mass flow rate, obtaining server volumetric flow rates of approximately 50 CFM.

- Fluent computes the Airside turbulent flow and moves the solution forward by one time step
- The airflow data are used as inputs to the servers and heat exchangers
- MATLAB solves the servers and heat exchangers
- MATLAB output data become inlet boundary conditions for Fluent, and the fluid flow is updated
- Go back to Step 1 under these new conditions

#### 3.6. Grid Independence

## 4. Steady State Analysis

#### Entropy Generation in an Idealized Case

## 5. Unsteady Behavior during the Cooling Process

## 6. Conclusions

- The server temperature distributed uniformly throughout the racks. The positioning of the overhead heat exchangers allowed for the cooling airflow to undergo less resistance than the common perforated tile flow. This led to a uniform distribution of cold fluid entering the servers.
- Aisle containment reduced the Entropy Generation in the Airside to negligible levels when compared to previous results from a legacy data center.
- Using a second law analysis, we determined the room cooling efficacy, which quantified the deviation of server thermal management from optimum operation.
- In terms of cooling performance, the OUF and the ODF approaches showed nearly identical results (under the constraints of our idealized analysis); selecting the correct scheme might potentially depend on other aspects, e.g., geometrical, mechanical, economical.
- The unsteady first and second law metrics presented in this numerical study show promise towards the grand goal of providing instantaneous thermal management as the data center demands it.

## Author Contributions

## Funding

## Acknowledgments

## Conflicts of Interest

## References

- Hong-Koo, N.; Song, K.S.; Chun, S.K. The cooling characteristics on the air supply and return flow system in the telecommunication cabinet room. In Proceedings of the INTELEC—Twentieth International Telecommunications Energy Conference, San Francisco, CA, USA, 4–8 Octorber 1998; pp. 777–784. [Google Scholar]
- Nakao, M.; Hayama, H.; Nishioka, M. Which cooling air supply system is better for a high heat density room: Underfloor or overhead? In Proceedings of the Thirteenth International Telecommunications Energy Conference—INTELEC 91, Kyoto, Japan, 5–8 November 1991; pp. 393–400. [Google Scholar]
- Sorell, V.; Escalante, S.; Yang, J. Comparison of Overhead and Underfloor Air Delivery Systems in a Data Center Environment Using CFD Modeling. ASHRAE Trans.
**2005**, 111, 756–764. [Google Scholar] - Cho, J.; Lim, T.; Kim, B.S. Measurements and predictions of the air distribution systems in high compute density (Internet) data centers. Energy Build.
**2009**, 41, 1107–1115. [Google Scholar] [CrossRef] - Heydari, A.; Sabounchi, P. Refrigeration assisted spot cooling of a high heat density data center. In Proceedings of the Ninth Intersociety Conference on Thermal and Thermomechanical Phenomena in Electronic Systems, Las Vegas, NV, USA, 1–4 June 2004; pp. 601–606. [Google Scholar]
- Heydari, A. Thermodynamics Energy Efficiency Analysis and Thermal Modeling of Data Center Cooling Using Open and Closed-Loop Cooling Systems. In Proceedings of the ASME 2007 InterPACK Conference collocated with the ASME/JSME 2007 Thermal Engineering Heat Transfer Summer Conference, Vancouver, BC, Canada, 8–12 July 2007; pp. 859–870. [Google Scholar]
- Wu, K. A comparative study of various high density data center cooling technologies. Ph.D. Thesis, Stony Brook University, Stony Brook, NY, USA, 2008. [Google Scholar]
- Herrlin, M.K.; Belady, C. Gravity-assisted air mixing in data centers and how it affects the rack cooling effectiveness. In Proceedings of the 10th Intersociety Conference on Phenomena in Electronics Systems, San Diego, CA, USA, 30 May–2 June 2006. [Google Scholar]
- Shah, A.J.; Carey, V.P.; Bash, C.E.; Patel, C.D. Exergy analysis of data center thermal management systems. J. Heat Transf.
**2008**, 130, 021401. [Google Scholar] [CrossRef] - Kock, F.; Herwig, H. Local entropy production in turbulent shear flows: A high-Reynolds number model with wall functions. Int. J. Heat Mass Transf.
**2004**, 47, 2205–2215. [Google Scholar] [CrossRef] - Herwig, H.; Kock, F. Direct and indirect methods of calculating entropy generation rates in turbulent convective heat transfer problems. Heat Mass Transf.
**2007**, 43, 207–215. [Google Scholar] [CrossRef] - Herwig, H. The role of entropy generation in momentum and heat transfer. Trans. ASME J. Heat Transf.
**2012**, 134, 031003. [Google Scholar] [CrossRef] - Zhang, L.; Lang, J.; Jiang, K.; Wang, S. Simulation of Entropy Generation under Stall Conditions in a Centrifugal Fan. Entropy
**2014**, 16, 3573–3589. [Google Scholar] [CrossRef][Green Version] - Silva-Llanca, L.; Ortega, A.; Fouladi, K.; del Valle, M.; Sundaralingam, V. Determining wasted energy in the air side of a perimeter-cooled data center via direct computation of the Exergy Destruction. Appl. Energy
**2018**, 213, 235–246. [Google Scholar] [CrossRef] - Fouladi, K.; Wemhoff, A.P.; Silva-Llanca, L.; Abbasi, K.; Ortega, A. Optimization of data center cooling efficiency using reduced order flow modeling within a flow network modeling approach. Appl. Therm. Eng.
**2017**, 124, 929–939. [Google Scholar] [CrossRef] - Díaz, A.J.; Cáceres, R.; Cardemil, J.M.; Silva-Llanca, L. Energy and exergy assessment in a perimeter cooled data center: The value of second law efficiency. Appl. Therm. Eng.
**2017**, 124, 820–830. [Google Scholar] [CrossRef] - Bhalerao, A.; Fouladi, K.; Silva-Llanca, L.; Wemhoff, A.P. Rapid prediction of exergy destruction in data centers due to airflow mixing. Numer. Heat Transf. Part A Appl.
**2016**, 70, 48–63. [Google Scholar] [CrossRef] - Launder, B.E.; Sharma, B.I. Application of the energy-dissipation model of turbulence to the calculation of flow near a spinning disc. Lett. Heat Mass Transf.
**1974**, 1, 131–137. [Google Scholar] [CrossRef] - Erden, H.S.; Khalifa, H.E.; Schmidt, R.R. Transient Thermal Response of Servers Through Air Temperature Measurements. In Proceedings of the ASME 2013 International Technical Conference and Exhibition on Packaging and Integration of Electronic and Photonic Microsystems, Burlingame, CA, USA, 16–18 July 2013; pp. 1–6. [Google Scholar]
- Demetriou, D.W.; Erden, H.S.; Khalifa, H.E.; Schmidt, R.R. Development of an IT equipment lumped capacitance parameter database for transient data center simulations. In Proceedings of the Fourteenth Intersociety Conference on Thermal and Thermomechanical Phenomena in Electronic Systems (ITherm), Orlando, FL, USA, 27–30 May 2014; pp. 1330–1337. [Google Scholar]
- Del Valle, M.; Ortega, A. Numerical and compact models to predict the transient behavior of cross-flow heat exchangers in data center applications. In Proceedings of the Fourteenth Intersociety Conference on Thermal and Thermomechanical Phenomena in Electronic Systems (ITherm), Orlando, FL, USA, 27–30 May 2014; pp. 698–705. [Google Scholar]
- Shah, R.K.; Sekulic, D.P. Fundamentals of Heat Exchanger Design; John Wiley & Sons: Hoboken, NJ, USA, 2003. [Google Scholar]
- Spiga, M.; Spiga, G. Transient temperature fields in crossflow heat exchangers with finite wall capacitance. J. Heat Transf.
**1988**, 110, 49–53. [Google Scholar] [CrossRef] - Bejan, A. Entropy Generation Minimization: The Method of Thermodynamic Optimization of Finite-Size Systems and Finite-Time Processes; CRC Press: Boca Raton, FL, USA, 1996. [Google Scholar]

**Figure 1.**Schematic of the room and boundary conditions for the two approaches: (

**a**) downward flow and (

**b**) upward flow.

**Figure 3.**Schematic representation of the phenomena that destroys entropy during the cooling process.

**Figure 6.**Conduction and Dissipation Entropy Generation distribution inside the room for the two approaches. Arrow indicates flow direction in the overhead heat exchanger.

**Figure 7.**Entropy Generation Number ${N}_{S}$ as a function of the effectiveness ratio ${\xi}_{s}/{\xi}_{\mathit{HX}}$.

N of Nodes | ${\dot{\mathit{S}}}_{\mathbf{gen},\mathit{s}}$ (Servers) | ${\dot{\mathit{S}}}_{\mathbf{gen},\mathbf{airside}}$ (Room + Aisle) | |
---|---|---|---|

Mesh 1 | 108,573 | 203.5 | 0.059 |

Mesh 2 | 167,493 | 203.4 | 0.062 |

Mesh 3 | 315,671 | 203.3 | 0.073 |

Mesh 4 | 563,859 | 203.9 | 0.075 |

**Table 2.**Total Entropy Generation (W/K) for racks, overhead heat exchangers, and the Airside (room-aisle).

Servers | Overhead Heat Exchangers | Airside | |
---|---|---|---|

ODF | 190.9 | 17.65 | 0.318 |

OUF | 203.4 | 18.55 | 0.062 |

ODF | OUF | |
---|---|---|

$\overline{\eta}$ | 0.66 | 0.68 |

${\sigma}_{\eta}$ | 0.0012 | 0.0006 |

© 2019 by the authors. Licensee MDPI, Basel, Switzerland. This article is an open access article distributed under the terms and conditions of the Creative Commons Attribution (CC BY) license (http://creativecommons.org/licenses/by/4.0/).

## Share and Cite

**MDPI and ACS Style**

Silva-Llanca, L.; del Valle, M.; Ortega, A.; Díaz, A.J. Cooling Effectiveness of a Data Center Room under Overhead Airflow via Entropy Generation Assessment in Transient Scenarios. *Entropy* **2019**, *21*, 98.
https://doi.org/10.3390/e21010098

**AMA Style**

Silva-Llanca L, del Valle M, Ortega A, Díaz AJ. Cooling Effectiveness of a Data Center Room under Overhead Airflow via Entropy Generation Assessment in Transient Scenarios. *Entropy*. 2019; 21(1):98.
https://doi.org/10.3390/e21010098

**Chicago/Turabian Style**

Silva-Llanca, Luis, Marcelo del Valle, Alfonso Ortega, and Andrés J. Díaz. 2019. "Cooling Effectiveness of a Data Center Room under Overhead Airflow via Entropy Generation Assessment in Transient Scenarios" *Entropy* 21, no. 1: 98.
https://doi.org/10.3390/e21010098