# Numerical Evaluation of the Hydrothermal Process in a Water-Surrounded Heater of Natural Gas Pressure Reduction Plants

^{1}

^{2}

^{3}

^{*}

## Abstract

**:**

^{4}, 8 × 10

^{4}, 1 × 10

^{5}, and 12 × 10

^{5}standard cubic meters per hour (or 16.67, 22.22, 27.78, and 33.33 m

^{3}/s). The results indicate that the natural gas outlet temperature achieved to a temperature higher than required. By installing a regulator on the burner, the gas consumption can be reduced, resulting in station cost savings, and also reducing the environmental impacts. The outcomes depict that the maximum possible reductions in monthly gas consumption and economic savings in the proposed system are 67,500 m

^{3}and IRR 25 million at a gas mass flow rate of 60,000 SCMH.

## 1. Introduction

_{2}emissions.

## 2. Materials and Methods

#### 2.1. Geometrical Parameters

^{3}/s; it can absorb 819,500 kcal/h (0.953 kW) with 4 coils. It has eight gas pipes. Coil diameter and length are 4 in (0.1016 m) and 236.22 in (6 m), respectively. Additionally, the operational temperature and pressure of the heater under investigation are 40 °C and 1050 psi (7239.49 kPa), respectively. Moreover, the maximum and minimum burner capacity are 150,000 kCal/h (174.45 kW) and 750,000 kCal/h (827.25 kW), respectively. Furthermore, the fire tube diameter and length are 4 in (0.6 m) and 267.72 in (6.8), respectively.

#### 2.2. Governing Equations and Parameters

**Momentum Conservation Equations [18,19,20,21]:**

_{Mi}, for the amount of momentum in the direction i per unit volume and per unit time, where i includes x, y, or z directions. If the body forces only include gravity, which is the case in the present problem, then S

_{Mx}= S

_{Mz}= 0 and S

_{My}= −ρg.

_{k}is the production of turbulence due to viscous forces, which is defined as follows:

^{+}distribution on the surface of the tube is shown in Figure 2, which shows the acceptable values of y

^{+}in the presented model.

**Mass Conservation Equation [18,19,20,21]:**

**Turbulent Energy Equation [18,19,20,21]:**

#### 2.3. Boundary Conditions

_{S}− T

_{∞}) D

^{3}/ν

^{2}) is used to determine the flow regime in free convection heat transfer. This number indicates whether the flow is laminar or turbulent. The Grashof number is obtained from the ratio of the buoyancy force to the viscous force. In this correlation, the parameters g, β, T

_{S}, T

_{∞}, D, and υ express the gravitational acceleration, volumetric expansion coefficient, hot surface temperature, cold surface temperature, length characteristics, and kinematic viscosity, respectively. If the Grashof number is greater than 10 + 8, the flow is turbulent. According to the specifications of this issue, the Grashof number is about 6 × 10 + 6, so the flow regime is laminar. On the other hand, due to the high liquid flow rate inside the fire tube and gas line, the Reynolds number of the flow is much higher than 2300, so the liquid flow is completely turbulent.

^{3}/s). The gas inlet temperature in the heater was assumed to be 10 °C according to the ambient conditions. An inlet velocity of 5 m/sec and a temperature of 800 K were assumed for the inlet boundary of the fire tube assuming an additional fuel-to-air ratio of 1.8, an air inlet temperature of 30 °C, and a methane flame temperature of 2400 K at a pressure of 1 bar. The volumetric expansion coefficient of water was assumed to be 0.0005 K

^{−1}to model the effects of natural convection. The gas entering the heater consists of various components with different ratios. Table 1 shows the components of the gas and the volume fraction of each component. As can be seen, about 90% of the gas consists of methane gas, so for simplicity’s sake, only methane gas was considered as a component of the city gas in further modeling processes.

## 3. Results and Discussion

^{3}/s). The results include the outlet temperature of methane and combustion gas, the temperature and velocity distribution in the heater, and the thermal efficiency of the heater.

#### 3.1. The Mesh-Independent and Validation Analyses

^{3}/s). The numerical results obtained for these networks are shown in Table 4. It can be concluded that the grid with 4,777,825 cells is suitable for use in the following sections of this work. Images showing grid generated for the heater under consideration from different perspectives are shown in Figure 4. It can be seen that to increase the accuracy of the numerical simulation, the boundary layer grid was used in both the gas tube and the fire tube.

#### 3.2. Investigating the Performance of the Gas Heater at 120,000 SCMH

^{2}.

^{2}.

#### 3.3. Investigating the Impact of Gas Mass Flow Rate

^{3}/s). The parameters studied in this section include the outlet temperature of the coil and the fire tube.

^{3}/s) to 120,000 (33.33 m

^{3}/s) SCHM (100% increase).

^{3}/s), the average temperature of the hot water was 337 K, and with the increase in the mass flow rate to 120,000 SCMH (33.33 m

^{3}/s), the average temperature of the hot water decreased to 325 K. The temperature contours on a slice (X = 0) at different mass flow rates are shown in Figure 14. As can be seen, the water temperature inside the shell dropped significantly when the flow rate was increased.

^{3}/s) to 120,000 SCMH (33.33 m

^{3}/s), the exit temperature of the fire tube increased from about 416 to 409 K.

#### 3.4. Investigating the Fuel Consumption Reduction Using the Considered Heater

_{P}is the specific heat capacity of the water, and (T

_{2}− T

_{1}) is the difference between the primary and secondary temperatures of the tank water.

^{3}. The initial temperature of the fluid, T

_{1}, is obtained according to numerical calculations employing ANSYS Fluent software and is the average temperature of the hot water bath. The secondary fluid temperature, T

_{2}, is assumed to be 300 K. Therefore, using the relationships and assumptions provided, the amount of energy stored in the hot water tank can be determined for different mass flow rates as we know the hot water bath temperature from numerical calculations. The amount of time it takes for the energy to be transferred to the fluid or, in other words, the time it takes for the temperature of the hot water bath to go from T

_{1}to T

_{2}, can be calculated as follows:

_{P}is the heat capacity of the gas, and T

_{1}and T

_{2}are the initial and secondary temperatures of the gas, respectively. Finally, the time needed to transfer energy between the hot water bath and the coils, indicated as burner off time, is determined as follows:

^{3}/s −100% growth), the burner off time declined by about 65.87%.

_{Coil}indicates the time required to heat the gas input to the heater, which, considering that the temperature of the output gas should not be less than 20 degrees, is continuously being heated and has no time delay. Additionally, t

_{Water}, which represents the time required to heat the water to the target temperature before the burner is turned off, is calculated as follows, considering the volume of the bath water and the difference between the desired temperature and the power of the burner:

^{3}and IRR 25 million at a gas mass flow rate of 60,000 SCMH.

## 4. Conclusions

^{3}/s) to 120,000 SCMH (33.33 m

^{3}/s), and by installing a regulator on the burner, gas consumption can be reduced.

## Author Contributions

## Funding

## Data Availability Statement

## Conflicts of Interest

## References

- Shokouhmand, H.; Rezaei Barmi, M.; Tavakoli, B. Gas Heater Availability Analysis and Consideration of Replacement Gas Heaters by Inline Heaters in the Pressure Reducing Stations of Natural Gas. In Proceedings of the ASME International Mechanical Engineering Congress and Exposition, Seattle, DC, USA, 11–15 November 2007; Volume 43025, pp. 1231–1240. [Google Scholar]
- Hedman, B.A. Waste Energy Recovery Opportunities for Interstate Natural Gas Pipelines; Interstate Natural Gas Association of America: Washington, DC, USA, 2008. [Google Scholar]
- Farzaneh-Gord, M.; Arabkoohsar, A.; Rezaei, M.; Deymi-Dashtebayaz, M.; Rahbari, H.R. Feasibility of employing solar energy in natural gas pressure drop stations. J. Energy Inst.
**2011**, 84, 165–173. [Google Scholar] [CrossRef] - Clay, A.; Tansley, G.D. Exploration of a simple, low cost, micro gas turbine recuperator solution for a domestic combined heat and power unit. Appl. Therm. Eng.
**2011**, 31, 2676–2684. [Google Scholar] [CrossRef][Green Version] - Howard, C.; Oosthuizen, P.; Peppley, B. An investigation of the performance of a hybrid turboexpander-fuel cell system for power recovery at natural gas pressure reduction stations. Appl. Therm. Eng.
**2011**, 31, 2165–2170. [Google Scholar] [CrossRef][Green Version] - Andrei, I.; Valentin, T.; Cristina, T.; Niculae, T. Recovery of wasted mechanical energy from the reduction of natural gas pressure. Procedia Eng.
**2014**, 69, 986–990. [Google Scholar] [CrossRef][Green Version] - Ashouri, E.; Veysi, F.; Shojaeizadeh, E.; Asadi, M. The minimum gas temperature at the inlet of regulators in natural gas pressure reduction stations (CGS) for energy saving in water bath heaters. J. Nat. Gas Sci. Eng.
**2014**, 21, 230–240. [Google Scholar] [CrossRef] - Farzaneh-Gord, M.; Ghezelbash, R.; Arabkoohsar, A.; Pilevari, L.; Machado, L.; Koury, R.N.N. Employing geothermal heat exchanger in natural gas pressure drop station in order to decrease fuel consumption. Energy
**2015**, 83, 164–176. [Google Scholar] [CrossRef] - Ghezelbash, R.; Farzaneh-Gord, M.; Sadi, M. Performance assessment of vortex tube and vertical ground heat exchanger in reducing fuel consumption of conventional pressure drop stations. Appl. Therm. Eng.
**2016**, 102, 213–226. [Google Scholar] [CrossRef] - Salari, S.; Goudarzi, K. Heat transfer enhancement and fuel consumption reduction in heaters of CGS gas stations. Case Stud. Therm. Eng.
**2017**, 10, 641–649. [Google Scholar] [CrossRef] - Olfati, M.; Bahiraei, M.; Heidari, S.; Veysi, F. A comprehensive analysis of energy and exergy characteristics for a natural gas city gate station considering seasonal variations. Energy
**2018**, 155, 721–733. [Google Scholar] [CrossRef] - Naderi, M.; Ahmadi, G.; Zarringhalam, M.; Akbari, O.; Khalili, E. Application of water reheating system for waste heat recovery in NG pressure reduction stations, with experimental verification. Energy
**2018**, 162, 1183–1192. [Google Scholar] [CrossRef] - Rahmatpour, A.; Shaibani, M.J. Techno-economic assessment of gas pressure-based electricity generation (A case study of Iran). Energy Sources Part A Recovery Util. Environ. Eff.
**2018**, 40, 2236–2247. [Google Scholar] [CrossRef] - Khosravi, M.; Arabkoohsar, A.; Alsagri, A.S.; Sheikholeslami, M. Improving thermal performance of water bath heaters in natural gas pressure drop stations. Appl. Therm. Eng.
**2019**, 159, 113829. [Google Scholar] [CrossRef] - Noorollahi, Y.; Ghasemi, G.; Kowsary, F.; Roumi, S.; Jalilinasrabady, S. Modelling of heat supply for natural gas pressure reduction station using geothermal energy. Int. J. Sustain. Energy
**2019**, 38, 773–793. [Google Scholar] [CrossRef] - Foo, K.; Liang, Y.Y.; Goh, P.S.; Fletcher, D.F. Computational fluid dynamics simulations of membrane gas separation: Overview, challenges and future perspectives. Chem. Eng. Res. Des.
**2023**, 191, 127–140. [Google Scholar] [CrossRef] - Li, W.L.; Ouyang, Y.; Gao, X.Y.; Wang, C.Y.; Shao, L.; Xiang, Y. CFD analysis of gas–liquid flow characteristics in a microporous tube-in-tube microchannel reactor. Comput. Fluids
**2018**, 170, 13–23. [Google Scholar] [CrossRef] - Siavash Amoli, B.; Mousavi Ajarostaghi, S.S.; Sedighi, K.; Aghajani Delavar, M. Evaporative pre-cooling of a condenser airflow: Investigation of nozzle cone angle, spray inclination angle and nozzle location. Energy Sources Part A Recovery Util. Environ. Eff.
**2022**, 44, 8040–8059. [Google Scholar] [CrossRef] - Salhi, J.E.; Mousavi Ajarostaghi, S.S.; Zarrouk, T.; Saffari Pour, M.; Salhi, N.; Salhi, M. Turbulence and thermo-flow behavior of air in a rectangular channel with partially inclined baffles. Energy Sci. Eng.
**2022**, 10, 3540–3558. [Google Scholar] [CrossRef] - Mohammadi, S.; Mousavi Ajarostaghi, S.S.; Pourfallah, M. The latent heat recovery from boiler exhaust flue gas using shell and corrugated tube heat exchanger: A numerical study. Heat Transfer
**2020**, 49, 3797–3815. [Google Scholar] [CrossRef] - Nouri Kadijani, O.; Kazemi Moghadam, H.; Mousavi Ajarostaghi, S.S.; Asadi, A.; Saffari Pour, M. Hydrothermal performance of humid air flow in a rectangular solar air heater equipped with V-shaped ribs. Energy Sci. Eng.
**2022**, 10, 2276–2289. [Google Scholar] [CrossRef] - Masoumpour-Samakoush, M.; Miansari, M.; Ajarostaghi, S.S.M.; Arıcı, M. Impact of innovative fin combination of triangular and rectangular fins on melting process of phase change material in a cavity. J. Energy Storage
**2022**, 45, 103545. [Google Scholar] [CrossRef] - Pakzad, K.; Mousavi Ajarostaghi, S.S.; Sedighi, K. Numerical simulation of solidification process in an ice-on-coil ice storage system with serpentine tubes. SN Appl. Sci.
**2019**, 1, 1–12. [Google Scholar] [CrossRef][Green Version] - Riahi, M.; Yazdirad, B.; Jadidi, M.; Berenjkar, F.; Khoshnevisan, S.; Jamali, M.; Safary, M. Optimization of combustion Efficiency in indirect water bath heaters of Ardabil city gate stations. In Proceedings of the Seventh Mediterranean Combustion Symposium (MCS-7), Cagliari, Italy, 11–15 September 2011; pp. 11–15. [Google Scholar]
- Naderi, M.; Zargar, G.; Khalili, E. A numerical study on using air cooler heat exchanger for low grade energy recovery from exhaust flue gas in natural gas pressure reduction stations. Iran. J. Oil Gas Sci. Technol.
**2018**, 7, 93–109. [Google Scholar]

**Figure 3.**The thermophysical properties of the exhaust gas flow in the fire tube as a function of gas temperature: (

**a**) density, (

**b**) viscosity, (

**c**) heat capacity, and (

**d**) thermal conductivity [25].

**Figure 4.**Various views of the generated grid for the heater under study: (

**a**) shell, (

**b**) fire tube and gas tubes, (

**c**) close-up of gas tube, and (

**d**) different view of gas tubes.

**Figure 8.**The distribution of temperature in the various slices inside the shell: (

**a**) Slice 1, (

**b**) Slice 2, and (

**c**) Slice 3.

**Figure 9.**The distribution of velocity magnitude in the various slices inside the shell: (

**a**) Slice 1, (

**b**) Slice 2, (

**c**) and Slice 3.

**Figure 14.**The temperature distribution across the middle (X = 0) at various inlet mass flow rates: (

**a**) $\dot{\mathrm{m}}$ = 60,000 SCMH (16.67 m

^{3}/s), (

**b**) $\dot{\mathrm{m}}$ = 80,000 SCMH (22.22 m

^{3}/s), (

**c**) $\dot{\mathrm{m}}$ = 100,000 SCMH (27.78 m

^{3}/s), and (

**d**) $\dot{\mathrm{m}}$ = 120,000 SCMH (33.33 m

^{3}/s).

**Figure 16.**The streamline with the contour of velocity magnitude inside the water tank of the heater under study.

**Figure 17.**The iso-surfaces of velocity magnitude with various values inside the water tank of the heater under consideration.

**Figure 19.**The burner off time versus the gas mass flow rate needed to maintain a temperature of 20 degrees for the gas coil output.

**Figure 20.**The burner operation time elapsed before turning it off, after restarting it, and the duration of the burner operation at various gas mass flow rates.

**Figure 21.**(

**a**) The monthly reduction in gas consumption, and (

**b**) the economic savings at different gas mass flow rates in one month.

**Table 1.**Volumetric fraction of natural gas composition [24].

Name | Chemical Formula | Volume Percentage | ||
---|---|---|---|---|

Gas Analysis | Lower Limit | Higher Limit | ||

Methane | CH_{4} | 88.332 | 85 | 95 |

Ethan | C_{2}H_{6} | 4.672 | 2 | 9 |

Propane | C_{3}H_{8} | 4.137 | 0.5 | 3 |

Isobutene | C_{4}H_{10} | 0.484 | 0.2 | 0.3 |

Normal Butane | C_{4}H_{10} | 0.484 | 0.25 | 0.5 |

Isopentane | C_{5}H_{12} | 0.181 | 0.1 | 0.15 |

Normal Pentane | C_{5}H_{12} | 0.181 | 0.06 | 0.1 |

Carbon Dioxide | CO_{2} | 0.694 | 0.1 | 0.4 |

Nitrogen | N_{2} | 4.5 | 2 | 5.7 |

Sulfide | H_{2}S | 0.849 ppm | 1.25 | 6.25 |

Heavy/compound | - | 0 | 0.02 | 0.2 |

**Table 2.**The thermophysical properties of methane at T = 20 °C and P = 700 psi (4826.33 kPa) [25].

Property | Value | |
---|---|---|

Density (kg.m^{−3}) | $\rho $ | 34.76 |

Specific Heat Capacity (kJ/(kg.K)) | C_{P} | 2.57 |

Dynamic Viscosity (Pa.s) | μ | 11.96 × 10^{−6} |

Static Viscosity (m^{2}/s) | υ | 0.344 × 10^{−6} |

**Table 3.**Composition of combustion exhaust gases [24].

Fuel Flow Rate (m^{3}/hr) | Carbon Monoxide (ppm) | Carbon Dioxide (ppm) | Nitrogen Oxides (ppm) | Oxygen (%) | Stack Temperature at Input Gate (°C) | Ambient Temperature (°C) | Combustion Efficiency (%) |
---|---|---|---|---|---|---|---|

102 | 81 | 4.14 | 22 | 13.69 | 274 | 8.4 | 73.35 |

111 | 284 | 5.63 | 25 | 11.60 | 314 | 9.7 | 76.55 |

180 | 202 | 7.92 | 39 | 7.20 | 412 | 9.7 | 76.54 |

186 | 301 | 8.14 | 37 | 6.64 | 407 | 9.7 | 77.33 |

192 | 159 | 7.52 | 33 | 7.73 | 427 | 9.5 | 74.56 |

204 | 111 | 8.41 | 42 | 6.16 | 437 | 1.1 | 76.31 |

228 | 44 | 8.36 | 47 | 6.25 | 455 | 0.8 | 75.11 |

252 | 32 | 8.89 | 57 | 5.31 | 488 | 9.8 | 74.61 |

Number | Grid Cell | The Outlet Temperature of the Methane (K) | Error (%) |
---|---|---|---|

1 | 3,708,213 | 313.2 | 0.45 |

2 | 4,777,825 | 314.68 | 0.022 |

3 | 6,210,401 | 314.61 | - |

Number | Mass Flow Rate (SCMH (m^{3}/s)) | Experimental Heater Outlet Temperature (°C) | Numerical Heater Outlet Temperature (°C) | Error (%) |
---|---|---|---|---|

1 | 80,000 (22.22) | 34.5 | 33.85 | 1.88 |

2 | 100,000 (27.78) | 30.1 | 29.15 | 3.15 |

3 | 120,000 (33.33) | 27 | 26.05 | 3.52 |

Disclaimer/Publisher’s Note: The statements, opinions and data contained in all publications are solely those of the individual author(s) and contributor(s) and not of MDPI and/or the editor(s). MDPI and/or the editor(s) disclaim responsibility for any injury to people or property resulting from any ideas, methods, instructions or products referred to in the content. |

© 2023 by the authors. Licensee MDPI, Basel, Switzerland. This article is an open access article distributed under the terms and conditions of the Creative Commons Attribution (CC BY) license (https://creativecommons.org/licenses/by/4.0/).

## Share and Cite

**MDPI and ACS Style**

Kazemi Moghadam, H.; Mousavi Ajarostaghi, S.S.; Saffari Pour, M.; Akbary, M.
Numerical Evaluation of the Hydrothermal Process in a Water-Surrounded Heater of Natural Gas Pressure Reduction Plants. *Water* **2023**, *15*, 1469.
https://doi.org/10.3390/w15081469

**AMA Style**

Kazemi Moghadam H, Mousavi Ajarostaghi SS, Saffari Pour M, Akbary M.
Numerical Evaluation of the Hydrothermal Process in a Water-Surrounded Heater of Natural Gas Pressure Reduction Plants. *Water*. 2023; 15(8):1469.
https://doi.org/10.3390/w15081469

**Chicago/Turabian Style**

Kazemi Moghadam, Hamid, Seyed Soheil Mousavi Ajarostaghi, Mohsen Saffari Pour, and Mohsen Akbary.
2023. "Numerical Evaluation of the Hydrothermal Process in a Water-Surrounded Heater of Natural Gas Pressure Reduction Plants" *Water* 15, no. 8: 1469.
https://doi.org/10.3390/w15081469