Open Access
This article is

- freely available
- re-usable

*Climate*
**2018**,
*6*(2),
37;
doi:10.3390/cli6020037

Article

A Multi-Criteria Approach to Achieve Constrained Cost-Optimal Energy Retrofits of Buildings by Mitigating Climate Change and Urban Overheating

^{1}

Department of Industrial Engineering, Università degli studi di Napoli Federico II, Piazzale Tecchio 80, 80125 Naples, Italy

^{2}

Department of Medicine, Università degli studi del Molise, Via Cesare Gazzani 47, 86100 Campobasso, Italy

^{*}

Author to whom correspondence should be addressed.

Received: 23 March 2018 / Accepted: 4 May 2018 / Published: 8 May 2018

## Abstract

**:**

About 40% of global energy consumption is due to buildings. For this reason, many countries have established strict limits with regard to building energy performance. In fact, the minimization of energy consumption and related polluting emissions is undertaken in the public perspective with the main aim of fighting climate change. On the other hand, it is crucial to achieve financial benefits and proper levels of thermal comfort, which are the principal aims of the private perspective. In this paper, a multi-objective multi-stage approach is proposed to optimize building energy design by addressing the aforementioned public and private aims. The first stage implements a genetic algorithm by coupling MATLAB

^{®}and EnergyPlus pursuing the minimization of energy demands for space conditioning and of discomfort hours. In the second stage, a smart exhaustive sampling is conducted under MATLAB^{®}environment with the aim of finding constrained cost-optimal solutions that ensure a drastic reduction of global costs as well as of greenhouse gas (GHG) emissions. Furthermore, the impact of such solutions on heat emissions into the external environment is investigated because these emissions highly affect urban overheating, external human comfort and the livability of our cities. The main novelty of this approach is the possibility to properly conjugate the public perspective (minimization of GHG emissions) and the private one (minimization of global costs). The focus on the reduction of heat emissions, in addition to the assessment of energy demands and GHG emissions, is novel too for investigations concerning building energy efficiency. The approach is applied to optimize the retrofit of a reference building related to the Italian office stock of the 1970s.Keywords:

building energy performance; energy simulation; building retrofit; multi-objective optimization; genetic algorithm; urban overheating; cost-optimal analysis; lifecycle analysis; office buildings; sustainability## 1. Introduction and State of the Art

Global energy consumption has strong implications on human socio-economic and political spheres. Improved data about the global energy consumption reveal systemic patterns and trends that can be useful for solving current energy issues. In this regard, looking at the worldwide scenario, the energy consumption increased by just 1% in 2016, by following a growth of 0.9% in 2015 and 1% in 2014, and the 10-year average is 1.8% per year [1]. Moreover, in the last decade, with reference to the European Union (EU) there was even a slow but continuous decrease of energy consumption (the 10-year average is −1.1% per year) [1]. This is due to the EU’s rigorous policy regarding the reduction of energy consumption. The recent weak growth in energy demand implied that the global greenhouse gas (GHG) emissions from energy consumption were almost flat during 2016 for the third consecutive year. They increased by only 0.1% in 2016 and during 2014–2016 the average emission growth was the lowest over any three-year period since 1981–1983 [1]. This means that, during recent years, many governments are moving in the direction of sustainable development [2].

In this scenario, buildings bear a large responsibility as they account for about 40% of energy consumption and 36% of CO

_{2}-eq emissions in the EU. For this reason, it is fundamental to act on them to strongly reduce energy consumption and polluting emissions. In fact, by improving the energy efficiency of buildings, it is possible to reduce total EU energy consumption by 5–6% as well as CO_{2}-eq emissions by about 5% [3]. Therefore, the mandatory improvement of energy performance of existing buildings, as well as the high energy quality of new constructions have been established by several European guidelines, Directives and regulations, starting from 2002, when the first version of the Energy Performance of Buildings Directive (EPBD), i.e., the Directive 2002/91/EU [4], was enacted. More recently, the EPBD recast 2010/31/EU [5] upgraded the previous version, introducing the concept of nearly zero-energy buildings and proposing the new methodology of cost-optimality, detailed in the Delegated Regulation 244/2012 [6]. Other mandatory prescriptions, mainly emphasizing the exemplary role of the public hand, were provided by the so-called energy-efficiency Directive, namely the 2012/27/EU [7].The cited EU guidelines outline that the reduction of building energy consumption is a crucial issue of our generation and is fundamental to promote a sustainable development. In this regard, to optimize building energy performance, firstly it is important to act on building thermal envelope because this enables strong reductions of thermal energy demand (TED), since around 50% of a general-purpose building’s energy needs depend on heat losses through the envelope [8]. However, a comprehensive intervention on the envelope composition is possible only for new buildings, while existing ones constitute the largest portion of buildings in service. This can be a problem, but it can be easily solved because there are many other solutions to reduce building energy consumption. In fact, while the envelope defines the TED, the primary energy consumption and the GHG emissions depend on the whole system “building + energy plants” and the designers operate on this whole system when investigating the retrofit of an existing building.

Generally, the minimization of energy consumption and related polluting emissions is the main objective of the public perspective, since it allows the fighting of crucial issues of contemporary society such as climate change and energy poverty. However, when the optimization of building energy performance is faced, it is fundamental to consider the cost-effectiveness of the design and the respect of a certain level of thermal comfort, which are the principal aims of the private perspective. For this reason, the optimization of building design is a complex multi-objective problem with a huge domain of design variables and several potential objective functions. In this regard, occupants’ thermal comfort—which is defined as “the order at which occupants have no intention to modify their environment” [9]—represents a very critical aspect [10] because it has serious health-related consequences [9,11,12] and, as clear, a significant impact on energy consumption [13]. Aiming at understanding the extensive influence of occupants and thermal comfort on building energy performance, many studies have been performed in recent years. Unfortunately, there is a deep gap between the theoretical results of the researches and the practical aspects of their application to real-world buildings, mainly because of the financial implications. For this reason, the scientific literature provides many papers reporting attempts to design optimal financially-appealing retrofit strategies ([8,14,15] for instance). Finally, to develop a retrofit design that can be cost-effective and practically feasible—attracting investments from decision-makers—it is important to accurately estimate the energy savings and the financial benefits.

In addition, nowadays environmental problems, such as climate change and thus GHG emissions, have pushed designers to comprehensively assess the environmental impact of building designs according to current law prescriptions. At the same time, customer expectations on the design budget imposes higher pressure on designers to limit the project costs. Aiming at better understanding building environmental impact, different procedures and indicators have been implemented during the last decades, such as the life cycle assessment (LCA). “The LCA includes accumulating of all environmentally relevant streams inventory associated with production processes, transportation, and demolition of a product” [16]. According to this, a relevant number of studies has been conducted to identify the optimal designs with minimum life cycle cost (LCC) [17,18] and life cycle emission (LCE) [19]. The literature shows many investigations that implemented different strategies to support the professionals in determining the environmental impact of their designs (e.g., [17,18]). In the same vein, during the last few years, designs of high-energy performance using optimization techniques have had a significant diffusion. Many studies have been performed to find out which are the best strategies to minimize building energy needs and many other objective functions, such as global costs, environmental impact, occupants’ discomfort. For instance, Asadi et al. [20] proposed an optimization technique that makes use of a genetic algorithm and artificial neural networks, with the aim of minimizing the retrofit cost, the energy consumption and the thermal discomfort hours. The two latter objectives were the main aims also of Delgarm et al. in [21], in which an artificial bee colony methodology was used.

More in general, Nguyen et al. [22] provided an accurate explanation concerning the optimization process in building design. To properly design a new building or to retrofit an existing one, dynamic energy simulation tools should be used by designers. The “parametric simulation method” approach is very common to improve building energy performance. According to this method, the designer must vary the input of each variable with the aim of highlighting the effect of the selected variable on the objective functions. This procedure can be iterated with all the variables. However, the limit is that this method often requires a huge computational time and it gives reliable results only in partial improvements because of the non-linear interactions among the different input variables. A different and more robust approach is the one known as “simulation-based optimization” or “numerical optimization”, which performs sequences of progressively better approximations to a solution that satisfies an “optimality condition”, previously-defined. This permits the attainment of the optimal solution to a problem (or a sub-optimal solution sufficiently close to the optimum [23]) with lower computational time and effort. The simulation-based optimization of building performance is usually conducted automatically by means of the coupling between a building simulation software and an optimization “engine”, which implements one or several optimization algorithms that need to be properly set [24]. Generally, a simplification of the building model to be optimized should be done, but it is crucial to not over-simplify, to avoid the risk of inaccurate modeling of building phenomena. In addition, the convergence of the adopted optimization algorithm should be monitored. Convergence behaviors of different optimization algorithms are an extremely active research area [25,26]. Regarding errors, it is fundamental to say that they may occur because of infeasible combinations of variables (e.g., windows areas that extend the boundary of a surface), output reading errors (as in the coupling between MATLAB

^{®}[27] and EnergyPlus [28]), and so on. Furthermore, the entire optimization process may crash by a single simulation failure. To minimize such errors, some authors run parametric simulations to make sure that there are no failed simulation runs before running the optimization [22], or they make use of evolutionary algorithms because even the presence of a failed solution among the population does not interrupt the optimization process. Finally, it is important to verify if the found solutions are reliable and robust. There are no standard rules for this task, but the literature provides many strategies (for instance, the sensitivity-analysis [25,29], the brute-force search method [30], the comparison with different models [31]).Since the building sector accounts for a large amount of global energy consumption and GHG emissions, the optimization of building energy design, in terms of minimization of energy demands and global costs, is strictly related to climatic conditions at large scale and can significantly support the mitigation of climate change and urban overheating. The proposed study aims to address this strong correlation between energy performance and climate to highlight that the optimization of building energy design is fundamental for solving the climatic issues of contemporary society.

#### Research Aim and Originality

Among the numerous optimization methodologies described in literature, the methodology proposed in this paper is structured in two consequent and interdependent stages, as in [32]. More precisely, during the first stage, there is the implementation of the GA and, by means of the continuous coupling between MATLAB

^{®}[27] and EnergyPlus [28], the thermal energy demands (TED) for heating and cooling, respectively, and the discomfort hours (DH) are minimized. Conversely, the second stage is entirely conducted under MATLAB^{®}environment and enables the discovery of constrained cost-optimal solutions that ensure a drastic reduction of global cost (GC) as well as of CO_{2}-eq (i.e., GHG) emissions. Then, the effect of such solutions on building heat emissions into the external environment is assessed to evaluate the contribution to the mitigation of urban overheating, which highly affects the external human comfort and the livability of our cities. This is a crucial aspect, due to the constantly increasing urbanization, in fact more than half the global population (i.e., the 54%) lives in urban areas nowadays [33,34] and it is forecasted to be rising during the next few years [35,36], with obvious implications on environmental degradation, being the cities and their inhabitants the principal players in heat wasting and CO_{2}emitting [35,37].The main novelty of the proposed methodology consists of the possibility to satisfy both the perspectives, the public one (by reducing the GHG emissions) and the private one (by minimizing GC and reducing DH), thereby allowing to fight climate change and ensuring the design cost-effectiveness at the same time. The focus on the reduction of heat emissions is a further novel aspect for investigations concerning building energy efficiency. In this regard, since the second stage is conducted entirely in MATLAB

^{®}it is not time-consuming, thus many objective functions can be investigated and optimized without computational efforts. It should be noticed that similar optimization methodologies—based on the coupling of EnergyPlus and MATLAB^{®}to implement a genetic algorithm—have been already proposed by the authors, such as in [32,38,39]. However, the frameworks and final purposes of these previous studies were different, such as to find cost-optimal retrofit solutions for single complex hospital [32] or educational buildings [38] or for a whole building category by using artificial neural networks [39]. The aforementioned studies applied a financial approach (detailed in the EU Commission Delegate Regulation [6]) in global cost assessment without considering the cost of GHG emissions and building heat emissions into the external environment. Therefore, they did not comprehensively address the issues of climate change and urban overheating related to building energy performance. Finally, the originality of this study is combining the optimization of building energy design in terms of global cost minimization to the reduction of building environment impact in terms of contribution to climate change and urban overheating. The global cost is assessed through a macro-economic approach by considering also the cost of CO_{2}eq emissions, and thus the achieved cost-optimal solution implies a drastic reduction of GHG emissions. Indeed, the results will show the solution that minimizes the global cost is very close to the one that minimizes CO_{2}-eq emissions, ensuring a very satisfying trade-off between the private and the public perspectives. Therefore, the application of the methodology at large scale can produce a significant reduction of building environmental impact since the detected solutions imply a drastic reduction of GHG emissions, thereby giving a strong support to the mitigation of climate change and urban overheating.As a case study, the methodology is applied to a typical existing office building, representative of the Italian building stock since the 1970s.

## 2. Methodology

#### 2.1. Framework

The proper choice of the energy efficiency measures to adopt for a new building or an existing one is a highly complicated issue, which affects two different perspectives:

- the private one, whose aim is to achieve financial benefits or minor indoor discomfort;
- the public one, whose aim is to reduce energy consumption, polluting emissions and to have an exemplary role for all citizens.

Regarding these differences, the methodology proposed in this paper ensures the best trade-off between these two perspectives, because it allows the addressing of more objectives at the same time, ensuring a good level of satisfaction for both the private and the public perspectives. Finding the cost-optimal solution usually requires high computational efforts, because of the huge amount of energy efficiency measures’ combinations that must be simulated by means of building performance simulation (BPS) tools, which run time-costly dynamic simulations. For this computational issue, the cost-optimal analysis could not be applied to every building. Conversely, it should be limited to reference buildings (RBs) only, as established in the EPBD-recast. However, even when only RBs are examined, the robust assessment of cost-optimality is very time costly. For this reason, it is crucial to adopt proper building performance optimization (BPO) algorithms that can reduce the required computational efforts, by reducing, at the same time, the domain of the explored scenarios without affecting the detection of robust cost-optimal solutions. In this paper, a multi-objective and multi-stage optimization procedure is implemented to find a constrained cost-optimal solution that fulfils these three conditions:

- it ensures the Pareto optimization of TED (thermal energy demand) for heating, TED for cooling, discomfort hours (DH) if the retrofit involves the building envelope (in fact, it can be effective to act merely on the energy systems);
- it implies a drastic reduction of GHG emissions since a macroeconomic approach is applied for global cost (GC) assessment thereby considering the cost of such emissions [6];
- minimizes GC by respecting the first two conditions, which is why it is defined “constrained”.

Once fixed the main boundary conditions, concerning geometry, occupancy profiles and climatic conditions, several energy efficiency measures are combined and examined. The considered energy efficiency measures concern all levers of energy efficiency in buildings, i.e.,

- the building envelope (e.g., new kind of low-emissive or selective glazing, addition of thermal insulation, particular plasters);
- the primary energy systems, considering also renewable energy sources (e.g., efficient air-source heat pumps, photovoltaic generators).

Specifically, EnergyPlus is used for dynamic energy simulations, because it ensures high accuracy and reliability, while MATLAB

^{®}is used to run the optimization algorithm and to perform the data-processing, because of its large opportunities of programming. Furthermore, MATLAB^{®}is used to launch EnergyPlus simulations. Thus, the coupling of these two software allows the automatic running of a huge set of dynamic energy simulations that are managed by the optimization algorithm, developed directly in MATLAB^{®}environment. More precisely, the methodology performs a multi-stage and multi-objective optimization by implementing a genetic algorithm (GA)—1st stage—and running a smart exhaustive sampling—2nd stage. The GA, born as a modification of NSGA-II, operates by iteratively improving the models of the building with the aim of identifying the non-dominated solutions (i.e., the Pareto front) for what concerns the building envelope design or retrofit, by minimizing TED for heating, TED for cooling and DH. Then, the smart exhaustive sampling stage allows the investigation of the Pareto front solutions obtained during the 1st stage and the baseline situation, aiming at reducing GC and GHG emissions thereby conducting a constrained cost-optimal analysis. Thus, decision making is performed by providing a recommended trade-off design/retrofit solution. A similar technique was used in [32,38], but this study addresses different objective functions to provide solutions that allow the fighting of climate change and ensure cost-effectiveness at the same time. This represents the main worthy and original contribution of the proposed approach that enables the conciliation of the private and public perspectives.Since the 2nd stage is conducted entirely in MATLAB

^{®}, the required computational efforts are strongly reduced. The following subsections provide a description of the two methodology stages.#### 2.2. 1st Methodology Stage: Optimization Algorithm

In this stage, the baseline energy performance of the building (“as built”) is assessed, in terms of TED for space cooling, TED for space heating and DH, respectively. The building is modeled in EnergyPlus by using the graphical interface DesignBuilder [40], that allows a careful definition of geometry and subdivision into thermal zones. It is quite important, for the EnergyPlus model, to set:

- the thermo-physical characteristics of the building envelope;
- the profiles of building use for each thermal zone, in terms of hourly schedules of occupancy, people activity, ventilation need, and so on;
- the operation of HVAC (heating, ventilating and air conditioning) systems by setting the values of set-point temperatures;
- the type of HVAC systems in terms of characteristics of the heating and cooling terminals as well as of the distribution network.

It should be noted that the heating/cooling primary systems are not modeled in this phase, because, during this stage, the aim is to calculate the thermal energy demand (i.e., the “net requirement”) and not the primary energy consumption, which is assessed later by means of MATLAB

^{®}. After modeling the baseline building (BB), an EnergyPlus simulation is run by using a proper weather data file, usually available at the EnergyPlus online database. The annual values of TED for space heating (TED_{heat}), for space cooling (TED_{cool}) per unit of conditioned area, and DH are the simulation outputs. DH provides the annual percentage of discomfort hours. As done in [39], an occupied hour is considered a discomfort one if the average predicted mean vote (PMV) in the building thermal zones is out of the range −0.85 ÷ 0.85, implying a value of predicted percentage of dissatisfied (PPD) higher than 20%.After the investigation of the energy behavior of the BB, a set of “n” energy efficiency measures for the reduction of TED

_{heat}, TED_{cool}and DH is identified, based on the current energy performance, building peculiarities and best practices. A design variable is associated to each energy efficiency measure and it can be, potentially, discrete or continuous, even if in the case study presented in this paper all variables are considered as “discrete”. Finally, “n” variables are introduced, and a range of variability is assigned to each of them, by defining the sample space that should be explored with the aim of examining the energy efficiency measures’ combinations. At this point, the GA carries out a smart research within the entire solution domain by investigating only a limited number of solutions, properly selected by the optimization logic. As aforementioned, a large amount of computational time is saved if the method is compared to exhaustive researches. Since three objective functions are chosen—i.e., TED_{heat}, TED_{cool}and DH—the algorithm provides one three-dimensional (3-D) and three bi-dimensional (2D) Pareto fronts (one for each couple of objectives), by collecting the non-dominated solutions, which represent optimal packages of the investigated energy efficiency measures. Obviously, the goal is the minimization of all targets at the same time, but this is impossible because usually the objective functions are conflicting. Thus, the GA provides trade-off solutions collected in the aforementioned Pareto fronts (for this reason we call them “non-dominated”). The used GA has been already implemented by Ascione et al. [39] in MATLAB^{®}environment according to the scheme reported in Figure 1, where the vector F collects the objective functions (F = [TED_{heat}, TED_{cool}, DH]) while the vector x is composed of bits that encode the design variables representing energy efficiency measures.Each design variable can assume a limited number of values, because this allows the reduction of the solution domain and it is much closer to reality and availability of the market. The possible values must be carefully chosen according to best practices and experiences. The GA performs, iteratively, an evolution of a population of “s” (population size) individuals, denoted as “chromosomes”, each one characterized by a set of values of the vector x, whose components are called “genes” and correspond to a combination of building energy efficiency measures. The process is performed through numerous iterations, the so-called “generations”. It is required to improve the characteristics of the population by the selection of the best chromosomes as well as through the operations of mutation and crossover of their genes (e.g., the bits encoding the thicknesses of thermal insulation layer) in order to have new individuals that improve the energy and thermal performance of the building. The individuals that derive from crossover, called “children”, are randomly generated by combining the design variables (i.e., bit strings) of two parents. The population fraction that originates from crossover is indicated by the crossover fraction “f

_{c}”. All other remaining individuals (“mutated children”) are originated by the mutation of random parents, specifically by changing each bit with a mutation probability equal to “f_{m}”. The best chromosomes are called “parents” and are chosen based on a rank assigned from the values of objective functions and from the average crowding distance among individuals. The best parents constitute the “elite” that survives to the generation. After the random creation of the initial population, the described “Darwinian evolution” occurs during each generation and ends when one of the following termination criteria is satisfied:- a threshold number of generations (${\mathrm{g}}_{\mathrm{max}}$) is reached;
- the Pareto front does not change significantly between two following generations. This means that the variation of the front spread is lower than a tolerance “$\mathrm{tol}$”.

In the case study here investigated, the used termination criterion is the first one and most GA parameters take the same values employed in [32,38], namely (n is the number of design variables):

- c
_{e}= 2; - f
_{c}= 0.6: - f
_{m}= 0.1; - s = 4∙n;
- g
_{max}= 20.

For what concerns the values of s and ${\mathrm{g}}_{\mathrm{max}}$, it is important to notice that these must be properly set depending on the complexity of the case study, because they crucially affect the reliability of the results and the required computational efforts. Ascione et al. [32] assessed that reliable “s” values are 2–6 times the number of design variables (in this study, it is set equal to 4), while reliable ${\text{\u201c}\mathrm{g}}_{\mathrm{max}}\u201d$ values are included in the range 10–100 generations. In this paper, this is set equal to 20.

Specifically, for each energy efficiency measures’ combination, which is encoded by certain values of the vector x, MATLAB

^{®}launches EnergyPlus to run a dynamic energy simulation. Then, the results of this simulation are post-processed for obtaining the values of the objective functions (i.e., TED_{heat}, TED_{cool}, DH) with reference to each examined combination. The coupling scheme between the two software is shown in Figure 2The “coupling function” between EnergyPlus and MATLAB

^{®}” converts x into a new building model to be simulated (the “.idf” file) and consequently handles the output file of EnergyPlus (the “.csv” file) to calculate the values of the objectives contained in F. It is noticed that the energy efficiency measures are implemented and parametrized directly within the “.idf” EnergyPlus file. Moreover, also a constrain is defined, since all solutions that cause an increase of DH compared to the base building configuration are excluded. This constraint is set to ensure that the optimized energy retrofit does not cause a worsening of occupants’ thermal comfort. Indeed, energy efficiency should not prejudice people well-being. Hence, the GA implementation must be followed by the decision-making process, which aims at selecting one recommended solution from the Pareto front. This process is performed during the second stage.#### 2.3. 2nd Methodology Stage: Decision-Making

In this phase, the decision-making process is performed, aiming at selecting one combination of energy efficiency measures among all non-dominated configurations. It is a crucial task and it can be carried out according to different criteria. Obviously, none of the solutions of the Pareto front can be chosen “a priori”, because it cannot be defined better than another. For this reason, a selection criterion is essential. For what concerns the methodology described in this paper, the chosen criterion is the so-called “cost-optimality”, which means that, at the end of the entire optimization process, the chosen solution (i.e., package of energy efficiency measures) is the one that minimizes the global cost (GC) over building predicted lifecycle, assessed according to a macro-economic approach [6]. The cost-optimal analysis is applied by means of a smart exhaustive sampling. This latter permits the investigation of further energy efficiency measures—addressed to primary energy systems—besides those examined in the 1st stage, which are addressed to the envelope and to the operation parameters of the HVAC systems. It is important to notice that GC considers the initial investment cost, the GHG emissions costs and the running costs, those latter evaluated for a certain number of years (depending on the category of the building) and actualized at the starting time. Such cost-optimal analysis is conducted according to EU guidelines, reported in the Energy Performance of Buildings Directive (EPBD) recast 2010/31/EU [5] and detailed in the Delegated Regulation 244/2012 [6]. In particular, in the global cost assessment, the macro-economic approach is used to consider the cost of CO

_{2}-eq emissions. This allows the comprehensive consideration and minimization of the impact of building energy performance on climate change, which is one to of the main goals of the proposed study. Indeed, the achieved cost-optimal solution will imply a drastic reduction of GHG emissions, as shown in the Section 4, thereby ensuring a very satisfying trade-off between the private and the public perspectives.Specifically, during this stage, a smart exhaustive sampling is carried out by investigating the energy performance of different solutions of primary energy systems, in presence of the non-dominated energy efficiency measures’ combinations selected in the first stage, and in absence of energy efficiency measures (baseline configuration). For each combination, the GC and the GHG emissions are evaluated, and, finally, the cost-optimal solution is found. A sensitivity analysis is then performed in correspondence of different values of the discount rate, to investigate the robustness of the found cost-optimal solution. This stage is entirely implemented in MATLAB

^{®}environment, without launching further EnergyPlus simulations. For this reason, it needs a negligible computational time compared to the first stage (i.e., the order of magnitude is few seconds). The exhaustive sampling is “smart” [32] because:- it is performed in MATLAB
^{®}environment, without needing further EnergyPlus simulations; - it explores, besides the baseline building (BB), only the packages of energy efficiency measures that are properly selected through the GA implementation.

More precisely, the chosen energy efficiency package represents a “constrained” cost-optimal solution, since only suitable packages are selected for the cost-optimal analysis based on the results of the 1st methodology stage. Furthermore, the impact of such optimal retrofit solution on the annual heat emissions of building HVAC systems into the external environment is assessed. This analysis aims at investigating the contribution to the mitigation of urban overheating, which significantly affects the external thermal comfort of people, and thus the livability of our cities, as well as building energy needs.

## 3. Description of the Case Study

The case study is an existing office building, typical of the Italian building stock in reinforced concrete as structural material. It is theoretical reference building, provided by an accurate ENEA (“Italian National agency for new technologies, Energy and sustainable economic development”) study [41], which examined the national building stock and proposed many reference buildings. The investigation of reference buildings can be particularly interesting because the achieved outcomes can be applied—with a good approximation and reliability—to several buildings (i.e., the ones represented by the investigated one).

#### 3.1. Baseline Building (BB)

The building is supposed to be situated in Naples (South Italy) and it has five floors above the ground, each one having a net height of 3 m (see Figure 3). The building gross floor area is equal to 2400 ${\mathrm{m}}^{2}$ (480 ${\mathrm{m}}^{2}$ per level). It is possible to notice that the glazing area changes with the exposure. Specifically, for the west and the east façades, it is about the 55% of the whole area (i.e., about 128 ${\mathrm{m}}^{2}$), while, for the south exposure, it is about the 33%, and for the north side it is about the 30%. Shading systems are absent. For what concerns the air infiltration rate, according to common Italian values for existing buildings, it has been set at 0.5 air changes per hour (ACH). It is noticed that the building envelope, the schedules of building use and operation, the HVAC systems have been accurately modeled by considering the statistical analysis of ENEA—which developed the investigated reference building [41], the standard Italian constructive practice as well as the typical operation schedules for an office building taken from DesignBuilder [40].

As for the building use, 50 thermal zones can be individuated, and thus 10 for each floor. There are three different categories of thermal zones, as shown in Figure 4. On the other hand, the following Table 1, Table 2 and Table 3 show the composition of the opaque building envelope components. The attention is focused on ground floor, roof, and external walls by considering the necessity to rigorously respect the national law limits about the thermal transmittance (i.e., U-value). Finally, Table 4 reports the thermo-physical properties of the cited materials.

With regard to the transparent building envelope, the windows are double-glazed with clear float glasses, air-filling and aluminum frames. The window U-value is equal to 3.74 W/m

^{2}K while the solar heat gain coefficient (SHGC) is equal to 0.76. Finally, the U-values of all envelope components are reported in Table 5, which provides an overview of the baseline configuration of the reference building, with regard to HVAC systems too. In this regard, there is a primary centralized system, which supplies hot and cold water to four-pipes fan coils. All building thermal zones are equipped with such terminals. The heating primary system is a traditional natural gas boiler, while the cooling one is an electric air-cooled chiller. The nominal efficiency (η) of the boiler at the LHV (lower heating value) is 0.85, the nominal coefficient of performance (COP) of the chiller is 2.3. The heating load of the entire building is about 220 kW, while the cooling load is about 235 kW.With regard to the economic assumptions, the considered specific prices for electricity and natural gas are the following ones:

- 0.25 €/kWh
_{el}for the electricity; - 0.90 €/Sm
^{3}for the gas with an LHV equal to 9.59 kWh/Sm^{3}.

In addition, as for the discount rate (denoted with r) applied in the assessment of global cost, three different values are considered (i.e., 1%, 3% and 5%). The assumed calculation period is 20 years, since the investigated building is an office [5,6].

Finally, Table 5 shows the explored performance indicators of the baseline building (BB), namely:

- thermal energy demand for space heating (TED
_{heat}); - thermal energy demand for space cooling (TED
_{cool}); - annual percentage of thermal discomfort hours (DH);
- global cost due to energy uses (GC);
- GHG emissions due to energy uses in terms of CO
_{2}-eq emissions.

The GC is calculated for a long-time period $\mathsf{\tau}$ of 20 years with the equation established by EU Guidelines [6] and reported below:
where:

$$\mathrm{GC}\left(\mathsf{\tau}\right)=\mathrm{IC}+\text{}{\displaystyle \sum}_{\mathrm{j}}\left[{\displaystyle \sum}_{\mathrm{i}}^{\mathsf{\tau}}\left(\mathrm{RC}\left(\mathrm{i}\right){\ast \mathrm{R}}_{\mathrm{d}}\left(\mathrm{i}\right)+{\mathrm{C}}_{\mathrm{c},\mathrm{i}}\left(\mathrm{j}\right)\right)-{\mathrm{V}}_{\mathrm{f},\mathsf{\tau}}\left(\mathrm{j}\right)\right]$$

- “IC” stands for the initial investment cost;
- “RC” is the running cost per year, and by means of R
_{d}it is actualized for each year of the evaluating period; - “R
_{d}” is the actualization factor, which permits the actualization of the RC; - “C
_{c,I}” states for the cost of the GHG emissions. For ${\mathrm{C}}_{\mathrm{c},\mathrm{i}}\left(\mathrm{j}\right)$ it is used a cost of 20 €/tCO_{2}-eq until the year 2025, 35 €/tCO_{2}-eq until 2030 and then 50 €/tCO_{2}-eq, as specified in [6]; - “V
_{f,τ}” is the residual value at the end of the evaluation period.

Equation (1) permits the adoption of a macro-economic approach, which is fundamental to choose proper energy efficiency measures aiming at reducing building environmental. In fact, mid-polluting measures’ combinations—which could be the most efficient trade-offs between the two main objectives (minimization of GC and GHG emissions) in short-midterm evaluations—turn out to be inefficient for a long-term period, once considering also the cost of the GHG emissions.

#### 3.2. Energy Retrofit Scenarios

With regard to building energy retrofit, 11 different design variables—representing retrofit measures for the reduction of thermal energy demands and/or discomfort—are considered to perform the 1st stage of the optimization process, namely:

- setpoint temperature for space heating;
- setpoint temperature for space cooling;
- thermal emissivity of the most external layer of the vertical walls;
- solar absorbance of the most external layer of the vertical walls;
- thermal emissivity of the most external layer of the roof;
- solar absorbance of the most external layer of the roof;
- thickness of an additional external layer of thermal insulation for the vertical walls—polyurethane panels are considered (density = 25 kg/m
^{3}, conductivity = 0.028 W/mK, specific heat = 1340 J/kgK); - thickness of an additional external layer of thermal insulation (polyurethane) for the roof;
- type of windows;
- type of shading systems;
- position of the shading systems.

The values that the aforementioned variables can assume are all discrete as shown in the following Table 6, Table 7 and Table 8, where the acronym BB denotes the value of the baseline building configuration.

It should be noted that our main target was to propose a methodology. In future studies, the possible ranges and values that can be assumed by the variables can be better defined, according to the real availability of some solutions in the market of energy efficiency measures and building components. This may concern reflectance and emissivity of building external coatings that should comply with the fact that emissivity is high for almost all non-metal materials and that the soiling largely affects the solar absorptance. In this study, the ranges of variability of most design variables are set according to [38], which investigated the energy retrofit of an educational building for a similar climatic location.

Concerning the 2nd stage of the optimization process, 4 heating primary systems and 2 cooling primary systems are considered, as shown in Table 9 and Table 10. When the air-source electric heat pump and the high-efficiency electric air-cooled chiller are implemented together, the installation of only one reversible heat pump is considered.

Furthermore, the 2nd optimization stage considers the installation of photovoltaic (PV) panels. Two different solutions are investigated—monocrystalline panels (more efficient) and polycrystalline ones—installed on the roof to satisfy the electricity needs of lighting, equipment and HVAC systems. In detail, 10 different roof coverage percentages are considered, from 10% to 100% by means of increments of 10%. The PV panels are installed with an inclination equal to 30°. In presence of PV panels, the price assumed for the electricity sold to the grid is 0.07 €/kWh

_{el}according to current Italian tariffs.With regard to the cost-optimal analysis, the assumed values of investment costs for the energy retrofit measures are reported in Table 11. These values are taken partly from previous studies [42] and partly from quotations of suppliers. Finally, the conversion factors adopted to evaluate the GHG emissions due to the electricity and the gas needs are those reported in Table 5.

Regarding the evaluation of GC, proper incentives are considered for each energy efficiency measure to be adopted, as established in the Italian economic balance law [43].

Aiming at investigating the urban overheating too, the heat emissions into the external environment due to HVAC systems are finally evaluated, with reference to both the heating and the cooling seasons. Specifically, only the direct thermal energy contributions are considered and thus merely the waste heat of the primary energy systems, namely:

- the thermal emissions of the gas boiler due to the smokes and the heat losses through the boiler metal box;
- the heat discharged into the ambient by the condenser of the cooling system.

For the BB, the heat emissions into the external environment are shown in Figure 5.

With reference to Figure 5, it should be noted that the heat loss emitted into the external environment due to the hot water gas fired boiler is much lower than the one due to the air-cooled chiller, i.e., for the heating season it is equal to 6.10 MWh, while for the cooling one it is around 189 MWh. In the intervals between 2000–3000 h and between 7000–8000 h, there are periods with no heat emissions, because during this mid-season climates both the heating and the cooling systems are supposed to be turned off.

## 4. Results and Discussion

During the 1st stage of the optimization process, the genetic algorithm (GA) is implemented to find optimal solutions for the building energy retrofit with regard to the minimization of thermal energy demands and discomfort hours. A starting population of 44 individuals is considered and 20 generations are set as termination criterion of the GA. Considering also the randomly generated starting population, more than 900 different dynamic energy simulations (through the automatic coupling between EnergyPlus and MATLAB

^{®}) are run to achieve the Pareto minimization of TED_{heat}, TED_{cool}and DH. The resulting Pareto fronts (one 3-D and three 2-D) for the multi-objective optimization are shown in Figure 6, Figure 7, Figure 8 and Figure 9:Therefore, Figure 6 represents all non-dominated solutions, which for clarity reasons, are better represented in Figure 7, Figure 8 and Figure 9. It is noticed (see Figure 9) that DH tends to increase with TED

_{heat}. In this regard, DH refers to the whole year, also to the intermediate seasons (which have a high impact), and therefore it can increase or decrease with the heating demand (TED_{heat}). For instance, when the thickness of the thermal insulation layers decreases, clearly TED_{heat}increases and it is very likely that also DH increases. Indeed, discomfort hours tend to increase in the heating and intermediate seasons (indoor air temperature and surface radiant temperatures tend to decrease when the envelope thermal resistance decreases) and can increase during the cooling season because of the indoor overheating effect. When the first effect is predominant, DH increases with the heating demand.To have a general outline of the GA outcomes, the attention is focused on the solutions that produce the mono-objective minimization of TED

_{heat}, TED_{cool}and DH, respectively. These represent the “extreme” solutions of the Pareto fronts and allow understanding of how the Pareto non-dominated solutions vary depending on the weight given to each objective function.The solution that minimizes TED

_{heat}provides the following energy efficiency measures:- installation of a 0.12 m-thick external thermal insulation layer on the vertical walls;
- installation of a 0.10 m-thick external thermal insulation layer on the roof;
- installation of plasters with particular radiative properties, i.e., thermal emissivity (e) and solar absorptance (a). For the roof the provided values of e and a are 0.1 and 0.75, respectively, while for the vertical walls optimal values of e and a are 0.8 and 0.1, respectively;
- installation of triple-glazed windows with argon filling and low-e coatings in replacement of the existing ones;
- installation of external low reflection—medium transmittance shading system.

The set-point temperatures for space heating and cooling should be set equal to 19 °C and to 25 °C, respectively. This combination of retrofit measures produces the following outcomes:

- TED
_{heat}passes from 10.7 kWh/m^{2}a (BB, baseline building) to 5.6 kWh/m^{2}a; - TED
_{cool}increases from 62.2 kWh/m^{2}a (BB) to 74.5 kWh/m^{2}a; - DH passes from 52.4%(BB) to 37.1%.

The adoption of a high insulated envelope strongly reduces TED

_{heat}and DH but causes an increase of TED_{cool}of around 20% because of the indoor overheating effect.The solution that minimizes TED

_{cool}provides the following energy efficiency measures:- installation of a 0.05 m-thick external thermal insulation layer on the roof, while for the vertical walls no additional insulation is provided;
- installation of plasters with e equal to 0.8 and a equal to 0.1 for both roof and vertical walls; therefore, the use of cool plasters is recommended;
- installation of tinted double-glazed windows with argon filling and low-e coating coatings in replacement of the existing ones;
- installation of an external medium reflection—medium transmittance shading system.

In this case, the set-point temperatures for space heating and cooling should be higher than the previous ones, more precisely they should be set equal to 21 °C and to 27 °C, respectively. This combination of retrofit measures produces the following outcomes:

- TED
_{heat}slightly increases from 10.7 kWh/m^{2}a (BB) to 11.8 kWh/m^{2}a; - TED
_{cool}decreases from 62.2 kWh/m^{2}a (BB) to 32.1 kWh/m^{2}a; - DH passes from 52.4%(BB) to 53.0%.

Thus, the retrofit solution minimizing TED

_{cool}does not exert significant effects on the other two objective functions, differently from the previous solution. However, this solution will be cut off during the 2nd optimization stage because it causes an increase of DH compared to the baseline.Finally, the solution that minimizes DH provides the following energy efficiency measures:

- installation of a 0.12 m-thick external thermal insulation layer on both the vertical walls and the roof;
- installation of plasters with particular values of e and a. For the vertical walls the optimal values of e and a are 0.9 and 0.9, respectively, while for the roof the optimal values of e and a are 0.1 and 0.5, respectively;
- installation of triple-glazed windows with argon-filling and low-e coating in replacement of the existing ones;
- installation of an internal low reflection—high transmittance shading system;

In this final case, the set-point temperatures for space heating and cooling should be set equal to 19 °C and to 24 °C, respectively. This combination of retrofit measures produces the following outcomes:

- TED
_{heat}strongly decreases from 10.7 kWh/m^{2}a (BB) to 5.7 kWh/m^{2}a; - TED
_{cool}increases from 62.2 kWh/m^{2}a (BB) to 83.7 kWh/m^{2}a; - DH passes from 52.4% (BB) to 32.5%.

Finally, this solution is very similar to the one minimizing TED

_{heat}. The installation of high-thick insulation layers and triple-glazed windows allow reduction of TED_{heat}and, obviously, DH, while TED_{cool}increases of around 35% mainly because of summer overheating.The achieved Pareto non-dominated solutions are 224, most of which implies a significant improvement of occupants’ thermal comfort compared to BB. Only twelve Pareto solutions cause an increase of DH compared to BB, and thus they are excluded in the 2nd methodology stage. This latter is implemented by conducting the smart exhaustive sampling. Thus, also the replacement of primary energy systems is considered, and globally 32,802 different energy retrofit scenarios are investigated by assessing GC and GHG emissions (see Figure 10). Specifically, the differences in global cost (dGC) and GHG emissions (dCO

_{2}-eq) compared to the baseline are evaluated to obtain more representative results.For a discount rate (r) equal to 3%, the resulting cost-optimal solution provides the following energy retrofit measures:

- installation of a 0.12 m-thick external thermal insulation layer on roof and vertical walls;
- installation of plasters with particular radiative properties, i.e., thermal emissivity (e) and solar absorptance (a). For the roof the optimal values of e and a are 0.7 and 0.1, respectively, while for the vertical walls optimal values of e and a are 0.8 and 0.1, respectively. Therefore, the optimization procedure recommends the use of cool plasters;
- installation of tinted double-glazed windows with argon-filling and low-e coating ones in replacement of the existing ones;
- installation of the reversible electric heat pump for both space heating and cooling;
- installation of PV monocrystalline panels covering the 100% of the usable roof area.

Finally, the set-point temperatures for heating and for cooling should be set equal to 20 °C and to 27 °C respectively. It should be noticed that the combination among envelope thermal insulation, cool plasters, tinted windows and high-efficiency primary systems is highly synergic and produces simultaneously reductions of:

- TED
_{heat}which passes from 10.7 kWh/m^{2}a (BB) to 8.5 kWh/m^{2}a; - TED
_{cool}which passes from 62.2 kWh/m^{2}a (BB) to 36.8 kWh/m^{2}a; - discomfort hours: DH passes from 52.4% (BB) to 49.9%;
- global cost: dGC = −119.3 €/m
^{2}; - GHG emissions: dCO
_{2}-eq = −25.3 kg/m^{2}a; - annual heat emissions into the external environment, which pass from 195 MWh (BB) to 105 MWh (in percentile terms, this means that the reduction is around 46%).

Regarding this last result, it is fundamental to highlight that the beneficial effect on heat emissions due to the installation of the air-source electric heat pump (which “removes” heat from the external environment) is not considered in order to avoid the overestimation of the goodness of the cost-optimal solution found in terms of urban overheating mitigation too. Hourly heat emissions into the external environment for the cost-optimal solution are reported in Figure 11.

It is highlighted that the achieved constrained cost-optimal solution produces a drastic reduction of GHG emissions. Indeed, as shown in Figure 10, the employed macro-economic approach for GC assessment implies that the solution minimizing GC is very close to the one that minimizes CO

_{2}-eq emissions, thereby ensuring a very satisfying trade-off between the private and the public perspectives. Therefore, the application of the methodology at large scale can produce a significant reduction of building environmental impact, giving a strong support to the mitigation of climate change and urban overheating.The robustness of the solution is examined by assessing the cost-optimal solution for other two values of the discount rate r (i.e., 1% and 5%). Specifically, when the discount rate is varied the cost-optimal solution remains the aforementioned one. Clearly, only the value of dGC changes and it is equal to −153.2 €/m

^{2}for r = 1% and to −93.2 €/m^{2}for r = 5%.Other different models of comfort and criteria for evaluating hygrothermal conditions in civil buildings, with reference to both cities and urban areas, can be used, as inferred by Paolini et al. [44] recently. Specifically, the authors performed a deep investigation of effects of local climate conditions, that, in cities, can be more significant in summertime (i.e., higher cooling loads) and less critical in wintertime (given the urban heat island effect) compared to rural zones. In this case, conditions of local climate (e.g., city, urban canyon, cooler backcountry or coastline) must be considered and the standard weather files cannot be considered as sufficient. Analogously, also improvement and variation of comfort models can be thought and considered. For instance, solar radiation entering into the building through fenestration can strongly affect human comfort, and this particular role was deeply studied by Arens et al. [45] who developed a new model for understanding the impacts of radiation on the energy balance of human body. According to the authors, the so-called “SolarCal”, besides an improvement of comfort models, can help in choosing the most suitable kind of windows and fenestrations for a building, to improve its indoor thermal comfort conditions. However, in this study we used DH—which is based on Fanger theory [46]—because it is a well-accredited comfort index (used in several previous works, e.g., from Asadi et al. [20], Delgarm at al. [21], Ascione at al. [38,39] and Mauro et al. [42]) and provides an objective function to be minimized, which is fundamental for the implementation of the optimization procedure. Nevertheless, future optimization studies will be addressed to a more detailed characterization of thermal comfort. Another critical aspect concerning comfort is the risk of overheating during heatwaves in summertime. This risk can be significant for the considered case study, given the cooling-dominated climate as well the use destination (office buildings present high internal heat gains). Clearly, the proposed methodology cannot foresee extreme meteorological events because energy simulations are based on typical and average weather data files. However, the main aim of the multi-objective optimization is to design building energy refurbishments suitable for improving comfort, costs and energy demands, by reducing, at the same time, also the heat emission into the urban environment. Therefore, in the optimization algorithm, one objective function is the minimization of thermal discomfort, by considering all occupied hours of the year and, particularly, of the cooling season. Indeed, even if the building is fully equipped with air-conditioning systems (so that comfort conditions are allowed also during the cooling peaks, in the hottest hours of the summer period), the run period of the HVAC system is not 24 h/day, and thus it is recommended the refurbishment configuration that improves thermal conditions also during the off-periods of the cooling plant. In this way, by considering both energy demands and thermal comfort (for all the occupied hours), we can consider, in the same methodology and retrofit configuration, both passive and active energy conservation measures. This allows minimization of the risk of indoor overheating during heatwaves in summertime.

## 5. Conclusions

The paper proposes an optimization methodology for building energy design/retrofit based on two main objective functions, and thus the reduction of global costs and GHG emissions, to perfectly conjugate the two involved perspectives: the private one (minimization of financial expenditure) and the public one (minimization of pollution and environmental impacts of buildings).

The optimization process is structured in two consequent stages. The first one consists of the implementation of a genetic algorithm by means of the coupling of MATLAB

^{®}and EnergyPlus, while during the second stage a smart exhaustive sampling is conducted entirely in MATLAB^{®}, thereby ensuring feasible computational times even when around 30,000 retrofit scenarios are investigated. As a case study, a typical office reference building representative of the Italian building stock since 1971 is investigated. The cost-optimal solution provided by the application of the proposed methodology to this case study permits a strong reduction in the GHG emissions, which change from 78.8 kg/m^{2}a to 53.5 kg/m^{2}a, as well as the global cost, which decreases by around 119 €/m^{2}(assuming a discount rate equal to 3%).The importance of the application of the proposed optimization methodology is that the reduction of the CO

_{2}-eq emissions can enable the different countries to respect the limits imposed by the international agreements on polluting emissions for fighting climate change, while the minimization of the GC makes the adoption of proper energy efficiency measures more appealing to building owners, letting them play also an important role for the community.Finally, the applied methodology enables the reaching of more than satisfying results not only in fighting climate change under a macroscopic approach, but also in contrasting the urban overheating by adopting a local-limited approach.

## Author Contributions

All authors have contributed with the same weight and effort. In detail, G.M.M. and D.F.N. provided the literature investigations and the development of the numerical studies, together with F.A. that framed this study into the scientific vein in matter of impacts of buildings on the city energy balances and on the urban heating. N.B. and G.P.V. contributed, together with the other co-authors, in coordination, analysis of data and writing of the manuscript.

## Conflicts of Interest

The authors declare no conflicts of interest.

## Nomenclature

Symbols | ||

dCO_{2}-eq | difference in CO_{2}-eq emissions compared to BB | kg/m^{2}a |

dGC | difference in GC compared to BB | €/m^{2} |

dGHG | difference in GHG emissions compared to BB | kg/m^{2}a |

g_{max} | maximum number of generations | --- |

r | discount rate | --- |

s | population size | --- |

x | vector of design variables of the multi-objective optimization problem | --- |

DH | annual percentage of discomfort hours | % |

F | vector of objective functions of the multi-objective optimization problem | --- |

GC | global cost | € |

IC | initial investment cost | € |

PEC | annual primary energy consumption per unit of net floor area | kWh/m^{2}a |

TED | thermal energy demand | kWh/m^{2}a |

U | thermal transmittance of building envelope components | W/m^{2}K |

Subscripts | ||

cool | referred to the energy needs for space cooling | |

heat | referred to the energy needs for space heating | |

roof | referred to the roof | |

tot | referred to the sum of the energy needs for space cooling and heating | |

wall | referred to the external vertical walls | |

windows | referred to the windows (frame + glasses) | |

Acronyms | ||

BB | baseline building | |

GA | genetic algorithm | |

GHG | greenhouse gas | |

HVAC | heating, ventilating and air conditioning | |

NZEB | net zero-energy buildings | |

PV | Photovoltaic |

## References

- BP Annual Report. 2016. Available online: https://www.bp.com/content/dam/bp/en/corporate/pdf/investors/bp-annual-report-and-form-20f-2016.pdf (accessed on 24 January 2018).
- Asikainen, A.; Pärjälä, E.; Jantunen, M.; Tuomisto, J.T.; Sabel, C.E. Effects of Local Greenhouse Gas Abatement Strategies on Air Pollutant Emissions and on Health in Kuopio, Finland. Climate
**2017**, 5, 43. [Google Scholar] [CrossRef] - Europa. Available online: https://ec.europa.eu/energy/en/topics/energy-efficiency/buildings (accessed on 25 January 2018).
- EU Commission and Parliament. Directive 2002/91/EC of the European Parliament and of the Council of 16 December 2002 on the Energy Performance of Buildings (EPBD). Available online: https://eur-lex.europa.eu/legal-content/EN/TXT/?uri=celex%3A32002L0091 (accessed on 8 May 2018).
- EU Commission and Parliament. Directive 2010/31/EU of the European Parliament and of the Council of 19 May 2010 on the Energy Performance of Buildings (EPBD Recast). Available online: http://www.buildup.eu/en/practices/publications/directive-201031eu-energy-performance-buildings-recast-19-may-2010 (accessed on 8 May 2018).
- Commission Delegated Regulation No 244/2012. Available online: http://www.buildup.eu/sites/default/files/content/l_08120120321en00180036.pdf (accessed on 8 May 2018).
- EU Commission and Parliament. Directive 2012/27/EU of the European Parliament and of the Council of 25 October 2012 on Energy Efficiency, Amending Directives 2009/125/EC and 2010/30/EU and Repealing Directives 2004/8/EC and 2006/32/EC. Available online: https://eur-lex.europa.eu/legal-content/EN/TXT/?uri=celex:32012L0027 (accessed on 8 May 2018).
- Fan, Y.; Xia, X. A multi-objective optimization model for energy-efficiency building envelope retrofitting plan with rooftop PV system installation and maintenance. Appl. Energy
**2017**, 189, 327–335. [Google Scholar] [CrossRef] - Jamei, E.; Rajagopalan, P. Thermal comfort of multiple user groups in indoor aquatic centres. Energy Build.
**2015**, 105, 129–138. [Google Scholar] - Asadi, S.; Mostavi, E.; Boussaa, D. Development of a new methodology to optimize building life cycle cost, environmental impacts, and occupant satisfaction. Energy
**2017**, 121, 606–615. [Google Scholar] - Artuso, P.; Santiangeli, A. Energy solutions for sports facilities. Int. J. Hydrogen Energy
**2008**, 33, 3182–3187. [Google Scholar] [CrossRef] - Nematchoua, M.K.; Orosa, J.A.; Tchinda, R. Thermal comfort and energy consumption in modern versus traditional buildings in Cameroon: A questionnaire-based statistical study. Appl. Energy
**2014**, 114, 687–699. [Google Scholar] [CrossRef] - Day, J.K.; Gunderson, D.E. Understanding high performance buildings: The link between occupant knowledge of passive design systems, corresponding behaviours, occupant comfort and environmental satisfaction. Build. Environ.
**2014**, 84, 114–124. [Google Scholar] [CrossRef] - Antunes, C.H.; Asadi, E.; da Silva, M.G.; Dias, L. Multi-objective optimization for building retrofit strategies: A model and an application. Energy Build.
**2012**, 44, 81–87. [Google Scholar] - Fan, Y.; Xia, X. A multi-objective optimization model for building envelope retrofit planning. Energy Procedia
**2015**, 75, 1299–1304. [Google Scholar] [CrossRef] - Hawkins, T.R.; Majeau-Bettez, G.; Singh, B.; Strømman, A.H. Comparative environmental life cycle assessment of conventional and electric vehicles. J. Ind. Ecol.
**2013**, 17, 53–64. [Google Scholar] [CrossRef] - Gálvez, D.M.; Kerdan, I.G.; Raslan, R.; Ruyssevelt, P. ExRET-Opt: An automated exergy/exergoeconomic simulation framework for building energy retrofit analysis and design optimisation. Appl. Energy
**2017**, 192, 33–58. [Google Scholar] - Attia, S.; Carlucci, S.; Hamdy, M.; O’Brien, W. Assessing gaps and needs for integrating building performance optimization tools in net zero energy buildings design. Energy Build.
**2013**, 60, 110–124. [Google Scholar] [CrossRef] - Amiri, S.S.; Asadi, S.; Mottahedi, M. On the development of multi-linear regression analysis to assess energy consumption in the early stages of building design. Energy Build.
**2014**, 85, 246–255. [Google Scholar] - Asadi, E.; da Silva, M.G.; Antunes, C.H.; Dias, L.; Glicksman, L. Multi-objective optimization for building retrofit: A model using genetic algorithm and artificial neural network and an application. Energy Build.
**2014**, 81, 444–456. [Google Scholar] [CrossRef] - Delgarm, N.; Sajadi, B.; Delgarm, S. Multi-objective optimization of building energy performance and indoor thermal comfort: A new method using artificial bee colony (ABC). Energy Build.
**2016**, 131, 42–53. [Google Scholar] [CrossRef] - Nguyen, A.T.; Reiter, S.; Rigo, P. A review on simulation-based optimization methods applied to building performance analysis. Appl. Energy
**2014**, 113, 1043–1058. [Google Scholar] [CrossRef] - Alcayde, A.; Baños, R.; Gil, C.; Gómez, J.; Manzano-Agugliaro, F.; Montoya, F.G. Optimization methods applied to renewable and sustainable energy: A review. Renew. Sustain. Energy Rev.
**2011**, 15, 1753–1766. [Google Scholar] - Wright, J.; Alajmi, A. Efficient Genetic Algorithm sets for optimizing constrained building design problem. Int. J. Sustain. Built Environ.
**2016**, 5, 123–131. [Google Scholar] [CrossRef] - Alajmi, A.; Wright, J.A. The robustness of genetic algorithms in solving unconstrained building optimization problems. In Proceedings of the 9th International Building Performance Simulation Association Conference, Montreal, QC, Canada, 15–18 August 2005; pp. 1361–1368. [Google Scholar]
- Wetter, M.; Polak, E. A convergent optimization method using pattern search algorithms with adaptive precision simulation. Build. Serv. Eng. Res. Technol.
**2004**, 25, 327–338. [Google Scholar] [CrossRef] - MathWorks. MATLAB-MATrixLABoratory (2015)-8.5.0; User’s Guide; MathWorks: Natick, MA, USA, 2015. [Google Scholar]
- EnergyPlus 8.5.0. Available online: https://github.com/NREL/EnergyPlus/releases/tag/v8.5.0 (accessed on 8 December 2017).
- Krarti, M.; Tuhus-Dubrow, D. Genetic-algorithm based approach to optimize building envelope design for residential buildings. Build. Environ.
**2010**, 45, 1574–1581. [Google Scholar] - Hasan, A.; Sirén, K.; Vuolle, M. Minimisation of life cycle cost of a detached house using combined simulation and optimisation. Build. Environ.
**2008**, 43, 2022–2034. [Google Scholar] [CrossRef] - Eisenhower, B.; Fonoberov, V.A.; Mezić, I.; Narayanan, S.; O’Neill, Z. A methodology for meta-model based optimization in building energy models. Energy Build.
**2012**, 47, 292–301. [Google Scholar] [CrossRef] - Ascione, F.; Bianco, N.; De Stasio, C.; Mauro, G.M.; Vanoli, G.P. Multi-stage and multi-objective optimization for energy retrofitting a developed hospital reference building: A new approach to assess cost-optimality. Appl. Energy
**2016**, 174, 37–68. [Google Scholar] [CrossRef] - Muscio, A. The Solar Reflectance Index as a Tool to Forecast the Heat Released to the Urban Environment: Potentiality and Assessment Issues. Climate
**2018**, 6, 12. [Google Scholar] [CrossRef] - United Nations. World Urbanization Prospects: 2014 Revision; United Nations: New York, NY, USA, 2014. [Google Scholar]
- Vuckovic, M.; Maleki, A.; Mahdavi, A. Strategies for Development and Improvement of the Urban Fabric: A Vienna Case Study. Climate
**2018**, 6, 7. [Google Scholar] [CrossRef] - United Nations. Department of Economic and Social Affairs, Population Division. World Population Prospects: The 2015 Revision, Key Findings and Advance Tables; Working Paper No. ESA/P/WP.241; United Nations: New York, NY, USA, 2015. [Google Scholar]
- Wilson, B.; Chakraborty, A. The Environmental Impacts of Sprawl. Sustainability
**2013**, 5, 3302–3327. [Google Scholar] [CrossRef] - Ascione, F.; Bianco, N.; De Masi, R.F.; Mauro, G.M.; Vanoli, G.P. Energy retrofit of educational buildings: Transient energy simulations, model calibration and multi-objective optimization towards nearly zero-energy performance. Energy Build.
**2017**, 144, 303–319. [Google Scholar] [CrossRef] - Ascione, F.; Bianco, N.; De Stasio, C.; Mauro, G.M.; Vanoli, G.P. CASA, cost-optimal analysis by multi-objective optimisation and artificial neural networks: A new framework for the robust assessment of cost-optimal energy retrofit, feasible for any building. Energy Build.
**2017**, 146, 200–219. [Google Scholar] [CrossRef] - DesignBuilder Software-V. 5.0.3.7; DesignBuilder Software Ltd.: Gloucestershire, UK, 2017; Available online: www.designbuilder.co.uk (accessed on 8 December 2017).
- Citterio, M. Analisi Statistica sul Parco Edilizio non Residenziale e Sviluppo di Modelli di Calcolo Semplificati (Statistical Analysis on the Non-Residential Building Stock and Development of Simplified Calculation Tools). 2009. Available online: http://old.enea.it/attivita_ricerca/energia/sistema_elettrico/Condizionamento/RSE161.pdf (accessed on 8 May 2018). (In Italian)
- Mauro, G.M.; Hamdy, M.; Vanoli, G.P.; Bianco, N.; Hensen, J.L.M. A new methodology for investigating the cost-optimality of energy retrofitting a building category. Energy Build.
**2015**, 107, 456–478. [Google Scholar] [CrossRef] - Italian Government Law. Legge 11 Dicembre 2016, n. 232. Bilancio di Previsione Dello Stato per
**l**’nno Finanziario 2017 e Bilancio Pluriennale per il Triennio 2017–2019 (State Estimated Budget for the Financial Year 2017 and Multi-Year Budget for the Three-Year Period 2017–2019). Available online: http://www.agenziaentrate.gov.it/wps/file/Nsilib/Nsi/Schede/Agevolazioni/DetrRistrEdil36/NP/Articolo+1+commi+2+e+3+legge+232_2016/art+1+commi+2+e+3+legge+11+dicembre+2016.pdf (accessed on 8 May 2018). (In Italian) - Paolini, R.; Zani, A.; MeshkinKiya, M.; Castaldo, V.L.; Pisello, A.L.; Antretter, F.; Poli, T.; Cotana, F. The hygrothermal performance of residential buildings at urban and rural sites: Sensible and latent energy loads and indoor environmental conditions. Energy Build.
**2017**, 152, 792–803. [Google Scholar] [CrossRef] - Arens, E.; Hoyt, T.; Zhou, X.; Huang, L.; Zhang, H.; Schiavon, S. Modeling the comfort effects of short-wave solar radiation indoors. Build. Environ.
**2015**, 88, 3–9. [Google Scholar] [CrossRef] - Fanger, P.O. Thermal Comfort. Analysis and Applications in Environmental Engineering. 1970. Available online: http://journals.sagepub.com/doi/abs/10.1177/146642407209200337 (accessed on 8 May 2018).

**Figure 1.**Scheme of the GA, adapted from [39].

**Figure 2.**Scheme of the 1st optimization stage, adapted from [32].

**Figure 10.**dGC vs dCO

_{2}-eq emissions for all the investigated energy retrofit scenarios for r = 3%. The cost-optimal solution is highlighted by a bigger marker.

Layer n° | Material | Thickness (m) |
---|---|---|

1 | Plaster | 0.025 |

2 | Hollow bricks | 0.12 |

3 | Polystyrene | 0.08 |

4 | Air gap | 0.12 |

5 | Hollow bricks | 0.08 |

6 | Plaster | 0.025 |

Layer n° | Material | Thickness (m) |
---|---|---|

1 | Pebbles | 0.18 |

2 | Slab | 0.30 |

3 | Semi-rigid panels | 0.05 |

4 | Screed | 0.03 |

5 | Tiles | 0.02 |

Layer n° | Material | Thickness (m) |
---|---|---|

1 | Roof plaster | 0.03 |

2 | Roof slab | 0.18 |

3 | Semi-rigid panels | 0.03 |

4 | Screed | 0.03 |

5 | Cement | 0.03 |

Material | Density (kg/m^{3}) | Specific Heat (J/kg K) | Conductivity (W/m K) |
---|---|---|---|

Plaster | 2000 | 1000 | 1.40 |

Hollow bricks | 2000 | 1000 | 0.90 |

Polystyrene | 1100 | 1450 | 0.17 |

Pebbles | 1500 | 1000 | 0.70 |

Semi-rigid panels | 16 | 1660 | 0.046 |

Screed | 1800 | 1000 | 0.90 |

Tiles | 2300 | 840 | 1.00 |

Roof plaster | 800 | 1000 | 0.70 |

Roof screed | 400 | 1000 | 1.40 |

Cement | 2000 | 1000 | 1.40 |

Dimensions and Geometry | |||

Length (E-W direction) | 30 m | Length (N-S direction) | 16 m |

Height | 15 m (5 floors) | Total Area | 2400 m^{2} |

Surface to Volume Ratio | 0.33 m^{−1} | Total Volume | 7200 m^{3} |

Main Boundary Conditions of Energy Simulations | |||

Climatic data | IWEC → EPW | Design occupancy | 230 people |

Number of thermal zones | 50 | ||

Winter setpoint temperature | 20 °C (8 a.m.–1 p.m., 2 p.m.–7 p.m.) | Summer setpoint temperature | 26 °C (8 a.m.–1 p.m., 2 p.m.–7 p.m.) |

Artificial lighting, lighting levels and electric equipment are diversified depending on the thermal zone use | |||

Building Envelope | |||

U_{WALL} | 0.97 W/m^{2}K | U_{GROUNDFLOOR} | 0.51 W/m^{2}K |

U_{ROOF} | 0.85 W/m^{2}K | U_{WINDOWS} | 3.74 W/m^{2}K |

Shading systems | Absent | SHGC_{WINDOWS} | 0.76 |

Infiltration rate | 0.50 ACH | ||

HVAC System | |||

HVAC typology | Four pipe fan coils, hot and cold water loops, no heat recovery | Ventilation Air | 2.5 m^{3}/s globally |

Sensible load control | Yes | Latent load control | Not |

Boiler nominal capacity | 250 kW | Boiler type | Hot water, Gas fired η = 0.85 |

Chiller nominal capacity | 260 kW | Chiller type | Electric air-cooled, COP = 2.3 |

Energy Prices, Conversion Factors and Emission Factors | |||

Electricity price | 0.25 €/kWh | Gas price | 0.90 €/Sm^{3} |

Electricity selling price | 0.07 €/kWh | ||

Electrical-to-primary energy conversion factor | 1.95 | Gas-to-primary energy conversion factor | 1.05 |

Electricity LCA emission factor | 0.708 t CO_{2}/MWh | Gas LCA emission factor | 0.237 t CO_{2} / MWh |

Renewable electricity LCA emission factor | 0.035 t CO_{2} / MWh | ||

Baseline Performance Indicators | |||

TED_{heat} | 10.7 kWh/m^{2}a | TED_{cool} | 62.2 kWh/m^{2}a |

DH | 52.4% | CO_{2}-eq emissions | 161.2 t/a |

GC (r = 1%) | 560.8 €/m^{2} | GC (r = 3%) | 471.9 €/m^{2} |

GC (r = 5%) | 404.1 €/m^{2} |

Design Variables | Values |
---|---|

Setpoint temperature for space heating (°C) | 19; 20 (BB); 21; 22 |

Set-point temperature for space cooling (°C) | 24; 25; 26 (BB); 27 |

Emissivity of the vertical walls (-) | 0.1; 0.25; 0.4; 0.5; 0.6; 0.7; 0.8; 0.9 (BB) |

Absorbance of the vertical walls (-) | 0.1; 0.25; 0.4; 0.5; 0.6 (BB); 0.7; 0.8; 0.9 |

Emissivity of the roof (-) | 0.1; 0.25; 0.4; 0.5; 0.6; 0.7; 0.8; 0.9 (BB) |

Absorbance of the roof (-) | 0.1; 0.2; 0.3; 0.4; 0.5; 0.6 (BB); 0.75; 0.9 |

Additional insulation thickness of the vertical walls (m) | 0 (BB); 0.03; 0.04; 0.05; 0.06; 0.08; 0.10; 0.12 |

Additional insulation thickness of the roof (m) | 0 (BB); 0.03; 0.04; 0.05; 0.06; 0.08; 0.10; 0.12 |

Type of windows (-) | 1 (BB); 2; 3; 4; 5; 6; 7; 8 (see Table 7) |

Type of shading systems (-) | 0 (BB); 1; 2; 3; 4; 5; 6; (see Table 8) |

Position of the shading systems (-) | 1 (internal); 2 (external) |

N° | TYPE | U (W/m^{2}K) | SHGC (-) |
---|---|---|---|

1 | Double-glazed with air-filling. Aluminum frame (BB) | 3.74 | 0.76 |

2 | Double-glazed with air-filling and low-e coating. PVC frame | 2.12 | 0.69 |

3 | Tinted double-glazed with air-filling and low-e coating. PVC frame | 1.95 | 0.38 |

4 | Selective double-glazed with air-filling and low-e coating. PVC frame | 1.84 | 0.43 |

5 | Double-glazed with argon-filling and low-e coating. PVC frame | 1.90 | 0.69 |

6 | Tinted double-glazed with argon-filling and low-e coating. PVC frame | 1.72 | 0.37 |

7 | Selective double-glazed with argon-filling and low-e coating. PVC frame | 1.59 | 0.43 |

8 | Triple-glazed with argon-filling and low-e coating. PVC frame | 1.35 | 0.58 |

N° | TYPE | Solar Transmittance | Solar Reflectance | Visible Transmittance | Visible Reflectance |
---|---|---|---|---|---|

0 | Shading system is absent (BB) | / | / | / | / |

1 | Low reflect—Low trans shade | 0.1 | 0.2 | 0.1 | 0.2 |

2 | Low reflect—Medium trans shade | 0.4 | 0.2 | 0.4 | 0.2 |

3 | Low reflect—High trans shade | 0.7 | 0.2 | 0.7 | 0.2 |

4 | Medium reflect—Low trans shade | 0.1 | 0.5 | 0.1 | 0.5 |

5 | Medium reflect—Medium trans shade | 0.4 | 0.5 | 0.4 | 0.5 |

6 | High reflect—Low trans shade | 0.1 | 0.8 | 0.1 | 0.8 |

Heating System | Efficiency |
---|---|

Traditional boiler (BB) | η = 0.85 |

High-efficiency natural gas boiler | η = 0.95 |

Condensing natural gas boiler | η = 1.05 |

Air-source electric heat pump | COP = 3.5 |

Cooling System | COP |
---|---|

Air-cooled electric chiller (BB) | 2.3 |

High-efficiency electric air-cooled chiller | 1.2 |

ENVELOPE | ||

Energy Efficiency Measure | Characterization | Investment Cost [€/m^{2}] |

Use of an additional insulation layer (roof, external walls) of thickness: | 0.03 m | 30 |

0.04 m | 35 | |

0.05 m | 40 | |

0.06 m | 45 | |

0.08 m | 55 | |

0.10 m | 65 | |

0.12 m | 75 | |

Replacement of the windows | Double-glazed with air-filling and low-e coating. PVC frame | 250 |

Tinted double-glazed with air-filling and low-e coating. PVC frame | 260 | |

Selective double-glazed with air-filling and low-e coating. PVC frame | 260 | |

Double-glazed with argon-filling and low-e coating. PVC frame | 270 | |

Tinted double-glazed with argon-filling and low-e coating. PVC frame | 280 | |

Selective double-glazed with argon-filling and low-e coating. PVC frame | 280 | |

Triple-glazed with argon-filling and low-e coating. PVC frame | 320 | |

Installation of shading systems | Each type of considered shading system | 50 |

HVAC SYSTEM + RES | ||

Energy Efficiency Measure | Characterization | Investment Cost |

Replacement of the primary heating/cooling system * | High-efficiency natural gas boiler | 12,390 € |

Condensing natural gas boiler | 21,260 € | |

Air-source electric heat pump | 41,300 € | |

High-efficiency electric air-cooled chiller | 43,775 € | |

Reversible air-source electric heat pump | 65,662 € | |

Installation of PV panels | Polycrystalline PV panels | 250 €/m^{2} |

Monocrystalline PV panels | 430 €/m^{2} |

* All the HVAC systems are oversized by considering an oversizing factor equal to 1.1.

© 2018 by the authors. Licensee MDPI, Basel, Switzerland. This article is an open access article distributed under the terms and conditions of the Creative Commons Attribution (CC BY) license (http://creativecommons.org/licenses/by/4.0/).