Experimental Analysis of Local Condensation Heat Transfer Characteristics of CF 3 I Inside a Plate Heat Exchanger

: Due to its low global warming potential (GWP) and good environmental properties, CF 3 I can be a suitable component of refrigerant mixtures in the ﬁeld of refrigeration and air conditioning. In this work, the local condensation heat transfer characteristics of CF 3 I were experimentally investigated in a plate heat exchanger (PHE). The condensation heat transfer experiments were carried out under conditions of vapor qualities from 1.0 to 0.0, at saturation temperatures of 25–30 ◦ C, mass ﬂuxes of 20–50 kg/m 2 s, and heat ﬂuxes of 10.4–13.7 kW/m 2 . Local heat transfer coefﬁcients were found to vary in both the horizontal and vertical directions of the plate heat exchanger showing similar trends in all mass ﬂuxes. In addition, the characteristics of local heat ﬂux and wall temperature distribution as a function of distance from the inlet to the outlet of the refrigerant channel were explored in detail. The comparison of the experimental data of CF 3 I with that of R1234yf in the same test facility showed that the heat transfer coefﬁcients of CF 3 I were comparable to R1234yf at a low vapor quality and a mass ﬂux of 20 kg/m 2 s. However, R1234yf exhibited a transfer coefﬁcient about 1.5 times higher at all vapor qualities and a mass ﬂux of 50 kg/m 2 s. The newly developed correlation predicts well the experimentally obtained data for both CF 3 I and R1234yf within ± 30%.


Introduction
Plate heat exchangers (PHEs) are nowadays extensively being used in several industrial applications such as dairy processing, paper/pulp, refrigeration, heating, ventilation, and air conditioning.PHEs are superior to other kinds of heat exchangers in several ways.They are useful for energy and space-saving because they generally have a higher heat transfer area to volume ratio and have less weight, flexible designs, and good thermal efficiency.Their adaptable design gives them an advantage in changing the heat transfer area since it makes it easy to add or remove plates without disrupting the pipe connections.Plate-type heat exchangers have been widely used as two-phase heat exchangers in heating and refrigeration systems due to their advantages.
Yan et al. [1] conducted experiments to measure the condensation heat transfer coefficient and frictional pressure drop of R134a in a vertical plate heat exchanger.Their investigation of the effect of refrigerant mass flux, imposed heat flux, and system pressure on condensation heat transfer showed that with the imposed heat flux, refrigerant mass flux, and vapor quality, both the heat transfer coefficient and pressure drop increased.Additionally, the increase in pressure drop caused by the vapor quality was higher than the heat transfer coefficient.It was also observed that the heat transfer coefficients were somewhat lower at a greater system pressure.Correlations for the experimentally measured heat transfer coefficient and frictional pressure drop were developed.
Han et al. [2] carried out experiments to determine the condensation heat transfer coefficient and the pressure drop of R410A and R22 in brazed plate heat exchangers (BPHEs) with different chevron angles, such as 45 • , 55 • , and 70 • .They determined the condensation heat transfer coefficients and pressure drop by varying the mass flux, condensation temperature, and refrigerant vapor quality.The pressure drop and heat transfer coefficient both increased proportionately as the refrigerant mass flux and vapor quality increased, but inversely with the condensation temperature.The heat transfer coefficient was also found to increase with chevron angles.For the tested BPHEs, correlations of the Nusselt number and the friction factor with the geometrical parameters were proposed.
Jokar et al. [3,4] also experimentally measured the heat transfer coefficients and pressure drop during condensation of HFC-134a inside BPHEs and applied dimensional analysis to develop new correlations of heat transfer and pressure drop.
Longo et al. [5] conducted an experimental investigation on the use of a "crossgrooved" surface and the vaporization and condensation of the refrigerant HCFC-22 within a BPHE with herringbone macro-scale corrugation.Compared to conventional herringbone plates with a smooth surface, herringbone plates with a "cross-grooved" surface demonstrated a 30% to 40% increase in evaporation and a 60% increase in the condensation heat transfer coefficient.
Kuo et al. [6] presented empirical correlations for heat transfer and pressure drop and reported experimental results on HFC-410A condensation within a BPHE.The friction factor was shown to be substantially impacted by the mass flux and vapor quality, whereas the heat transfer coefficient was found to depend mainly on the heat flux and the mass flux.
Longo and Zilio [7] illustrated the heat transfer coefficient and pressure drop of HFC1234yf in condensation heat transfer and also compared the results with HFC134a under the same operating conditions.According to their findings, the heat transfer coefficient of HFO1234yf shows weak sensitivity to saturation temperature and strong sensitivity to the mass flux of the refrigerant.They also showed that the condensation heat transfer coefficients of superheated vapor are almost 8-11% higher than those of saturated vapor.Furthermore, HFO1234 exhibits a heat transfer coefficient almost 10-12% lower and a pressure drop about 10-20% lower than those of HFC134a under similar thermal conditions.
Longo et al. [8] investigated HFO1234ze(E) condensation inside a brazed plate heat exchanger at various mass fluxes and condensation temperatures.According to their studies, for low refrigerant mass fluxes (G < 20 kg/m 2 s), condensation is indeed caused by gravity, however, for higher refrigerant mass fluxes (G > 20 kg/m 2 s), forced convective condensation occurs.HFO1234ze(E), in comparison to HFC134a, displays lower (4-6%) heat transfer coefficients and a higher (10%) frictional pressure drop.
Table 1 summarizes some of the previous research work dedicated to condensation heat transfer (HT) and pressure drop (PD) in plate heat exchangers.
Many researchers have studied the heat transfer properties of various refrigerants in different types of plate heat exchangers, particularly for condensation and evaporation, over the years.The use of refrigerants with low global warming potential (GWP) has received more attention in recent years due to concerns about global warming [9].[5] HT and PD R22 65 39.5-44.4 23.5-40.915.8-27.8Kuo et al., 2005 [6] HT and PD R410A 60 20-31.5 50-150 5-20 The CF 3 I refrigerant is gaining interest for use in refrigeration and air conditioning applications due to its low GWP (<1), low ozone depletion potential (ODP = 0.019), and ability to suppress flammability [12].CF 3 I has good environmental, safety, and flammability characteristics, as well as good oil solubility and material compatibility.Therefore, it is also being considered as a promising alternative, especially as a component in mixtures [13], to replace high-GWP refrigerants.The molecule CF 3 I, or trifluoro iodomethane, has three fluorines, one iodine, and one carbon in a tetrahedral structure, as illustrated in Figure 1 [12].REFPROP 10.0 [14] and other literature [12,15] contain extensive detail on the thermophysical characteristics of CF 3 I.
2003 [2] HT R410A, R22 and 70 20-30 The CF3I refrigerant is gaining interest for use in refrigeration and air cond applications due to its low GWP (<1), low ozone depletion potential (ODP = 0.0 ability to suppress flammability [12].CF3I has good environmental, safety, and f bility characteristics, as well as good oil solubility and material compatibility.Th it is also being considered as a promising alternative, especially as a component tures [13], to replace high-GWP refrigerants.The molecule CF3I, or trifluoro iodom has three fluorines, one iodine, and one carbon in a tetrahedral structure, as illust Figure 1 [12].REFPROP 10.0 [14] and other literature [12,15] contain extensive d the thermophysical characteristics of CF3I.The characteristics and properties of CF3I are provided in Table 2.The characteristics and properties of CF 3 I are provided in Table 2.Much research on various refrigerants in plate heat exchangers has been carried out over the years, which can be found reported by Amalfi et al. [21,22], Eldeeb et al. [23], and Tao and Ferreira [24].However, CF 3 I is a working fluid whose heat transfer characteristics are still to be investigated.
Additionally, most of the literature discusses the overall heat transfer coefficient, and very few papers have discussed local heat transfer characteristics inside the brazed plate heat exchanger.To further understand the heat transfer characteristics from the information on local heat transfer, a specially designed test section was constructed for the present study to measure the local heat transfer coefficient obtained from local wall temperature and heat flux.
In this experimental work, the condensation local heat transfer coefficients of the refrigerant CF 3 I in a vertical brazed plate heat exchanger were measured and analyzed as a function of the mass flux, saturation temperature, vapor quality, and heat flux.In addition, the obtained data were compared with R1234yf experimental data from the same test facility.Along with the results that are described, the measurement methods and experimental procedures are also explained.This work investigated the heat transfer characteristics of CF 3 I with a newly developed prediction method.Although CF 3 I is not used as a pure refrigerant, the reported data and proposed correlation will contribute to the design of PHE with a refrigerant mixture such as R466A (39.5% CF 3 I, 49% R32, and 11.5% R125).

Experimental Apparatus and Procedures
The experimental setup comprised five different loops and a data acquisition system to investigate the condensation heat transfer of the refrigerant CF 3 I in a vertical brazed plate heat exchanger.It included a refrigerant loop, three water loops for the preheater, a test section and condenser, and a cold-water brine loop for the subcooler.The refrigerant CF 3 I was circulated through the refrigerant loop as shown in Figure 2.
To achieve the various test conditions of CF 3 I, such as imposed mass flux, saturation temperature and inlet vapor quality in the test section, it was necessary to regulate the flow and control temperature in the other loops.The desired vapor quality at the test section inlet was provided by the preheater circuit.The heating circuit provided the heating of the test section as well.To achieve the various test conditions of CF3I, such as imposed mass flux, saturation temperature and inlet vapor quality in the test section, it was necessary to regulate the flow and control temperature in the other loops.The desired vapor quality at the test section inlet was provided by the preheater circuit.The heating circuit provided the heating of the test section as well.

Refrigerant Flow Loop
A refrigerant pump, a refrigerant mass flow meter, a preheater, a test section "the plate heat exchanger", a condenser, a subcooler, three mixing chambers, and three sight glasses comprised the refrigerant loop.The refrigerant pump was a Shimpo pump powered by a DC motor that was controlled by a variable DC output motor controller.A rotating DC motor controlled the fluctuation of the liquid CF3I flow rate by changing the DC current.A mass flow meter (MASSMAX), positioned between the pump and preheater, with an accuracy of ±0.1%, was used to monitor the refrigerant flow rate.The preheater transferred heat from hot water to CF3I to evaporate the refrigerant to a specific vapor quality at the inlet of the test section.The saturated vapor then entered into the test section and the CF3I condensed there.The vapor-liquid two-phase refrigerant from the outlet of the test section was finally condensed in the condenser.Then the refrigerant was subcooled by controlling the flow rate of a low-temperature water brine mixture in the subcooler.The system pressure of the refrigerant loop could be controlled by adjusting the temperature in the condenser.The purpose of the filter was to remove any solid particles that may have been present in the loop.The refrigerant coming from the exit of the test section was maintained in a subcooled condition to prevent cavitation at the pump inlet.Three mixing chambers were installed before and after the test section, as well as before the preheater, to monitor the absolute pressure and temperature of the refrigerant.The state of the refrigerant flowing through the refrigerant loop of the experimental apparatus

Refrigerant Flow Loop
A refrigerant pump, a refrigerant mass flow meter, a preheater, a test section "the plate heat exchanger", a condenser, a subcooler, three mixing chambers, and three sight glasses comprised the refrigerant loop.The refrigerant pump was a Shimpo pump powered by a DC motor that was controlled by a variable DC output motor controller.A rotating DC motor controlled the fluctuation of the liquid CF 3 I flow rate by changing the DC current.A mass flow meter (MASSMAX), positioned between the pump and preheater, was used to monitor the refrigerant flow rate.The preheater transferred heat from hot water to CF 3 I to evaporate the refrigerant to a specific vapor quality at the inlet of the test section.The saturated vapor then entered into the test section and the CF 3 I condensed there.The vapor-liquid two-phase refrigerant from the outlet of the test section was finally condensed in the condenser.Then the refrigerant was subcooled by controlling the flow rate of a low-temperature water brine mixture in the subcooler.The system pressure of the refrigerant loop could be controlled by adjusting the temperature in the condenser.The purpose of the filter was to remove any solid particles that may have been present in the loop.The refrigerant coming from the exit of the test section was maintained in a subcooled condition to prevent cavitation at the pump inlet.Three mixing chambers were installed before and after the test section, as well as before the preheater, to monitor the absolute pressure and temperature of the refrigerant.The state of the refrigerant flowing through the refrigerant loop of the experimental apparatus could be observed through the sight glasses.The entire pressure drop across the refrigerant side of the vertical PHE was measured using a differential pressure transducer.K-type and T-type thermocouples were used after calibration to measure all the temperatures in the loop.

Test Section
The specially designed test section [25] used in this study, as shown in Figure 3, was constructed with 8 stainless steel plates (material SUS303) brazed to each other.Among these, two were processed chevron plates with a 60 • angle.could be observed through the sight glasses.The entire pressure drop across the refrigerant side of the vertical PHE was measured using a differential pressure transducer.K-type and T-type thermocouples were used after calibration to measure all the temperatures in the loop.

Test Section
The specially designed test section [25] used in this study, as shown in Figure 3, was constructed with 8 stainless steel plates (material SUS303) brazed to each other.Among these, two were processed chevron plates with a 60° angle.The flow of the refrigerant occurs in the channel created by the space between these two chevron plates.Two flat plates were set for heat transfer measurements next to the chevron-shaped plates.The other four plates were dedicated to forming two water flow channels.The red and blue regions, shown in Figure 4b, indicate, respectively, the refrigerant and cooling water channels.The flow of the refrigerant occurs in the channel created by the space between these two chevron plates.Two flat plates were set for heat transfer measurements next to the chevron-shaped plates.The other four plates were dedicated to forming two water flow channels.The red and blue regions, shown in Figure 4b, indicate, respectively, the refrigerant and cooling water channels.
Table 3 shows the geometrical characteristics of the test section.The dimensions of the plates were 186 mm, 84 mm, and 5 mm, respectively.The chevron plates had a corrugation pitch of 5.6 mm, a depth of 1.5 mm, and a chevron angle of 60 • .The length between the inlet and outlet port centers was 136 mm, with each connection port having a diameter of 18.5 mm.The two processed chevron plates forming the refrigerant channel had a height and width of 117.5 mm and 64 mm, respectively.Five straight grooves were machined at both outsides of the plate (dedicated to measuring heat flux) perpendicular to the flow direction.A stainless-steel tube with an outer diameter of 1.6 mm was inserted into each groove and brazed.Sheath K-type thermocouples with a diameter of 0.5 mm were inserted in the small tubes for the measurement of wall temperatures and heat fluxes.Table 3 shows the geometrical characteristics of the test section.The dimensions of the plates were 186 mm, 84 mm, and 5 mm, respectively.The chevron plates had a corrugation pitch of 5.6 mm, a depth of 1.5 mm, and a chevron angle of 60°.The length between the inlet and outlet port centers was 136 mm, with each connection port having a diameter of 18.5 mm.The two processed chevron plates forming the refrigerant channel had a height and width of 117.5 mm and 64 mm, respectively.Five straight grooves were machined at both outsides of the plate (dedicated to measuring heat flux) perpendicular to the flow direction.A stainless-steel tube with an outer diameter of 1.6 mm was inserted into each groove and brazed.Sheath K-type thermocouples with a diameter of 0.5 mm were inserted in the small tubes for the measurement of wall temperatures and heat fluxes.Table 3. Geometrical characteristics of the test section [27].

Parameters Value
Fluid Flow plate length (mm) 117 The locations of the temperature measurement points were set vertically at 14.75, 36.75, 58.75, 80.75, and 102.75 mm from the bottom port of the plate.The horizontal arrangements of the measurement points were 4, 12, 20, 28, 36, 44, 52, and 60 mm from the end face of the cross-section, shown in Figure 4a.The wall temperatures were measured at a total of 160 points during the experiment, with 4 sets of 5 points in the vertical direction and 8 points in the horizontal direction of the test section.The heat flux across the plate and the local heat transfer coefficients were calculated by the values of the set thermocouples on the surface of the plates in Figure 4b.

Water Loop for Preheater
The preheater was a brazed PHE.Hot water flowing through the outer passageways heated the liquid CF 3 I flowing through the inner passage in the preheater to achieve the desired conditions at the inlet of the test section.The test section, the preheater, and the connecting pipe between them were all thermally insulated.A 34 L hot water thermostatic bath with 6.0 kW heaters made up the hot water loop for the preheater.The hot water was then sent to the preheater using a water pump with an inverter at a certain water flow rate.A bypass water valve was also used to adjust the flow rate.

Water Loop for Test Section
A constant temperature water bath with a 3.6 kW heater was included in the water loop in the system to precisely control the water temperature intended for circulating cold water through the test section.Cold water was driven at a predetermined flow rate to the plate heat exchanger using a pump with an inverter.The water flow rate could also be adjusted using a different bypass valve.

Water Loop for Condenser
The condenser that had the role of adjusting the pressure of the entire experimental setup included a water loop as well.By changing the temperature of the refrigerant in the condenser, the pressure could be set to the experimental conditions.

Water Brine Loop for Subcooler
A water brine loop was designed for subcooling the CF 3 I refrigerant coming from the condenser.A pump drove the water brine to the subcooler at a predetermined flow rate.The flow rate of the water brine was also adjustable by using a bypass valve.

Data Acquisition
A Keithley 3700 system switch data logger was combined with a personal computer in the data acquisition unit.Temperature and voltage data were recorded using the data logger.The water flow meter and differential pressure transducer required a power supply as a driver to output an electric current.The Kickstart ® 2020 interface was used to link the data logger to the computer, allowing all measured data from the data logger to be transmitted to the computer and subsequently analyzed using a spreadsheet.

Experimental Procedure
In each experiment, the system pressure in the experimental setup was first maintained at a specified level by adjusting the temperature in the condenser.The temperature and flow rate of the hot water loop for the preheater was then adjusted to obtain the desired vapor quality of CF 3 I at the inlet of the test section.Finally, the heat transfer rate between the counter flow channels in the test section could be varied by changing the temperature and flow rate in the water loop for the test section.The temperature and pressure of the flow fluctuated with any change to the system variables.The time it took to attain a statistically stable state condition was between 20 and 100 min.The data acquisition unit was then started, and it scanned every data channel 10 times in 40 s.To determine the heat transfer coefficient, the mean values of the data for each channel were collected.To ensure that the corresponding heat transfer occurs, the water flow rate in the test section should be high enough to provide a turbulent flow on the water side.Furthermore, the flow velocity of water in the test section should be high enough to provide a turbulent flow on the water side, allowing the related heat transfer to balance the condensation heat transfer on the refrigerant side.

Data Reduction for Local Heat Transfer Coefficient
A data reduction analysis is needed for the current measurement to determine the local heat transfer rate between the refrigerant flow and the water flow in the test section.The local heat flux was measured using the thermocouples located in the test plates shown in Figure 5.
that the corresponding heat transfer occurs, the water flow rate in the test section should be high enough to provide a turbulent flow on the water side.Furthermore, the flow velocity of water in the test section should be high enough to provide a turbulent flow on the water side, allowing the related heat transfer to balance the condensation heat transfer on the refrigerant side.

Data Reduction for Local Heat Transfer Coefficient
A data reduction analysis is needed for the current measurement to determine the local heat transfer rate between the refrigerant flow and the water flow in the test section.The local heat flux was measured using the thermocouples located in the test plates shown in Figure 5.With the assumption that the local heat flux qx can be estimated from one-dimensional, steady-state heat conduction, qx can be expressed by Equation (1) as follows.

𝑞 = 𝜆 𝑇
where λ is the thermal conductivity of stainless steel (SUS303), l1 is the distance between each thermocouple on the water side and the refrigerant side, Twall,r and Twall,w are the measured temperatures of the wall surface on the refrigerant side and water side, respectively.The wall temperature of the working fluid side (Twall,x) is calculated by Equation ( 2): where l2 is the distance between the wall surface and the thermocouple.The local heat transfer coefficient αx is calculated by Equation (3): With the assumption that the local heat flux q x can be estimated from one-dimensional, steady-state heat conduction, q x can be expressed by Equation (1) as follows.
where λ is the thermal conductivity of stainless steel (SUS303), l 1 is the distance between each thermocouple on the water side and the refrigerant side, T wall,r and T wall,w are the measured temperatures of the wall surface on the refrigerant side and water side, respectively.The wall temperature of the working fluid side (T wall,x ) is calculated by Equation (2): where l 2 is the distance between the wall surface and the thermocouple.The local heat transfer coefficient α x is calculated by Equation (3): T sat is the saturation temperature of the working fluid side that is derived by using the saturation pressure at the inlet of the test section.Also, since a plate's inside has a pressure drop, it should be considered when determining the local saturation pressure and temperature along the flow.The horizontal average values for the front and back heat transfer coefficients, α h,F and α h,B , respectively, are determined as follows.
where α i is the local heat transfer coefficient measured at different horizontal positions from Equation (3) The average value of the heat transfer coefficient is calculated by Equation ( 5) The local specific enthalpy (h i ) on the test plate is derived using the following procedure.The subcooled working fluid first flowed into the inlet of the preheater.The specific enthalpy (h) at the preheater was then determined from the temperature and pressure of the fluid by using the REFPROP 10 [14] The amount of heat exchange in the preheater (Q w,pre ) is calculated by Equation ( 7): where .m w is the mass flow rate of water and h w,pre,in and h w,pre,in are the specific enthalpies of the preheater outlet and the inlet of the water, respectively.
The specific enthalpy at the inlet of the test section (h t,in ) was obtained from the amount of heat exchange (Q w,pre ) for the preheater, mass flow rate ( .m r ) of the refrigerant, and heat loss (Q loss ) from the outlet of the preheater to the inlet of the test section: The heat loss Q loss is calculated from the steady state heat conduction equation of the multilayer cylinder.Here, the increase in the stock of specific enthalpy between neighboring thermocouples is calculated using the heat flow Q i between two neighboring thermocouples and the mass flow rate ( .m), similar to the calculation shown in Equation (1).Here, Q i is obtained from the local heat flux q x and the heat transfer area A i .The local specific enthalpy is calculated as follows: The local vapor quality (x i ) is determined by specific enthalpy as follows: where h l and h v are the specific enthalpies of the saturated liquid and saturation vapor, respectively, which are calculated from REFPROP using the pressure obtained from the pressure transducer at the inlet of the test section.

Uncertainty Analysis
The experimental uncertainty (U) was determined using measurement error (B) and random error (R), as shown in Equation (11).[28] Uncertainty in temperature, pressure, and flow rate monitoring instruments is known as measurement error (B).On the contrary, the arithmetic mean of the data group determines one experimental point, and the random error (R) is computed based on the standard deviation of the data group (σ), as stated in Equation (12).
where X is the individual value of the data group and X is the average value.N is the number of data in each data group.The estimated uncertainty of the heat transfer coefficient is 7.48%.Table 4 provides an overview of the outcomes of the uncertainty analysis.

Results and Discussion
The heat transfer coefficients (both local and average) of the plate heat exchanger were determined for the condensation experiment with CF 3 I refrigerant.The condensation heat transfer experiments were carried out at mass fluxes of 20 kg/m 2 s and 50 kg/m 2 s, saturation temperatures of 25-30 • C, and heat fluxes of 10.4-13.7 kW/m 2 .The flow direction of the refrigerant was downward and the flow direction for the water side of the test section was counter to the refrigerant flow, i.e., the water was flowing upwards at both sides of the only refrigerant channel, as if sandwiched.The experimental conditions for the condensation heat transfer in the plate heat exchanger are shown in Table 5.The results for the heat transfer coefficients at the corresponding measurement points are described with respect to the horizontal distance for both the front sides and back sides of the plates.These plates formed the refrigerant flow channel in the test section.The measured results are provided to show how the local condensation heat transfer coefficient changes with the vapor quality in the test section for different flow and thermal conditions.The local heat flux and the local wall temperature distribution inside the test plates are also shown.The experimentally obtained average heat transfer coefficients of CF 3 I are compared with those of R1234yf in the same test facility and with available correlations from the literature.A newly proposed correlation is considered to predict all the experimental data reported in the work.CF3I are compared with those of R1234yf in the same test facility and with availab relations from the literature.A newly proposed correlation is considered to predic experimental data reported in the work.These data indicate that the local condensation heat transfer coefficient is gre the higher vapor qualities of x = 0.92 and 0.71.However, there were some signific ferences in the local heat transfer coefficients from the front and back side plates zontal distances of 28 mm and 36 mm and a vapor quality of 0.92.For a vapor qu 0.71, the heat transfer coefficient of the back side of the test section plate was high These data indicate that the local condensation heat transfer coefficient is greater for the higher vapor qualities of x = 0.92 and 0.71.However, there were some significant differences in the local heat transfer coefficients from the front and back side plates at horizontal distances of 28 mm and 36 mm and a vapor quality of 0.92.For a vapor quality of 0.71, the heat transfer coefficient of the back side of the test section plate was higher than that of the front side at horizontal distances from 36 mm to 54 mm.As shown in Figure 4a, the chevron direction is different on the front and back sides of the plate.On the front side plate, the chevron corrugations act to collect condensate to the center part of the plate.On the back side plate, the chevron corrugations act to diverge the condensate on the center part of the plate.Because a thinner condensate film gives a higher heat transfer coefficient, the back side plate tends to give a higher heat transfer coefficient.Of course, the condensate flows on the front and back side plates interact with each other, and the heat transfer coefficients show opposite values or similar values downstream.The values of the local heat transfer coefficient in the horizontal direction show similar trends in the condensation experiment, with minimum values at the edges and maximum values in the middle [29].
Figure 7 illustrates the horizontal average condensation heat transfer coefficient for a mass flux of 20 kg/m 2 s and a maximum heat flux of 12.8 kW/m 2 in relation to vapor quality at the front and back sides of the PHE.These heat transfer coefficients were obtained from the average heat transfer coefficient data at various positions in horizontal distances for the front and back side, respectively, at a certain vapor quality.
Fluids 2023, 8, x FOR PEER REVIEW 13 of 27 that of the front side at horizontal distances from 36 mm to 54 mm.As shown in Figure 4a, the chevron direction is different on the front and back sides of the plate.On the front side plate, the chevron corrugations act to collect condensate to the center part of the plate.
On the back side plate, the chevron corrugations act to diverge the condensate on the center part of the plate.Because a thinner condensate film gives a higher heat transfer coefficient, the back side plate tends to give a higher heat transfer coefficient.Of course, the condensate flows on the front and back side plates interact with each other, and the heat transfer coefficients show opposite values or similar values downstream.The values of the local heat transfer coefficient in the horizontal direction show similar trends in the condensation experiment, with minimum values at the edges and maximum values in the middle [29].Figure 7 illustrates the horizontal average condensation heat transfer coefficient for a mass flux of 20 kg/m 2 s and a maximum heat flux of 12.8 kW/m 2 in relation to vapor quality at the front and back sides of the PHE.These heat transfer coefficients were obtained from the average heat transfer coefficient data at various positions in horizontal distances for the front and back side, respectively, at a certain vapor quality.The results show that the heat transfer coefficient decreased with decreasing vapor quality because, in condensation experiments, lower vapor quality results in a thicker liquid film that reduces the heat transfer efficiency.The heat transfer coefficient of the back side of the PHE is slightly higher than that of the front side at higher vapor qualities.Specifically, a significant difference was observed in t h e vapor qualities of 0.71 and 0.92.The condensation heat transfer coefficient at the vapor quality of 0.92 is about 30% higher than that at 0.13 for the front side of PHE.Also, the condensation heat transfer coefficient at the vapor quality of 0.71 is about 40% higher than that at 0.35 for the back side of PHE.This difference between front heat transfer coefficient and back heat transfer coefficient is due to the effect of plate geometries of the test section, as explained in Figure 6.The results show that the heat transfer coefficient decreased with decreasing vapor quality because, in condensation experiments, lower vapor quality results in a thicker liquid film that reduces the heat transfer efficiency.The heat transfer coefficient of the back side of the PHE is slightly higher than that of the front side at higher vapor qualities.Specifically, a significant difference was observed in the vapor qualities of 0.71 and 0.92.The condensation heat transfer coefficient at the vapor quality of 0.92 is about 30% higher than that at 0.13 for the front side of PHE.Also, the condensation heat transfer coefficient at the vapor quality of 0.71 is about 40% higher than that at 0.35 for the back side of PHE.This difference between front heat transfer coefficient and back heat transfer coefficient is due to the effect of plate geometries of the test section, as explained in Figure 6.
Figure 8 indicates the variation of local heat flux with distance from the inlet to the outlet of the PHE, i.e., along the vertical cross-section of the PHE at a mass flux of 20 kg/m 2 s, a saturation temperature of 30 • C, and a horizontal position of 12 mm from the end face of the cross-section of the test plates.There is no significant difference in the local Fluids 2023, 8, 150 14 of 27 heat flux found for the front and back sides of the PHE except at the inlet (117.5 mm from the bottom port of the test section) where the back side heat flux is slightly higher than that of the front side.This also signifies that the heat transfer coefficients in the condensation inlet and the very next measurement point of the back side of the PHE (at vapor quality 0.92 and 0.71) are higher than those of the front side, which has already been discussed in Figures 6 and 7. Hence, it is observed that the heat flux follows a similar trend with the local heat transfer coefficient and vapor quality in a certain mass flux.The local heat flux varies from 10.4 kW/m 2 to a maximum of 12.8 kW/m 2 in the PHE for condensation heat transfer for the mass flux of 20 kg/m 2 s.
Figure 8 indicates the variation of local heat flux with distance from the inlet to the outlet of the PHE, i.e., along the vertical cross-section of the PHE at a mass flux of 20 kg/m 2 s, a saturation temperature of 30 °C, and a horizontal position of 12 mm from the end face of the cross-section of the test plates.There is no significant difference in the local heat flux found for the front and back sides of the PHE except at the inlet (117.5 mm from the bottom port of the test section) where the back side heat flux is slightly higher than that of the front side.This also signifies that the heat transfer coefficients in the condensation inlet and the very next measurement point of the back side of the PHE (at vapor quality 0.92 and 0.71) are higher than those of the front side, which has already been discussed in

Condensation at Mass Flux G = 50 kg/m 2 s
Figure 10 explains the variation of local heat transfer coefficients on the front and back sides of the plate for the CF3I condensation experiment at x = 0.97, 0.89, 0.49 and 0.37, respectively, for a mass flux of 50 kg/m 2 s, at an inlet saturation temperature of 30 °C, and a maximum heat flux of 13.7 kW/m 2 .These data indicate that the local condensation heat transfer coefficient increases with the vapor quality.There is also a significant difference in the local heat transfer coefficient on the front and back sides of the test section, at horizontal distances from 12 mm to 28 mm, and at a high vapor quality of 0.97.Also, at a vapor quality of 0.89 the heat transfer coefficient of the back side of the plate of the test section is higher than that of the front side at the horizontal distances of 44 mm to 52 mm.The front and back sides of the plate have distinct chevron directions, as shown in Figure 4a.The chevron corrugations on the front side plate act to direct condensate to the center part of the plate, whereas the chevron corrugations on the back side plate act to diverge the condensate on the center part of the plate.Because a thinner condensate film gives a higher heat transfer coefficient, the back side plate tends to give a higher heat transfer coefficient.The condensate flows on both the front and back side plates simply interact with one another, and the heat transfer coefficients in the downstream region exhibit opposing values or comparable values.An almost similar trend is observed as for a mass flux of 20 kg/m 2 s.C, and a maximum heat flux of 13.7 kW/m 2 .These data indicate that the local condensation heat transfer coefficient increases with the vapor quality.There is also a significant difference in the local heat transfer coefficient on the front and back sides of the test section, at horizontal distances from 12 mm to 28 mm, and at a high vapor quality of 0.97.Also, at a vapor quality of 0.89 the heat transfer coefficient of the back side of the plate of the test section is higher than that of the front side at the horizontal distances of 44 mm to 52 mm.The front and back sides of the plate have distinct chevron directions, as shown in Figure 4a.The chevron corrugations on the front side plate act to direct condensate to the center part of the plate, whereas the chevron corrugations on the back side plate act to diverge the condensate on the center part of the plate.Because a thinner condensate film gives a higher heat transfer coefficient, the back side plate tends to give a higher heat transfer coefficient.The condensate flows on both the front and back side plates simply interact with one another, and the heat transfer coefficients in the downstream region exhibit opposing values or comparable values.An almost similar trend is observed as for a mass flux of 20 kg/m 2 s. Figure 11 illustrates the horizontal average condensation heat transfer coefficient for a mass flux of 50 kg/m 2 s and a maximum heat flux of 13.5 kW/m 2 in relation to vapor quality on the front and back side of the PHE.These heat transfer coefficients are obtained from the average heat transfer coefficient data at various positions in horizontal distances for the front and back sides, respectively, at a certain vapor quality.The heat transfer coefficients for the back side of the plate do not have significant differences for lower vapor qualities.However, the heat transfer coefficients on the back side of the PHE is significantly higher at higher vapor qualities (x > 0.85) due to the plate geometric effect of the test section, as has already been discussed in Figure 10.Moreover, the refrigerant mass flux has little impact on the condensation heat transfer coefficient in the low vapor quality regime (x < 0.40).The condensation heat transfer coefficient affected by the mass flux is observed as the vapor quality exceeds 0.4.In addition, the heat transfer coefficient for the larger mass flux increases with vapor quality more quickly than it does for the lower mass flux.The condensation heat transfer coefficient at the vapor quality of 0.81 is about 1.8 times higher than that at 0.24 for the front side of the PHE and the condensation heat transfer coefficient at the vapor quality of 0.96 is about 1.9 times higher than that of 0.13 for the back side of the PHE.The findings in Figure 11 also show that, mainly due to the Figure 11 illustrates the horizontal average condensation heat transfer coefficient for a mass flux of 50 kg/m 2 s and a maximum heat flux of 13.5 kW/m 2 in relation to vapor quality on the front and back side of the PHE.These heat transfer coefficients are obtained from the average heat transfer coefficient data at various positions in horizontal distances for the front and back sides, respectively, at a certain vapor quality.The heat transfer coefficients for the back side of the plate do not have significant differences for lower vapor qualities.However, the heat transfer coefficients on the back side of the PHE is significantly higher at higher vapor qualities (x > 0.85) due to the plate geometric effect of the test section, as has already been discussed in Figure 10.Moreover, the refrigerant mass flux has little impact on the condensation heat transfer coefficient in the low vapor quality regime (x < 0.40).The condensation heat transfer coefficient affected by the mass flux is observed as the vapor quality exceeds 0.4.In addition, the heat transfer coefficient for the larger mass flux increases with vapor quality more quickly than it does for the lower mass flux.The condensation heat transfer coefficient at the vapor quality of 0.81 is about 1.8 times higher than that at 0.24 for the front side of the PHE and the condensation heat transfer coefficient at the vapor quality of 0.96 is about 1.9 times higher than that of 0.13 for the back side of the PHE.The findings in Figure 11 also show that, mainly due to the convective effect, an increase in the refrigerant mass flow always results in a large increase in the condensation heat transfer coefficient at a high vapor quality.A high convective effect is caused by a high vapor quality and high mass flux of the refrigerant, in a similar observation to Kuo et al. [6].The front and back sides of the plate heat exchanger do not have significant differences in local heat flux at the corresponding measurement point.The local heat flux on the back side is also high, as similarly observed for a mass flux of 20 kg/m 2 s.The local heat flux varies from 11.6 kW/m 2 to a maximum of 13.7 kW/m 2 in the PHE for condensation heat transfer at the mass flux of 50 kg/m 2 s.
Figure 13 shows the variation in the local wall temperature in relation to distance from the inlet to the outlet of the test section for a mass flux of G = 50 kg/m 2 s, saturation temperature of 30 • C, a maximum heat flux of 13.6 kW/m 2 , and at a horizontal position of 12 mm from the end face of the cross-section of the test plates.The measured local wall surface temperatures of the water side and the refrigerant side are plotted for both the front and back sides of the PHE.The wall surface temperatures were observed to decrease along the condensation path similar to the observation for the mass flux of 20 kg/m 2 s.The front and back sides of the plate heat exchanger do not have significant differences in local heat flux at the corresponding measurement point.The local heat flux on the back side is also high, as similarly observed for a mass flux of 20 kg/m 2 s.The local heat flux varies from 11.6 kW/m 2 to a maximum of 13.7 kW/m 2 in the PHE for condensation heat transfer at the mass flux of 50 kg/m 2 s.
Figure 13 shows the variation in the local wall temperature in relation to distance from the inlet to the outlet of the test section for a mass flux of G = 50 kg/m 2 s, saturation temperature of 30 °C, a maximum heat flux of 13.6 kW/m 2 , and at a horizontal position of 12 mm from the end face of the cross-section of the test plates.The measured local wall surface temperatures of the water side and the refrigerant side are plotted for both the front and back sides of the PHE.The wall surface temperatures were observed to decrease along the condensation path similar to the observation for the mass flux of 20 kg/m 2 s.The results of heat transfer coefficient for mass flux 50 kg/m 2 s was not possible to obtain in our specified test section in one time between vapor quality 1.0 to 0.0 because of high mass flow rate.The local heat flux distribution and local wall temperature distribution reported for 50 kg/m 2 s were measured for vapor quality 1.0 to 0.50.

Comparison of Heat Transfer with Another Refrigerant
Figure 14 shows the comparison of experimentally measured heat transfer coefficient for R1234yf and CF3I refrigerant for a mass flux of 20 kg/m 2 s in the same test facility.The condensation heat transfer experiments for CF3I and R1234yf were conducted at saturation temperatures of 25 °C and 30 °C respectively.These heat transfer coefficient data are the average of the front and back side heat transfer coefficients for both refrigerants.The heat transfer coefficient for CF3I is approximately identical to R1234yf with a low mass flux and low vapor quality (x < 0.45).Gravity-controlled condensation occurs under low mass flow and low vapor quality conditions, and the shear stress effect has little impact on the condensation heat transfer coefficient.However, the heat transfer coefficient for The results of heat transfer coefficient for mass flux 50 kg/m 2 s was not possible to obtain in our specified test section in one time between vapor quality 1.0 to 0.0 because of high mass flow rate.The local heat flux distribution and local wall temperature distribution reported for 50 kg/m 2 s were measured for vapor quality 1.0 to 0.50.

Comparison of Heat Transfer with Another Refrigerant
Figure 14 shows the comparison of experimentally measured heat transfer coefficient for R1234yf and CF 3 I refrigerant for a mass flux of 20 kg/m 2 s in the same test facility.The condensation heat transfer experiments for CF 3 I and R1234yf were conducted at saturation temperatures of 25 • C and 30 • C respectively.These heat transfer coefficient data are the average of the front and back side heat transfer coefficients for both refrigerants.The heat transfer coefficient for CF 3 I is approximately identical to R1234yf with a low mass flux and low vapor quality (x < 0.45).Gravity-controlled condensation occurs under low mass flow and low vapor quality conditions, and the shear stress effect has little impact on the condensation heat transfer coefficient.However, the heat transfer coefficient for R1234yf is significantly higher than CF 3 I in the high vapor quality region (x > 0.50).For instance, in the plate heat exchanger, the heat transfer coefficient for R1234yf was almost 1.5 times higher than that for CF 3 I at a vapor quality of 0.92.
higher on the plate surface, while the liquid film is relatively very thin.This, reduces the heat transfer resistance from the plate surface to the refrigerant an increase in the heat transfer coefficient of the plate heat exchanger.The coefficients for R1234yf are all larger than those for CF3I in all vapor quali high mass flux.For instance, at the vapor quality of 0.37, the heat transfer R1234yf is approximately 50% higher than that for CF3I.The heat transfer R1234yf is about 60% higher than that for CF3I in the plate heat exchanger at ity of 0.96.Given the thermophysical characteristics of R1234yf and CF3I quite significant.The liquid thermal conductivity of R1234yf and CF3I are 62.0 and 52.8 spectively, at a saturation temperature of 30 °C [14].Generally, greater l conductivity results in a greater heat transfer coefficient because the liquid ductivity affects the thermal resistance of the refrigerant.
The thermophysical properties of CF3I and R1234yf at 30 °C derived fr [14] are shown in Table 6. Figure 15 shows the comparison of experimentally measured heat transfer coefficients for R1234yf and CF 3 I refrigerants for a mass flux of 50 kg/m 2 s in the same test facility.The condensation heat transfer experiments for both CF 3 I and R1234yf were conducted at saturation temperature of 30 • C. The front and back side heat transfer coefficients for both refrigerants were averaged to provide these heat transfer coefficient statistics.The findings demonstrate that the condensation heat transfer coefficient gradually increases with vapor quality in PHE for a certain imposed mass flux and saturation temperature.This increase is rather significant.This can be simply understood from the fact that in the high vapor quality region, the vapor and liquid shear stresses are substantially higher on the plate surface, while the liquid film is relatively very thin.This, consequently, reduces the heat transfer resistance from the plate surface to the refrigerant and results in an increase in the heat transfer coefficient of the plate heat exchanger.The heat transfer coefficients for R1234yf are all larger than those for CF 3 I in all vapor quality regions in a high mass flux.For instance, at the vapor quality of 0.37, the heat transfer coefficient for R1234yf is approximately 50% higher than that for CF 3 I.The heat transfer coefficient for R1234yf is about 60% higher than that for CF 3 I in the plate heat exchanger at a vapor quality of 0.96.Given the thermophysical characteristics of R1234yf and CF 3 I, this result is quite significant.

Comparison with Heat Transfer Correlations
The experimental data obtained in the current work were compared with the previous correlations of Yan et al. [1], Longo et al. [5], Shon et al. [28], and Zhang et al. [30] and a newly developed correlation in the present study.The development of the new correlation is described later.The experimental conditions and refrigerants used for their correlations are shown in Table 7.The liquid thermal conductivity of R1234yf and CF 3 I are 62.0 and 52.8 mW/m•K, respectively, at a saturation temperature of 30 • C [14].Generally, greater liquid thermal conductivity results in a greater heat transfer coefficient because the liquid thermal conductivity affects the thermal resistance of the refrigerant.
The thermophysical properties of CF 3 I and R1234yf at 30 • C derived from REF-PROP [14] are shown in Table 6.

Comparison with Heat Transfer Correlations
The experimental data obtained in the current work were compared with the previous correlations of Yan et al. [1], Longo et al. [5], Shon et al. [28], and Zhang et al. [30] and a newly developed correlation in the present study.The development of the new correlation is described later.The experimental conditions and refrigerants used for their correlations are shown in Table 7.

Development of a New Heat Transfer Correlation
Based on the experimental results for CF3I, a correlation for the Nusselt number was developed.Additionally, by comparing the Nusselt number with the experimental results, the precision of the correlations is confirmed.Three nondimensional numbers are considered in the correlation for the prediction of the Nusselt number, and the empirical correlation is developed in a power form of those dimensionless parameters as shown in Equation ( 13) where  is the heat transfer coefficient, Dh is the hydraulic diameter of the test section, λl is the thermal conductivity of the refrigerant, C is the coefficient, and n1, n2, and n3 are the exponents for the Reynolds number Reeq, Prandtl number Prl, and Boiling number Bo, respectively.
The Reynold equivalent number defined in Equation ( 14) includes the equivalent mass flux expressed in Equation (15) in the concept of compensating the effect of vapor quality proposed by Akers et al. [32].
where Geq is the equivalent mass flux, µl is the liquid viscosity, and Dh is the hydraulic diameter of the test section.
where G is refrigerant mass flux, ρl and ρv are the liquid and vapor density, respectively,

Development of a New Heat Transfer Correlation
Based on the experimental results for CF 3 I, a correlation for the Nusselt number was developed.Additionally, by comparing the Nusselt number with the experimental results, the precision of the correlations is confirmed.Three nondimensional numbers are considered in the correlation for the prediction of the Nusselt number, and the empirical correlation is developed in a power form of those dimensionless parameters as shown in Equation ( 13) where α is the heat transfer coefficient, D h is the hydraulic diameter of the test section, λ l is the thermal conductivity of the refrigerant, C is the coefficient, and n 1 , n 2 , and n 3 are the exponents for the Reynolds number Re eq , Prandtl number Pr l , and Boiling number Bo, respectively.The Reynold equivalent number defined in Equation ( 14) includes the equivalent mass flux expressed in Equation (15) in the concept of compensating the effect of vapor quality proposed by Akers et al. [32].
where G eq is the equivalent mass flux, µ l is the liquid viscosity, and D h is the hydraulic diameter of the test section.
where G is refrigerant mass flux, ρ l and ρ v are the liquid and vapor density, respectively, and x is the vapor quality of the refrigerant.The Boiling number is added to the correlation to reflect the effect of heat flux in the heat transfer even in condensation heat transfer [28].
where q is heat flux, G is refrigerant mass flux, and i fg is the latent heat.The liquid Prandtl number is also defined by Equation ( 17) where C p,l is the specific heat capacity for the liquid phase and λ l is the liquid thermal conductivity.Keeping the exponents n 1 and n 2 of Re eq and Pr l , rounding off to two decimals (as proposed by Zhang et al. [30]), and only fitting the exponent n 3 of newly introduced Bo and coefficient C in a nonlinear curve fitting analysis, the following results are obtained (Table 8).The newly developed correlation equation is shown in Equation (18).Nu = 16.1Re 0.54 eq Pr 0.33 l Bo 0.37 (18) The average deviation and mean deviation are applied for the evaluation of the predicted correlation for condensation heat transfer in respect of the experimental data and are defined as follows.It is observed from the graphical representation of Figure 18 that all the data for CF 3 I and R1234yf are within ±30% with a mean deviation of 7.03% and an average deviation of −6.70% for the CF 3 I refrigerant and a mean deviation of 9.35% and an average deviation of −4.51% for the R1234yf refrigerant, respectively.The prediction formula shows an overall mean deviation of 8.48% and an average deviation of −5.33% for all the experimentally obtained data.The new correlations enable significantly better prediction accuracies for the experimental results in this study than existing correlations.

Conclusions
The local condensation heat transfer coefficient of a vertical brazed plate heat exchanger with the refrigerant CF3I was studied experimentally.The effect of mass fluxes, saturation temperature, and heat fluxes on the condensation heat transfer were analyzed using the results of the heat transfer coefficient, local heat flux distribution, and local wall temperature distribution under various thermal conditions.The experimental data obtained for CF3I were compared with R1234yf in the same test facility.Comparisons of the CF3I data with the available correlations in the literature were also carried out.The findings are summarized as follows.

•
The heat transfer coefficients were found to be independent of the low mass flux of 20 kg/m 2 s, possibly due to gravity-controlled condensation.For a high mass flux of 50 kg/m 2 s, the heat transfer coefficient is dependent on mass flux and forced convection condensation takes place.The increase in the heat transfer coefficient value is notable at a higher vapor quality on the same flux.

•
The local surface wall temperature distributions were observed to decrease downstream of the test section in the direction where condensation progresses.

•
The CF3I experimental data is comparable to R1234yf for a low mass flux (20 kg/m 2 s) and low vapor qualities.However, the heat transfer coefficient of CF3I is lower than that of R1234yf at a high mass flux (50 kg/m 2 s) and for all vapor qualities.

Conclusions
The local condensation heat transfer coefficient of a vertical brazed plate heat exchanger with the refrigerant CF 3 I was studied experimentally.The effect of mass fluxes, saturation temperature, and heat fluxes on the condensation heat transfer were analyzed using the results of the heat transfer coefficient, local heat flux distribution, and local wall temperature distribution under various thermal conditions.The experimental data obtained for CF 3 I were compared with R1234yf in the same test facility.Comparisons of the CF 3 I data with the available correlations in the literature were also carried out.The findings are summarized as follows.

•
The heat transfer coefficients were found to be independent of the low mass flux of 20 kg/m 2 s, possibly due to gravity-controlled condensation.For a high mass flux of 50 kg/m 2 s, the heat transfer coefficient is dependent on mass flux and forced convection condensation takes place.The increase in the heat transfer coefficient value is notable at a higher vapor quality on the same flux.

•
The local surface wall temperature distributions were observed to decrease downstream of the test section in the direction where condensation progresses.

•
The CF 3 I experimental data is comparable to R1234yf for a low mass flux (20 kg/m 2 s) in only low vapor qualities.However, the heat transfer coefficient of CF 3 I is lower than that of R1234yf for a high mass flux (50 kg/m 2 s) in all vapor qualities.

•
The data of CF 3 I and R1234yf obtained from the experimental thermal conditions show great agreement with the predicted correlation for heat transfer of all the data within ±30% with a mean deviation of 8.48% and an average deviation of −5.33%.

Figure 2 .
Figure 2. Schematic diagram of the refrigerant flow loop.

Figure 2 .
Figure 2. Schematic diagram of the refrigerant flow loop.

Figure 4 .
Figure 4. Detailed view of (a) thermocouple measurement points and (b) cross-section of the test plate.

Figure 4 .
Figure 4. Detailed view of (a) thermocouple measurement points and (b) cross-section of the test plate.
on the refrigerant side 1 Number of channels on the water side 2 Thermal conductivity of the plate (W/m•K) 16.7

Figure 5 .
Figure 5. Thermocouple position details in the test section.

Figure 5 .
Figure 5. Thermocouple position details in the test section.

Fluids 1 .Figure 6
Figure 6 explains the variation of the local heat transfer coefficient on the front and back sides of the plate for the condensation experiment with the CF 3 I refrigerant at x = 0.92, 0.71, 0.53, and 0.34, respectively, for the mass flux of 20 kg/m 2 s, an inlet saturation temperature of 25 • C and a maximum heat flux of 12.8 kW/m 2 .

4. 1 .Figure 6 Figure 6 .
Figure 6 explains the variation of the local heat transfer coefficient on the fro back sides of the plate for the condensation experiment with the CF3I refrigeran 0.92, 0.71, 0.53, and 0.34, respectively, for the mass flux of 20 kg/m 2 s, an inlet sat temperature of 25 °C and a maximum heat flux of 12.8 kW/m 2 .

Figure 6 .
Figure 6.Variation of local condensation heat transfer coefficients with horizontal distance of PHE for various vapor qualities (a) x = 0.92, (b) x = 0.71, (c) x = 0.53 and (d) x = 0.34 for mass flux G = 20 kg/m 2 s.

Figure 7 .
Figure 7. Horizontal average condensation heat transfer coefficients for mass flux G = 20 kg/m 2 s.

Figure 7 .
Figure 7. Horizontal average condensation heat transfer coefficients for mass flux G = 20 kg/m 2 s.
Figure8indicates the variation of local heat flux with distance from the inlet to the outlet of the PHE, i.e., along the vertical cross-section of the PHE at a mass flux of 20 kg/m 2 s, a saturation temperature of 30 °C, and a horizontal position of 12 mm from the end face of the cross-section of the test plates.There is no significant difference in the local heat flux found for the front and back sides of the PHE except at the inlet (117.5 mm from the bottom port of the test section) where the back side heat flux is slightly higher than that of the front side.This also signifies that the heat transfer coefficients in the condensation inlet and the very next measurement point of the back side of the PHE (at vapor quality 0.92 and 0.71) are higher than those of the front side, which has already been discussed in Figures 6 and 7. Hence, it is observed that the heat flux follows a similar trend with the local heat transfer coefficient and vapor quality in a certain mass flux.The local heat flux varies from 10.4 kW/m 2 to a maximum of 12.8 kW/m 2 in the PHE for condensation heat transfer for the mass flux of 20 kg/m 2 s.

Figure 8 .
Figure 8. Variation of local heat flux as a function of distance from the inlet of the test section for mass flux G = 20 kg/m 2 s.

Figure 9
Figure9shows the variation of the local wall temperature with the distance from the inlet to the outlet of the test section for a mass flux of G = 20 kg/m 2 s, saturation temperature of 25 °C, a maximum heat flux of 12.8 kW/m 2 , and at a horizontal position of 12 mm from the end face of the cross-section of the test plates.The measured local wall surface temperatures of the water side and the refrigerant side are plotted for both the front and back side of the PHE.The wall surface temperatures were observed to decrease gradually toward the distance downstream of the condensation process, similar to the observation of Mahmud et al.[27]

Figure 8 .
Figure 8. Variation of local heat flux as a function of distance from the inlet of the test section for mass flux G = 20 kg/m 2 s.

Figure 9 Figure 9 .
Figure9shows the variation of the local wall temperature with the distance from the inlet to the outlet of the test section for a mass flux of G = 20 kg/m 2 s, saturation temperature of 25 • C, a maximum heat flux of 12.8 kW/m 2 , and at a horizontal position of 12 mm from the end face of the cross-section of the test plates.The measured local wall surface temperatures of the water side and the refrigerant side are plotted for both the front and back side of the PHE.The wall surface temperatures were observed to decrease gradually toward the distance downstream of the condensation process, similar to the observation of Mahmud et al.[27]

Figure 9 .
Figure 9. Variation of the local wall temperature as a function of distance from the inlet of the test section for a mass flux of G = 20 kg/m 2 s.

4. 2 .
Figure10explains the variation of local heat transfer coefficients on the front and back sides of the plate for the CF 3 I condensation experiment at x = 0.97, 0.89, 0.49 and 0.43, respectively, for a mass flux of 50 kg/m 2 s, at an inlet saturation temperature of 30 • C, and a maximum heat flux of 13.7 kW/m 2 .These data indicate that the local condensation heat transfer coefficient increases with the vapor quality.There is also a significant difference in the local heat transfer coefficient on the front and back sides of the test section, at horizontal distances from 12 mm to 28 mm, and at a high vapor quality of 0.97.Also, at a vapor quality of 0.89 the heat transfer coefficient of the back side of the plate of the test section is higher than that of the front side at the horizontal distances of 44 mm to 52 mm.The front and back sides of the plate have distinct chevron directions, as shown in Figure4a.The chevron corrugations on the front side plate act to direct condensate to the center part of the plate, whereas the chevron corrugations on the back side plate act to diverge the condensate on the center part of the plate.Because a thinner condensate film gives a higher heat transfer coefficient, the back side plate tends to give a higher heat transfer coefficient.The condensate flows on both the front and back side plates simply interact with one another, and the heat transfer coefficients in the downstream region exhibit opposing values or comparable values.An almost similar trend is observed as for a mass flux of 20 kg/m 2 s.

Figure 10 .
Figure 10.Variation of local condensation heat transfer coefficients with horizontal distances of PHE for various vapor qualities (a) x = 0.97, (b) x = 0.89, (c) x = 0.49 and (d) x = 0.37 for mass flux G = 50 kg/m 2 s.

Figure 10 .
Figure 10.Variation of local condensation heat transfer coefficients with horizontal distances of PHE for various vapor qualities (a) x = 0.97, (b) x = 0.89, (c) x = 0.49 and (d) x = 0.43 for mass flux G = 50 kg/m 2 s.

Fluids 2023, 8 ,
x FOR PEER REVIEW 17 of 27 in the condensation heat transfer coefficient at a high vapor quality.A high convective effect is caused by a high vapor quality and high mass flux of the refrigerant, in a similar observation to Kuo et al[6].

Figure 11 .
Figure 11.Horizontal average condensation heat transfer coefficients for mass flux G = 50 kg/m 2 s.

Figure 12
Figure 12 indicates the variation of local heat flux with distances from the inlet to the outlet of the PHE, i.e., along the vertical cross-section of the PHE for a mass flux of 50 kg/m 2 s, a saturation temperature 30 °C, and at a horizontal distance of 12 mm from the end face of the cross-section of the test plates.

Figure 12 .
Figure 12.Variation of local heat flux as a function of distance from the inlet of the test section for mass flux G = 50 kg/m 2 s.

Figure 11 .
Figure 11.Horizontal average condensation heat transfer coefficients for mass flux G = 50 kg/m 2 s.

Figure 12
Figure 12 indicates the variation of local heat flux with distances from the inlet to the outlet of the PHE, i.e., along the vertical cross-section of the PHE for a mass flux of 50 kg/m 2 s, a saturation temperature 30 • C, and at a horizontal distance of 12 mm from the end face of the cross-section of the test plates.

Fluids 2023, 8 ,
x FOR PEER REVIEW 17 of 27 in the condensation heat transfer coefficient at a high vapor quality.A high convective effect is caused by a high vapor quality and high mass flux of the refrigerant, in a similar observation to Kuo et al[6].

Figure 11 .
Figure 11.Horizontal average condensation heat transfer coefficients for mass flux G = 50 kg/m 2 s.

Figure 12
Figure 12 indicates the variation of local heat flux with distances from the inlet to the outlet of the PHE, i.e., along the vertical cross-section of the PHE for a mass flux of 50 kg/m 2 s, a saturation temperature 30 °C, and at a horizontal distance of 12 mm from the end face of the cross-section of the test plates.

Figure 12 .
Figure 12.Variation of local heat flux as a function of distance from the inlet of the test section for mass flux G = 50 kg/m 2 s.

Figure 12 .
Figure 12.Variation of local heat flux as a function of distance from the inlet of the test section for mass flux G = 50 kg/m 2 s.

Figure 13 .
Figure 13.Variation of local wall temperature as a function of distance from the inlet of the test section for mass flux G = 50 kg/m 2 s.

Figure 13 .
Figure 13.Variation of local wall temperature as a function of distance from the inlet of the test section for mass flux G = 50 kg/m 2 s.

Figure 14 .
Figure 14.Comparison of average heat transfer coefficients of CF3I and R1234yf fo 20 kg/m 2 s.

Figure 14 .
Figure 14.Comparison of average heat transfer coefficients of CF 3 I and R1234yf for mass flux G = 20 kg/m 2 s.

FluidsFigure 15 .
Figure 15.Comparison of average heat transfer coefficients of CF3I and R1234yf for mass flux G = 50 kg/m 2 s.

Figure 15 .
Figure 15.Comparison of average heat transfer coefficients of CF 3 I and R1234yf for mass flux G = 50 kg/m 2 s.

Figure 16 Figure 16
Figure 16 presents a comparison of the experimental data with available correlations in the open literature and a proposed correlation for the mass flux of 20 kg/m 2 s.It is observed that all the correlations underestimate the experimental heat transfer coefficient data for CF 3 I condensation in the plate heat exchanger at all the vapor qualities.The prediction of Shon et al. [28] is closer to the present data compared to the other correlations of Yan et al. [1], Longo et al. [31], and Zhang et al. [30].The newly developed correlation shows good agreement with the experimental data.

Figure 17
Figure 16 presents a comparison of the experimental data with available correl in the open literature and a proposed correlation for the mass flux of 20 kg/m 2 s.It served that all the correlations underestimate the experimental heat transfer coeff data for CF3I condensation in the plate heat exchanger at all the vapor qualities.Th diction of Shon et al[28] is closer to the present data compared to the other correl of Yan et al[1], Longo et al.[31], and Zhang et al.[30].The newly developed corre shows good agreement with the experimental data.Figure17presents a comparison of the experimental data with available correl in the open literature and a proposed correlation for the mass flux of 50 kg/m 2 s.The is almost similar to that observed for the mass flux of 20 kg/m 2 s, except for Shon 2018 for the vapor quality x = 0.54.The predictions of Shon et al. [24] are closer present data compared to the other correlations of Yan et al. [1], Longo et al. [31 Zhang et al.[30]

Figure 16 .
Figure 16.Comparison of experimental data with correlations in the literature and the pro correlation for a mass flux of 20 kg/m 2 s.

Figure 16 .
Figure 16.Comparison of experimental data with correlations in the literature and the proposed correlation for a mass flux of 20 kg/m 2 s.

Figure 17 27 Figure 17 .
Figure 17 presents a comparison of the experimental data with available correlations in the open literature and a proposed correlation for the mass flux of 50 kg/m 2 s.The trend is almost similar to that observed for the mass flux of 20 kg/m 2 s, except for Shon et al., 2018 for the vapor quality x = 0.54.The predictions of Shon et al. [24] are closer to the present data compared to the other correlations of Yan et al. [1], Longo et al. [31], and Zhang et al. [30] Fluids 2023, 8, x FOR PEER REVIEW 22 of 27

Figure 17 .
Figure 17.Comparison of experimental data with correlations in the literature and the proposed correlation for a mass flux of 50 kg/m 2 s.

Figure 18 .
Figure 18.Comparison of the developed correlation with the experimental data for the condensation heat transfer coefficient.

Figure 18 .
Figure 18.Comparison of the developed correlation with the experimental data for the condensation heat transfer coefficient.

Table 1 .
History of condensation heat transfer and pressure drop research on PHE.

Table 2 .
Characteristics of CF 3 I.

Table 4 .
Summary of the uncertainty analysis in the present study.

Table 5 .
Experimental conditions for the condensation heat transfer experiments.

Table 7 .
Literature of HT correlations.

Table 6 .
Thermophysical properties of CF 3 I and R1234yf at 30 • C.

Table 7 .
Literature of HT correlations.

Table 8 .
Coefficient and exponents of the correlation for the Nusselt number.