# Calculation of Dry Weather Flows in Pumping Stations to Identify Inflow and Infiltration in Urban Drainage Systems

^{*}

## Abstract

**:**

## 1. Introduction

## 2. Materials and Methods

#### 2.1. Inventory and Configuration Phase

_{p}pumps, a total of${\mathrm{N}}_{\mathrm{SC}}{=2}^{{\mathrm{N}}_{\mathrm{p}}}$ potential pump status combinations (SC) can be defined. These are all the theoretical combinations of the different pumps being idle or active. The total number of transitions from one status combination to another, further called pump status combination changes (SCC), equals ${\mathrm{N}}_{\mathrm{SCC}}{=\mathrm{N}}_{\mathrm{SC}}^{2}$. These SCs and SCCs can be grouped in operational regimes and regime changes: e.g., all SCs that contain a single active pump can be grouped into a regime “single pump use”; all SCs that contain two active pumps can be grouped into a regime “double pump use”, etc. Possible regime changes are then, e.g., the switch from “single pump use” to “double pump use” or vice versa. Appendix A gives an elaborated example of the operational regimes and regime changes for a typical “2 + 1” pump configuration (2 active pumps + 1 spare).

#### 2.2. Data Preprocessing Phase

#### 2.3. Flow Calculation Phase (Cycle Based)

^{3});

_{in}(t): the flow entering the pumping station (m

^{3}/s);

_{out}(t): the flow pumped out from the pumping station (m

^{3}/s).

_{DWF}: the control volume between the dry weather switch-on and switch-off level (m

^{3}) (see Figure 2);

^{3}/s);

^{3}/s);

^{3}/s);

_{fill}: the duration of the filling cycle (s);

_{empt}: the duration of the emptying cycle (s).

_{DWF}is assumed to be constant. However, in reality, settings of switch levels can change over time, meaning that during the processing of longer data sets, V

_{DWF}can vary throughout the data set. This has to be handled during the data preprocessing phase, resulting in a list of V

_{DWF}values per cycle.

_{DWF}for the shortened cycles must be calculated by using the interpolated level at the moment of forced switch-on.

#### 2.4. Linearising the Cycle-Averaged Flows

_{in,2avg}for cycle 2 is transformed into a time-dependent flow varying linearly between Q

_{in,2,1}at time t

_{2,1}, the start of the cycle, and Q

_{in,2,2}at time t

_{2,2}, the end of the cycle. The gradient of this linear variation during the cycle is found by averaging the gradients of the lines that connect the average flows of the successive filling cycles at their respective midpoints. After this linearisation of the filling flows, the flows during the emptying cycles are calculated as linearly varying flows by connecting the end and start values of the linearised flows of the surrounding filling cycles.

#### 2.5. Correction for Phase-Out Time of Pump Flows

_{ph}). In some cases, this can cause the water level in the wet well to continue dropping down after the pump has switched off. A similar phenomenon occurs at the switch-on of pumps: because the pump has a delay time to reach its full capacity, the water level can initially continue to rise above the switch level. However, this delayed start does not affect cycle-based calculations and therefore will not be considered further here.

_{ph}is not known, it must be derived from the observed time at which the level reaches the switch-off level again after the initial dropdown. This is further indicated as the zero-level recovery time, or Δt

_{0}(see Figure 5). In many cases, it will not be possible to derive Δt

_{0}from the available level records. Either the time during which the level drops down below the switch-off level can be shorter than the time interval of the available level data series, or the combination of the incoming flow and pump flow can be such that the water level does not initially drop down at all. In such cases, Δt

_{ph}is set to 0.

_{1}and zero flow at the (still unknown) time t

_{ph}(=t

_{1}+ Δt

_{ph}) and (ii) a linear variation of the incoming flow between Q

_{in,1}, at switch-off time t

_{1}, and Q

_{in,2}, at switch-on time t

_{2}, with the cycle duration ∆t

_{c}= t

_{2}− t

_{1}, Δt

_{0}can be calculated as:

_{0}≤ ∆t

_{ph}(Equation (4)) and ∆t

_{0}≥ ∆t

_{ph}(Equation (5)).

_{ph}from the observed ∆t

_{0}, which yields Equation (6) for ∆t

_{0}≤ ∆t

_{ph}:

_{0}≥ ∆t

_{ph}:

_{ph}can now be consolidated into a single median value per pump $\tilde{\Delta {\mathrm{t}}_{\mathrm{ph},\mathrm{p}}}$(p = 1…N

_{P}). The limitation of this procedure is the assumption that no more than 1 pump is active during dry weather emptying cycles.

#### 2.6. Further Iterative Calculation of Pump Flows and Incoming Flows

## 3. Results

#### 3.1. Results of the Flow Calculation Phase

_{DWF}(see further, Section 3.2).

#### 3.2. Estimation of the Uncertainty of the Results

_{DWF}, and the relative error on the calculated flows δQ equals the sum of the relative errors of the control volume and the cycle duration (δV

_{DWF}+ δ (Δt

_{c})). From these two parameters, the control volume is the one with the highest uncertainty. Even if detailed information to calculate this volume is available, it remains very difficult to account for space taken up by objects such as pump bodies, lifting chains, rising mains and valves, ladders, and benchings. Therefore relative errors of >10% on V

_{DWF}are not unusual. If the control volume extends well into the incoming pipes, this error may be even higher, as explained in Appendix D.

_{DWF}.

_{DWF}and hence of the calculated flows can be reduced if independent flow measurements are available. Because the incoming flows and the pump flows are linked by the continuity equation, it takes only one reference flow, either the incoming flow or the pump flows, to correct both calculations.

_{vol}can be determined from the comparison between reference and calculated flows, e.g., based on daily volumes or averages. Because of the linear relationship, as expressed in Equations (2) and (3), the calculated flows simply need to be multiplied by this correction factor. This is illustrated in Figure 9, where reference pump flows are available from electromagnetic flow meters at the rising mains. The remaining deviations between the calculated and measured pump flows per emptying cycle after correction are due to (i) the differences between the fixed time interval of the measurements (1 min) and the instantaneous registration of the switch times (resolution 1 sec) and (ii) the variability of the pumped flows over the duration of the cycle as a result of the pumps being variable-frequency-driven.

_{DWF}varies over time due to varying switch-on/-off levels or forced switch-on, multiple correction factors have to be determined for different periods. Moreover, when the flow dependency of the in-pipe control volume would have a significant impact on the calculated flows, a simple linear correction may not be sufficient to bring the calculated flows in accordance with reference flows. This is explained in more detail in Appendix D. More investigation is needed to assess what accuracy can be obtained in such cases.

#### 3.3. Identifying the Presence of Inflow and Infiltration

## 4. Discussion

- Pumping stations that have at least one pump permanently active during periods of minimum dry weather flow. This means that in such cases, there are no filling cycles without active pumps, for which the incoming flow is only a function of the control volume and the cycle duration.
- Pumping stations with only one set of switch levels that make it harder to distinguish between dry weather and non-dry weather cycles, especially for periods of light rain.
- Pumping stations with extremely low switch frequencies, where the low number of cycles per day does not allow the reliable linearisation of the calculated average cycle flows.

## 5. Conclusions

## Author Contributions

## Funding

## Institutional Review Board Statement

## Informed Consent Statement

## Data Availability Statement

## Conflicts of Interest

## Appendix A

_{P}= 3;

_{SC}= 8;

_{SCC}= 64.

- “zero” (no pumps working);
- “single” (1 pump working);
- “double” (2 pumps working in parallel).

Status Comb n° | Pump1 | Pump2 | Pump3 | Regime |
---|---|---|---|---|

1 | 0 | 0 | 0 | Zero |

2 | 0 | 0 | 1 | Single |

3 | 0 | 1 | 0 | Single |

4 | 0 | 1 | 1 | Double |

5 | 1 | 0 | 0 | Single |

6 | 1 | 0 | 1 | Double |

7 | 1 | 1 | 0 | Double |

8 | 1 | 1 | 1 | - |

- “single on” (S1) (transition from “zero” to “single” regime);
- “single off” (S0) (transition from “single” to “zero” regime);
- “double on” (D1) (transition from “single” to “double” regime);
- “double off” (D0) (transition from “double” to “single” regime);
- “single change” (Sx) (transition between “single” regimes with different status combinations);
- “double change” (Dx) (transition between “double” regimes with different status combinations).

To Stat Comb | 1 | 2 | 3 | 4 | 5 | 6 | 7 | 8 | |
---|---|---|---|---|---|---|---|---|---|

From Stat Comb | |||||||||

1 | - | S1 | S1 | - | S1 | - | - | - | |

2 | S0 | - | Sx | D1 | Sx | D1 | - | - | |

3 | S0 | Sx | - | D1 | Sx | - | D1 | - | |

4 | - | D0 | D0 | - | - | Dx | Dx | - | |

5 | S0 | Sx | Sx | - | - | D1 | D1 | - | |

6 | - | D0 | - | Dx | D0 | - | Dx | ||

7 | - | - | D0 | Dx | D0 | Dx | - | - | |

8 | - | - | - | - | - | - | - | - |

## Appendix B

_{sw}situated between h

_{sw,forw}(i.e., the switch level calculated by forward extrapolation) and h

_{sw,backw}(i.e., the switch level calculated by backward extrapolation). For every such value, one can calculate the gradients of the level curves between h

_{prec}and h

_{sw}, on one hand (S

_{prec}), and between h

_{sw}and h

_{succ}, on the other hand (S

_{succ}). In this, h

_{prec}represents the last level record before the switch and h

_{succ}is the first level record after the switch. These gradients can then be compared with the gradients of the level curves that are used for the forward and backward extrapolation (S

_{forw}and S

_{backw}). The optimal value of h

_{sw}can be defined as the value that yields the minimum value of δ

_{S}(the average relative difference with the extrapolation gradients) (Equation (A1)).

## Appendix C

Pumping Station | Drainage Area | Nr. Pumps Configuration | Nominal Pump Capacities (Single Use) | Nr. PE Connected | Impervious Area Connected |
---|---|---|---|---|---|

Wauberg | Peer | 3 pumps (2 + 1) | P1 and P2: 18 L/s P3: 27 L/s | 982 | 11 ha |

Wijgmaalsesteenweg | Leuven | 3 pumps (2 + 1) | 69 L/s | 4857 | 48 ha |

Vuntlaan | Leuven | 3 pumps (2 + 1) | 198 L/s | 22,484 | 183 ha |

Zuidstraat | Leuven | 2 pumps (1 + 1) | 31 L/s | 1254 | 13 ha |

#### Appendix C.1. Inventory and Configuration Phase

- Pump configuration and operational regimes/regime changes including the history of switch-on/-off levels;
- Indication of which regimes are considered dry weather regimes;
- Storage geometry (pump well and incoming pipes);
- Assumed nominal pump capacities per pump and per regime;
- (History of) conversion parameters between locally measured levels and national reference levels (TAW);
- Indication of potential cycle duration limits.

#### Appendix C.2. Data Preprocessing Phase

^{3}instead of 3.4 m

^{3}).

## Appendix D

**Figure A6.**(

**a**) Static storage-based delineation (left); (

**b**,

**c**) backwater curve-based delineation (right top and right bottom). The dark blue volumes are considered dead storage; the light blue ones are active storage.

## References

- Beheshti, M.; Sægrov, S. Detection of Extraneous Water Ingress into the Sewer System Using Tandem Methods—A Case Study in Trondheim City. Water Sci. Technol.
**2019**, 79, 231–239. [Google Scholar] [CrossRef] [PubMed] - Dakša, G.; Dejus, S.; Rubulis, J. Assessment of Infiltration from Private Sewer Laterals: Case Study in Jurmala, Latvia. Water
**2022**, 14, 2870. [Google Scholar] [CrossRef] - Jenssen Sola, K.; Bjerkholt, J.; Lindholm, O.; Ratnaweera, H. Infiltration and Inflow (I/I) to Wastewater Systems in Norway, Sweden, Denmark, and Finland. Water
**2018**, 10, 1696. [Google Scholar] [CrossRef][Green Version] - Diem, J.E.; Pangle, L.A.; Milligan, R.A.; Adams, E.A. How Much Water Is Stolen by Sewers? Estimating Watershed-Level Inflow and Infiltration throughout a Metropolitan Area. J. Hydrol.
**2022**, 614, 128629. [Google Scholar] [CrossRef] - Dirckx, G.; Bixio, D.; Thoeye, C.; De Gueldre, G.; Van De Steene, B. Dilution of Sewage in Flanders Mapped with Mathematical and Tracer Methods. Urban Water J.
**2009**, 6, 81–92. [Google Scholar] [CrossRef] - Dirckx, G.; Fenu, A.; Wambecq, T.; Kroll, S.; Weemaes, M. Dilution of Sewage: Is It, after All, Really Worth the Bother? J. Hydrol.
**2019**, 571, 437–447. [Google Scholar] [CrossRef] - Bentes, I.; Silva, D.; Vieira, C.; Matos, C. Inflow Quantification in Urban Sewer Networks. Hydrology
**2022**, 9, 52. [Google Scholar] [CrossRef] - Ohlin Saletti, A.; Lindhe, A.; Söderqvist, T.; Rosén, L. Cost to Society from Infiltration and Inflow to Wastewater Systems. Water Res.
**2023**, 229, 119505. [Google Scholar] [CrossRef] - Rezaee, M.; Tabesh, M. Effects of Inflow, Infiltration, and Exfiltration on Water Footprint Increase of a Sewer System: A Case Study of Tehran. Sustain. Cities Soc.
**2022**, 79, 103707. [Google Scholar] [CrossRef] - Franz, T. Spatial Classification Methods for Efficient Infiltration Measurements and Transfer of Measuring Results. Ph.D. Thesis, Technische Universität Dresden, Dresden, Germany, 2007. [Google Scholar]
- Guo, S.; Ding, R.; Huang, B.; Zhu, D.Z.; Zhou, W.; Li, M. Experimental Study on Three Simple Tracers for the Assessment of Extraneous Water into Sewer Systems. Water Sci. Technol.
**2022**, 85, 633–644. [Google Scholar] [CrossRef] - Guo, S.; Shi, X.; Luo, X.; Yang, H. River Water Intrusion as a Source of Inflow into the Sanitary Sewer System. Water Sci. Technol.
**2020**, 82, 2472–2481. [Google Scholar] [CrossRef] [PubMed] - Heiderscheidt, E.; Tesfamariam, A.; Marttila, H.; Postila, H.; Zilio, S.; Rossi, P.M. Stable Water Isotopes as a Tool for Assessing Groundwater Infiltration in Sewage Networks in Cold Climate Conditions. J. Environ. Manag.
**2022**, 302, 114107. [Google Scholar] [CrossRef] [PubMed] - Zhang, M.; Liu, Y.; Dong, Q.; Hong, Y.; Huang, X.; Shi, H.; Yuan, Z. Estimating Rainfall-Induced Inflow and Infiltration in a Sanitary Sewer System Based on Water Quality Modelling: Which Parameter to Use? Environ. Sci. Water Res. Technol.
**2018**, 4, 385–393. [Google Scholar] [CrossRef] - De Bénédittis, J.; Bertrand-Krajewski, J.-L. Measurement of Infiltration Rates in Urban Sewer Systems: Use of Oxygen Isotopes. Water Sci. Technol.
**2005**, 52, 229–237. [Google Scholar] [CrossRef] - Kracht, O.; Gresch, M.; Gujer, W. A Stable Isotope Approach for the Quantification of Sewer Infiltration. Environ. Sci. Technol.
**2007**, 41, 5839–5845. [Google Scholar] [CrossRef] - Beheshti, M. Application of Infrastructure Asset Management in Enhancing the Performance of Sewer Networks. Ph.D. Thesis, Norwegian University of Science and Technology: Trondheim, Norway, 2019. [Google Scholar]
- Thapa, J.B.; Jung, J.K.; Yovichin, R.D. A Qualitative Approach to Determine the Areas of Highest Inflow and Infiltration in Underground Infrastructure for Urban Area. Adv. Civ. Eng.
**2019**, 2019, 2620459. [Google Scholar] [CrossRef] - Schilperoort, R.; Hoppe, H.; de Haan, C.; Langeveld, J. Searching for Storm Water Inflows in Foul Sewers Using Fibre-Optic Distributed Temperature Sensing. Water Sci. Technol.
**2013**, 68, 1723–1730. [Google Scholar] [CrossRef] - Beheshti, M.; Sægrov, S. Quantification Assessment of Extraneous Water Infiltration and Inflow by Analysis of the Thermal Behavior of the Sewer Network. Water
**2018**, 10, 1070. [Google Scholar] [CrossRef][Green Version] - Panasiuk, O.; Hedström, A.; Langeveld, J.; de Haan, C.; Liefting, E.; Schilperoort, R.; Viklander, M. Using Distributed Temperature Sensing (DTS) for Locating and Characterising Infiltration and Inflow into Foul Sewers before, during and after Snowmelt Period. Water
**2019**, 11, 1529. [Google Scholar] [CrossRef][Green Version] - Panasiuk, O.; Hedström, A.; Langeveld, J.; Viklander, M. Identifying Sources of Infiltration and Inflow in Sanitary Sewers in a Northern Community: Comparative Assessment of Selected Methods. Water Sci. Technol.
**2022**, 86, 1–16. [Google Scholar] [CrossRef] - Beheshti, M.; Sægrov, S.; Ugarelli, R. Infiltration/Inflow Assessment and Detection in Urban Sewer System. Vann J.
**2015**, 1, 24–34. [Google Scholar] - Karpf, C.; Hoeft, S.; Scheffer, C.; Fuchs, L.; Krebs, P. Groundwater Infiltration, Surface Water Inflow and Sewerage Exfiltration Considering Hydrodynamic Conditions in Sewer Systems. Water Sci. Technol.
**2011**, 63, 1841–1848. [Google Scholar] [CrossRef] - Sowby, R.B.; Jones, D.R. A Practical Statistical Method to Differentiate Inflow and Infiltration in Sanitary Sewer Systems. J. Environ. Eng.
**2022**, 148, 06021006. [Google Scholar] [CrossRef] - ATV-DVWK. Arbeitsblatt ATV-DVWK-A 198, Vereinheitlichung und Herleitung von Bemessungswerten für Abwasseranlagen (Standardisation and Derivation of Dimensioning Values for Wastewater Facilities); ATV-DVWK Deutsche Vereinigung für Wasserwirtschaft, Abwasser und Abfall e.V.: Hennef, Germany, 2003; Volume Band A 198. [Google Scholar]
- Weiß, G.; Brombach, H.; Haller, B. Infiltration and Inflow in Combined Sewer Systems: Long-Term Analysis. Water Sci. Technol.
**2002**, 45, 11–19. [Google Scholar] [CrossRef] - Zhang, K.; Parolari, A.J. Impact of Stormwater Infiltration on Rainfall-Derived Inflow and Infiltration: A Physically Based Surface–Subsurface Urban Hydrologic Model. J. Hydrol.
**2022**, 610, 127938. [Google Scholar] [CrossRef] - Jayasooriya, M.; Dahlhaus, P.; Vic, M.H.; Barton, A.; Gell, P. An Assessment of the Monitoring Methods and Data Limitations for Inflow and Infiltration in Sewer Networks. In Proceedings of the 36th HWRS: The Art and Science of Water, Hobart, Australia, 7–10 December 2015; Engineers Australia: Hobart, Australia, 2015. [Google Scholar]
- Bogusławski, B.; Sobczak, P.; Głowacka, A. Assessment of Extraneous Water Inflow in Separate Sewerage System by Different Quantitative Methods. Appl. Water Sci.
**2022**, 12, 278. [Google Scholar] [CrossRef] - De Bénédittis, J.; Bertrand-Krajewski, J.-L. Infiltration in Sewer Systems: Comparison of Measurement Methods. Water Sci. Technol.
**2005**, 52, 219–227. [Google Scholar] [CrossRef] [PubMed] - Sola, K.J.; Bjerkholt, J.T.; Lindholm, O.G.; Ratnaweera, H. Analysing Consequences of Infiltration and Inflow Water (I/I-Water) Using Cost-Benefit Analyses. Water Sci. Technol.
**2020**, 82, 1312–1326. [Google Scholar] [CrossRef] - Ohlin Saletti, A.; Rosén, L.; Lindhe, A. Framework for Risk-Based Decision Support on Infiltration and Inflow to Wastewater Systems. Water
**2021**, 13, 2320. [Google Scholar] [CrossRef] - Tomperi, J.; Rossi, P.M.; Ruusunen, M. Estimation of Wastewater Flowrate in a Gravitational Sewer Line Based on a Low-Cost Distance Sensor. Water Pract. Technol.
**2022**, 18, 40–52. [Google Scholar] [CrossRef] - Bertrand-Krajewski, J.-L.; Clemens-Meyer, F.; Lepot, M. (Eds.) Metrology in Urban Drainage and Stormwater Management: Plug and Pray; IWA Publishing: London, UK, 2021; ISBN 978-1-78906-011-9. [Google Scholar]
- Fencl, M.; Grum, M.; Borup, M.; Mikkelsen, P.S. Robust Model for Estimating Pumping Station Characteristics and Sewer Flows from Standard Pumping Station Data. Water Sci. Technol.
**2019**, 79, 1739–1745. [Google Scholar] [CrossRef] [PubMed] - Zhang, Z.; Laakso, T.; Wang, Z.; Pulkkinen, S.; Ahopelto, S.; Virrantaus, K.; Li, Y.; Cai, X.; Zhang, C.; Vahala, R.; et al. Comparative Study of AI-Based Methods—Application of Analyzing Inflow and Infiltration in Sanitary Sewer Subcatchments. Sustainability
**2020**, 12, 6254. [Google Scholar] [CrossRef] - Matlab, 2019; The MathWorks, Inc.: Natick, MA, USA, 2019.

**Figure 6.**Example of individual cycles’ flows: (

**a**) pumped flows per cycle per pump (top); (

**b**) average incoming flows for filling and emptying cycles and linearised flows for all cycles (bottom) (PS Zuidstraat).

**Figure 7.**Example of calculated pump flows with pumps of different nominal capacities: (

**a**) pumped flows per cycle per pump (top); (

**b**) average incoming flows for filling and emptying cycles and linearised flows for all cycles (bottom) (PS Wauberg).

**Figure 8.**Effect of missing pump loggings on the calculated cycle flows: (

**a**) pumped flows per cycle per pump (top); (

**b**) average incoming flows for filling and emptying cycles and linearised flows for all cycles (bottom) (PS Wijgmaalsesteenweg).

**Figure 9.**Calculated vs. measured pump flows before (

**a**) and after (

**b**) control volume correction (PS Vuntlaan).

**Figure 10.**Overview of daily incoming volumes: (

**a**) only dry weather days (top); (

**b**) all days including rainfall for the selected period (bottom) (PS Zuidstraat).

**Figure 11.**Calculated incoming flows at the start and end of a dry period with high initial infiltration (PS Zuidstraat).

**Figure 12.**Example of the impact of a construction site’s pumped groundwater drainage. The inflow period extends from 22 June 2022 to 22 July 2022. (PS Wauberg).

Disclaimer/Publisher’s Note: The statements, opinions and data contained in all publications are solely those of the individual author(s) and contributor(s) and not of MDPI and/or the editor(s). MDPI and/or the editor(s) disclaim responsibility for any injury to people or property resulting from any ideas, methods, instructions or products referred to in the content. |

© 2023 by the authors. Licensee MDPI, Basel, Switzerland. This article is an open access article distributed under the terms and conditions of the Creative Commons Attribution (CC BY) license (https://creativecommons.org/licenses/by/4.0/).

## Share and Cite

**MDPI and ACS Style**

Van Assel, J.; Kroll, S.; Delgado, R. Calculation of Dry Weather Flows in Pumping Stations to Identify Inflow and Infiltration in Urban Drainage Systems. *Water* **2023**, *15*, 864.
https://doi.org/10.3390/w15050864

**AMA Style**

Van Assel J, Kroll S, Delgado R. Calculation of Dry Weather Flows in Pumping Stations to Identify Inflow and Infiltration in Urban Drainage Systems. *Water*. 2023; 15(5):864.
https://doi.org/10.3390/w15050864

**Chicago/Turabian Style**

Van Assel, Johan, Stefan Kroll, and Rosalia Delgado. 2023. "Calculation of Dry Weather Flows in Pumping Stations to Identify Inflow and Infiltration in Urban Drainage Systems" *Water* 15, no. 5: 864.
https://doi.org/10.3390/w15050864