A Feasibility Study on the Use of an Atmospheric Water Generator (AWG) for the Harvesting of Fresh Water in a Semi-Arid Region A ﬀ ected by Mining Pollution

: Worldwide, the shortage of fresh water has increased exponentially due to population growth and contamination of available water, especially in water tables that provide water for general consumption. One of the main pollutants of water is arsenic (As), present in the environment and in most mining / metallurgical processes, which is a major health risk, especially as a carcinogen. In the region of Matehuala, San Luis Potosi (SLP), Mexico, a highly productive mining area, arsenic concentrations of 138.1 mg / kg have been found in soils—6.2 times higher than what is allowed in domestic soils, while in water it is reported up to 158 mg / L, exceeding permissible limits for human consumption. In addition to As pollution, the region su ﬀ ers from water shortage both in the city and in rural communities. Therefore, it is necessary to explore new technologies to provide the population with fresh water. This paper presents a feasibility study on the use of an atmospheric water generator (AWG) to capture fresh water in the region of Matehuala, SLP. The region was found to have the necessary environmental conditions to use AWGs, with an annual average relative humidity (RH) of approximately 60%. Using a mathematical model of a dehumidiﬁer, water harvesting can be evaluated under the region’s prevailing climatic conditions. The month with lowest harvest was found to be January, with 0.89 to 3.6 L / day, while the month with largest harvest was August at 3.9 to 18 L / day and water production costs of 0.0093 and $ 0.038 USD / L, respectively. The study concludes that the use of AWGs would help alleviate water shortages, thus beneﬁting marginalized people or communities, preserving ecosystems and the environment.


Introduction
The lack of water suitable for human activities is a matter of global priority, since water is an element of survival for living beings. Despite the vast amount of water on the planet, most of it (97.5%) is in seas with high salt content, rendering it unsuitable for human consumption, while the rest is found as fresh water (2.5%). Of this fresh water, 70% is frozen and about 30% exists in the form of moisture or in drilling deep wells, of which 30% failed. Therefore, it is necessary to look for alternatives to supply freshwater without affecting the environment and with adequate conditions for human consumption or use in other activities. At a global level, various strategies have been presented to reduce water scarcity, specifically in the improvement of hydraulic distribution systems (storage, distribution, and irrigation systems), rainwater harvesting, seawater desalination technologies, water management, and atmospheric water harvesting [21][22][23][24][25][26][27][28][29]. From the latter, fog and dew are major sources of water for arid regions [30]. Dew is formed through two main steps: (1) Nucleation of a liquid phase forming a droplet on an obstacle, and (2) growth of the droplet at the expense of the surrounding atmosphere [31,32]. Based on the foregoing, various technologies have been developed for water harvesting, such as (i) salts or desiccants (liquids, solids and compounds) operating on various energy sources [33][34][35][36], (ii) smart materials such as bioinspired materials, nanostructured materials, gels and hydrogels [21,37,38], (iii) radiative cooling (Radiator-Condensers) by emitting thermal infrared radiation to the cold universe through the atmospheric window [39,40] and (iv) direct cooling by commonly using conventional vapour compression (VC) refrigeration systems or other cooling technology [2,41,42]. This last method consists of cooling the air humidity mixture to a temperature below dew point, causing moisture condensation and water harvesting, which depend on atmospheric air, a huge and renewable water deposit. There are approximately 3100 cubic miles of water in the atmosphere, 98% of which are in the form of vapour, and 2% in the form of clouds. It is known that about 280 cubic miles of water evaporate or transpire daily into the atmosphere, and the amount of water in atmospheric air is about 14,000 km 3 compared to only about 1200 km 3 of fresh water on earth [41]. Devices that harvest water from the atmosphere are called atmospheric water generators (AWGs) and can be used successfully both in arid areas with low moisture content and in humid areas with high moisture content [22,42,43]. In this work, we present a feasibility study on the use of atmospheric water generators (AWGs) for harvesting atmospheric air water in the region of Matehuala, SLP. This area has high levels of As contamination from mining and metallurgical activities. The first stage of the work was to carry out a climatological study of the region to determine the environmental conditions and the possibilities of the use of renewable energies in AWGs; in the second stage, a basic dehumidifier model was developed to evaluate water capture in the region; finally, a feasibility analysis was conducted.

Methodology
The initial stage consisted of an analysis of the behaviour and predominant magnitudes of climatological variables such as temperature, humidity and radiation in the Matehuala region of SLP, Mexico. With this, a zone of opportunity can be established for the design and/or evaluation of atmospheric water generators (AWGs) within a psychrometric chart. In addition, a simple mathematical model was developed to analyse the energy process of a water dehumidifier that will be used as an AWG to obtain water from the environment under the predominant conditions of the study region.

Study Area and Climatological Analysis
Variables such as temperature, humidity, radiation and wind impact AWG use by controlling their capacity to capture water and the power source for operation. In this work, the climatological study is relevant for detecting the high, low and average temperature, humidity and radiation values in the study region in order to analyse the feasibility of using AWGs. The study was conducted in the municipality of Matehuala, San Luis Potosí, Mexico (Figure 1), which is located between 23 • 38'49" North and 100 • 38'37" West, with a land area of 1165.87 km 2 , 223 towns and approximately 99,015 inhabitants. Matehuala is at an average height of 1570 m above sea level, with calci-gypsiferous, clayey soil poor in organic matter (0.2%). The city's main economic activities are mining and commerce. Climatological data were obtained from the meteorological station of the National Water Commission (CONAGUA), records were used from the network of automatic weather stations (EMAs) managed by the General Coordination of National Weather Service (CGSMN) with satellite transmission. These Figure 2a shows temperature behaviour throughout the year, with an average high temperature of 22.88 °C in June and an average low temperature of 13.14 °C in January. Based on the results, the high temperature is most frequently registered after noon, while the low temperature occurs mostly in the early morning hours. Humidity behaves differently to temperature, decreasing from January to April and increasing until September. The minimum average humidity is 48.49% and the maximum average is 70.29% (Figure 2b). Figure 2c shows no significant relationship between temperature and relative humidity since, as mentioned above, the maximum amount of water vapour that air can contain depends on the temperature, though the amount of water is not guaranteed to be the same for each temperature point. Here it is observed that humidity does not follow the temperature pattern nor vice versa, since each is independent of the other.  Figure 2a shows temperature behaviour throughout the year, with an average high temperature of 22.88 • C in June and an average low temperature of 13.14 • C in January. Based on the results, the high temperature is most frequently registered after noon, while the low temperature occurs mostly in the early morning hours. Humidity behaves differently to temperature, decreasing from January to April and increasing until September. The minimum average humidity is 48.49% and the maximum average is 70.29% (Figure 2b). Figure 2c shows no significant relationship between temperature and relative humidity since, as mentioned above, the maximum amount of water vapour that air can contain depends on the temperature, though the amount of water is not guaranteed to be the same for each temperature point. Here it is observed that humidity does not follow the temperature pattern nor vice versa, since each is independent of the other. Figure 2a shows temperature behaviour throughout the year, with an average high temperature of 22.88 °C in June and an average low temperature of 13.14 °C in January. Based on the results, the high temperature is most frequently registered after noon, while the low temperature occurs mostly in the early morning hours. Humidity behaves differently to temperature, decreasing from January to April and increasing until September. The minimum average humidity is 48.49% and the maximum average is 70.29% (Figure 2b). Figure 2c shows no significant relationship between temperature and relative humidity since, as mentioned above, the maximum amount of water vapour that air can contain depends on the temperature, though the amount of water is not guaranteed to be the same for each temperature point. Here it is observed that humidity does not follow the temperature pattern nor vice versa, since each is independent of the other.  Temperature analysis corresponded with the area's type of climate whose temperature range is not extreme despite being located in a desert region. Moisture analysis results reveal that, despite being a desert area, the region has the potential and necessary resources for water extraction from the environment, using air humidity with a minimum average of 48.49% humidity as a source, sufficient for the operation of an AWG [42].

Radiation and Wind Analysis
The study showed that radiation and energy captured per square meter in the study region was considerable, with a maximum radiation value of 729.24 W/m 2 and a minimum value of 407.81 W/m 2 per day. The low general radiation mean was 150.04 W/m 2 and the high mean was 287.24 W/m 2 ( Figure 3). Temperature analysis corresponded with the area's type of climate whose temperature range is not extreme despite being located in a desert region. Moisture analysis results reveal that, despite being a desert area, the region has the potential and necessary resources for water extraction from the environment, using air humidity with a minimum average of 48.49% humidity as a source, sufficient for the operation of an AWG [43].

Radiation and Wind Analysis
The study showed that radiation and energy captured per square meter in the study region was considerable, with a maximum radiation value of 729.24 W/m 2 and a minimum value of 407.81 W/m 2 per day. The low general radiation mean was 150.04 W/m 2 and the high mean was 287.24 W/m 2 ( Figure 3). Likewise, peak sun hours (PSH) for each month of the year were evaluated as shown below: August shows 7.29 peak hours and January the lowest number of hours, at 4.08. There is a great potential of solar radiation energy that can be exploited as a possible source of energy for AWGs. Likewise, peak sun hours (PSH) for each month of the year were evaluated as shown below: August shows 7.29 peak hours and January the lowest number of hours, at 4.08. There is a great potential of solar radiation energy that can be exploited as a possible source of energy for AWGs. With regard to wind energy, Figure 4 shows the variation of wind speed in the region throughout an average day for each month from 2010 to 2017. Temperature analysis corresponded with the area's type of climate whose temperature range is not extreme despite being located in a desert region. Moisture analysis results reveal that, despite being a desert area, the region has the potential and necessary resources for water extraction from the environment, using air humidity with a minimum average of 48.49% humidity as a source, sufficient for the operation of an AWG [43].

Radiation and Wind Analysis
The study showed that radiation and energy captured per square meter in the study region was considerable, with a maximum radiation value of 729.24 W/m 2 and a minimum value of 407.81 W/m 2 per day. The low general radiation mean was 150.04 W/m 2 and the high mean was 287.24 W/m 2 ( Figure 3). Likewise, peak sun hours (PSH) for each month of the year were evaluated as shown below: August shows 7.29 peak hours and January the lowest number of hours, at 4.08. There is a great potential of solar radiation energy that can be exploited as a possible source of energy for AWGs. The results show top wind speeds of 6 m/s for a Beaufort scale classification of "Strong Breeze". A minimum wind speed of 0 m/s, classified as "Calm", is also observed ( Figure 5). In the early hours of the morning, winds range from 2.8 to 6.1 m/s, a "Gentle and Moderate Breeze" that fluctuates during the early hours of the morning. The wind speed tends to decrease, reaching soft winds, light winds and calm winds in an average of approximately 3 h, after which time, the wind increases and its speed in the last remaining hours reaches a high of 6 m/s. With regard to wind energy, Figure 4 shows the variation of wind speed in the region throughout an average day for each month from 2010 to 2017. The results show top wind speeds of 6 m/s for a Beaufort scale classification of "Strong Breeze". A minimum wind speed of 0 m/s, classified as "Calm", is also observed ( Figure 5). In the early hours of the morning, winds range from 2.8 to 6.1 m/s, a "Gentle and Moderate Breeze" that fluctuates during the early hours of the morning. The wind speed tends to decrease, reaching soft winds, light winds and calm winds in an average of approximately 3 h, after which time, the wind increases and its speed in the last remaining hours reaches a high of 6 m/s. Results showed that the highest wind speeds occur at night in spring and the end of summer with average speed ranging from 2.15 to 6.2 m/s. In addition, average speeds prevailing throughout the year were 2.15 to 4.2 m/s. These results suggest that the study area may be suitable for the generation of electrical or mechanical energy on a small scale, with several small turbines connected together to generate enough electric power.
Weather conditions for the city of Matehuala, SLP, are favourable for AWG use because its RH makes it a good source of water extraction. At the same time its high levels of solar radiation and wind can be used as an energy source for AWGs.

Psychrometric Chart Characterisation in the Region
The characterisation of the psychrometric zone of the study region was of great interest for this work since it provided information on the thermodynamic properties of humid air. The data of the variables of interest obtained in the statistical study were used to feed a simple model of a dehumidifier used as an AWG. With the dehumidifier model, the energy required to condense a specific amount of moisture contained in the atmospheric air could be estimated. In order to characterise the psychrometric zone of the study region, two input data were required-temperature, and high and low air humidity-which were located on the psychrometric chart to create the region's psychrometric zone. The values used were: low of 13.14 °C and 48.49%, high of 22.8 °C and 70.29%. The psychrometric zone can be seen in Figure 6 below. Results showed that the highest wind speeds occur at night in spring and the end of summer with average speed ranging from 2.15 to 6.2 m/s. In addition, average speeds prevailing throughout the year were 2.15 to 4.2 m/s. These results suggest that the study area may be suitable for the generation of electrical or mechanical energy on a small scale, with several small turbines connected together to generate enough electric power.
Weather conditions for the city of Matehuala, SLP, are favourable for AWG use because its RH makes it a good source of water extraction. At the same time its high levels of solar radiation and wind can be used as an energy source for AWGs.

Psychrometric Chart Characterisation in the Region
The characterisation of the psychrometric zone of the study region was of great interest for this work since it provided information on the thermodynamic properties of humid air. The data of the variables of interest obtained in the statistical study were used to feed a simple model of a dehumidifier used as an AWG. With the dehumidifier model, the energy required to condense a specific amount of moisture contained in the atmospheric air could be estimated. In order to characterise the psychrometric zone of the study region, two input data were required-temperature, and high and low air humidity-which were located on the psychrometric chart to create the region's psychrometric zone. The values used were: low of 13.14 • C and 48.49%, high of 22.8 • C and 70.29%. The psychrometric zone can be seen in Figure 6 below. According to the above figure, the region's psychrometric zone is favourable in terms of humidity and temperature since water vapour must be brought to dew point to extract air moisture. Proximity to the saturation curve can also be observed, indicating that there is not much road to be travelled to condense air humidity. This distance on the psychrometric chart is the amount of energy that has to be extracted from water vapour to be condensed.

Mathematical Model of the Dehumidifier Used as AWG
Moist air is a non-reactive mixture of dry air and water vapour. The mass ratio of water vapour and dry air is better known as specific humidity, varying depending on the area's features. In a given thermodynamic state, each of the components has certain properties that help determine the amount of energy required to condense water vapour. For a given system, during any continuous process in which there are interactions between dry air and water vapour, whether a humidifier, a dehumidifier or a dryer, humid air is supplied, and water can be extracted or added to that air and transfer heat, Q, from or to the system, for various purposes. The masses of water vapour ( ) and dry air ( ) are extensive properties that contributed to the mixture's total mass ( ), which are related as follows: (1) For the atmospheric water generator system, this mixture is the entry point, since energy calculations are made from it. For the process, the AWG system was considered an interaction process between dry air and water vapour represented by the physical model of  According to the above figure, the region's psychrometric zone is favourable in terms of humidity and temperature since water vapour must be brought to dew point to extract air moisture. Proximity to the saturation curve can also be observed, indicating that there is not much road to be travelled to condense air humidity. This distance on the psychrometric chart is the amount of energy that has to be extracted from water vapour to be condensed.

Mathematical Model of the Dehumidifier Used as AWG
Moist air is a non-reactive mixture of dry air and water vapour. The mass ratio of water vapour and dry air is better known as specific humidity, varying depending on the area's features. In a given thermodynamic state, each of the components has certain properties that help determine the amount of energy required to condense water vapour. For a given system, during any continuous process in which there are interactions between dry air and water vapour, whether a humidifier, a dehumidifier or a dryer, humid air is supplied, and water can be extracted or added to that air and transfer heat, Q, from or to the system, for various purposes. The masses of water vapour (m v ) and dry air (m a ) are extensive properties that contributed to the mixture's total mass (m t ), which are related as follows: For the atmospheric water generator system, this mixture is the entry point, since energy calculations are made from it. For the process, the AWG system was considered an interaction process between dry air and water vapour represented by the physical model of Figure 7. extensive properties that contributed to the mixture's total mass ( ), which are related as follows: (1) For the atmospheric water generator system, this mixture is the entry point, since energy calculations are made from it. For the process, the AWG system was considered an interaction process between dry air and water vapour represented by the physical model of   During the dehumidification process, mass and energy exchanges took place. Energy exchanges were estimated by considering the properties of the mixture under the system's inlet and outlet conditions. Inlet properties were determined by the system surroundings, while the outlet parameters were determined by the properties required for condensation and were proposed according to the percentage of water vapour reduction by condensation; in this case 25%, 50% and 75% reduction of water vapour. These percentages were selected so as not to affect the area's environmental surroundings or the ecosystems present in the region.
The following assumptions were made for the development of the model: • The dry air entering the system changes only temperature in the process.

•
Inlet specific humidity is necessarily greater than outlet specific humidity.

•
Condensed water is in the sub-cooled state.

•
Inlet and outlet enthalpy of water vapour depends on the amount of moisture contained in the water vapour.

Thermodynamic Analysis
In order to balance mass and energy, the mixture properties must be known. In the climatological study carried out in this work, the psychrometric zone of the region was built. This zone has all the possible meteorological cases that can occur; therefore, this psychrometric zone was used to collect the data to be used in the model.
For the AWG process, the amount of moist air mass at the inlet is the mixture of dry air and water vapour that undergoes a condensation process until it leaves the system. Ideally, one would expect the water vapour in the incoming mixture to be completely condensed, but the reality is that it does not completely condense. The incoming dry air only undergoes a temperature change, being the means of transport for water vapour, and can be neglected. According to the conservation of mass, for the stationary process of condensation, component masses are related as follows: Specific humidity, ω, is the ratio water vapour and dry air masses.
Specific humidity at input and output will then be: Using Equations (5) and (6) in Equation (3): Equation (7) is the mass balance in terms of specific humidity. The specific enthalpy depends on the properties of the material, such as the temperature of the mixture at the input and output. The energy balance for the stationary system, disregarding kinetic and potential energy changes between input and output, and there being no work done on or from the system, is ( where . Q = Heat transfer ratio to or from the system, in J/s h a1 = Dry air inlet enthalpy, in J/kg h a2 = Dry air outlet enthalpy, in J/kg. h v1 = Water vapor inlet enthalpy, in J/kg. h v2 = Water vapor outlet enthalpy, in J/kg h 3l = Condensed water enthalpy, in J/kg Dividing by the mass of dry air, the above equation, in terms of specific humidity, gives: Using Equation (7) in Equation (9) gives: Then, heat transfer for each unit of mass of dry air from the system to the surroundings gives: With the above equation, heat transfer from the system to the surroundings that must be extracted for each unit of mass of dry air entering the system was determined. The heat transfer method used could be geothermal energy, solar energy, thermal energy from the sea, biomass energy, hybrid energy systems or by means of a refrigeration cycle, the latter being used for the case study presented herein [42,[44][45][46][47][48][49][50][51]].

Case Study
As mentioned above, there are several ways to transfer energy (Q) to and from the AWG. For this study, a conventional vapour compression (VC) refrigeration system was proposed to extract the steam energy that enters the dehumidification process. Three packages of different cooling capacities were proposed: 1 ton of refrigeration, 1 2 ton of refrigeration and 1 4 ton of refrigeration in order to detect the capacities of humidity condensation and the amount of water harvested during a day in each month of the year. The cooling system was powered by a photovoltaic energy system consisting of several solar photovoltaic (PV) panels, with the intention of taking better advantage of the natural resources of the study area, such as solar radiation. Therefore, dimensioning of the photovoltaic systems for the proposed cooling capacities was carried out.

Case Study Evaluation Process
To solve the water dehumidifier model used as AWG, a computer program was developed that helps to obtain the value of the heat (Q) necessary to extract for water harvesting. The process route is as follows: 1.
Statistical analysis of the variables of interest, such as temperature, humidity and solar radiation.

3.
Delimitation of the psychrometric zone of opportunity for the Matehuala region belonging to the Altiplano Potosino region. The general data of the region's psychrometric zone were entered and vectors were created with increments of 0.2 with the entered data.

4.
Collection of all thermodynamic properties for water vapour and dry air (enthalpies, dew point, specific volume, specific humidity, etc.) from the psychrometric zone.

5.
Data obtained in Step 4 were entered into the mathematical model of the dehumidifier to obtain the amount of energy that must be extracted to the air-steam mixture to reduce its relative humidity by 25%, 50% and 75%. 6.
The case study was applied to n refrigeration packages with the proposed refrigeration capacities. 7.
Feasibility analysis was done with the results obtained.

Results
The amounts of heat extraction required to condense moisture for the three humidity reduction percentages (25%, 50% and 75%) and for the percentages of relative air humidity (50%, 60%, and 70%) are shown in the following figure: The Figure 8 shows the behaviour of heat to be extracted in order to condense the air humidity and the behaviour of each at the different amounts of relative humidity. For 25%, 50% and 75% of humidity reduction, emphasis is placed on the minimum and maximum values as can be seen in the following table.
7. Feasibility analysis was done with the results obtained.

Results
The amounts of heat extraction required to condense moisture for the three humidity reduction percentages (25%, 50% and 75%) and for the percentages of relative air humidity (50%, 60%, and 70%) are shown in the following figure: (a) (b) (c) Figure 8. Heat to be removed for the three percent humidity reduction (25%, 50% and 75%) with air humidity content of 50%(c), 60%(b), and 70%(a).
The Figure 8 shows the behaviour of heat to be extracted in order to condense the air humidity and the behaviour of each at the different amounts of relative humidity. For 25%, 50% and 75% of humidity reduction, emphasis is placed on the minimum and maximum values as can be seen in the following table.  Table 1 is very important for the purposes of this paper and for AWG dimensioning as it defines the range of heat that must be extracted from the air entering the system. With the above results, the maximum amount of heat to be extracted is 46.2541 KJ/kg and the minimum of 13.449 kJ/kg. To carry Figure 8. Heat to be removed for the three percent humidity reduction (25%, 50% and 75%) with air humidity content of 50% (c), 60% (b), and 70% (a). Table 1 is very important for the purposes of this paper and for AWG dimensioning as it defines the range of heat that must be extracted from the air entering the system. With the above results, the maximum amount of heat to be extracted is 46.2541 KJ/kg and the minimum of 13.449 kJ/kg. To carry out a study that covers the maximum and minimum values, the graph lines whose value is the highest for each of the lines of 25%, 50% and 75% reduction were used, since by studying these lines the values below them will be covered. As mentioned above, once the amount of heat that must be extracted (Q) from the dehumidification process is known, any type or medium of possible energy can be used to carry out the heat transfer of that amount of heat. The possible energy sources that can be used directly in the processes can include geothermal energy or solar energy, or indirect means that produce electrical energy by means of wind energy or photovoltaic solar energy that provide the AWG with electrical energy for its operation. It is noteworthy that the Matehuala region has all these energy resources available for use.

Case Study Evaluation
Based on the previous results, the case study for three types of refrigeration packages with the following capacities was carried out: 1 ton of refrigeration (3516.85 J/s, 1141 W consumption), 1 2 ton of refrigeration (1758.42 J/s, 570.5 W consumption) and 1 4 ton of refrigeration (879.21 J/s, 285.25 W consumption). The previous capacities were selected so that they could be used in common households predominant among the majority of the population. The compressor energy consumption could be used to dimension the photovoltaic energy source. The required power, the region's peak solar hours (PSH) and daily operating time of the compressors had to be known in order to dimension the solar panels. The Table 2 shows the power required and generated for the refrigeration package: The amount of watts generated by each panel during each month of the year could be calculated by multiplying the PSH for each month by the power of the panel, as shown in the Figure 9: can be used to carry out the heat transfer of that amount of heat. The possible energy sources that can be used directly in the processes can include geothermal energy or solar energy, or indirect means that produce electrical energy by means of wind energy or photovoltaic solar energy that provide the AWG with electrical energy for its operation. It is noteworthy that the Matehuala region has all these energy resources available for use.

Case Study Evaluation
Based on the previous results, the case study for three types of refrigeration packages with the following capacities was carried out: 1 ton of refrigeration (3516.85 J/s, 1141 W consumption), ½ ton of refrigeration (1758.42 J/s, 570.5 W consumption) and ¼ ton of refrigeration (879.21 J/s, 285.25 W consumption). The previous capacities were selected so that they could be used in common households predominant among the majority of the population. The compressor energy consumption could be used to dimension the photovoltaic energy source. The required power, the region's peak solar hours (PSH) and daily operating time of the compressors had to be known in order to dimension the solar panels. The Table 2 shows the power required and generated for the refrigeration package: The amount of watts generated by each panel during each month of the year could be calculated by multiplying the PSH for each month by the power of the panel, as shown in the Figure 9: The following table shows the time it would take for the AWG to condense the moisture present in the air for the proposed refrigeration packages: Table 3 attempts to estimate the time that the AWG would use to condense the moisture contained in the air, and thus relate the time to PSH, which is the system's working time. Table 3. Condensation times for each refrigeration package in seconds.

Water Harvesting
The harvesting (condensation) of relative air humidity is the main factor in this research, and is calculated as follows: Kg water harvested = (PSH * 3600)(Humidity * % reduction) Time to condense (13) The application of the above equation involves all the factors calculated above. The results of the water harvested for the case study are shown in the Tables 4-6.
The above tables show the behaviour of AWG water harvesting for each refrigeration package proposed and for the study region's conditions. The month with the least amount of water collection was January, with minimum quantities of 3.6 to 0.89 L/day, whereas August was the month with the highest amount of harvesting with a maximum of 18 to 3.9 L/day. The variations in the amount of water captured by the AWG were due to the daily hours of operation in each month of the year (equal to the PSH), the amount of moisture present in the air and the refrigeration packages used.

Cost per Litre of Water Produced
It is possible to estimate the cost per litre or the cost of generating a litre of water with the maximum and minimum values of water harvested. As is well known, for the case studies photovoltaic panels were used as the AWG power source; in order to estimate the cost we will consider electrical power to have been supplied by the local power company, CFE, at the corresponding rate (1A). Rates for the Matehuala region have three levels: Basic (is the first 150 kWh of usage, charged at a rate of 0.062 USD), intermediate (the following 150 kWh of usage after the basic rate, charged at a rate of 0.077 USD) and surplus (any usage exceeding the intermediate rate, charged at a rate of 0.221 USD per kWh).
To calculate the cost per litre of water produced by the AWG, the following equation was used: USD/litre = (Watts produced)($ per KWh) Litres of water produced (14) For this analysis, the maximum and minimum amounts of water harvested during the months of the year (January and February) were taken into account and the cost of water production in the region was estimated using the different refrigeration packages. Results are shown in Figure 10 The results show that the cost per litre of water was very low, even when an average consumption was maintained (average rate), in a range of $ 0.0093 and $ 0.038 USD/L of water harvested by the AWG. The costs obtained per litre harvested were affordable to any type of population that lacks water services.

Discussion
The use of AWGs as a solution to water scarcity has the advantages of simplicity of implementation and energy-free or renewable-energy operation. However, at the same time, there are also disadvantages in terms of seasonality, geographical location and climates [40]. The climatological study developed shows that the conditions of the Matehuala, SLP, region are favourable for the design and use of AWGs for the harvesting of atmospheric air water. The literature notes that favourable conditions for AWG use are above 40% RH (≥ 40%) [43]. With an average annual humidity of approximately 60% despite being a semi-arid region, the humidity levels are suitable for the application proposed in this work. To evaluate the profitability and functionality of the AWG, a new moisture harvest index (MHI) presented in [52] was introduced, which relates the latent heat of condensation to the total heat transfer in the dehumidifier. This index establishes that the economic, energy and operational conditions are unfavourable for the use of AWGs in conditions or regions that have an MHI < 0.3. For the region studied from the psychrometric chart, the values of the MHI can vary in the proposed range of temperatures and humidity of approximately 0.3 to 0.45, the former being the worst case and the latter the best case that can prevail in the region. However, air quality is one of the parameters that is most questioned in the use of AWGs because it is related to the quality of the water collected. There is little literature devoted to the study of inhalation as a route of exposure to arsenic, whereas most consider that the main exposure is based on oral exposure through drinking water or as indicated by CSTEE (2001), through food. However, CSTEE (2001) states that, although air is not a major route of exposure in quantitative terms, the presence of arsenic in the environment is due to the following: Air < 1%, cigarette smoke 0-16%, fresh water 0-33% and food 50-98% [53]. Human exposure to arsenic through air generally occurs at very low concentrations ranging from 0.4 to 30 ng/m 3 . The United States Environmental Protection Agency has estimated that approximately 40 to 90 ng of arsenic per day are inhaled by humans. In non-contaminated areas, approximately 50 ng or less of arsenic per day are inhaled [54,55]. A very recurrent discussion in scientific forums is whether arsenic or contaminants in the air affect the quality of water collected by the AWG or by collecting rainwater. There are no exact data on arsenic levels in the air in the study region, but results found in scientific review show that the levels should be acceptable, without greatly affecting the quality of water harvested from the atmospheric air. It has been reported that the water harvested from the atmospheric air [56][57][58] presents important quantities of faecal, while parameters such as pH, hardness, dissolved solids, and conductivity, heavy metals, alkalinity, odour, flavour, nitrites and nitrates are within the limits established by national standards for drinking water. Few studies The results show that the cost per litre of water was very low, even when an average consumption was maintained (average rate), in a range of $ 0.0093 and $ 0.038 USD/L of water harvested by the AWG. The costs obtained per litre harvested were affordable to any type of population that lacks water services.

Discussion
The use of AWGs as a solution to water scarcity has the advantages of simplicity of implementation and energy-free or renewable-energy operation. However, at the same time, there are also disadvantages in terms of seasonality, geographical location and climates [40]. The climatological study developed shows that the conditions of the Matehuala, SLP, region are favourable for the design and use of AWGs for the harvesting of atmospheric air water. The literature notes that favourable conditions for AWG use are above 40% RH (≥ 40%) [42]. With an average annual humidity of approximately 60% despite being a semi-arid region, the humidity levels are suitable for the application proposed in this work. To evaluate the profitability and functionality of the AWG, a new moisture harvest index (MHI) presented in [52] was introduced, which relates the latent heat of condensation to the total heat transfer in the dehumidifier. This index establishes that the economic, energy and operational conditions are unfavourable for the use of AWGs in conditions or regions that have an MHI < 0.3. For the region studied from the psychrometric chart, the values of the MHI can vary in the proposed range of temperatures and humidity of approximately 0.3 to 0.45, the former being the worst case and the latter the best case that can prevail in the region. However, air quality is one of the parameters that is most questioned in the use of AWGs because it is related to the quality of the water collected. There is little literature devoted to the study of inhalation as a route of exposure to arsenic, whereas most consider that the main exposure is based on oral exposure through drinking water or as indicated by CSTEE (2001), through food. However, CSTEE (2001) states that, although air is not a major route of exposure in quantitative terms, the presence of arsenic in the environment is due to the following: Air < 1%, cigarette smoke 0-16%, fresh water 0-33% and food 50-98% [53]. Human exposure to arsenic through air generally occurs at very low concentrations ranging from 0.4 to 30 ng/m 3 . The United States Environmental Protection Agency has estimated that approximately 40 to 90 ng of arsenic per day are inhaled by humans. In non-contaminated areas, approximately 50 ng or less of arsenic per day are inhaled [54,55]. A very recurrent discussion in scientific forums is whether arsenic or contaminants in the air affect the quality of water collected by the AWG or by collecting rainwater. There are no exact data on arsenic levels in the air in the study region, but results found in scientific review show that the levels should be acceptable, without greatly affecting the quality of water harvested from the atmospheric air. It has been reported that the water harvested from the atmospheric air [56][57][58] presents important quantities of faecal, while parameters such as pH, hardness, dissolved solids, and conductivity, heavy metals, alkalinity, odour, flavour, nitrites and nitrates are within the limits established by national standards for drinking water. Few studies report the presence of arsenic in harvested water; the arsenic indexes reported are less than 0.007 mg/L, thus remaining within the standard of water for human consumption [59]. In Mexico, rainwater has been harvested [27] in which very low levels of fluoride and arsenic have been measured in the water collected. A maximum concentration of 0.004 mg/L was found, well below NOM-127-SSA1-1994 [60] (0.025 mg/L) and WHO guidelines [61] (0.010 mg/L). The water harvesting procedure does not contemplate water coming into contact with soil. In contrast in [47] they report arsenic levels of 0.2 mg/L in the water collected from rain that entered into contact with soil. In general, it is reported that water captured from the environment has excellent conditions for human use as long as it goes through a process of microbiological quality improvement [62]. Feasibility not only contemplates the availability of environmental resources for the design and use of AWG, but also considers the cost of producing freshwater. In our study, we obtained costs in the range of 0.0093 and $ 0.038 USD/L. These costs are affordable to the population compared to the investment or costs of other water supply technologies. For example, in [33] costs ranging from 0.2 to 0.27 USD/L using different types of salts and solar energy have been reported, while Deniz et al. [63] reported a cost of 0.0981 USD/L with a solar distillation system. Tariq et al. [47] reported a cost of 0.030 USD/L using a desalination humidifier-dehumidifier system. The costs that we obtained in the production of fresh water are competitive and even lower than those reported in the literature.

Conclusions
In this work, a feasibility analysis was conducted on the use of atmospheric water generators (AWGs) as a possible solution to water pollution and scarcity in the Matehuala, SLP, Mexico region, which has a lot of mining activity. It was found that the main sources of As exposure in the region are food, soil and water, especially in the hydraulic network system that supplies the region's population. Much of the local and rural population suffers water shortages. The following conclusions are obtained from the analysis carried out in our work:

•
Population growth in the region is inevitable, and the demand for fresh water will increasingly be a matter of government priority. Current figures show that despite the growth of the population and the demand for water, the volumetric production has remained relatively constant for 10 years. In 2000, there were 64,206 inhabitants with a volumetric water production that could supply 6, 274,629 m 3 . By 2017, there were over 99,015 inhabitants, while volumetric water production was 6,641,262 m 3 . In 2000, there were 18,159 water intakes compared to 28,576 in 2018. This will gradually lead to the search for new technologies to provide water.

•
The region of Matehuala, SLP, Mexico has the necessary environmental conditions for the use of AWGs for the harvesting of atmospheric air water, with an average relative humidity of approximately 60%. This value is adequate from the point of view of functionality, economy and viability. In addition to the above, solar (annual average of 5.5 PSH and 720 W/m 2 max) and wind (average annual speeds of 2.2 m/s to 4.1 m/s) energy sources are viable. • Using the mathematical model developed in this work and evaluated with the climatic conditions of the region, monthly water harvesting was determined. January had the lowest harvest, with minimum quantities of 3.6 to 0.89 L/day, whereas August had the greatest harvest, with maximum amounts of 18 to 3.9 L/day.

•
Water production costs were obtained in the range of $ 0.0093 and $ 0.038 USD per litre of water captured by the AWG, showing that the costs obtained per litre harvested are affordable to any type of population that lacks water services.
In general, the region of Matehuala, SLP, Mexico was found to be a feasible area for the use of atmospheric water generators (AWGs) for capturing water from atmospheric air. The implementation of AWGs will help the preservation of ecosystems and the environment in general, benefiting people or communities with limited water supply.