# Early Detection and Identification of Damage in In-Service Waterworks Pipelines Based on Frequency-Domain Kurtosis and Time-Shift Coherence

^{1}

^{2}

^{3}

^{*}

## Abstract

**:**

## 1. Introduction

## 2. Source Localization of Impact Damage

#### 2.1. Conventional Source Location of Leaks in Fluid-Filled Pipelines

_{f}, B

_{f}, a, E, ρ, h, and ω denote the longitudinal wave speed of a fluid in free space, the bulk modulus of the internal fluid, the mean pipe radius, which is calculated based on the outer and inner diameter of a pipe, Young’s modulus of the pipe, the density of the pipe material, the pipe thickness, and the angular frequency, respectively.

#### 2.2. Source Location of Impact Damage in Fluid-Filled Buried Pipelines

## 3. Experiments

## 4. Results and Discussion

## 5. Conclusions

## Author Contributions

## Funding

## Data Availability Statement

## Conflicts of Interest

## References

- Morgan, K.C. Managing Water Main Breaks: Field Guide; American Water Works Association: Denver, CO, USA, 2012. [Google Scholar]
- European Gas Incident Data Group. Gas Pipeline Incidents; 7th report, Report no. EGIG 08.TV-B.0502; European Gas Incident Data Group: Online, 2008. [Google Scholar]
- Goodfellow, G. Ukopa Pipeline Product; Report no. UKOPA/RP/21/001; UKOPA: Belper, UK, 2021. [Google Scholar]
- Li, S.; Peng, R.; Liu, Z. A surveillance system for urban buried pipeline subject to third-party threats based on fiber optic sensing and convolutional neural network. Struct. Health Monit.
**2020**, 20, 1704–1715. [Google Scholar] [CrossRef] - Puust, R.; Kapelan, Z.; Savic, D.A.; Koppel, T. A review of methods for leakage management in pipe networks. Urban Water J.
**2010**, 7, 25–45. [Google Scholar] [CrossRef] - Brainard, F.S. Leakage Problems and the Benefits off Leak Detection Programs. J.-Am. Water Work. Assoc.
**1979**, 71, 64–65. [Google Scholar] [CrossRef] - Cole, E.S. Methods of Leak Detection: An Overview. J.-Am. Water Work. Assoc.
**1979**, 71, 73–75. [Google Scholar] [CrossRef] - Fuchs, H.; Riehle, R. Ten years of experience with leak detection by acoustic signal analysis. Appl. Acoust.
**1991**, 33, 1–19. [Google Scholar] [CrossRef] - Muggleton, J.; Brennan, M.; Linford, P. Axisymmetric wave propagation in fluid-filled pipes: Wavenumber measurements in in vacuo and buried pipes. J. Sound Vib.
**2003**, 270, 171–190. [Google Scholar] [CrossRef] - Fuller, C.; Fahy, F. Characteristics of wave propagation and energy distributions in cylindrical elastic shells filled with fluid. J. Sound Vib.
**1982**, 81, 501–518. [Google Scholar] [CrossRef] - Muggleton, J.; Yan, J. Wavenumber prediction and measurement of axisymmetric waves in buried fluid-filled pipes: Inclusion of shear coupling at a lubricated pipe/soil interface. J. Sound Vib.
**2013**, 332, 1216–1230. [Google Scholar] [CrossRef][Green Version] - Lee, Y.-S.; Yoon, D.-J. Improved Estimation of Leak Location of Pipelines Using Frequency Band Variation. J. Korean Soc. Nondestruct. Test.
**2014**, 34, 44–52. [Google Scholar] [CrossRef] - Behari, N.; Sheriff, M.Z.; Rahman, M.A.; Nounou, M.; Hassan, I.; Nounou, H. Chronic leak detection for single and multiphase flow: A critical review on onshore and offshore subsea and arctic conditions. J. Nat. Gas Sci. Eng.
**2020**, 81, 103460. [Google Scholar] [CrossRef] - Shin, S.-M.; Suh, J.-H.; Im, J.-S.; Kim, S.B.; Yoo, H.-R. Development of Third-Party Damage Monitoring System for Natural Gas Pipeline. KSME Int. J.
**2003**, 17, 1423–1430. [Google Scholar] [CrossRef] - Park, C.-S.; Lee, S.-H.; Yoon, D.-J. Enhancing Impact Localization from Fluid-Pipe Coupled Vibration under Noisy Environment. Appl. Sci.
**2021**, 11, 4197. [Google Scholar] [CrossRef] - Bjorklund, S.; Ljung, L. A review of time-delay estimation techniques. In Proceedings of the 42nd IEEE International Conference on Decision and Control (IEEE Cat. No.03CH37475), Maui, HI, USA, 9–12 December 2003; Volume 3, pp. 2502–2507. [Google Scholar] [CrossRef][Green Version]
- Lee, Y.-S. Effects of windowing filters in leak locating for buried water-filled cast iron pipes. J. Mech. Sci. Technol.
**2009**, 23, 401–408. [Google Scholar] [CrossRef] - Hannan, E.J.; Thomson, P.J. Estimating group delay. Biometrika
**1973**, 60, 241–253. [Google Scholar] [CrossRef] - Roth, P.R. Effective measurements using digital signal analysis. IEEE Spectr.
**1971**, 8, 62–70. [Google Scholar] [CrossRef] - Carter, G.; Nuttall, A.; Cable, P. The smoothed coherence transform. Proc. IEEE
**1973**, 61, 1497–1498. [Google Scholar] [CrossRef] - Lee, S.-H.; Park, C.-S.; Yoon, D.-J. Experimental Verification of Impact Damage Detection in Long Range Buried Water Supply Pipeline. J. Korean Soc. Nondestruct. Test.
**2020**, 40, 241–250. [Google Scholar] [CrossRef] - Randall, R.; Tech, B. Frequency analysis (bruel & kjaer). In Preventative Maintenance Program Handbook (IRD Mechanalysis); Estate Ltd.: Hong Kong, China, 1987. [Google Scholar]
- Almeida, F.C.; Brennan, M.J.; Joseph, P.F.; Dray, S.; Whitfield, S.; Paschoalini, A.T. Towards an in-situ measurement of wave velocity in buried plastic water distribution pipes for the purposes of leak location. J. Sound Vib.
**2015**, 359, 40–55. [Google Scholar] [CrossRef] - Dwyer, R.F. A technique for improving detection and estimation of signals contaminated by under ice noise. J. Acoust. Soc. Am.
**1983**, 74, 124–130. [Google Scholar] [CrossRef] - Dwyer, R. Use of the kurtosis statistic in the frequency domain as an aid in detecting random signals. IEEE J. Ocean. Eng.
**1984**, 9, 85–92. [Google Scholar] [CrossRef][Green Version] - Ottonello, C.; Pagnan, S. Modified frequency domain kurtosis for signal processing. Electron. Lett.
**1994**, 30, 1117–1118. [Google Scholar] [CrossRef] - Foti, S.; Hollender, F.; Garofalo, F.; Albarello, D.; Asten, M.; Bard, P.-Y.; Comina, C.; Cornou, C.; Cox, B.; Di Giulio, G.; et al. Guidelines for the good practice of surface wave analysis: A product of the InterPACIFIC project. Bull. Earthq. Eng.
**2017**, 16, 2367–2420. [Google Scholar] [CrossRef] - Colaço, A.; Ferreira, M.A.; Costa, P.A. Empirical, Experimental and Numerical Prediction of Ground-Borne Vibrations Induced by Impact Pile Driving. Vibration
**2022**, 5, 80–95. [Google Scholar] [CrossRef] - Astrauskas, T.; Grubliauskas, R.; Januševičius, T. Investigation and Evaluation of Speed Table Influence on Road Traffic Induced Ground Borne Vibration. In Environmental Engineering, Proceedings of the International Conference on Environmental Engineering; Department of Construction Economics & Property, Vilnius Gediminas Technical University: Vilnius, Lithuania, 2017; Volume 10, pp. 1–7. [Google Scholar] [CrossRef]
- Graff, K.F. Wave Motion in Elastic Solids; Courier Corporation: Chelmsford, MA, USA, 2012. [Google Scholar]

**Figure 4.**Virtual measurement signal: (

**a**) virtual measurement signal x(t) and (

**b**) virtual measurement signal y(t).

**Figure 5.**Frequency response calculated by the virtual measurement signal: (

**a**) frequency response calculated by virtual measurement signal x(t) and (

**b**) frequency response calculated by virtual measurement signal y(t).

**Figure 7.**Results of FDK: (

**a**) FDK using virtual measurement signal x(t) and (

**b**) FDK using virtual measurement signal y(t).

**Figure 9.**Time signal obtained after the optimal bandpass filter process: (

**a**) using signal x(t) and (

**b**) using signal y(t).

**Figure 17.**Time-domain signal obtained after the optimal bandpass filter process: (

**a**) sensor 1 and (

**b**) sensor 2.

**Figure 19.**Time-domain signals obtained from each sensor including a ground-borne wave: (

**a**) propagation distance of 60 m and (

**b**) propagation distance of 80 m.

**Figure 20.**Excavation signals obtained at various points: (

**a**) results of the excavation test at 60 m, (

**b**) results of the excavation test at 80 m, (

**c**) results of the excavation test at 100 m, (

**d**) results of the excavation test at 120 m, (

**e**) results of the excavation test at 150 m, and (

**f**) results of the excavation test at 180 m.

**Figure 21.**Results of source location comparisons of raw signal and filtered signal: (

**a**) results of the excavation test at 60 m, (

**b**) results of the excavation test at 80 m, (

**c**) results of the excavation test at 100 m, (

**d**) results of the excavation test at 120 m, (

**e**) results of the excavation test at 150 m, and (

**f**) results of the excavation test at 180 m.

Disclaimer/Publisher’s Note: The statements, opinions and data contained in all publications are solely those of the individual author(s) and contributor(s) and not of MDPI and/or the editor(s). MDPI and/or the editor(s) disclaim responsibility for any injury to people or property resulting from any ideas, methods, instructions or products referred to in the content. |

© 2023 by the authors. Licensee MDPI, Basel, Switzerland. This article is an open access article distributed under the terms and conditions of the Creative Commons Attribution (CC BY) license (https://creativecommons.org/licenses/by/4.0/).

## Share and Cite

**MDPI and ACS Style**

Lee, S.-H.; Park, C.-S.; Yoon, D.-J.
Early Detection and Identification of Damage in In-Service Waterworks Pipelines Based on Frequency-Domain Kurtosis and Time-Shift Coherence. *Water* **2023**, *15*, 1189.
https://doi.org/10.3390/w15061189

**AMA Style**

Lee S-H, Park C-S, Yoon D-J.
Early Detection and Identification of Damage in In-Service Waterworks Pipelines Based on Frequency-Domain Kurtosis and Time-Shift Coherence. *Water*. 2023; 15(6):1189.
https://doi.org/10.3390/w15061189

**Chicago/Turabian Style**

Lee, Sun-Ho, Choon-Su Park, and Dong-Jin Yoon.
2023. "Early Detection and Identification of Damage in In-Service Waterworks Pipelines Based on Frequency-Domain Kurtosis and Time-Shift Coherence" *Water* 15, no. 6: 1189.
https://doi.org/10.3390/w15061189