Thermal Energy Storage for Building Load Management: Application to Electrically Heated Floor
AbstractIn cold climates, electrical power demand for space conditioning becomes a critical issue for utility companies during certain periods of the day. Shifting a portion or all of it to off-peak periods can help reduce peak demand and reduce stress on the electrical grid. Sensible thermal energy storage (TES) systems, and particularly electrically heated floors (EHF), can store thermal energy in buildings during the off-peak periods and release it during the peak periods while maintaining occupants’ thermal comfort. However, choosing the type of storage system and/or its configuration may be difficult. In this paper, the performance of an EHF for load management is studied. First, a methodology is developed to integrate EHF in TRNSYS program in order to investigate the impact of floor assembly on the EHF performance. Then, the thermal comfort (TC) of the night-running EHF is studied. Finally, indicators are defined, allowing the comparison of different EHF. Results show that an EHF is able to shift 84% of building loads to the night while maintaining acceptable TC in cold climate. Moreover, this system is able to provide savings for the customer and supplier if there is a significant difference between off-peak and peak period electricity prices. View Full-Text
Share & Cite This Article
Thieblemont, H.; Haghighat, F.; Moreau, A. Thermal Energy Storage for Building Load Management: Application to Electrically Heated Floor. Appl. Sci. 2016, 6, 194.
Thieblemont H, Haghighat F, Moreau A. Thermal Energy Storage for Building Load Management: Application to Electrically Heated Floor. Applied Sciences. 2016; 6(7):194.Chicago/Turabian Style
Thieblemont, Hélène; Haghighat, Fariborz; Moreau, Alain. 2016. "Thermal Energy Storage for Building Load Management: Application to Electrically Heated Floor." Appl. Sci. 6, no. 7: 194.
Note that from the first issue of 2016, MDPI journals use article numbers instead of page numbers. See further details here.