- freely available
Membranes 2013, 3(4), 285-297; doi:10.3390/membranes3040285
Published: 11 October 2013
Abstract: A secondary treatment for olive mill wastewater coming from factories working with the two-phase olive oil production process (OMW-2) has been set-up on an industrial scale in an olive oil mill in the premises of Jaén (Spain). The secondary treatment comprises Fenton-like oxidation followed by flocculation-sedimentation and filtration through olive stones. In this work, performance modelization and preliminary cost analysis of a final reverse osmosis (RO) process was examined on pilot scale for ulterior purification of OMW-2 with the goal of closing the loop of the industrial production process. Reduction of concentration polarization on the RO membrane equal to 26.3% was provided upon increment of the turbulence over the membrane to values of Reynolds number equal to 2.6 × 104. Medium operating pressure (25 bar) should be chosen to achieve significant steady state permeate flux (21.1 L h−1 m−2) and minimize membrane fouling, ensuring less than 14.7% flux drop and up to 90% feed recovery. Under these conditions, irreversible fouling below 0.08 L h−2 m−2 bar−1 helped increase the longevity of the membrane and reduce the costs of the treatment. For 10 m3 day−1 OMW-2 on average, 47.4 m2 required membrane area and 0.87 € m−3 total costs for the RO process were estimated.
Two principal wastewater streams are nowadays by-produced in olive mills working with the two-phase system during the production process of olive oil: olives washing wastewater (OWW), which is produced during the olive-fruit washing procedure in the washing machines, and olive oil washing wastewater (OOW), which is derived in the olive oil extraction process during the washing of the olive oil in the vertical centrifuges (Figure 1). The treatment of the liquid effluents generated during olive oil production in olive mills, together called olive mill wastewater (OMW-2), is currently still a hard task, due to multiple factors [1,2].
At the present, an average-sized olive oil factory working in continuous mode leads to a daily amount of up to 10–15 m3 of OOW, in sum to 1 m3 day−1 of OWW. In order to get an idea of the dimensions of this, in Spain alone, this generates a total volume of more than 9 million m3 of OMW-2 per year. Furthermore, the pollutants load of these effluents is extremely variable, not only owing to the extraction process, but also to edaphoclimatic and cultivation parameters, the type of the olives, their quality and maturity, and other factors [1,3]. These factors, in addition to small size and widespread geographical dispersion of olive oil factories, establish important difficulties for the management of these hazard effluents.
These wastewaters are highly phytotoxic and hazardous for water bodies, soil and aquifers due to the presence of aromatic compounds and a wide range of other organic pollutants, such as phenols, tannins and long-chain fatty acids, which are not suitable to be biologically managed. Due to the resistance of OMW-2 to microbial degradation , biological treatment of OMW-2 is not applied on an industrial scale as it is not efficient. Within this context, advanced operation processes (AOPs) are required for the depuration of these bio-refractory wastewaters [4,5,6,7,8,9,10,11,12,13,14,15,16].
Moreover, these effluents also exhibit high saline toxicity, and thus very significant electroconductivity (EC) values owing to the presence of a high concentration of inorganic compounds among which chloride, sulfate and phosphoric salts of potassium, calcium, iron, magnesium, sodium, copper and traces of other elements are common characteristics . This fact also makes it necessary to resort to advanced separation technologies in order to attempt complete depuration of OMW-2, since it is not viable to abate the high concentration of dissolved monovalent and divalent ions by conventional physicochemical treatments. In this regard, as regulations become more stringent, membranes technology offers many advantages compared with other separation processes [17,18].
A secondary treatment for olive mill wastewater coming from factories working with the two-phase olive oil production process (OMW-2) has been recently set-up and transferred to an industrial scale in an olive oil mill in the premises of Baeza (Jaén, Spain) by the Chemical and Biochemical Processes Technology Research Group of the University of Granada (Granada, Spain) (Figure 2). The secondary treatment comprises Fenton-like oxidation, flocculation and filtration through olive stones. Fenton’s process appears to be the most economically advantageous AOP since it may be conducted at ambient temperature and pressure conditions, and also due its equipment simplicity and operational ease. Furthermore, the use of olive stones boosts the cost-effectiveness of the secondary treatment process as it is an abundant and renewable agricultural residue available at zero cost.
In this research work, ulterior purification of OMW-2 was intended with the goal of closing the loop of the industrial production process, pursuing the quality standards for reuse of the purified effluent in the proper olive washing machines. With this intention, modelization of the performance and preliminary cost analysis of a final reverse osmosis (RO) process was studied on a pilot scale.
2. Experimental Section
2.1. Analytical Methods
Analytical grade reagents and 99% purity chemicals were used for the analytical procedures, applied at least in triplicate. Chemical oxygen demand (COD), total suspended solids (Tss), total phenols (TPh), total iron, electroconductivity (EC) and pH measurements were carried out in the raw OMW-2 stream and in the treated effluent at the end of each depuration step following standard methods .
Chemical oxygen demand (COD) was determined by the photometric determination of the concentration of chromium (III) after 2 h of oxidation with potassium dichromate/sulfuric acid/silver sulfate at 148 ± 0.5 °C (German standard methods DIN 38 409-H41-1 and DIN ISO 15 705-H45) . At the time of the determination of COD, manganese oxide was used to remove residual hydrogen peroxide which remained unreacted in samples taken from the reactor.
To determine the total suspended solids concentration (Tss), wastewater samples were filtered through 1.6 μm standard GF/F glass fiber filters. The residue retained on the filter was dried in an oven at 105 ± 0.5 °C until constant weight was observed. The increase in weight of the filter represents the Tss. Ashes correspond to the mineral salts remaining after the waste sample was calcined further at 600 ± 0.5 °C for 3 h .
Total phenols and phenol derivatives were analyzed by reaction with a derivative thiazol, giving a purple azo dye which was determined photometrically at 475 nm (Standard German methods ISO 8466-1 and DIN 38402 A51) .
EC and pH measurements were performed with a Crison GLP31 conductivity-meter and a Crison GLP21 pH-meter, with autocorrection of temperature. A Helios Gamma UV-visible spectrophotometer (Thermo Fisher Scientific) served for COD, TPh and total iron measurements. Effluent samples were diluted when necessary with MilliQ® water for their analysis, whereas samples of RO permeate were analyzed directly without dilution.
Ionic concentrations were analyzed in the raw OMW-2, in the effluent exiting the secondary treatment (OMWST-2) as well as in the permeate stream of the final RO membrane stage with a Dionex DX-120 ion chromatograph as described in previous works [20,21].
Total iron concentration was measured by reducing all iron ions to iron ions (II) in a thioglycolate medium with a derivative of triazine, forming a reddish-purple complex photometrically determined at 565 nm (Standard German methods ISO 8466-1 and German DIN 38402 A51) .
2.2. The OMW-2 Stream
Samples of both OWW and OOW were collected during winter months from various olive oil factories working with the modern two-phase olive oil extraction process in the Andalusian province of Jaén (Spain). The physicochemical characterization of the raw OWW and OOW samples are reported in Table 1.
|Table 1. Physicochemical characterization determined of raw OWW and OOW.|
|Parameters||Raw OWW||Raw OOW|
|EC, mS cm−1||1.5||2.7|
|BOD5, mg O2 L−1||0.50||0.79|
|COD, mg O2 L−1||0.7||7.4|
|Total phenols, mg L−1||3.7||561.5|
|Total solids, %||0.27||0.6|
|Organic substances, %||0.10||0.49|
Firstly, OWW and OOW samples were rapidly analyzed in the laboratory. Afterwards, both effluents were mixed in 1:1 (v/v) proportion in order to stabilize the mean value of the organic concentration and avoid sensible fluctuations in the COD parameter of the stream entering the treatment system (OMW-2) (Table 2). OMW-2 stream was conducted to the secondary treatment already set-up on an industrial scale by the Chemical and Biochemical Processes Technology Research Group of the University of Granada (Granada, Spain). The secondary treatment consists basically in an AOP based on Fenton’s reagent. In the industrial plant, the use of the cheaper ferric (FeCl3) catalyst (Fenton-like oxidation) instead of ferrous ones highly improves the cost-effectiveness of the process [5,6]. Following the oxidation reactor, flocculation-sedimentation and filtration in series ensure recovery of the catalyst [22,23]: the iron-rich sludge sedimented in the decanter is recirculated to the OWW tank (Figure 3) to reduce the catalyst consumption , whereas olive stones permit eliminating the residual iron which is known to be especially harmful for polymeric membranes . In this regard, olive stones represent an abundant and renewable agricultural residue available at zero cost. A scheme of the industrial-scale secondary treatment is given in Figure 3, and the physicochemical composition of the raw OMW-2 stream and the effluent exiting the secondary treatment (OMWST-2) is reported in Table 2.
|Table 2. Olive mill wastewater (OMW-2) characterization at the outlet of each secondary treatment stage.|
|Parameters||Raw OMW-2||OMW-2 at the outlet of the secondary treatment|
|EC, mS cm−1||2.3||3.43|
|Tss, mg L−1||60.1||13.1|
|COD, mg O2 L−1||4050.5||150.8|
|Total phenols, mg L−1||282.6||0.4|
|Total iron, mg L−1||7.9||0.03|
|Cl−, mg L−1||554.5||990.9|
|Na+, mg L−1||486.2||718.6|
2.3. Membranes Pilot Plant
The research study on the final RO membrane operation was conducted in a pilot plant provided with a 100 L feed tank (FT), where the pretreated feedstock was loaded through a feed line, and a pumping system consisting of a centrifugal booster pump (P1) and a volumetric piston pump (P2) that served to drive the OMWST-2 stream to the spiral-wound (SW) membrane module fitted in housing M1 (Figure 4).
Tangential-flow RO experiments were performed in semicontinuous operation mode (diafiltration): the permeate stream was collected whereas the concentrate stream was recycled back the feed tank while entering new fresh OMWST-2 feedstock to the membrane system.
The selected RO membrane was a commercial spiral-wounded thin-film composite (TFC) membrane provided by GE Water and Process Technologies (Minnetonka, MN, USA), consisting of a polyamide active layer on a polysulfone ultrafiltration support, with an active area of 2.5 m2. Nominal characteristics of the selected virgin RO membrane and of the spacer are reported in Table 3.
|Table 3. Membrane specifications.|
|Membrane model||SC series (RO)|
|Nominal salt rejection, %||98.9|
|Effective surface area, m2||2.5|
|Permeability, L h−1 m−2 bar−1||1.4 ± 0.2|
|Chemical composition||TFC aromatic polyamide/polysulfone|
|Maximum pressure, bar||40|
|Maximum temperature, °C||90|
|Spacer configuration||45 mil parallel|
|Spacer mesh diameter, mm||2|
The desired operating pressure over the membrane and the feed flow rate to the module could be adjusted by acting on the regulation valves V1 and V2, which are shown in Figure 4, with an accuracy of 0.5 bar and 10 L h−1 respectively. The V1 valve was used for by-pass whereas the V2 valve served for regulating the flow rate of the concentrate stream, which was recirculated to the feedwater tank. Operating pressure and feed flow rate were respectively measured by analogue manometers and a turbine flow meter, whereas permeate flux was calculated during operation time by weighing the mass of collected permeate on a precision electronic mass balance (AX-120 Cobos, 0.1 mg accuracy). In all experiments, operating temperature was controlled at a fixed value equal to ambient temperature (22 °C) by means of a plate heat exchanger (E) (see Figure 4), regulated automatically (Tset point ± 0.1 °C) via a proportional–integral–derivative (PID) electronic temperature controller (Yokogawa model UT100) and a magnetic valve in the temperature-controlling loop.
3. Results and Discussion
The objective of this work was to close the loop of the industrial production process of an olive mill working with the two-phase extraction procedure in Baeza (Jaén, Spain). With this intention, optimization of a final RO operation to achieve the quality standards for reuse of the purified OMW-2 effluent in the proper olive washing machines was examined. Performance of the RO membrane module was modelized, including permeate flux and membrane rejection as function of the main operating variables, i.e., operating pressure and tangential velocity. Finally, membrane fouling and life-time service as well as simplified economical analysis of the RO process was studied.
Firstly, the effect of the net driving pressure of the system on the permeate flux of the selected RO membrane was studied by fitting the experimental data to the solution-diffusion model:
The data regarding the dependence of the membrane permeability on the net driving pressure and tangential velocity are reported in Table 4 in the form of pure water permeability (Kw) and permeability with the OMWST-2 effluent (K), obtained for ambient operating temperature (22 °C). The osmotic pressure of OMWST-2, equal to 1.5 bar at 22 °C, was calculated by means of Van’t Hoff equation πf = Σci,f·RT, where ci,f is the feed molar concentration of ion i (mol L−1), R is the ideal gas constant (8.314 J K−1 mol−1) and T is the absolute temperature (K).
|Table 4. Permeability coefficients and resistances of the selected reverse osmosis (RO) membrane.|
|vt, m s−1||NRe||Kw, L h−1 m−2 bar−1||Rm, m−1||K, L h−1 m−2 bar−1||RCP, m−1|
|2.55||1.3 × 104||1.41 ± 0.1||2.6 × 1014||0.86 ± 0.1||1.9 × 1014|
|5.09||2.6 × 104||1.41 ± 0.1||2.6 × 1014||0.90 ± 0.1||1.4 × 1014|
Notes: Operating conditions: 3–35 bar, 22 °C; vt: tangential velocity; NRe: Reynolds number.
Results withdrawn show a value of the pure water permeability coefficient (Kw) of 1.41 L h−1 m−2 bar−1, whereas K measured with the secondary-treated effluent (OMWST-2) was equal to 0.86 L h−1 m−2 bar−1 upon turbulent regime over the membrane (tangential velocity equal to vt = 2.55 m s−1, corresponding to Reynolds number NRe = 1.3 × 104). The striking difference in the permeability coefficients between pure water and OMWST-2 (36.2%– 39.0% for NRe = 1.3 × 104 − 2.6 × 104) shall be attributed to concentration polarization and fouling resistance taking place on the boundary region of the RO membrane (Table 4) [25,26]. A guided focus on Table 4 permits us to note that reduction of the concentration polarization (RCP) on the RO membrane equal to 26.3% was provided upon an increment of the turbulence on the membrane to values of NRe = 2.6 × 104.
Secondly, membrane fouling was examined by calculating the fouling index (b) at every operating condition during diafiltration run time. With this purpose, the experimental permeate flux data were fitted with the threshold flux equation proposed by Field and Pearce (2011) :
Results are given in Table 5, showing that medium operating pressure should be chosen (25 bar) upon turbulent regime over the membrane (5.09 m s−1, that is NRe = 2.6 × 104) to achieve significant steady state permeate flux (21.1 L h−1 m−2) and minimize membrane fouling (b index equal to 0.32), ensuring less than 14.7% permeate flux drop and up to 90% feed recovery.
|Table 5. Results determined for the RO performance at several operating conditions.|
|vt, m s−1||PTM, bar||T, °C||J0, L h−1 m−2||Jss, L h−1 m−2||−ΔJp, %||b, h−1||Y, %|
Notes: vt: tangential velocity; Jss: steady-state permeate flux; −ΔJp: permeate flux loss at the end of experiment; REC, RCOD: conductivity and COD rejection; b: fouling index; Y: volume recovery; n.o.: not observed.
Finally, selectivity of the selected RO membrane was modelized by means of the Spiegler-Kedem model:
|Table 6. Coefficients for electroconductivity (EC) and chemical oxygen demand (COD) rejection.|
|Parameter||Rejection, %||σi||βi, bar|
A simplified economical balance of the treatment process was performed based on a daily amount of 10 m3 OMW-2 on average. In our former studies [6,22], the secondary treatment process was presented as an economically advantageous AOP, providing high mineralization of the recalcitrant organic matter present in the raw effluent . Estimated operating costs of approximately 2.4 € m−3 for conductive-diamond electrochemical oxidation, 8.5 € m−3 for ozonation and 0.7 € m−3 for Fenton-like process highlight the latter as the most cost-effective one. Furthermore, filtration through olive stones is costless .
Under the best operating conditions studied for the final RO operation, significant steady-state permeate flux production was attained (21.1 L h−1 m−2) and the constant fouling parameter a was estimated to be −0.08 L h−2 m−2 bar−1. The a parameter takes into account the irreversible fouling irretrievably attained on the RO membrane that steadily reduces its virgin permeability and therefore has direct implications in the module substitution periodicity. A membrane lifetime over 5 years can be ensured for a mean daily operating time equal to 10 h and taking into consideration that the olive oil campaign, when the OMW-2 is generated, lasts 90 days a year on average. The minimum required membrane area is equal to 47.4 m2 for the daily volume of OMW-2 treated. This implies the need of two RO membrane modules of 32 m2 surface each. The modules would work in parallel configuration: one in service, whereas the other would be in cleaning protocol when the diafiltration cycle finishes. This means an overdesign of 26% of the required membrane surface. Energy costs were fixed at 0.10 € kWh−1, whereas membrane module and housing were equal to 22 € m−2 and 380 €. Pumps, piping and instrumentation of the RO membrane plant represent approximately 50% of the membrane housing costs, whereas facility space needs and services represent 15% of total costs [35,36].
Finally, the total expenses of the whole integrated OMW-2 treatment process, taking into account the final purification of the effluent by the selected TFC RO membrane and the secondary treatment, are given in Table 7, and the physicochemical characteristics of the final permeate stream are reported in Table 8. The proposed integrated treatment permits us to close the loop of the olive oil production process (Figure 5), rending it environmentally respectful (Figure 6) and boosting its cost-effectiveness.
|Table 7. Cost evaluation of RO operation and whole integrated process.|
|Parameter||Cost, € m−3|
|Housing and piping||0.22|
|Total costs of RO operation||0.87|
|Total costs of the integrated process||1.57|
|Table 8. Physicochemical composition of permeate stream.|
|Parameter||Value in permeate stream|
|EC, µS cm−1||95.0–97.0|
|Tss, mg L−1||0|
|COD, mg L−1||2.3–3.7|
|Total phenols, mg L−1||0|
|[Fe]Total, µg L−1||0|
|[Cl−], mg L−1||15.5–20.7|
|[Na+], mg L−1||11.1–16.7|
Performance modelization and preliminary cost analysis of a final reverse osmosis (RO) treatment was examined on a pilot scale for ulterior purification of the effluents generated by olive oil factories working with the two-phase olive oil extraction procedure. The goal was closing the loop of the industrial production process of an olive oil mill in the premises of Jaén (Spain), where a secondary treatment comprising Fenton-like oxidation, flocculation and filtration through olive stones has been successfully set-up.
Reduction of concentration polarization on the RO membrane equal to 26.3% was provided upon increment of the turbulence over the membrane to values of Reynolds number equal to 2.6 × 104. Medium operating pressure (25 bar) helped achieve significant steady state permeate flux (21.1 L h−1 m−2) and minimize membrane fouling, ensuring less than 14.7% flux drop and up to 90% feed recovery. Under these conditions, less than 0.08 L h−2 m−2 bar−1 irreversible fouling was measured, increasing the longevity of the membranes and reducing the capital and operating costs of the treatment. Finally, 47.4 m2 required membrane area and 0.87 € m−3 total costs were estimated for the RO process on a daily basis of 10 m3 OMW-2. The proposed integrated process permits us to close the loop of olive oil production, rending it environmentally respectful and boosting its cost-effectiveness.
Spanish Ministry of Science and Innovation is gratefully acknowledged for funding the project CTQ2010-21411: Depuration of wastewater from olive oil industry for its reutilization in the process.
Conflicts of Interest
The authors declare no conflict of interest.
- Voreadou, K. Olive Mill Wastewater: A Trial for the Water Ecosystems. In Proceedings of Symposium on Treatment of Wastes from Olive Mills; Greek Agrotechnical Society: Heraklion, Greece, 1989.
- Ochando-Pulido, J.M.; Hodaifa, G.; Victor-Ortega, M.D.; Rodriguez-Vives, S.; Martinez-Ferez, A. Effective treatment of olive mill effluents from two-phase and three-phase extraction processes by batch membranes in series operation upon threshold conditions. J. Hazard. Mater. 2013, doi:10.1016/j.jhazmat.2013.03.041.
- Hodaifa, G.; Eugenia-Sánchez, M.; Sánchez, S. Use of industrial wastewater from olive-oil extraction for biomass production of Scenedesmus obliquus. Bioresour. Technol. 2008, 99, 1111–1117, doi:10.1016/j.biortech.2007.02.020.
- De Heredia, J.B.; Garcia, J. Process integration: Continuous anaerobic digestion–ozonation treatment of olive mill wastewater. Ind. Eng. Chem. Res. 2005, 44, 8750–8755, doi:10.1021/ie040232x.
- Nieto, L.M.; Hodaifa, G.; Rodríguez, S.; Giménez, J.A.; Ochando, J. Degradation of organic matter in olive oil mill wastewater through homogeneous Fenton-like reaction. Chem. Eng. J. 2011, 173, 503–510, doi:10.1016/j.cej.2011.08.022.
- Hodaifa, G.; Ochando-Pulido, J.M.; Rodriguez-Vives, S.; Martinez-Ferez, A. Optimization of continuous reactor at pilot scale for olive-oil mill wastewater treatment by Fenton-like process. Chem. Eng. J. 2013, 220, 117–124, doi:10.1016/j.cej.2013.01.065.
- Stoller, M.; Bravi, M. Critical flux analyses on differently pretreated olive vegetation wastewater streams: Some case studies. Desalination 2010, 250, 578–582, doi:10.1016/j.desal.2009.09.027.
- De Caprariis, B.; Di Rita, M.; Stoller, M.; Verdone, N.; Chianese, A. Reaction-precipitation by a spinning disc reactor: Influence of hydrodynamics on nanoparticles production. Chem. Eng. Sci. 2012, 76, 73–80, doi:10.1016/j.ces.2012.03.043.
- Sacco, O.; Stoller, M.; Vaiano, V.; Ciambelli, P.; Chianese, A.; Sannino, D. Photocatalytic degradation of organic dyes under visible light on n-doped photocatalysts. Int. J. Photoenergy 2012, 2012, 626759:1–626759:8.
- Papastefanakis, N.; Mantzavinos, D.; Katsaounis, A. DSA electrochemical treatment of olive mill wastewater on Ti/RuO2 anode. J. Appl. Electrochem. 2010, 40, 729–737, doi:10.1007/s10800-009-0050-9.
- Altay, U.; Koparal, A.S.; Ogutveren, U.B. Complete treatment of olive mill wastewaters by electrooxidation. Chem. Eng. J. 2008, 139, 445–452, doi:10.1016/j.cej.2007.08.009.
- Cañizares, P.; Martinez, L.; Paz, R.; Saéz, C.; Lobato, J.; Rodrigo, M.A. Treatment of Fenton-refractory olive oil mill wastes by electrochemical oxidation with boron-doped diamond anodes. J. Chem. Technol. Biotechnol. 2006, 81, 1331–1337, doi:10.1002/jctb.1428.
- Grafias, P.; Xekoukoulotakis, N.P.; Mantzavinos, D.; Diamadopoulos, E. Pilot treatment of olive pomace leachate by vertical-flow constructed wetland and electrochemical oxidation: An efficient hybrid process. Water Res. 2010, 44, 2773–2780, doi:10.1016/j.watres.2010.02.015.
- Lafi, W.K.; Shannak, B.; Al-Shannag, M.; Al-Anber, Z.; Al-Hasan, M. Treatment of olive mill wastewater by combined advanced oxidation and biodegradation. Sep. Purif. Technol. 2009, 70, 141–146, doi:10.1016/j.seppur.2009.09.008.
- Khoufi, S.; Aloui, F.; Sayadi, S. Treatment of olive oil mill wastewater by combined process electro-Fenton reaction and anaerobic digestion. Water Res. 2006, 40, 2007–2016, doi:10.1016/j.watres.2006.03.023.
- Rizzo, L.; Lofrano, G.; Grassi, M.; Belgiorno, V. Pretreatment of olive mill wastewater by chitosan coagulation and advanced oxidation processes. Sep. Purif. Technol. 2008, 63, 648–653, doi:10.1016/j.seppur.2008.07.003.
- Iaquinta, M.; Stoller, M.; Merli, C. Optimization of a nanofiltration membrane for tomato industry wastewater treatment. Desalination 2009, 245, 314–320, doi:10.1016/j.desal.2008.05.028.
- Ochando-Pulido, J.M.; Martinez-Ferez, A. A focus on pressure-driven membrane technology in olive mill wastewater reclamation: State of the art. Water Sci. Technol. 2012, 66, 2505–2516, doi:10.2166/wst.2012.506.
- Greenberg, A.E.; Clesceri, L.S.; Eaton, A.D. Standard Methods for the Examination of Water and Wastewater, 16th ed.; APHA/AWWA/WEF: Washington, DC, USA, 1992.
- Ochando-Pulido, J.M.; Rodriguez-Vives, S.; Martinez-Ferez, A. The effect of permeate recirculation on the depuration of pretreated olive mill wastewater through reverse osmosis membranes. Desalination 2012, 286, 145–154, doi:10.1016/j.desal.2011.10.041.
- Ochando-Pulido, J.M.; Hodaifa, G.; Rodriguez-Vives, S.; Martinez-Ferez, A. Impacts of operating conditions on reverse osmosis performance of pretreated olive mill wastewater. Water Res. 2012, 46, 4621–4632, doi:10.1016/j.watres.2012.06.026.
- Nieto, L.M.; Hodaifa, G.; Rodríguez, S.; Giménez, J.A.; Ochando, J. Flocculation-sedimentation combined with chemical oxidation process. CleanSoil Air Water 2011, 39, 949–955, doi:10.1002/clen.201000594.
- Nieto, L.M.; Alami, S.B.D.; Hodaifa, G.; Faur, C.; Rodríguez, S.; Giménez, J.A.; Ochando, J. Adsorption of iron on crude olive stones. Ind. Crops Prod. 2010, 32, 467–471, doi:10.1016/j.indcrop.2010.06.017.
- Yiantsios, S.G.; Karabelas, A.J. An assessment of the Silt Density Index based on RO membrane colloidal fouling experiments with iron oxide particles. Desalination 2002, 15l, 229–238.
- Vincent-Vela, M.C.; Cuartas-Uribe, B.; Álvarez-Blanco, S.; Lora-García, J. Analysis of fouling resistances under dynamic membrane filtration. Chem. Eng. Process. 2011, 50, 404–408, doi:10.1016/j.cep.2011.02.010.
- Sioutopoulos, D.C.; Yiantsios, S.G.; Karabelas, A.J. Relation between fouling characteristics of RO and UF membranes in experiments with colloidal organic and inorganic species. J. Membr. Sci. 2010, 350, 62–82, doi:10.1016/j.memsci.2009.12.012.
- Field, R.W.; Pearce, G.K. Critical, sustainable and threshold fluxes for membrane filtration with water industry applications. Adv. Colloid Interface Sci. 2011, 164, 38–44, doi:10.1016/j.cis.2010.12.008.
- Stoller, M. Effective fouling inhibition by critical flux based optimization methods on a NF membrane module for olive mill wastewater treatment. Chem. Eng. J. 2011, 168, 1140–1148, doi:10.1016/j.cej.2011.01.098.
- Stoller, M.; Ochando-Pulido, J.M. Going from a critical flux concept to a threshold flux concept on membrane processes treating olive mill wastewater streams. Procedia Eng. 2012, 44, 607–608, doi:10.1016/j.proeng.2012.08.500.
- Stoller, M.; Bravi, M.; Chianese, A. Threshold flux measurements of a nanofiltration membrane module by critical flux data conversion. Desalination 2013, 315, 142–148, doi:10.1016/j.desal.2012.11.013.
- Stoller, M.; de Caprariis, B.; Cicci, A.; Verdone, N.; Bravi, M.; Chianese, A. About proper membrane process design affected by fouling by means of the analysis of measured threshold flux data. Sep. Purif. Technol. 2013, 114, 83–89, doi:10.1016/j.seppur.2013.04.041.
- Stoller, M.; Chianese, A. Optimization of membrane batch processes by means of the critical flux theory. Desalination 2006, 191, 62–70, doi:10.1016/j.desal.2005.07.021.
- Stoller, M.; Chianese, A. Influence of the adopted pretreatment process on the critical flux value of batch membrane processes. Ind. Eng. Chem. Res. 2007, 46, 2249–2253, doi:10.1021/ie060964k.
- Cañizares, P.; Paz, R.; Sáez, C.; Rodrigo, M.A. Costs of the electrochemical oxidation of wastewaters: a comparison with ozonation and Fenton oxidation processes. J. Environ. Manag. 2009, 90, 410–420, doi:10.1016/j.jenvman.2007.10.010.
- Scott, K.; Hughes, R. Industrial Membrane SeparationTechnology; Chapman & Hall: London, UK, 1996.
- Cheryan, M. UF and MF Handbook; Technomics: Lancaster, PA, USA, 1998.
© 2013 by the authors; licensee MDPI, Basel, Switzerland. This article is an open access article distributed under the terms and conditions of the Creative Commons Attribution license (http://creativecommons.org/licenses/by/3.0/).