# Design and Optimization of a Spiral-Tube Instantaneous Water Heater Using Response Surface Methodology

^{1}

^{2}

^{*}

## Abstract

**:**

## 1. Introduction

#### 1.1. Heat Transfer in STHEs

#### 1.2. RSM for the Optimization of HEs

_{2}O

_{3}-H

_{2}O nanofluid. The authors claimed that the pitch ratio has the most significant effect on the Nusselt number increment and the friction factor reduction and is able to increase efficiency up to five times. Xie et al. [23] worked on the optimal design of fin-tube HEs equipped with vortex generators using RSM and Artificial Neural Network (ANN). In their research, the explanatory variables included arc angle, attack angle, and length of the vortex generators, and target variables included the friction factor and Nusselt number. The results showed that both optimization approaches achieved reliable data. Zhou et al. [24] investigated the optimization of a perforated-finned heat sink. The design variables included the fins’ size and cross-sectional shape and the Reynolds number. Additionally, the Nusselt number and drag forces were considered as target parameters. The authors suggested the optimal design variables based on computational fluid dynamics and RSM methods. Additionally, a multi-objective RSM was used for a new design of a heat sink [25]. In this study [25], the effects of heights, angles, and circumferences of the fins were examined, and the optimal values were introduced. The results stated that heat-dissipation efficiency would be increased by the synchromesh of the display field [25]. Chananipoor et al. [26] optimized a double-pipe HE, which used nano-encapsulated phase change material (NPCM) slurry as the working flow. The authors used RSM to improve the convection heat transfer caused by NPCM slurry. The input parameters were NPCM concentration, inlet temperature, and Reynolds number (Re). The maximum improvement of thermal efficiency was considered the target parameter. The results showed that the inlet temperature and the mass fraction of NPCM have the most influence on the heat transfer behavior. Liu et al. [27] worked on the optimization of a fuel-air tube-in-tube helical coil HE using a combination of RSM and a multi-objective genetic algorithm. The results demonstrated that the hydraulic diameter of the HE’s annulus side and the inner diameter of the HE’s inner tube were the most influential parameters in the thermal and hydraulic characteristics of this kind of HE. Additionally, an optimization study on the same HE was conducted by Liu et al. [28] using RSM. Dagdevir [29] used Taguchi-based Grey relational analysis and RSM to obtain the lowest pressure drop and the highest convective coefficient in a dimpled HE tube. The design parameters of dimple diameter, dimple pitch length, and dimple height were considered. The results indicated that dimple pitch length has the most effect on the target parameters. Furthermore, the RSM optimization of spiral ground HEs was focused on in many studies [30,31].

## 2. Materials and Methods

_{c}) in an ideal case was set to 40 L/min. A thermometer was used to calculate the temperature difference between the water and the HE’s surface. In the experimental work, tests were performed at different levels of the three major factors, i.e., fin number, exhaust, and flow rate. The observed values of water temperature difference, WFR, and hot water output time were recorded (Table 1).

#### 2.1. RSM

#### 2.2. DoE Using CCD

#### 2.3. DoE and Presentation of the Mathematical Model

_{0}is a constant coefficient, n is the number of variables, B

_{i}is a linear coefficient, B

_{ij}denotes an interaction coefficient, B

_{ii}refers to quadratic coefficients, and X

_{i}and X

_{j}are coded values of the independent variables (e.g., factors) [40]. Each variable must be coded within its range to normalize it into a [–1, 1] interval. This is conducted to ensure that the regression analysis works properly, because independent variables may come in different units or different ranges. The normalization can be achieved through Equation (4) [39].

_{i}is the natural value of the ith variable, and X

_{max}and X

_{min}are the maximum and minimum levels of the ith variable, respectively.

^{2}), while its statistical significance was examined by an F-test (i.e., F-value). The significance of different regression coefficients was also calculated using the so-called t-test. It should be considered that R

^{2}alone is not able to clarify the model accuracy adequately, as it expresses the variations around the mean response [41]. Accordingly, practitioners use another index called adjusted R

^{2}(R

^{2}

_{adj}). For calculating this index, in contrast to R

^{2}, the average sum of squares is utilized as a substitute for the sum of squares. Equations (5) and (6) express the relations for calculating these parameters.

^{2}measures the quality of fitting the experimental data to the model, while R

^{2}

_{adj}is an adjusted representation of R

^{2}, into which the degree of freedom is further incorporated. The higher the number of data points and the closer the values of R

^{2}and R

^{2}

_{adj}are to 1, the more acceptable the fitting results will be.

## 3. Results and Discussion

#### 3.1. Final Equations for Obtaining the Effect of Factors on Responses

#### 3.2. Results of ANOVA for the Efficiency Response

^{2}), exhaust outlet diameter (B

^{2}), and WFR (C

^{2}) were close to zero, indicating their strong impacts on the response variable. The p-value for the mutual effect of fin number and exhaust outlet diameter (AB) was calculated at 0.022, i.e., below the significance level of 0.05, indicating the acceptable significance of this factor. The obtained p-values for the exhaust outlet diameter (B) and the mutual effect of the exhaust outlet diameter and WFR (BC) were higher than 0.05, indicating the insignificant impacts of these factors, especially for the exhaust outlet diameter.

^{2}

_{adj}of 0.9835, indicating proper agreement of the experimental data with the predicted results by the model developed for optimizing the HE.

#### 3.3. Summary of Statistical Results for the HTR Response

^{2}), exhaust outlet diameter (B

^{2}), and WFR (C

^{2}) were close to zero, while p-value for the mutual effect of fin number and exhaust outlet diameter (AB) was calculated at 0.0427, i.e., below the significance level of 0.05. These results indicate the significance of the mentioned variables for optimizing the HE. The exhaust outlet diameter (B) and the mutual effect of the exhaust outlet diameter and WFR (BC) exhibited p-values higher than 0.05, indicating their insignificant effects.

^{2}

_{adj}of 0.9992, indicating proper agreement of the experimental data with the predicted results by the developed model.

#### 3.4. Graphical Demonstration of Response Surface and Contour Lines

#### 3.5. Response Surface and Contour Lines for Efficiency Response

#### 3.6. Response Surface and Contour Lines for HTR Response

#### 3.7. Optimization

## 4. Conclusions

## Author Contributions

## Funding

## Data Availability Statement

## Acknowledgments

## Conflicts of Interest

## Nomenclature

η | Efficiency (%) |

m | Water mass flow rate (L/min) |

m_{c} | Gas consumption (kcal/min) |

R | Fuel heat value (kcal/m^{3}) |

C | Specific heat capacity of water (J/kg.°C) |

Q | Heat transfer rate (W) |

h | Heat transfer coefficient (W/m^{2}k) |

$\underset{A}{\xaf}$ | Heat transfer area (m^{2}) |

ΔT | Temperature difference (k) |

## Abbreviations

CCD | Central Composite Design |

DoE | Design of Experiments |

HE | Heat Exchanger |

HTR | Heat Transfer Rate |

NPCM | Nano-Encapsulated Phase Change Material |

RSM | Response Surface Methodology |

STHE | Spiral-Tube Heat Exchanger |

WFR | Water Flow Rate |

## References

- Arabkoohsar, A.; Khosravi, M.; Alsagri, A.S. Effect of various twisted-tape designs on the thermal and environmental performance of line-heaters in city gate stations. Int. J. Heat Mass Transf.
**2020**, 148, 119123. [Google Scholar] [CrossRef] - Amiri Delouei, A.; Karimnejad, S.; Gharajeh, A.; Sajjadi, H.; Atashafrooz, M.; Xie, G.; Arabkoohsar, A. Bath heaters using alternative heat transfer medium: A thermo-economic analysis. J. Braz. Soc. Mech. Sci. Eng.
**2023**, 45, 73. [Google Scholar] [CrossRef] - Bayati Chaleshtari, M.H.; Jafari, M.; Khoramishad, H.; Craciun, E.M. Mutual Influence of Geometric Parameters and Mechanical Properties on Thermal Stresses in Composite Laminated Plates with Rectangular Holes. Mathematics
**2021**, 9, 311. [Google Scholar] [CrossRef] - Amiri Delouei, A.; Sajjadi, H.; Ahmadi, G. Ultrasonic Vibration Technology to Improve the Thermal Performance of CPU Water-Cooling Systems: Experimental Investigation. Water
**2022**, 14, 4000. [Google Scholar] [CrossRef] - Amiri Delouei, A.; Atashafrooz, M.; Sajjadi, H.; Karimnejad, S. The thermal effects of multi-walled carbon nanotube concentration on an ultrasonic vibrating finned tube heat exchanger. Int. Commun. Heat Mass Transf.
**2022**, 135, 106098. [Google Scholar] [CrossRef] - Shen, G.; Ma, L.; Zhang, S.; Zhang, S.; An, L. Effect of ultrasonic waves on heat transfer in Al
_{2}O_{3}nanofluid under natural convection and pool boiling. Int. J. Heat Mass Transf.**2019**, 138, 516–523. [Google Scholar] [CrossRef] - Abdelmagied, M. Thermal performance characteristics of a triple spiral tube heat exchanger. Chem. Eng. Process. Process Intensif.
**2020**, 149, 107707. [Google Scholar] [CrossRef] - Abdelmagied, M. Experimental study of a triple spirally coiled tube heat exchanger thermo-fluid characteristics. Appl. Therm. Eng.
**2020**, 180, 115803. [Google Scholar] [CrossRef] - Abraham, P.; Sharqawy, M.H.; Shawkat, M.E. Thermal and hydraulic characteristics of multiple row spiral finned tube heat exchangers. Int. J. Refrig.
**2021**, 130, 56–66. [Google Scholar] [CrossRef] - Kiatpachai, P.; Kaewkamrop, T.; Mesgarpour, M.; Ahn, H.S.; Dalkılıç, A.S.; Mahian, O.; Wongwises, S. Air-side performance of embedded and welded spiral fin and tube heat exchangers. Case Stud. Therm. Eng.
**2022**, 30, 101721. [Google Scholar] [CrossRef] - Kiatpachai, P.; Keawkamrop, T.; Asirvatham, L.G.; Mesgarpour, M.; Dalkılıc, A.S.; Ahn, H.S.; Mahian, O.; Wongwises, S. An experimental study of the air-side performance of a novel louver spiral fin-and-tube heat exchanger. Alex. Eng. J.
**2022**, 61, 9811–9818. [Google Scholar] [CrossRef] - Keawkamrop, T.; Mesgarpour, M.; Dalkılıç, A.S.; Ahn, H.S.; Mahian, O.; Wongwises, S. Effect of the segmented fin height on the air-side performance of serrated welded spiral fin-and-tube heat exchangers. Case Stud. Therm. Eng.
**2022**, 35, 102128. [Google Scholar] [CrossRef] - Moria, H. A comprehensive geometric investigation of non-circular cross section spring-wire turbulator through the spiral-tube based heat exchangers. Results Eng.
**2023**, 17, 100906. [Google Scholar] [CrossRef] - Zeinali, S.; Neshat, E. Energy, exergy, economy analysis and geometry optimization of spiral coil heat exchangers. Case Stud. Therm. Eng.
**2023**, 42, 102708. [Google Scholar] [CrossRef] - Pongsoi, P.; Pikulkajorn, S.; Wongwises, S. Heat transfer and flow characteristics of spiral fin-and-tube heat exchangers: A review. Int. J. Heat Mass Transf.
**2014**, 79, 417–431. [Google Scholar] [CrossRef] - Liang, B.; Chen, M.; Fu, B.; Li, H. Investigation on the thermal and flow performances of a vertical spiral-tube ground heat exchanger in sand combined with kaolin additive. Energy Build.
**2019**, 190, 235–245. [Google Scholar] [CrossRef] - Liang, B.; Chen, M.; Fu, B.A.; Guan, J. Thermal and flow characteristics in a vertical spiral-type ground heat exchanger based on linear non-equilibrium thermodynamic principle. Energy Build.
**2022**, 266, 112111. [Google Scholar] [CrossRef] - Dinh, B.H.; Kim, Y.S.; Yoon, S. Experimental and numerical studies on the performance of horizontal U-type and spiral-coil-type ground heat exchangers considering economic aspects. Renew. Energy
**2022**, 186, 505–516. [Google Scholar] [CrossRef] - Yoon, S.; Kim, M.J.; Jeon, J.S.; Jung, Y.B. Significance evaluation of performance factors on horizontal spiral-coil ground heat exchangers. J. Build. Eng.
**2021**, 35, 102044. [Google Scholar] [CrossRef] - Yang, W.; Xu, R.; Wang, F.; Chen, S. Experimental and numerical investigations on the thermal performance of a horizontal spiral-coil ground heat exchanger. Renew. Energy
**2020**, 147, 979–995. [Google Scholar] [CrossRef] - Suzuki, M.; Yoneyama, K.; Amemiya, S.; Oe, M. Development of a Spiral Type Heat Exchanger for Ground Source Heat Pump System. Energy Procedia
**2016**, 96, 503–510. [Google Scholar] [CrossRef][Green Version] - Arjmandi, H.; Amiri, P.; Saffari Pour, M. Geometric optimization of a double pipe heat exchanger with combined vortex generator and twisted tape: A CFD and response surface methodology (RSM) study. Therm. Sci. Eng. Prog.
**2020**, 18, 100514. [Google Scholar] [CrossRef] - Xie, C.; Yan, G.; Ma, Q.; Elmasry, Y.; Singh, P.K.; Algelany, A.M.; Wae-hayee, M. Flow and heat transfer optimization of a fin-tube heat exchanger with vortex generators using Response Surface Methodology and Artificial Neural Network. Case Stud. Therm. Eng.
**2022**, 39, 102445. [Google Scholar] [CrossRef] - Zhou, Y.; He, K.; Alizadeh, A.; AL-Khafaji, M.O.; Alawadi, A.H.R.; Maleki, H.; Ismail, M.M.; Shamsborhan, M.; Mohammed, S.H.; Adhab, A.H.; et al. Computational fluid dynamics and multi-objective response surface methodology optimization of perforated-finned heat sinks. J. Taiwan Inst. Chem. Eng.
**2023**, 104823. [Google Scholar] [CrossRef] - Lin, M.C.; Lin, R.F. Design Analysis of Heat Sink Using the Field Synergy Principle and Multitarget Response Surface Methodology. Energies
**2022**, 15, 8399. [Google Scholar] [CrossRef] - Chananipoor, A.; Azizi, Z.; Raei, B.; Tahmasebi, N. Optimization of the thermal performance of nano-encapsulated phase change material slurry in double pipe heat exchanger: Design of experiments using response surface methodology (RSM). J. Build. Eng.
**2021**, 34, 101929. [Google Scholar] [CrossRef] - Liu, P.; Han, H.; Bao, Z. Multi-objective optimization of fuel-air tube-in-tube helical coil heat exchangers for cooled cooling air system applied in aeroengines. Aerosp. Sci. Technol.
**2022**, 130, 107933. [Google Scholar] [CrossRef] - Liu, S.; Huang, W.; Bao, Z.; Zeng, T.; Qiao, M.; Meng, J. Analysis, prediction and multi-objective optimization of helically coiled tube-in-tube heat exchanger with double cooling source using RSM. Int. J. Therm. Sci.
**2021**, 159, 106568. [Google Scholar] [CrossRef] - Dagdevir, T. Multi-objective optimization of geometrical parameters of dimples on a dimpled heat exchanger tube by Taguchi based Grey relation analysis and response surface method. Int. J. Therm. Sci.
**2022**, 173, 107365. [Google Scholar] [CrossRef] - Liu, Q.; Tao, Y.; Shi, L.; Zhou, T.; Huang, Y.; Peng, Y.; Wang, Y.; Tu, J. Parametric optimization of a spiral ground heat exchanger by response surface methodology and multi-objective genetic algorithm. Appl. Therm. Eng.
**2023**, 221, 119824. [Google Scholar] [CrossRef] - Serageldin, A.A.; Radwan, A.; Katsura, T.; Sakata, Y.; Nagasaka, S.; Nagano, K. Parametric analysis, response surface, sensitivity analysis, and optimization of a novel spiral-double ground heat exchanger. Energy Convers. Manag.
**2021**, 240, 114251. [Google Scholar] [CrossRef] - Hadiyat, M.A.; Sopha, B.M.; Wibowo, B.S. Response Surface Methodology Using Observational Data: A Systematic Literature Review. Appl. Sci.
**2022**, 12, 10663. [Google Scholar] [CrossRef] - Samson, J.S.C.; Murugan, K.; Abhra, P.R.; Makarand, U.; Venugopal, N.; Gnanasekaran, S. Optimization of process parameters using response surface methodology: A review. Mater. Today Proc.
**2021**, 37, 1301–1304. [Google Scholar] [CrossRef] - Mäkelä, M. Experimental design and response surface methodology in energy applications: A tutorial review. Energy Convers. Manag.
**2017**, 151, 630–640. [Google Scholar] [CrossRef] - Tsai, C.Y.; Kim, J.; Jin, F.; Jun, M.; Cheong, M.; Yammarino, F.J. Polynomial regression analysis and response surface methodology in leadership research. Leadersh. Q.
**2022**, 33, 101592. [Google Scholar] [CrossRef] - Montgomery, D.C. Design and Analysis of Experiments, 6th ed.; John Wiley and Sons: New York, NY, USA, 2005. [Google Scholar]
- Bergman, T.L.; Lavine, A.S.; Incropera, F.P.; Dewitt, D.P. Fundamentals of Heat and Mass Transfer; John Wiley & Sons: New York, NY, USA, 2011. [Google Scholar]
- Holman, J. Heat Transfer; McGraw-Hill Education: New York, NY, USA, 2009. [Google Scholar]
- Akyürek, E.F.; Geliş, K.; Şahin, B.; Manay, E. Experimental Analysis for Heat Transfer of Nanofluid with Wire Coil Turbulators in a Concentric Tube Heat Exchanger. Results Phys.
**2018**, 9, 376–389. [Google Scholar] [CrossRef] - Yang, Z.H.; Huang, J.; Zeng, G.M.; Ruan, M.; Zhou, C.S.; Li, L.; Rong, Z.G. Optimization of flocculation conditions for kaolin suspension using the composite flocculant of MBFGA1 and PAC by response surface methodology. Bioresour. Technol.
**2009**, 100, 4233–4239. [Google Scholar] [CrossRef] - Esfe, M.H.; Motallebi, S.M.; Hatami, H.; Amiri, M.K.; Esfandeh, S.; Toghraie, D. Optimization of density and coefficient of thermal expansion of MWCNT in thermal oil nanofluid and modeling using MLP and response surface methodology. Tribol. Int.
**2023**, 183, 108410. [Google Scholar] [CrossRef]

**Figure 2.**A view of the internal structure of the aluminum threaded core. The figure on the right is a magnification of the “A” region.

**Figure 3.**(

**a**) Response surface representing efficiency as a function of fin number and WFR, and (

**b**) contour lines representing efficiency as a function of fin number and WFR.

**Figure 4.**(

**a**) Response surface representing HTR as a function of fin number and WFR, (

**b**) contour lines representing HTR as a function of fin number and WFR, (

**c**) response surface representing HTR as a function of fin number and exhaust outlet diameter, and (

**d**) contour lines representing HTR as a function of fin number and exhaust outlet diameter.

Test No. | Tube’s Internal Area (m^{2}) | Fin Area (m^{2}) | Total Area (m^{2}) | Fin Numbers | Exhaust Outlet Diameter (cm) | Flow Rate(L/min) | Efficiency (%) | HTR (W) |
---|---|---|---|---|---|---|---|---|

1 | 0.0753 | 0.01673 | 0.09203 | 3.5 | 2 | 8 | 40.8616780 | 7101.352304 |

2 | 0.0753 | 0.02868 | 0.10398 | 6 | 4 | 14 | 16.8253968 | 7838.943021 |

3 | 0.0753 | 0.02868 | 0.10398 | 6 | 2 | 14 | 25.2380952 | 7867.329561 |

4 | 0.0753 | 0.00478 | 0.08008 | 1 | 4 | 14 | 23.5555556 | 6054.636588 |

5 | 0.0753 | 0.01673 | 0.09203 | 3.5 | 4 | 8 | 43.2653061 | 7113.914399 |

6 | 0.0753 | 0.01673 | 0.09203 | 3.5 | 3 | 8 | 64.8979592 | 7226.973254 |

7 | 0.0753 | 0.01673 | 0.09203 | 3.5 | 3 | 14 | 21.031746 | 6950.607164 |

8 | 0.0753 | 0.02868 | 0.10398 | 6 | 4 | 2 | 37.2562358 | 8662.152681 |

9 | 0.0753 | 0.01673 | 0.09203 | 3.5 | 3 | 2 | 36.0544218 | 7641.522389 |

10 | 0.0753 | 0.00478 | 0.08008 | 1 | 3 | 8 | 72.1088435 | 6321.351036 |

11 | 0.0753 | 0.01673 | 0.09203 | 3.5 | 3 | 8 | 65.3786848 | 7229.485673 |

12 | 0.0753 | 0.01673 | 0.09203 | 3.5 | 3 | 8 | 65.3786848 | 7229.485673 |

13 | 0.0753 | 0.01673 | 0.09203 | 3.5 | 3 | 8 | 65.3786848 | 7229.485673 |

14 | 0.0753 | 0.00478 | 0.08008 | 1 | 4 | 2 | 24.0362812 | 6430.660236 |

15 | 0.0753 | 0.00478 | 0.08008 | 1 | 2 | 14 | 12.6190476 | 6026.216196 |

16 | 0.0753 | 0.01673 | 0.09203 | 3.5 | 3 | 8 | 65.3786848 | 7229.485673 |

17 | 0.0753 | 0.02868 | 0.10398 | 6 | 2 | 2 | 40.861678 | 8747.312301 |

18 | 0.0753 | 0.00478 | 0.08008 | 1 | 2 | 2 | 25.2380952 | 6452.522076 |

19 | 0.0753 | 0.01673 | 0.09203 | 3.5 | 2 | 8 | 67.3015873 | 7239.535349 |

20 | 0.0753 | 0.02868 | 0.10398 | 6 | 2 | 8 | 86.5306122 | 8293.127661 |

Factor | Unit | Min. | Max. |
---|---|---|---|

Fins | Count per unit area | 1 | 6 |

Water flow rate | L/min | 2 | 14 |

Exhaust | cm | 2 | 4 |

Std | Run | Space Type | Factor 1 | Factor 2 | Factor 3 | Response 1 | Response 2 | ||
---|---|---|---|---|---|---|---|---|---|

A: Fin (Number) | B: Exhaust Diameter (cm) | C: Water Flow (L/min) | Predicted Value | Efficiency (%) | Predicted Value | Q (W) | |||

11 | 1 | Axial | 3.5 | 2 | 8 | 43.58 | 40.8617 | 7118.83 | 7101.35 |

8 | 2 | Factorial | 6 | 4 | 14 | 19.16 | 16.8254 | 7829.27 | 7838.94 |

6 | 3 | Factorial | 6 | 2 | 14 | 22.74 | 25.2381 | 7846.17 | 7867.33 |

7 | 4 | Factorial | 1 | 4 | 14 | 20.50 | 23.5556 | 6078.18 | 6080.87 |

12 | 5 | Axial | 3.5 | 4 | 8 | 43.61 | 43.2653 | 7105.19 | 7113.91 |

20 | 6 | Center | 3.5 | 3 | 8 | 64.60 | 64.898 | 7227.82 | 7226.97 |

14 | 7 | Axial | 3.5 | 3 | 14 | 23.66 | 21.0317 | 6975.89 | 6938.05 |

4 | 8 | Factorial | 6 | 4 | 2 | 35.90 | 37.2562 | 8664.27 | 8662.15 |

13 | 9 | Axial | 3.5 | 3 | 2 | 36.49 | 36.0544 | 7612.44 | 7641.52 |

9 | 10 | Axial | 1 | 3 | 8 | 75.93 | 72.1088 | 6301.90 | 6321.35 |

19 | 11 | Center | 3.5 | 3 | 8 | 64.60 | 65.3787 | 7227.82 | 7229.49 |

18 | 12 | Center | 3.5 | 3 | 8 | 64.60 | 65.3787 | 7227.82 | 7229.49 |

16 | 13 | Center | 3.5 | 3 | 8 | 64.60 | 65.3787 | 7227.82 | 7229.49 |

3 | 14 | Factorial | 1 | 4 | 2 | 25.77 | 24.0363 | 6449.63 | 6430.66 |

5 | 15 | Factorial | 1 | 2 | 14 | 13.21 | 12.619 | 6021.91 | 6026.22 |

17 | 16 | Center | 3.5 | 3 | 8 | 64.60 | 65.3787 | 7227.82 | 7229.49 |

2 | 17 | Factorial | 6 | 2 | 2 | 43.15 | 40.8617 | 8747.82 | 8747.31 |

1 | 18 | Factorial | 1 | 2 | 2 | 22.14 | 25.2381 | 6460.01 | 6452.52 |

15 | 19 | Center | 3.5 | 3 | 8 | 64.60 | 67.3016 | 7227.82 | 7239.54 |

10 | 20 | Axial | 6 | 3 | 8 | 85.77 | 86.5306 | 8321.34 | 8293.13 |

Source | Sum of Squares | df | Mean Square | F-Value | p-Value | |
---|---|---|---|---|---|---|

Model | 0.9208 | 9 | 0.1023 | 126.85 | <0.0001 | significant |

A-Fin | 0.0242 | 1 | 0.0242 | 29.96 | 0.0003 | |

B-Exhaust diameter | 1.44 × 10^{−7} | 1 | 1.44 × 10^{−7} | 0.0002 | 0.9896 | |

C-Water flow | 0.0412 | 1 | 0.0412 | 51.07 | <0.0001 | |

AB | 0.0059 | 1 | 0.0059 | 7.33 | 0.0220 | |

AC | 0.0066 | 1 | 0.0066 | 8.17 | 0.0170 | |

BC | 0.0007 | 1 | 0.0007 | 0.8329 | 0.3829 | |

A^{2} | 0.0726 | 1 | 0.0726 | 90.05 | <0.0001 | |

B^{2} | 0.1213 | 1 | 0.1213 | 150.43 | <0.0001 | |

C^{2} | 0.3278 | 1 | 0.3278 | 406.41 | <0.0001 | |

Residual | 0.0081 | 10 | 0.0008 | |||

Lack of Fit | 0.0077 | 5 | 0.0015 | 21.52 | 0.0022 | significant |

Pure error | 0.0004 | 5 | 0.0001 | |||

Cor total | 0.9289 | 19 |

Summary of Statistical Results for the Efficiency Response | ||||
---|---|---|---|---|

Std. Dev. | 0.0284 | R^{2} | 0.9913 | |

Mean | 0.4496 | Adjusted R^{2} | 0.9835 | |

C.V. % | 6.32 | Predicted R^{2} | 0.8830 | |

Adeq. Precision | 36.1303 |

Source | Sum of Squares | df | Mean Square | F-Value | p-Value | |
---|---|---|---|---|---|---|

Model | 1.14 × 10^{7} | 9 | 1.26 × 10^{6} | 2542.29 | <0.0001 | significant |

A-Fin | 1.02 × 10^{7} | 1 | 1.02 × 10^{7} | 20,508.95 | <0.0001 | |

B-Exhaust diameter | 465.01 | 1 | 465.01 | 0.9354 | 0.3563 | |

C-Water flow | 1.01 × 10^{6} | 1 | 1.01 × 10^{6} | 2037.73 | <0.0001 | |

AB | 2676.88 | 1 | 2676.88 | 5.38 | 0.0427 | |

AC | 1.08 × 10^{5} | 1 | 1.07 × 10^{5} | 216.12 | <0.0001 | |

BC | 2220.76 | 1 | 2220.76 | 4.47 | 0.0607 | |

A^{2} | 19,311.08 | 1 | 19,311.08 | 38.85 | <0.0001 | |

B^{2} | 36,881.20 | 1 | 36,881.20 | 74.19 | <0.0001 | |

C^{2} | 12,103.84 | 1 | 12,103.84 | 24.35 | 0.0006 | |

Residual | 4971.21 | 10 | 497.12 | |||

Lack of fit | 4873.37 | 5 | 974.67 | 49.81 | 0.0003 | significant |

Pure error | 97.84 | 5 | 19.57 | |||

Cor total | 1.14 × 10^{7} | 19 |

Summary of Statistical Results for the HTR Response | |||
---|---|---|---|

Std. Dev. | 22.30 | R^{2} | 0.9996 |

Mean | 7244.99 | Adjusted R^{2} | 0.9992 |

C.V. % | 0.3077 | Predicted R^{2} | 0.9967 |

Adeq Precision | 172.9001 |

Number | Fin | Exhaust Diameter (cm) | Water Flow (L/min) | Efficiency (%) | Q (W) | Desirability |
---|---|---|---|---|---|---|

1 | 6.000 | 2.920 | 5.952 | 85.0 | 8479.001 | 0.940 |

2 | 6.000 | 2.910 | 5.959 | 85.0 | 8478.532 | 0.940 |

3 | 6.000 | 2.929 | 5.934 | 85.0 | 8480.356 | 0.940 |

4 | 6.000 | 2.931 | 5.991 | 85.1 | 8475.718 | 0.940 |

5 | 6.000 | 2.906 | 5.923 | 84.9 | 8481.438 | 0.940 |

6 | 6.000 | 2.940 | 5.984 | 85.1 | 8476.132 | 0.940 |

7 | 6.000 | 2.929 | 5.851 | 84.8 | 8486.981 | 0.940 |

8 | 6.000 | 2.895 | 5.950 | 85.0 | 8479.350 | 0.940 |

9 | 6.000 | 2.905 | 6.065 | 85.3 | 8470.079 | 0.940 |

10 | 6.000 | 2.945 | 6.041 | 85.2 | 8471.528 | 0.940 |

11 | 6.000 | 2.937 | 6.082 | 85.3 | 8468.378 | 0.940 |

Disclaimer/Publisher’s Note: The statements, opinions and data contained in all publications are solely those of the individual author(s) and contributor(s) and not of MDPI and/or the editor(s). MDPI and/or the editor(s) disclaim responsibility for any injury to people or property resulting from any ideas, methods, instructions or products referred to in the content. |

© 2023 by the authors. Licensee MDPI, Basel, Switzerland. This article is an open access article distributed under the terms and conditions of the Creative Commons Attribution (CC BY) license (https://creativecommons.org/licenses/by/4.0/).

## Share and Cite

**MDPI and ACS Style**

Rezaei, P.; Moheghi, H.R.; Amiri Delouei, A.
Design and Optimization of a Spiral-Tube Instantaneous Water Heater Using Response Surface Methodology. *Water* **2023**, *15*, 1458.
https://doi.org/10.3390/w15081458

**AMA Style**

Rezaei P, Moheghi HR, Amiri Delouei A.
Design and Optimization of a Spiral-Tube Instantaneous Water Heater Using Response Surface Methodology. *Water*. 2023; 15(8):1458.
https://doi.org/10.3390/w15081458

**Chicago/Turabian Style**

Rezaei, Pedram, Hamid Reza Moheghi, and Amin Amiri Delouei.
2023. "Design and Optimization of a Spiral-Tube Instantaneous Water Heater Using Response Surface Methodology" *Water* 15, no. 8: 1458.
https://doi.org/10.3390/w15081458