Methods of Extinguishing Fires in Objects with High Voltage

: In this study, based on a real ﬁre in an object intended to produce electricity, the method of ﬁre extinguishing by ﬁre protection units with components of the Integrated Rescue System was characterised. The goal was to examine the effectiveness of extinguishing the mentioned type of ﬁre in cooperation with other components of the Integrated Rescue System and the effectiveness of the intervention, where the priority task was the rescue of people from a ﬁre-endangered building with forces and resources deployed in the vicinity of the ﬁre. In the study, the time factor of the arrival of individual components, material and technical equipment, and security was also considered and, based on calculations, the possibilities of the starting units to extinguish the ﬁre and ensure the evacuation of people in the building. Subsequently, after evaluating and examining all possibilities, conclusions were chosen and determined from the results at the place of the intervention and recommendations were deﬁned for future ﬁres in similar objects.


Introduction
Electric energy has become an integral part of our lives, and with the current trend of energy consumption growth, the demands for its production are also increasing.Because of these increased requirements, new power plant blocks or sources of so-called green energy arise when the global demand for electrical energy has increased sharply.However, most countries generate electricity using fossil-fuel thermal power plants, which continue to play a significant role in energy systems worldwide.The electrification system, which includes elements for the production, transformation, transmission, distribution and consumption of electrical energy, is thus constantly growing.From the point of view of operational reliability, a fire protection system is fundamental, where the central unit or parameter is electrical protection.Its task is to determine, based on specific input values, information and set parameters, whether these objects are in an operational (permitted) state or a malfunction.A malfunction is understood as a short circuit, overload, overvoltage, asymmetric load, or reverse flow of power [1][2][3][4][5][6].
High-voltage overhead electrical transmission lines can be characterised as one of the cheapest and most efficient methods of electrical energy transmission, where their safe and continuous supply of electrical energy is vital for public services and users [7].
However, many errors disrupt high-voltage transmission lines, transmission line objects, and the transmission network itself.In many countries, fires under transmission lines are caused by many errors.For example, in South Africa, 1699 errors with fire were recorded, representing about 21% of all areas in 1993-2003 [8,9].
In Brazil, high-voltage transmission lines also suffered many failures, resulting in largescale fires.Also, in China, long-distance high-voltage lines caused failures and subsequent fires.Research into the failure mechanism in these devices and measures to prevent them is crucial for supplying electrical energy.Research focuses as well on the mechanism of decomposition during fire.Due to its dielectric properties, the air is an insulating medium between the high-voltage line and the ground in the transmission line system.During a fire, the properties of the air change and a discharge or breakdown occurs where the first flame causes the breakdown due to the conductive properties present in the air gap.The second phase begins that the fault is caused by the reduced air density resulting from fire heating, and the third phase suggests that small smoke particles present in the fire cause distortions in the electric field that induce flashover [10][11][12][13].
Particles that occur in the air gap reduce the breakdown voltage by shorting part of the gap, but this effect is not significant for large air gaps (~10 m) in HV transmission lines.It is believed that the first and second phases are primarily responsible for fire-induced failures in HV transmission lines [14][15][16].
The issue of transmission line fires and related objects attracts the interest of many researchers, some of whom have already undertaken a lot of work, including the mechanism and analysis of firefighters' interventions, monitoring the fire itself, etc. [17].
For example, A. Robledo-Martinez et al. studied the dielectric characteristics of a model transmission line in the presence of fire [18].
Sukhnandan et al. discussed different flash models under different fire conditions.Li Peng et al. studied the dielectric characteristics of the transmission line gap under fire conditions [1,19].
When it comes to the method of evaluating the dispatch of fire brigades, some researchers presented some calculation methods.Fire hazard warning methods for transmission lines have been discussed in the research of Guo et [20][21][22][23][24][25][26].
From the point of view of monitoring and analysing the spread of fire, a fire warning method based on satellite monitoring near the transmission line was proposed in the publications [15,[27][28][29].
Regarding the earlier papers, their research only focuses on fire warnings for transmission lines.However, there needs to be an overall strategy for controlling fires near high-voltage transmission lines and their facilities.The difficulty and challenge in the field of fire protection in the mentioned objects lies in the fact that:

•
Transmission lines work with high voltage, and firefighters are exposed to the risk of electric shock when extinguishing.Near the high-voltage transmission line, there is no effective fire extinguishing method that would ensure the safety of firefighters when extinguishing the fire;

The Current State of the Issue
Figure 1 and Tables 1-3 show the current state of the transmission system of the Slovak Republic.A fire in the vicinity of transmission lines and their objects is understood as an extraordinary event when a certain period elapses from the start of the fire to the failure of the transmission line.The transmission line may in time in case of fire should lead to broken circuit or failure.It is, therefore, essential to know the time from the fire's start to the transmission line's shutdown, which is important information for carrying out rescue operations in case of transmission line fires.It is assumed that the distance between fire and transmission line is d, and the average burning velocity of vegetation in the direction of the vertical transmission line is v f , as shown in Figure 2 [35][36][37].
A fire in the vicinity of transmission lines and their objects is understood as an extraordinary event when a certain period elapses from the start of the fire to the failure of the transmission line.The transmission line may in time in case of fire should lead to broken circuit or failure.It is, therefore, essential to know the time from the fire's start to the transmission line's shutdown, which is important information for carrying out rescue operations in case of transmission line fires.It is assumed that the distance between fire and transmission line is d, and the average burning velocity of vegetation in the direction of the vertical transmission line is vf, as shown in Figure 2 [35 -37].According to individual statistics, more than 78.6% of fires affecting transmission line objects are caused by power line breaks, which are generally far from rescue services.It takes a significantly long time for workers and fire protection systems to get the fire under control.Also, for this reason, the requirements for the timely rescue of transmission lines in case of fire are very high.It is, therefore, essential to detect the future risk of fire in advance and to deploy fire prevention measures, which requires an integrated control strategy for fire suppression [39][40][41][42][43].
A fire control strategy near transmission lines is proposed to avoid transmission line shutdowns caused by fires, as shown in Figure 3.According to individual statistics, more than 78.6% of fires affecting transmission line objects are caused by power line breaks, which are generally far from rescue services.It takes a significantly long time for workers and fire protection systems to get the fire under control.Also, for this reason, the requirements for the timely rescue of transmission lines in case of fire are very high.It is, therefore, essential to detect the future risk of fire in advance and to deploy fire prevention measures, which requires an integrated control strategy for fire suppression [39][40][41][42][43].
A fire control strategy near transmission lines is proposed to avoid transmission line shutdowns caused by fires, as shown in Figure 3.As shown in Figure 3, the strategy includes three key steps, which are: 1. Predicting the possibility of fire.
The time and sequence of extinguishing a fire on a transmission line are shown in  As shown in Figure 3, the strategy includes three key steps, which are: 1.
Predicting the possibility of fire.2.
Fire monitoring.
The time and sequence of extinguishing a fire on a transmission line are shown in Figure 4.The fire risk in the vicinity of transmission lines can be clarified by the method of fire prediction, and then fire extinguishing equipment can be activated.In the event of a fire, these devices can, with high-quality monitoring in real-time, locate and subsequently eliminate the arising fire, i.e., reach the fire field in time.Finally, active systems can ensure that power workers can extinguish a fire safely and quickly under high voltage, thus preventing the line from being shut down without the risk of electric shock.These three basic steps are a particular whole, and have internal relationships with each other from fire prediction, the arrangement of active fire protection systems and shortening the reach distance of firefighting units [47][48][49][50].

Methodology
The intervention occurred during a fire in the company's compressor station Eustream a. s., Veľké Kapušany, Energoblok E building (Figure 5).The intervention was carried out by units from the District Directorate of the Fire and Rescue Service in Michalovce on 13 April 2023, from the fire stations in Michalovce, Veľké Kapušany, Sobrance and the volunteer fire brigade of the village Čičarovce.
The goal of the intervention was to eliminate the fire in the compressor station of the company Eustream a.s.Veľké Kapušany, in building number 201 (Figure 5), on the premises of the thyristor factory, connected with the evacuation of employees.In addition to the activities associated with extinguishing, evacuation and rescue, it is necessary to analyse the abilities and skills of the command during the intervention, the establishment of

Methodology
The intervention occurred during a fire in the company's compressor station Eustream a. s., Vel'ké Kapušany, Energoblok E building (Figure 5).

Methodology
The intervention occurred during a fire in the company's compressor station Eustream a. s., Veľké Kapušany, Energoblok E building (Figure 5).The goal of the intervention was to eliminate the fire in the compressor station of the  The intervention was carried out by units from the District Directorate of the Fire and Rescue Service in Michalovce on 13 April 2023, from the fire stations in Michalovce, Vel'ké Kapušany, Sobrance and the volunteer fire brigade of the village Čičarovce.
The goal of the intervention was to eliminate the fire in the compressor station of the company Eustream a.s.Vel'ké Kapušany, in building number 201 (Figure 5), on the premises of the thyristor factory, connected with the evacuation of employees.In addition to the activities associated with extinguishing, evacuation and rescue, it is necessary to analyse the abilities and skills of the command during the intervention, the establishment of the command staff, and the management of forces and resources simultaneously with the coordination with the participating components of the Integrated Rescue System.

Operational-Tactical Characteristics of the Object
Object 201 Energoblok is part of a set of three construction objects (Figure 6): 1.

3.
Building 171 Control room E.  These are combined into a monoblock.Energoblok is located on the south side of this monoblock.In the Energoblok are electrical devices that are functionally an intermediate link between the 110 kV substation and the electrical aggregate for powering the electrical station.It also contains air conditioning equipment for air conditioning in the electrical equipment rooms of building 201.The building is connected to the control room through communication and electrical lines.It is connected to the 110 kV substation by an overhead line and cable ducts in communication.It is connected to the object 111 by passage tunnels.The building of the Energoblok is a four-storey made of steel structures.The perimeter shell comprises gas silicate panels anchored to the supporting frame with steel brackets and fasteners.The roof and ceilings are reinforced concrete.
In a separate area of the control room on the level of the first above-ground floor, there is a spare source of electricity in hall E with an operating tank of 0.  These are combined into a monoblock.Energoblok is located on the south side of this monoblock.In the Energoblok are electrical devices that are functionally an intermediate link between the 110 kV substation and the electrical aggregate for powering the electrical station.It also contains air conditioning equipment for air conditioning in the electrical equipment rooms of building 201.The building is connected to the control room through communication and electrical lines.It is connected to the 110 kV substation by an overhead line and cable ducts in communication.It is connected to the object 111 by passage tunnels.The building of the Energoblok is a four-storey made of steel structures.The perimeter shell comprises gas silicate panels anchored to the supporting frame with steel brackets and fasteners.The roof and ceilings are reinforced concrete.
In a separate area of the control room on the level of the first above-ground floor, there is a spare source of electricity in hall E with an operating tank of 0.3 m 3 of diesel fuel.The stairwell connecting the individual floors of the control room building forms a separate fire section.
The Energoblok building is divided into five sections.On the individual floors, technological devices ensure the power supply of 3 units of electrical station E.
Oil condensers ES1 and ES2 are in a separate room (not separated from the fire) on the first above-ground floor.The condenser room ES1 has a dry transformer TR9 of the KS 22.4 kV backup power supply.Automatic electric fire alarm detectors protect the premises of the condensers.In addition to the condenser rooms, on the first above-ground floor, there is a cable riser of control cables leading from the external 110 kV substation to the Energoblok.
On the second above-ground floor, under the self-consumption substation, there is a cable space (not separated by fire).On the second floor, there is also a machine room of a stable gas (CO 2 ) fire extinguishing device by Karosa Vysoké Mýto, intended for extinguishing fires in the Eustream dungeons in hall E. The second floor is connected to the first floor of the Energoblok through mounting holes.
On the third floor, there is a high voltage (HV) cable area and a self-consumption substation.An above-ground cable bridge (non-separated by fire) leads to coolers and gas filters from the self-consumption substation.Entrances to individual cable rooms are equipped with fire shutters.Transitions of cable routes through fire separation structures are not sealed.Automatic EPS detectors protect all premises.
On the fourth floor, HVAC machine rooms are in two structurally separate spaces.The air ducts are equipped with fire dampers at the inlets and outlets.Automatic EPS detectors are installed in the rooms of the HVAC machine room.In two rooms (separated by fire), oil tanks are placed in emergency tanks, which are used to cool the ES.
In Figure 7, there is object 171, which is a control object.
Fire 2023, 6, x FOR PEER REVIEW 8 On the third floor, there is a high voltage (HV) cable area and a self-consump substation.An above-ground cable bridge (non-separated by fire) leads to coolers and filters from the self-consumption substation.Entrances to individual cable rooms equipped with fire shutters.Transitions of cable routes through fire separation struct are not sealed.Automatic EPS detectors protect all premises.
On the fourth floor, HVAC machine rooms are in two structurally separate spa The air ducts are equipped with fire dampers at the inlets and outlets.Automatic detectors are installed in the rooms of the HVAC machine room.In two rooms (separ by fire), oil tanks are placed in emergency tanks, which are used to cool the ES.
In Figure 7, there is object 171, which is a control object.On the first floor are warehouses, an HVAC machine room for the control room exchange station, an alternate source of electricity, and a gas boiler room.
On the second floor are workshops, electrical, cable room, UPS room and kitche On the third floor, a cable area leads to the cable bridge, an electrical substation conditioning and warehouses.
On the fourth floor are control rooms for compressor halls E and T, electrical pro tion, social areas and offices.There is no permanent service in the control room.While EPS Schrack switchboard of halls E and T is located there, the control panel of the Si gas detection system is also located here, and at the same time, the machine room sw boards of halls E and T are in the control room.All signals from the EPS and mac room switchboards are taken to control room no.2, where permanent service exists.

Results
As a result of an electrical short circuit in the thyristor plant, a fire occurred in cooling system of the equipment in which the oil is located.The EPS automatic dete On the first floor are warehouses, an HVAC machine room for the control room, an exchange station, an alternate source of electricity, and a gas boiler room.
On the second floor are workshops, electrical, cable room, UPS room and kitchen.On the third floor, a cable area leads to the cable bridge, an electrical substation, air conditioning and warehouses.
On the fourth floor are control rooms for compressor halls E and T, electrical protection, social areas and offices.There is no permanent service in the control room.While the EPS Schrack switchboard of halls E and T is located there, the control panel of the Sieger gas detection system is also located here, and at the same time, the machine room switchboards of halls E and T are in the control room.All signals from the EPS and machine room switchboards are taken to control room no.2, where permanent service exists.

Results
As a result of an electrical short circuit in the thyristor plant, a fire occurred in the cooling system of the equipment in which the oil is located.The EPS automatic detector signals to the operator in the control room that a malfunction has occurred in the given room and automatically switches off the electricity supply in the building.
During the inspection, one of the employees discovers that the room has been engulfed in fire, because of which the enclosed spaces will very quickly become heavily smoky.Because of this, he can no longer return to the control room and runs up the metal stairs to the roof of the building, reports the fire to the gatehouse and waits for rescue.An employee of the gatehouse reports the fire to the Integrated Rescue System line 112.Two other people are in the control room.One person is unconscious, and the other is disoriented.As a result of the short circuit, the electrical system in the control room building failed.The first unit from the Vel'ké Kapušany fire station will arrive after the alarm is announced.Based on initial information, the commander of the intervention requests additional forces and resources from the District Directorate of the Fire and Rescue Service in Michalovce and the Sobrance fire station, volunteer fire brigade Čičarovce and other components of the Integrated Rescue System through the operations centre of the Regional Directorate of the Fire and Rescue Service in Košice.Due to the considerable number of deployed forces and resources, the intervention commander establishes a control staff.
Based on the request, the members of the Police force are thinning the traffic at the turn-off from the state road no.555 towards the Eustream plant.Extinguishing the fire in the closed spaces of the thyristor plant will take place with an extinguishing agent-heavy foam.
Water sources in the company are built through the fire water distribution.Aboveground hydrants are located near hall E. Water can be added to tank car sprinklers directly from a hydrant or by connecting to a fire water pumping station.
Access roads to the area are possible through several car entrances.The intra-campus roads are circular, reinforced, concrete, at least 3.0 m wide, and capable of withstanding a pressure of at least 80 kN per vehicle axle.Deploying mobile high-altitude firefighting equipment for firefighting is possible at every facility.No pipelines or conveyor bridges would limit the movement of firefighting equipment over the external intra-campus roads.
The access road to the intra-campus roads is located at approx.600 m and connects to the state road no.555 Michalovce-Vel'ké Kapušany-Král'ovský Chlmec.
The main tasks: 1. Search to determine the presence of persons at risk, possible hiding places, dangerous materials, paths of fire spread, the state of building structures, and possible emergency routes.2. Carry out the evacuation and rescue of all persons at risk, ensure that the power is turned off, and take measures to remove heat and smoke (natural or forced ventilation).3. Carry out the localisation and liquidation of the fire using a suitable extinguishing agent and additives to increase the extinguishing effects.4. Use the optimal amount of supplied extinguishing agent regarding fire extinguishing efficiency (streamline P6). 5. Take measures to protect property from the foam used for extinguishing.6.To improve cooperation in fighting fires in industrial buildings, members' skills in using ADP and providing first aid to injured persons are used.
Intervention sections: 1. Intervention section no.1: searching for people, evacuating people, locating and extinguishing the fire and providing first aid to injured people.2. Intervention section no.2: searching for people, evacuating people with the help of high-altitude equipment and providing first aid to injured people.3. Intervention section no.3: Ensure the cooling of the gas coolers E and T hall and the ventilation of smoky areas.4. Intervention section no.4: performing air quality monitoring using detection technology.The arrival time of the Vel'ké Kapušany fire brigade: t v -the dispatch time = 1 min, t j = (60 × L)/v j t j -the unit's driving time to the fire, L-distance in km, v j -average vehicle speed in kmh −1 (45 kmh −1 ), t j = (60 × 4)/45 = 6 min, t do = 1 + 5 = 6 min.
The arrival time of the DD FRS Michalovce fire brigade: t v -the dispatch time = 1 min, t j = (60 × L)/v j t j -the unit's driving time to the fire, L-distance in km, t v -the dispatch time = 10 min, t j = (60 × L)/v j t j -the unit's driving time to the fire, L-distance in km, v j -average vehicle speed in kmh −1 (45 kmh −1 ), t j = (60 × 5)/45 = 7 min, t do = 10 + 7 = 17 min.
Fire area in the room: where: n-the number of spreading directions = 2, a-the width of the room = 4 m, l-the distance of the fire spread from the fire core = 10 m.Fire spread distance (fire radius) r-with a burning time of more than ten minutes until the first streams are deployed: where: t 2 -the time of free spread of fire (till first streams), t vr -the free fire development time = 14 or 12 min, t 1 -the burn-up time (0-10 min) = 10 min, Fire 2023, 6, 442 t 2 = 4 min.
Due to the rapid fire spread of electrical installation material in combination with flowing transformer oil, including cable bridges, a value of twice the linear speed of fire spread was chosen: where: v-the linear speed of fire spread [m.min The radius of the fire r can reach a maximum of half the room's width, and the fire starts to spread in a straight-angle form (Figure 9), where: h-extinguishing depth [m], n-number of fire propagation directions, a-room width [m], l-the distance to which the fire spread from the core [m] [51][52][53][54][55].

Consumption of Fire Extinguishing Foam
To ensure the successful liquidation of a fire with foam, it is necessary to ensure its uninterrupted supply for at least 10 min.When extinguishing with foam, it is necessary to ensure a triple foam supply at the place.A foaming agent called M51 + 3% with 3% mixing was used during the intervention.
The fire in the thyristor room was extinguished using two streams of heavy foam with a foam generator P6.The P6 heavy foam generator has a foaming solution flow rate of 680 l/min at a pressure of 0.6 MPa.Foam consumption at 3% mixing is 20.4 l/min, and the resulting water consumption is 659.6 l/min.
According to Table 4 of the FRS president's instruction no.39/2003 on the content and procedure for processing documentation on fighting fires, the extinguishing area with one foam generator P6 is 56 m 2 .

Consumption of Fire Extinguishing Foam
To ensure the successful liquidation of a fire with foam, it is necessary to ensure its uninterrupted supply for at least 10 min.When extinguishing with foam, it is necessary to ensure a triple foam supply at the place.A foaming agent called M51 + 3% with 3% mixing was used during the intervention.
The fire in the thyristor room was extinguished using two streams of heavy foam with a foam generator P6.The P6 heavy foam generator has a foaming solution flow rate of 680 l.min at a pressure of 0.6 MPa.Foam consumption at 3% mixing is 20.4 l.min, and the resulting water consumption is 659.6 l.min.
According to Table 4 of the FRS president's instruction no.39/2003 on the content and procedure for processing documentation on fighting fires, the extinguishing area with one foam generator P6 is 56 m 2 .
The required amount of water and foaming agent is determined according to the formula (V p -the amount of foaming agent): where: n pr -the number of foam generators = 2 pcs, q p -the foam flow through the foam generator = 20.4l.min −1 , t n -the normative fire extinguishing time = 10 min, z-the foam supply coefficient = 3. Amount of foaming agent for heavy foam: Water consumption in the production of heavy foam V v : 576 l (predtým 39,360 l); (11) where: Q v -water flow through the foam generator.

Number of Streams for Fire Extinguishing
Necessary supply of extinguishing agent where: S h -fire area = 80 m 2 I p -the required intensity of supply according to instruction 39/2003 (Table 1, Annex no.2-A.Production, workshops, maintenance-electrical substations, transformers, substations and cable lines of electrical objects).
Number of extinguishing streams: where: Q ph -Necessary supply of extinguishing agent Q pr -the flow of the foaming solution through the foam generator.Necessary supply of extinguishing agent for cooling: where: S o -cooling area in square meters, i.e., the area of another object that needs to be cooled I p -The intensity of the supply of extinguishing agent.Number of streams for cooling: where: N pro = 2 combined streamlines (in this case, 2 C hoses with nozzles), Q po -the necessary amount of extinguishing agent intended for cooling, Q pr -streamline flow.

Actual Consumption of Extinguishing Agent
Calculation of the actual consumption of the extinguishing agent: where: N prh -number of extinguishing streams [pcs] Q pr -The P6 heavy foam generator has a foaming solution flow rate of 680 l.min at a pressure of 0.6 MPa.
Foam agent consumption at 3% mixing 24 l.min and the resulting water consumption 656 l.min.A combined flow line at a pressure of 0.6 MPa 280 l.min is used for cooling the technological equipment.

Determining the Number of Members of FRS
Calculation of the number of members: where: n pc -number of streams "P6" members for working with streams to locate and extinguish the fire.Other members involved in the intervention ensure the command during the intervention, the engineer's function, search, monitoring of air quality using detection technology, provision of first aid in the rescue nest and provision of positive pressure ventilation.Volunteer Fire Brigade Čičarovce, in cooperation with the staff, ensures the connection of fire trucks to the fire water pumping station and cooperates in traffic management and other activities required by the commander.Overpressure ventilation was used to remove smoke from the space, and natural ventilation through open windows and doors leading to the open space.
Calculation of the number of cisterns for the supply of water for extinguishing and cooling: where: N A -the number of fire trucks, Q p -necessary supply of extinguishing agent for extinguishing and protection [l.min −1 ], q A -supply of extinguishing agent, which can be provided by the fire brigade from its truck [l.min −1 ], N A = 1312/0.75× 3000 = 1 pcs CAS 30 to extinguish the fire, N A = 560/0.75× 3000 = 1 pcs CAS 30 for cooling.
The connection of the pumps at the given event is as follows.From the tank and the pump of the CAS 30 IVECO Trakker outlet, the attack line 1B, distributor and 2C streams were created.Additions to CAS 30 IVECO Trakker secured by connection to the existing hydrant network.Delivery of the foam agent is ensured by KHA Mercedes-Benz AROCS 6 × 6.

Analysis of Results
In Table 4, we can see the equipment involved in the intervention, the number of intervention members and the timetable for the arrival of the fire brigades.
In Table 5, we can see the schedule of the activities of the firefighting units.The intervention commander issues an instruction to conduct an initial search.With the help of responsible personnel, he ensures the evacuation of people.
Arrival of the fire brigade.Upon search, they find heavy smoke in the building.There are supposed to be three people in hall E.

8:12 Situation scouting
The intervention commander ordered a traffic and attack line to the building to locate the fire and search for people and their subsequent evacuation.

Establishment of intervention section no. 1 (commander of HS
Vel'ké Kapušany team)-for evacuating people, searching for people and locating the fire in the thyristor plant.

8:20
Fumigation of the thyristor room, corridors and control room Alarm announcement to VFB Čičarovce and the crew of emergency medical aid.Establishing a management staff in connection with an emergency.

8:25
First person saved The intervention commander reports the events to the management staff Found an adult in the control room.The person is conscious-removing the person and providing pre-medical assistance.The intervention commander reports events to the incident management staff An adult person was found unconscious, taken to a safe area using a stretcher and handed over to the care of paramedics.

8:40 Arrival of a unit from Sobrance
The commander of the intervention issues an order to cool the pipes of the gas coolers of the E and T hall Establishment of intervention section no. 3 (commander of the Sobrance team)-for cooling the pipes of the gas coolers of the E and T hall 8:42 Fire suppression The intervention commander reports events to the incident management staff Firefighters on the attack streams report that the fire has been extinguished.

8:47 Ventilation of premises
The intervention commander orders the unit from Michalovce to create overpressure ventilation in IS no. 1.
The unit performs ventilation using an overpressure fan.

8:50 Arrival of the volunteer Čičarovce unit
The intervention commander orders assistance in the evacuation of employees and assistance to firefighting units in various operations.
The unit performs tasks on the instruction of the intervention commander.

Search and evacuation of all persons and final search
The intervention commander orders a final search to be carried out The intervention commander performs with commander IS No. 1 a final search of the building object.

9:28 Termination of intervention
The intervention commander announces the end of the intervention Completion of intervention and concentration of equipment at the specified location.

Organisation of Connection and Determination of Radio Networks
The radio connection was made on the default frequency through the Regional Directorate of the Fire and Rescue Service operations centre in Košice (OC RD FRS in Košice) (Figure 10).
Connections during the intervention between OC RD FRS Košice and the intervention commander:
The connection between the commander of the intervention, the chief of staff and the commanders of the intervention sections was ensured through the SITNO digital network-channel 606 (backup talk group).
The connection between the management staff and OC RD FRS Košice was ensured using the SITNO digital network-channel 605.Connection at the point of intervention analogue network channel no. 5, channel no. 7, channel no. 9 and channel no.11 (vehicles according to individual intervention sections).

Conclusions
The mentioned method of extinguishing the fire was determined on the basis of an assessment of the operational-tactical use of forces and resources of the area of intervention, the documentation of fire safety of the building in connection with the individual methodological sheets, and based on the evaluation of this intervention, it is possible to summarize the results in the following evaluation and discussion conclusions.
From the point of view of the danger to the health of not only the responding firefighters, but also the personnel who may be in similar buildings, it is necessary to ensure that the supply of electricity and gas is turned off through the operation centre.

Conclusions
The mentioned method of extinguishing the fire was determined on the basis of an assessment of the operational-tactical use of forces and resources of the area of intervention, the documentation of fire safety of the building in connection with the individual methodological sheets, and based on the evaluation of this intervention, it is possible to summarize the results in the following evaluation and discussion conclusions.
From the point of view of the danger to the health of not only the responding firefighters, but also the personnel who may be in similar buildings, it is necessary to ensure that the supply of electricity and gas is turned off through the operation centre.
Based on the experience of interventions and the knowledge of extinguishing agents, it is possible to state that extinguishing fires under high voltage is impossible, as extinguishing agents as such do not allow fire to be extinguished at such high voltages.
After stopping the supplies of the mentioned energy sources, it is possible to carry out a survey, which will consist of several search groups, while immediately after finding people in the given objects, it is necessary to ensure evacuation based on the instructions of the intervention commander and to start providing pre-medical first aid to the affected persons.After carrying out the survey, the intervention commander must determine whether the necessary material and technical equipment and security at the intervention site will be sufficient for the localization and subsequent liquidation of the fire.
In addition to the already mentioned tasks, this survey must also consist of marking the places where the survey itself took place, ensuring the transport of injured and disabled persons to a medical facility, determining the degree of protection not only of the responding firefighters, but also of persons evacuated from the given object.This must be determined in advance based on the initial decision whether the forces and resources will be sufficient for such a complex intervention.
As for the use of the extinguishing agent, it must be determined in advance during the survey, taking into account the danger of high temperatures, where classic extinguishing agents such as water, classic types of foams without extra admixtures can cause an explosion and endanger all participating intervention units.
During the actual use of the extinguishing agent and the execution of extinguishing works, it is necessary to ensure ventilation of the interior spaces, where it is necessary to consider the use of positive pressure ventilation with regard to the height of the neutral plane in the building and the possibility of controlling the fire with ventilation.Despite the risks of the work of fire fighters, it is necessary to observe the rules of occupational safety applicable to all types of activities that will be carried out during the intervention, with a reminder that human life is the most valuable and has priority over possible damage to property.
The most important step in launching an intervention, from its announcement until its liquidation, where the intervention itself consists of the already mentioned steps, is communication with the operations centre, which forms information support for the intervention commander and the entire intervention unit and also, based on communication, provides the necessary forces and means of other rescue components that are needed at the scene of the intervention, from the police force, medical rescue service to volunteers, who will provide secondary activities.
As already mentioned, delivery of any extinguishing agent (water, foam, powder ABC, BC, D, inert gases and other alternative combinations) is not possible if objects, equipment and technologies are under high voltage.For this reason, as already explained, it is first necessary to ensure that the supply of electricity and gas is shut off.
As a possible suggestion and recommendation, it is to reevaluate the current active fire protection systems in these objects and incorporate into the legislative process the necessity to secure these objects with a certain type of EPS, but that is no longer the purpose of this publication.

Figure 1 .
Figure 1.Map of power system of the Slovak Republic [34].

Figure 5 .
Figure 5. Object Eustream a. s. (source: elaborated by authors).The intervention was carried out by units from the District Directorate of the Fire and Rescue Service in Michalovce on 13 April 2023, from the fire stations in Michalovce, Veľké Kapušany, Sobrance and the volunteer fire brigade of the village Čičarovce.The goal of the intervention was to eliminate the fire in the compressor station of the

Figure 6 .
Figure 6.Location on the object on cadastral map (source: elaborated by authors).
3 m 3 of diesel fuel.The stairwell connecting the individual floors of the control room building forms a separate fire section.The Energoblok building is divided into five sections.On the individual floors, technological devices ensure the power supply of 3 units of electrical station E. Oil condensers ES1 and ES2 are in a separate room (not separated from the fire) on the first above-ground floor.The condenser room ES1 has a dry transformer TR9 of the KS 22.4 kV backup power supply.Automatic electric fire alarm detectors protect the prem-

Figure 6 .
Figure 6.Location on the object on cadastral map (source: elaborated by authors).

Fire 2023, 6 ,
x FOR PEER REVIEW 12 of 23 Due to the rapid fire spread of electrical installation material in combination with flowing transformer oil, including cable bridges, a value of twice the linear speed of fire spread was chosen: linear speed of fire spread [m.min −1 ] [51], v = 0.5 [m.min −1 ].The radius of the fire r can reach a maximum of half the room's width, and the fire starts to spread in a straight-angle form (Figure 9), where: h-extinguishing depth [m], n-number of fire propagation directions, a-room width [m], l-the distance to which the fire spread from the core [m] [51-55].

N po = 2 × 2 ×
1.25 = 5 members for cooling the gas pipeline.Evacuation of persons: -Number of members for evacuation at least 6 (3 persons); -Evacuation of people using MB Atego AR L 39 Metz high-altitude equipment.

Figure 11
Figure 11 and 12 shows the deployment of forces and resources at the site of the intervention.

Figures 11 and 12
Figures 11 and 12  shows the deployment of forces and resources at the site of the intervention.

Figure 11
Figure 11 and 12 shows the deployment of forces and resources at the site of the intervention.

Figure 11 .
Figure 11.Deployment of forces and resources at the site of the intervention (source: elaborated by authors).

Figure 11 .
Figure 11.Deployment of forces and resources at the site of the intervention (source: elaborated by authors).

Table 1 .
External electrical lines-lengths of lines (source: elaborated by authors).

Table 2 .
External power lines-number of masts (source: elaborated by authors).

Table 2 .
External power lines-number of masts (source: elaborated by authors).

Table 4 .
Information about intervening fire stations (source: elaborated by authors).

Table 4 .
Information about intervening fire stations (source: elaborated by authors).

Table 5 .
Schedule of activities (source: elaborated by authors).