Isolation Microgrid Design for Remote Areas with the Integration of Renewable Energy: A Case Study of Con Dao Island in Vietnam

In remote areas, extending a power line to the primary electricity grid can be very expensive and power losses are high, making connections to the grid almost impossible. A well-designed microgrid that integrates renewable energy resources can help remote areas reduce investment costs and power losses while providing a reliable power source. Therefore, investigating the design of an independent and economically practical microgrid system for these areas is necessary and plays an important role. This paper introduces a design procedure to design an isolated microgrid using HOMER software (HOMERPro 3.14.5) for remote areas. In Vietnam, due to the obstruction of the mountainous terrain or the isolated island location, many remote areas or islands need electrification. A simple case study of a hybrid system with a 60 kW peak load demand on Con Dao island in Vietnam is used to illustrate the proposed design method. Specifically, a hybrid system that includes a PV system, batteries, and a diesel generator is designed. To provide the full information of the designed hybrid system designed, each solution is analyzed and evaluated in detail according to the sensitivity parameters.


Introduction
Recently, energy consumption has increased quickly due to the fast development of the global economy. The fossil energy resources such as coal, oil, and natural gas cannot be recreated and pollute the environment [1]. To address these issues, new renewable energy resources have become a key factor of choice. In developed countries and regions, renewable energy development strategies have been developed to maximize the use of renewable energy resources and increase energy efficiency [2][3][4].
The electricity sector is among the industries that generate the most global emissions, mainly from coal-powered sources. The participation of renewable energy resources in the electricity sector may support a significant reduction in the consumption of fossil fuel and lowering global warming emissions [5]. Distributed power generation technology is the leading vehicle that uses various energy resources, such as wind, solar, and marine energy, to generate electricity effectively. However, challenges exist in the development of these new energy systems. For example, providing a continuous and stable power supply using wind or solar energy is complex because these sources are random and intermittent. The instability of these energies significantly undermines the role of the distributed power plant and the reliability of the power system [6][7][8].
The microgrid (MG) concept, as a group of connected renewable energy resources, loads, and battery energy storage modules, first appeared in the United States [6]. They ensure maximum benefits of small grid models and promote the development of the entire power system [7]. Initially, the small grid was designed to operate independently Clean Technol. 2021, 3, FOR PEER REVIEW 3 and economical manner with intelligent monitoring and control technologies [26,27]. Although there are many different types and configurations of MGs, all of them are similar in nature, as shown in Figure 1.

Microgrid Operation Modes
An MG can operate in isolated mode or grid connection mode [28,29].
-Grid-connected operation mode: The MG is interconnected to the main network. This operating mode is divided into two types: grid connection but not supplying excess power to the grid, and grid connected but providing excess power back to the grid. The frequency of MG is synchronized with the frequency of the main grid without any technical problems. If the load is high and the distributed sources in the MG cannot meet the demand, the main grid will support the supply through the PCC. In this mode, the MG grid is guaranteed to operate safely even if distributed sources fail [30,31]. Figure 2 depicts the grid-connected microgrid model. -Islanded operating mode: The MG, when not connected to the main grid, is called a stand-alone MG. This operating model is commonly applied to grids built in mountainous areas, on islands, or in completely isolated areas, where the main grid cannot supply electricity. The model is also applied when the main power grid fails and

Microgrid Operation Modes
An MG can operate in isolated mode or grid connection mode [28,29].
-Grid-connected operation mode: The MG is interconnected to the main network. This operating mode is divided into two types: grid connection but not supplying excess power to the grid, and grid connected but providing excess power back to the grid. The frequency of MG is synchronized with the frequency of the main grid without any technical problems. If the load is high and the distributed sources in the MG cannot meet the demand, the main grid will support the supply through the PCC. In this mode, the MG grid is guaranteed to operate safely even if distributed sources fail [30,31]. Figure 2 depicts the grid-connected microgrid model. and economical manner with intelligent monitoring and control technologies [26,27]. Although there are many different types and configurations of MGs, all of them are similar in nature, as shown in Figure 1.

Microgrid Operation Modes
An MG can operate in isolated mode or grid connection mode [28,29].
-Grid-connected operation mode: The MG is interconnected to the main network. This operating mode is divided into two types: grid connection but not supplying excess power to the grid, and grid connected but providing excess power back to the grid. The frequency of MG is synchronized with the frequency of the main grid without any technical problems. If the load is high and the distributed sources in the MG cannot meet the demand, the main grid will support the supply through the PCC. In this mode, the MG grid is guaranteed to operate safely even if distributed sources fail [30,31]. Figure 2 depicts the grid-connected microgrid model. -Islanded operating mode: The MG, when not connected to the main grid, is called a stand-alone MG. This operating model is commonly applied to grids built in mountainous areas, on islands, or in completely isolated areas, where the main grid cannot supply electricity. The model is also applied when the main power grid fails and -Islanded operating mode: The MG, when not connected to the main grid, is called a stand-alone MG. This operating model is commonly applied to grids built in mountainous areas, on islands, or in completely isolated areas, where the main grid cannot supply electricity. The model is also applied when the main power grid fails and cannot supply power to an area [32,33]. The island separation of a small grid system helps reduce power outages, ensure the safe operation of the fault grid area, and improve the quality of power supply services. The disadvantage of this model is that the power source depends mainly on distributed energy sources, is unstable, and often changes suddenly depending on weather conditions. Figure 3 depicts the model of an islanded microgrid.
Clean Technol. 2021, 3, FOR PEER REVIEW 4 cannot supply power to an area [32,33]. The island separation of a small grid system helps reduce power outages, ensure the safe operation of the fault grid area, and improve the quality of power supply services. The disadvantage of this model is that the power source depends mainly on distributed energy sources, is unstable, and often changes suddenly depending on weather conditions. Figure 3 depicts the model of an islanded microgrid.

Microgrid Control
To maximize the benefits of distributed power sources, the enhancement of the power supply response and the operation of these power sources needs to be performed through the control system. In the MG grid, the control system is divided into three levels to be able to provide quality power [34]: -Primary control: Usually designed to ensure voltage and frequency stability for microgrids and adjust the power sharing among distributed generators. This level of control also helps minimize circulation currents between paralleled converters of three-phase generators, causing overcurrent in electrical equipment. -Secondary control: The function of this control level is to compensate for the voltage and frequency difference left by the primary control. This level of control has slower dynamics than the primary level, and is performed to satisfy power quality requirements. -Tertiary control, also known as the energy management system: This is the final control level that regulates the power of the MG, and between the MG and the main network. The third level of control also provides an economically optimal operation to minimize the electricity costs.

Energy Management in MG
Energy management is one of the critical components in the MG system, and operates the MG to meet various economic, technical, and environmental objectives as required by the operator [35]. The main objectives often include managing forecast load demand compared to the actual demand, power generation management, reactive power flow management, or loss reduction in the MG system [36].
An MG's energy management system will communicate with all other components to monitor and control the equipment to ensure optimal operation of the entire system. The controller and related components to manage the microgrid are hardware and software of the main controller, a power supply, an SCADA system, a system of renewable energy sources, a main power supply system such as a diesel generator, and a switching system.

Microgrid Control
To maximize the benefits of distributed power sources, the enhancement of the power supply response and the operation of these power sources needs to be performed through the control system. In the MG grid, the control system is divided into three levels to be able to provide quality power [34]: -Primary control: Usually designed to ensure voltage and frequency stability for microgrids and adjust the power sharing among distributed generators. This level of control also helps minimize circulation currents between paralleled converters of three-phase generators, causing overcurrent in electrical equipment. -Secondary control: The function of this control level is to compensate for the voltage and frequency difference left by the primary control. This level of control has slower dynamics than the primary level, and is performed to satisfy power quality requirements. -Tertiary control, also known as the energy management system: This is the final control level that regulates the power of the MG, and between the MG and the main network. The third level of control also provides an economically optimal operation to minimize the electricity costs.

Energy Management in MG
Energy management is one of the critical components in the MG system, and operates the MG to meet various economic, technical, and environmental objectives as required by the operator [35]. The main objectives often include managing forecast load demand compared to the actual demand, power generation management, reactive power flow management, or loss reduction in the MG system [36].
An MG's energy management system will communicate with all other components to monitor and control the equipment to ensure optimal operation of the entire system. The controller and related components to manage the microgrid are hardware and software of the main controller, a power supply, an SCADA system, a system of renewable energy sources, a main power supply system such as a diesel generator, and a switching system.

A Methodology for Designing Microgrid Using HOMER
Unlike in the case of the main power system, the optimal design and calculation of the structure parameters of an MG aim to adapt the load demand and operate the system efficiently, achieving benefits such as saving money, saving energy, and protecting the environment. In order to properly design the MG, it is important to investigate the factors affecting the design and the optimization of MG grid operation based on the system grid operation data. Typically, the design process of an MG grid structure involves three stages as shown in Figure 4 [37]: -Stage 1-Design of distributed energy sources: The objective of this stage is to evaluate the feasibility of the designed system. Questions that need to be answered at this stage include: How much backup power does the model need? This includes a rough assessment of operating costs and how that changes the design paradigm. -Stage 2-Detailed design: At this stage, the design options are narrowed down and focused on concretizing the equipment for the design model. It is necessary to update the data about the supplier's products, thereby refining the design by comparing supplier's information. -Stage 3-Final design: At this stage of the project, the contractor will produce detailed technical drawings and address site-specific issues such as equipment size, wiring, protection scheme, and construction challenges.

A Methodology for Designing Microgrid Using HOMER
Unlike in the case of the main power system, the optimal design and calculation of the structure parameters of an MG aim to adapt the load demand and operate the system efficiently, achieving benefits such as saving money, saving energy, and protecting the environment. In order to properly design the MG, it is important to investigate the factors affecting the design and the optimization of MG grid operation based on the system grid operation data. Typically, the design process of an MG grid structure involves three stages as shown in Figure 4 [37]: -Stage 1-Design of distributed energy sources: The objective of this stage is to evaluate the feasibility of the designed system. Questions that need to be answered at this stage include: How much backup power does the model need? This includes a rough assessment of operating costs and how that changes the design paradigm. -Stage 2-Detailed design: At this stage, the design options are narrowed down and focused on concretizing the equipment for the design model. It is necessary to update the data about the supplier's products, thereby refining the design by comparing supplier's information. -Stage 3-Final design: At this stage of the project, the contractor will produce detailed technical drawings and address site-specific issues such as equipment size, wiring, protection scheme, and construction challenges. The design phase of distributed energy sources is the most critical stage, and is used as a basis for developing detailed designs in this paper. Hybrid Optimization Model for Electric Renewable (HOMER) is a software tool that was originally developed by the US National Renewable Energy Laboratory (NREL), and can be used to evaluate economic and technical models for hybrid systems. The software models the physical characteristics of the power generation system and the life cycle costs of the system components [38]. HOMER allows users to compare and evaluate many different options to choose the most suitable solution while achieving optimal economic efficiency. It includes a large database and updated information about supplier products to aid in this process [39,40].

Model of Power Supply Components in the MG
An MG usually contains different power supply sources, such as small generators (microturbines), fuel cells, solar power, and wind power, or storage batteries. Depending on the requirements of each different project, the designer will choose suitable models to include in the calculation. -Wind turbine model: Data related to wind speed are needed to calculate the power output (PWT) of a wind turbine at each time t. The wind speed is measured over 24 h considering the minimum wind speed to put the turbine into operation (cut-in wind speed), and the maximum wind speed that must stop the turbine from running (cutout wind speed) [2].
where: a, b are wind coefficients and can be calculated as shown in the following equations: The design phase of distributed energy sources is the most critical stage, and is used as a basis for developing detailed designs in this paper. Hybrid Optimization Model for Electric Renewable (HOMER) is a software tool that was originally developed by the US National Renewable Energy Laboratory (NREL), and can be used to evaluate economic and technical models for hybrid systems. The software models the physical characteristics of the power generation system and the life cycle costs of the system components [38]. HOMER allows users to compare and evaluate many different options to choose the most suitable solution while achieving optimal economic efficiency. It includes a large database and updated information about supplier products to aid in this process [39,40].

Model of Power Supply Components in the MG
An MG usually contains different power supply sources, such as small generators (microturbines), fuel cells, solar power, and wind power, or storage batteries. Depending on the requirements of each different project, the designer will choose suitable models to include in the calculation.
-Wind turbine model: Data related to wind speed are needed to calculate the power output (P WT ) of a wind turbine at each time t. The wind speed is measured over 24 h considering the minimum wind speed to put the turbine into operation (cut-in wind speed), and the maximum wind speed that must stop the turbine from running (cut-out wind speed) [2].
where: a, b are wind coefficients and can be calculated as shown in the following equations: P R : wind turbine's rated power V: wind speed V ci : cut-in wind speed Clean Technol. 2021, 3

809
V co : cut-out wind speed -PV model: Solar power generation at date i, time t can be modeled according to the following equation [41]: where: A m : Solar panel surface area (m 2 ) η m : Module efficiency η Conv : Power conversion efficiency T r : Reference temperature of the solar cell β t : Heat coefficient G t : Solar irradiance (W/m 2 ) T c : Solar cell temperature The energy supplied by the PV system, E PV at date i, time t will be calculated according to the following formula: -Microturbine model: To assess the cost of a microturbine, two main cost components are considered: fuel cost C fuel and maintenance cost C O&M at time t -Battery model: The battery energy at date i, time t will be calculated based on the following equation [42]: where: V bat : Battery's nominal voltage C bat : nominal capacity of the battery (Ah) SOC: Battery's stage of charge, which can be calculated in the following equation: where: δ: Capacity available in battery η ch : Charging efficiency of the battery k: battery's status. k = 1 while charging and k = 0 while discharging I bat : Charging current

Optimization Problem for Designing Microgrid
The design of the power supply resources is performed based on the construction of the optimization problem, which can have a single objective or multiple objectives. Factors such as distributed power resources and batteries should be considered when selecting variables. Depending on different MG design and planning strategies, the relevant parameters need to be changed accordingly.
The basic model is usually expressed as follows [43]: Min f i (X), i = 1, 2, 3 . . . where: X is the variable; f i (X) is the objective function; G(X) and H(X) are constraint functions; Ω represents the space of possible solutions.
This optimization model helps to determine an ideal system configuration that satisfies the desired constraints and meets the load demand while eliminating non-viable parameters.
In HOMER, MG design models are selected according to the value of the economic cost optimization function (C NPC ) in the following equation [44]: where: C Annual,Total represents the annual cost R project represents the life of the project J represents the annual interest CRF is the annual return on capital calculated by the equation: where N is the number of years The energy cost (COE) is calculated according to the following equation: where: E primary : Energy supplied to the base load E def : Energy supplied to slow loads E grid, sell : Energy sold to the grid In this process, HOMER simulates a variety of system configurations, eliminating non-viable configurations. Possible solutions are those that satisfy the desired constraints. Possible configurations are sorted by lowest net current cost (C NPC ) and lowest energy cost (COE). The goal of the optimization problem is to analyze decision variables that can be controlled by the user to select the best configuration for the desired load.

An Application for Designing Isolation Microgrid in Con Dao Island, Vietnam
Con Dao is an isolated island located off the coast of South Vietnam. Having a total area of 76 km 2 and more than 10,000 inhabitants, Con Dao is oriented to become one of the national tourism sites of Vietnam. The island attracts 400,000 tourists every year [45]. The forecast electricity demand in Con Dao by 2030 is 33.3 MW. However, the current power supply is only about 11.8 MW [46]. Therefore, it is necessary to propose studies to design a grid system such as a microgrid to meet the future electricity demand for the island. This is also an opportunity to develop renewable-based microgrids in Vietnam [47]. The location of Con Dao island in relation to a Vietnam map is shown in Figure 5.
area of 76 km 2 and more than 10,000 inhabitants, Con Dao is oriented to become one of the national tourism sites of Vietnam. The island attracts 400,000 tourists every year [45]. The forecast electricity demand in Con Dao by 2030 is 33.3 MW. However, the current power supply is only about 11.8 MW [46]. Therefore, it is necessary to propose studies to design a grid system such as a microgrid to meet the future electricity demand for the island. This is also an opportunity to develop renewable-based microgrids in Vietnam [47]. The location of Con Dao island in relation to a Vietnam map is shown in Figure 5.

Application
This section presents a simulated grid design for a small area in Con Dao island, Vietnam, where the main power grid cannot be connected. The case study illustrates is an approach towards a better environment for remote areas by taking advantage of renewable energy resources, specifically solar energy.
The MG is designed to include a solar power system as the main source of generation, in addition to a battery to store excess energy from the solar generator and supply electricity to meet the load during non-sunny periods. Diesel generators are also considered to provide electricity at specific hours of the year. Based on the available data and economic feasibility, HOMER is applied to analyze scenarios and then propose the most suitable and cost-competitive power system for designers. The designed microgrid components are shown in Figure 6.

Application
This section presents a simulated grid design for a small area in Con Dao island, Vietnam, where the main power grid cannot be connected. The case study illustrates is an approach towards a better environment for remote areas by taking advantage of renewable energy resources, specifically solar energy.
The MG is designed to include a solar power system as the main source of generation, in addition to a battery to store excess energy from the solar generator and supply electricity to meet the load during non-sunny periods. Diesel generators are also considered to provide electricity at specific hours of the year. Based on the available data and economic feasibility, HOMER is applied to analyze scenarios and then propose the most suitable and cost-competitive power system for designers. The designed microgrid components are shown in Figure 6.   -Daily estimations of energy usage: The daily energy capacity in the considered area is about 623 kWh, the peak load capacity of the day is about 60 kW. The graph of load profiles is shown in Figure 7. The daily load estimates of a household's energy consumption in the considered area are shown in Table 1. The daily load estimates of a household's energy consumption in the considered area are shown in Table 1.  [48]. The model will run with different scenarios with and without a diesel generator to check if it is necessary to install this generator in the MG. The model of the generator is shown in Figure 8. -Model of PV system: The power output of the solar system is estimated based on the size of PV system, in addition to the temperature and solar energy data at the considered location. The solar irradiance, temperature, and clearness index at Con Dao island were imported from National Renewable Energy Laboratory (NREL) resources [49]. Figure 9 shows the monthly average solar irradiance and clearness index for Con Dao. The model of diesel generator: The simulated diesel generator has a fixed capacity of 40 kW. The capital cost of the generator is is USA 8000, its replacement cost is USD 15,000, and it has a lifetime of 15,000 h [48]. The model will run with different scenarios with and without a diesel generator to check if it is necessary to install this generator in the MG. The model of the generator is shown in Figure 8. -Model of PV system: The power output of the solar system is estimated based on the size of PV system, in addition to the temperature and solar energy data at the considered location. The solar irradiance, temperature, and clearness index at Con Dao island were imported from National Renewable Energy Laboratory (NREL) resources [49]. Figure 9 shows the monthly average solar irradiance and clearness index for Con Dao.   -Model of PV system: The power output of the solar system is estimated based on the size of PV system, in addition to the temperature and solar energy data at the considered location. The solar irradiance, temperature, and clearness index at Con Dao island were imported from National Renewable Energy Laboratory (NREL) resources [49]. Figure 9 shows the monthly average solar irradiance and clearness index for Con Dao.  The solar power generation system is designed to find the optimal power capacity using HOMER Optimizer. The system has a 25 year lifetime, the capital cost is about USD 75,000, and the replacement cost is USA 20,000 [50]. The model of the PV system is shown in Figure 10.
Clean Technol. 2021, 3, FOR PEER REVIEW 11 The solar power generation system is designed to find the optimal power capacity using HOMER Optimizer. The system has a 25 year lifetime, the capital cost is about USD 75,000, and the replacement cost is USA 20,000 [50]. The model of the PV system is shown in Figure 10. Model of the battery: The battery is used to store excess energy from the PV system at peak times and then supply electricity to the load when the system is out of power. The battery is modelled using vanadium redox flow battery specifications with a 40 kWh capacity. The capital cost is USD 15,000, replacement cost is USD 15,000, and the lifetime of the battery is 7 years [51,52]. The model of the battery is designed to find the optimal amount of battery for the system. The model is shown in Figure 11. -Model of the battery: The battery is used to store excess energy from the PV system at peak times and then supply electricity to the load when the system is out of power. The battery is modelled using vanadium redox flow battery specifications with a 40 kWh capacity. The capital cost is USD 15,000, replacement cost is USD 15,000, and the lifetime of the battery is 7 years [51,52]. The model of the battery is designed to find the optimal amount of battery for the system. The model is shown in Figure 11. -Model of the battery: The battery is used to store excess energy from the PV system at peak times and then supply electricity to the load when the system is out of power. The battery is modelled using vanadium redox flow battery specifications with a 40 kWh capacity. The capital cost is USD 15,000, replacement cost is USD 15,000, and the lifetime of the battery is 7 years [51,52]. The model of the battery is designed to find the optimal amount of battery for the system. The model is shown in Figure 11.

Results Analysis
The goal of this design problem is to optimize the average energy cost over 25 years. HOMER will analyze different scenarios based on the load demand and the given information of the considered system. The total cost of the project and the monthly electric production of each generator are shown in Figures 13 and 14.

Results Analysis
The goal of this design problem is to optimize the average energy cost over 25 years. HOMER will analyze different scenarios based on the load demand and the given information of the considered system. The total cost of the project and the monthly electric production of each generator are shown in Figures 13 and 14.
The selected model consists of a 40 kW diesel generator, a 67.5 kW solar power system, one 20-40 kWh battery, and a 22.2 kW power converter. The total optimal system cost was USD 677,663, less than the total cost of designing a basic system consisting of only a diesel generator and a battery. However, the initial cost of the selected system is USD 118,886 higher compared to the base system initial capital cost of USD 33,184 due to the high cost of the PV system.

Results Analysis
The goal of this design problem is to optimize the average energy cost over 25 years. HOMER will analyze different scenarios based on the load demand and the given information of the considered system. The total cost of the project and the monthly electric production of each generator are shown in Figures 13 and 14. The selected model consists of a 40 kW diesel generator, a 67.5 kW solar power system, one 20-40 kWh battery, and a 22.2 kW power converter. The total optimal system cost was USD 677,663, less than the total cost of designing a basic system consisting of only a diesel generator and a battery. However, the initial cost of the selected system is USD 118,886 higher compared to the base system initial capital cost of USD 33,184 due to the high cost of the PV system. As shown in Figure 14, the PV system contributes 40.6% of annual electric production, at 106,881 kWh per year, whereas diesel provides 59.4% of annual electric production, at 156,638 kWh per year. It can be observed that the diesel generator is the main generator of the system. The PV size had to increase to 67.5 kW and the battery size had to decrease to 22.2 kW to match with the model specifications. This means that the presizing of the PV system and the battery is not suitable for the design load. HOMER redesigned the system to give the most feasible configuration with lowest cost. The detailed calculation results are also clearly analyzed in Figure 15. As shown in Figure 14, the PV system contributes 40.6% of annual electric production, at 106,881 kWh per year, whereas diesel provides 59.4% of annual electric production, at 156,638 kWh per year. It can be observed that the diesel generator is the main generator of the system. The PV size had to increase to 67.5 kW and the battery size had to decrease to 22.2 kW to match with the model specifications. This means that the pre-sizing of the PV system and the battery is not suitable for the design load. HOMER redesigned the system to give the most feasible configuration with lowest cost. The detailed calculation results are also clearly analyzed in Figure 15.
It can be seen that the cost analysis helps the designer to clearly see which components in the system involve the highest investment costs and the sources of these costs. Based on the data in Figure 15, it can be seen that although diesel contributes only 60% of the energy to the system, the amount of investment needed for this generator is equal to 80.9% of the total cost. Most of the cost is associated with fuel, accounting for 72.12%; the replacement cost accounts for 15.32%; and the remainder is the initial investment and maintenance costs. In the future, it will be possible to consider increasing the size of the renewable energy power system to reduce the cost of using diesel generators, considering additional criteria for reducing emissions into the environment, towards the development of a clean and sustainable energy system. As shown in Figure 14, the PV system contributes 40.6% of annual electric production, at 106,881 kWh per year, whereas diesel provides 59.4% of annual electric production, at 156,638 kWh per year. It can be observed that the diesel generator is the main generator of the system. The PV size had to increase to 67.5 kW and the battery size had to decrease to 22.2 kW to match with the model specifications. This means that the presizing of the PV system and the battery is not suitable for the design load. HOMER redesigned the system to give the most feasible configuration with lowest cost. The detailed calculation results are also clearly analyzed in Figure 15.

Discussion
The above result is not the only system proposed; based on changes in fuel price, the minimum stage of charge in the battery, and the amount of solar radiation, other solutions were proposed by the software. The details of the results are presented in Table 2.
Depending on the individual evaluation criteria of the investors, the designer can choose the solution that suits their needs and financial ability. Sensitivity parameters are not limited to those given in Table 2, but can also consider the capacity of the solar power system, the number of batteries, the lifetime of the devices, etc. The greater the number of sensitivity parameters given, the more solutions are offered to choose from. Table 2 shows that, the larger the capacity of the PV system, the higher the investment costs, because the cost of the PV system is still high. However, as a result of the ongoing rapid decline in the cost of renewable energy electrical appliances, this will no longer be a concern in the future. Scenario 14 focuses on developing a solar power system with a total cost of USD 2.8 M; the scenario also requires 26 batteries to support the solar power generation system. Scenario 13 focuses on developing a diesel generator and battery system with a total cost of USD 843,417. However, scenario number 13 is not recommended for development because, due to its location in an isolated area, transporting oil fuel for diesel generators will be very expensive, and is thus not yet possible. Moreover, the price of fuel oil will increase in the future due to its increasing scarcity. The problem of environmental pollution is also an important factor affecting the decision of whether to use diesel generators. Furthermore, as a result of the current rapid decrease in the cost of renewable energy electrical equipment, investment costs for renewable energy generation systems will not be a concern in the future. HOMER gives the designer system parameters that are updated regularly, so the results are often close to reality. Users can use sample parameters from the software or easily import parameters they design themselves. From the obtained calculation results, it can be seen that HOMER is an efficient and easy-to-use optimization tool, significantly reducing the calculation time for the designer. By properly planning the location and capacity of power generation, an MG can make full use of renewable resources, satisfy load demand, meet special economic requirements, and provide environmental benefits. However, HOMER does not include voltage, frequency, losses, or power flow calculation functions, so the designer is not yet able to evaluate the stability of the designed system in operation.
Vietnam has been making efforts to develop microgrid models. However, current projects tend to focus on introducing technologies rather than operating models, and the benefits of microgrids are also being underestimated. From a technical perspective, Vietnam needs to focus on developing advanced MG control systems and solutions to enhance energy system management for MG, maximizing profits from renewable energy sources, and reducing transmission and distribution burden on the main grid.

Conclusions
In this paper, a procedure is proposed to design microgrid systems. The main contributions of this paper are providing an overview of the microgrid and proposing a flexible procedure to design an isolated microgrid using the HOMER model. The proposed procedure was applied to design an isolated microgrid for Con Dao island in Vietnam. The pre-sizing system was redesigned to have the lowest cost with the most feasible configuration. The total cost of the selected model, including a 67.5 kW PV system, a 40 kW diesel generator, and a battery, was only USD 677,663, which was USD 165,754 less than the base system. In addition, 13 other models were also offered, based on sensitivity parameters, to provide more choices for designers. The analyses and method presented in this paper can be used as a guideline in the design and implementation of isolated hybrid microgrids in Vietnam, and is applicable to similar isolated areas around the world. These hybrid microgrids will provide efficient, low-cost, and clean energy, and increase reliability and resiliency of the microgrid in isolated areas. In future work, the method will be developed to not only be applied on remote islands, but also in areas where electricity supply is already safely available. Research can also be extended to develop a design model for a network of interconnected microgrids.