Flow Analysis through Collector Well Laterals: A Case Study from Sonoma County Water Agency, California
AbstractThe Sonoma County Water Agency (SWCA) uses six radial collector wells along the Russian River west of Santa Rosa, to provide water for several municipalities and water districts in north-western California. Three collector wells (1, 2, and 6) are located in the Wohler area, and three collector wells (3, 4, and 5) are located in the Mirabel area. The objective of this paper is to highlight the performance of the three collector wells located in the Mirabel area since their construction. The 2015 investigation showed a lower performance of Collectors 3 and 4 compared to their original performances after construction in 1975, while the performance of Collector 5 was relatively stable since 1982. The potential change in capacity could be due to the increase in encrustation observed during the visual inspection of laterals in all three collector wells. Overall, the three collectors are still within the optimal design parameters (screen entrance velocity < 0.305 m min−1 and axial flow velocity of lateral screens < 1.524 m s−1). View Full-Text
- Supplementary File 1:
PDF-Document (PDF, 1481 KB)
Share & Cite This Article
D’Alessio, M.; Lucio, J.; Williams, E.; Warner, J.; Seymour, D.; Jasperse, J.; Ray, C. Flow Analysis through Collector Well Laterals: A Case Study from Sonoma County Water Agency, California. Water 2018, 10, 1848.
D’Alessio M, Lucio J, Williams E, Warner J, Seymour D, Jasperse J, Ray C. Flow Analysis through Collector Well Laterals: A Case Study from Sonoma County Water Agency, California. Water. 2018; 10(12):1848.Chicago/Turabian Style
D’Alessio, Matteo; Lucio, John; Williams, Ernest; Warner, James; Seymour, Donald; Jasperse, Jay; Ray, Chittaranjan. 2018. "Flow Analysis through Collector Well Laterals: A Case Study from Sonoma County Water Agency, California." Water 10, no. 12: 1848.
Note that from the first issue of 2016, MDPI journals use article numbers instead of page numbers. See further details here.