Behavior Characteristics of Hazardous Gas and Scattering Coal Dust in Coal Storage Sheds

: This study has comprehensively analyzed the ventilation system of an indoor coal storage shed using computational ﬂuid dynamics (CFD). In addition, the effects of the plan to improve the ventilation system were investigated by synthesizing the results. First, the velocity of inlet wind entering through the natural ventilation system was measured. Then, the concentration of carbon monoxide inside the coal storage shed was measured at the spontaneous combustion of coal. The boundary conditions were set using the measurement results. The characteristics of carbon monoxide concentration, ventilation volume, and behavior of scattering dust were analyzed. According to the CFD analysis results, the upper recirculation strength increased as the ﬂow rate of external air increased. The ﬂow-stagnation area occurred on the center wall. In particular, the concentration of carbon monoxide was high in the ﬂow-stagnation area. When the inﬂow velocity was 2.0 m/s, a risk of 30 ppm or more occurred in the area near the second-ﬂoor workspace and central retaining wall. When ventilation dropped sharply, coal dust emissions decreased to 14.5%. Thus, ventilation must be secured by installing a natural ventilation system, in case spontaneous ignition occurs in many cells or the ventilation sharply decreases. Finally, in order to improve the ventilation system, the effect on the additional installation of natural ventilation and the use of mobile blowers was analyzed. Finally, in order to improve the ventilation system, the effect on the additional installation of natural ventilation and the use of mobile blowers was analyzed. As a result of the analysis, we concluded that using a mobile blower is more effective than a method of additionally installing a natural ventilation device. Carbon monoxide may be locally diluted, and ventilation volume additionally secured. is slow, it stagnates at the top of the dust point. However, if the ﬂow rate is high, the emissions increase over the central retaining wall, and most dust is emitted outside.


Introduction
Recently, governments worldwide have been pushing for energy transformation to cope with severe climate change. Therefore, fossil-fuel use is decreasing, and eco-friendly energy use is increasing [1]. According to the 2019 statistics released by the US Energy Information Administration, South Korea ranked fifth among liquefied natural gas, coal, and petroleum fuel importers in the world, and ninth in energy consumption. As such, Korea is highly dependent on fossil fuels [2]. Changing the fossil-fuel-oriented energy industry in a short time is expensive. Therefore, actively solving the environmental problems of existing coal-fired power plants, while achieving energy conversion, is essential.
Power companies and governments are expanding investment in environmental facilities to respond to environmental problems caused by coal-fired power plants. A typical example is a coal storage shed. In the past, coal was stored outdoors. However, a large volume of coal dust occurs caused by fine dust, generating civil complaints in the surrounding areas [3]. By storing coal indoors, the scattering of coal dust can be prevented due to airflow. The shapes of indoor coal storage areas are divided into shed, dome, and silo types. The shed-type indoor coal storage is a warehouse-type storage yard, with a

Introduction of Latest Technologies and Research
This section introduces the latest technologies related to indoor air quality (IAQ) ventilation improvement systems.
Behrouz Pirouz et al. [20] analyzed the effects of indoor airflow patterns and exits in HVAC systems. CFD was used to improve the HVAC design in the study. It analyzed blind spots where residents were placed and dead zones with poor ventilation. As a result, it was found that the entrance and exit positions of the window and HVAC system had an important influence. Therefore, the analysis of airflow patterns is essential in designing HVAC systems.
Alessandro D'Amico et al. [21] analyzed the indoor air quality concentration related to the indoor VOC concentration using CFD. It was performed in consideration of a specific environment according to environmental parameters and the sampling of indoor pollutants. CFD simulation was performed under conditions similar to VOC sampling conditions. CFD was useful in emphasizing the role of ventilation in determining the spatial distribution of dispersed pollutants. The study confirmed the possibility, although it characterized by simplification due to the lack of data.
Rafat Al-Waked et al. [22] analyzed the carbon monoxide emitted from underground parking cars using CFD. It was derived that the ventilation system should be operated at an ACH value of 2 or more. In addition, criteria were presented to meet the allowable concentration of 50 ppm in the parking lot. In addition, it was derived that louver porosity did not significantly affect the CO concentration, when considering the underground parking lot as a single unit.
Lina Seduikyte et al. [23] numerically simulated the ventilation performance of the sports hall where the mechanical ventilation system works. At Lithuania's basketball training ground, thermal stratification conditions according to the performance of the HVAC system were analyzed. The same heating output as warm-air heating and floor heating was used. By combining mechanical mixing and displacement ventilation, the possibility of energy saving was shown. As a result, it was found possible to save energy by mixing with the low layer of air.
Ardalan Aflaki et al. [24] reviewed the simulation for predicting and evaluating the ventilation performance of the building. An experimental model and a CFD coupling building-energy simulation for the evaluation and prediction of natural ventilation (NV) were analyzed. Among the CFD turbulence models, it was concluded that the RANS equation turbulence model was the most appropriate and takes the least computational time. In addition, it was derived that further research is needed on the weaknesses of the k-ω model, compared with other models in buildings. Nayara Rodrigues Marques Sakiyama et al. [25] evaluated the natural ventilation of a 3D parameter model using CFD. The authors investigated 3D parameter modeling and natural ventilation, and the natural ventilation effect of the building was explained by analyzing the CFD output. An alternative to 3D design was explored to display and calculate ACH and generate a surface on which wind speed is calculated in parametric modeling.

Structure of Thesis
This paper comprehensively analyzes the natural ventilation performance of indoor coal fields and presents improvement measures by synthesizing the results. This section introduces the structure of the paper and explains the research method.
Section 1. The introduction explains the necessity of the thesis and the problems of indoor storage.
Section 2. The latest technology and research for improving ventilation systems and indoor air quality (IAQ) are introduced. Section 3. The introduction of the study is divided into two small sections. In 3-1, the composition of this paper is explained with regard each section. In 3-2, the research method is explained for analyzing air quality and improving plans in the coal storage shed. Section 4. The methodology is divided into four small sections. The methodology explains the structure of the indoor coal yard and measures the flow of velocity in the ventilation system. In addition, the boundary conditions and methods of the CFD numerical analysis are explained. Section 5. Results and discussions are divided into a total of three small sections. The results of the emission of internal flow fields, carbon monoxide-risk areas, and scattering dust are analyzed and explained. Section 6. In the result verification, the contents of the flow visualization test are described to verify the CFD simulation results. Information on the flow field is extracted using the tomography technique, and compared with the CFD results. Section 7. In the ventilation system improvement plan, an analysis is conducted on the additional louver-installation plan and the mobile-blower use plan.
Section 8. The results of the study are summarized, including the results of the internal flow characteristics according to wind direction and wind speed, carbon monoxide dangerous areas, scattering dust emissions, and measures to improve the indoor coal field ventilation system.

Research Method
This study analyzes the natural ventilation system of an indoor coal yard, verifies the simulation results, and analyzes the effect of the ventilation system improvement plan. It also explains how to conduct the research. Figure 1. Below shows the research method. First, CFD simulation was performed using the measured results. The results derived through the simulation were flow characteristics, carbon monoxide concentration, and the emission characteristics of scattered dust. The simulation results were verified. The results of the flow visualization experiment and the simulation results were compared and verified. The limitations of the model of this study are as follows: first, do not enlarge after spontaneous ignition occurs. It was assumed that spontaneous ignition occurred in one cell, and it was difficult to predict spontaneous speech. It was also difficult to predict the scale, because many variables had to be considered. Therefore, the analysis was conducted based on the measured values. If spontaneous speech expands, the results of this study cannot be the best alternative. In addition, most of the coal dust generated inside the indoor coal yard precipitated. However, this study focused on the emission of generated dust and analyzed it; therefore, the amount of precipitating dust was not considered. Therefore, it should be noted that the derived emission value differs from the theory. based on the measured values. If spontaneous speech expands, the results of this study cannot be the best alternative. In addition, most of the coal dust generated inside the indoor coal yard precipitated. However, this study focused on the emission of generated dust and analyzed it; therefore, the amount of precipitating dust was not considered. Therefore, it should be noted that the derived emission value differs from the theory. In this study, Ansys Fluent software [26] was used to analyze the concentration distribution of internal carbon monoxide in the event of spontaneous coal combustion in an indoor coal mine. The continuity, momentum, and energy equations were used as governing equations to perform flow analysis in the indoor coal mine. Equation (1) represents the continuity equation [27]. The steady-state continuity equation can be expressed as follows and applied to all fluids: Turbulence variability must be considered for most of the surrounding flow. It is divided into the average velocity and velocity fluctuation components to exclude turbulence variability, and the same can be applied to pressure. From Equation (2), the time-averaged Navier-Stokes equation can be expressed, as displayed in Equation (3): In this study, Ansys Fluent software [26] was used to analyze the concentration distribution of internal carbon monoxide in the event of spontaneous coal combustion in an indoor coal mine. The continuity, momentum, and energy equations were used as governing equations to perform flow analysis in the indoor coal mine. Equation (1) represents the continuity equation [27]. The steady-state continuity equation can be expressed as follows and applied to all fluids: . Turbulence variability must be considered for most of the surrounding flow. It is divided into the average velocity and velocity fluctuation components to exclude turbulence variability, and the same can be applied to pressure. From Equation (2), the time-averaged Navier-Stokes equation can be expressed, as displayed in Equation (3): where-ρu i u j in Equation (4) indicates the increase in momentum transport due to velocity variability, called the turbulent stress term (Reynolds stress term). The Navier-Stokes equations for u, v, and w are shown in Equations (5) Turbulence refers to the creation of unstable vortices that occur in high Reynolds number flows. The turbulence model relates to the treatment of the Reynolds stress term. This study used the Reynolds averaged Navier-Stokes (RANS) based model among other turbulence modeling methods [28]. The turbulent viscosity is defined as a function of turbulent kinetic energy and turbulent dissipation. The model can ignore the pressure diffusion term when modeling turbulent kinetic energy. The k − ε model [29,30] is the most widely used among the RANS models and is shown in Equations (8) and (9) [31]: The local mass fraction of each species should be predicted using the convection and diffusion equations to solve the conservation equation for chemical species. The conservation equations for carbon monoxide in the indoor coal pit are presented in Equations (10) and (11). The production rate of R i species by the chemical reaction is i, and S i is the production rate by the sum of the dispersed steps and sources:

Shed-Type Coal Storage
Building specifications and modeling shapes are listed in Table 1 and Figure 2, to analyze the flow characteristics of existing coal storage sheds for coal-fired power plants. port is transferred from the outside, and there is a worker's entrance door. The indoor coal storage shed measures 447 m in width, 125 m in length, and 66 m in height, and the coal storage shed models a 1:1 3D shape. The shutter is 6 m × 7 m, the louver is 1.5 m × 1.5 m, and the windows are all open. The grid of the modeling shape for the analysis of the internal flow characteristics of the coal storage shed is a tetrahedron, and the total number of grids is about 8 million.

Field Measurement
The internal flow characteristics of the coal storage shed are closely related to the surrounding meteorological conditions (wind direction, wind speed, and airflow change), The coal storage shed is a storage room that stores coal indoors to prevent the scattering of coal dust, and consists of three floors of workspace. Coal arriving at the pier through a coal carrier is transported to the indoor coal yard using a conveyor belt. Coal is stored in the telescopic chute above the workspace on the third floor. Sixteen cells, spaces for storing coal, are operated in the indoor coal yard, and a concrete wall separates each cell. The indoor coal storage facility is equipped with ventilation facilities that promote natural ventilation to manage harmful gases, scattering dust, and heat generated from internal coal. Ventilation is ensured by operating the monitor louver on the upper ceiling, the first-floor workspace, and the windows.
Furthermore, on the north and south sides of the coal storage, a conveyor belt transfer port is transferred from the outside, and there is a worker's entrance door. The indoor coal storage shed measures 447 m in width, 125 m in length, and 66 m in height, and the coal storage shed models a 1:1 3D shape. The shutter is 6 m × 7 m, the louver is 1.5 m × 1.5 m, and the windows are all open. The grid of the modeling shape for the analysis of the internal flow characteristics of the coal storage shed is a tetrahedron, and the total number of grids is about 8 million.

Field Measurement
The internal flow characteristics of the coal storage shed are closely related to the surrounding meteorological conditions (wind direction, wind speed, and airflow change), considering the location of the coal storage shed and depending on the local environmental characteristics. The wind speed is relatively great, compared with inland areas due to the nature of the coastal zone. In winter, relatively strong winds were recorded with an average wind speed of 1.92 m/s for 36 months, and a maximum wind speed of 12.7 m/s. In summer, the southwest air current is strongly influenced by the northwest air current in winter. In this study, inflow data were measured to identify seasonal wind speeds and temperatures in a coal storage shed to use as boundary conditions for computational analysis. The flow rate and temperature of incoming and outgoing air were measured 10 times a season, using the hot wire anemometer (TSI-9535) presented in Table 2. The measurement of the inflow rate to the west was high, due to the partial air current caused by the windproof fence installed in the east around the coal storage shed. The results of the measured flow rate are as follows. The speed was measured every month, and the average speed of each inlet is shown in the table. As a result of measuring the inflow flow rate, the maximum speed was 4.6 m/s and the minimum speed was 0.7 m/s. The rate of inflow from the west was generally high. The reason was that a dustproof wall is installed on the east side of the coal yard. Therefore, the speed in the west was relatively fast. Simulation boundary conditions were entered using the flow velocity measurement result.
The graph reveals the daily average value of the carbon monoxide concentration at four measurement points in the coal storage shed. When spontaneous combustion was actively occurring, a daily average of about 40.25 ppm of carbon monoxide was measured. In this study, 40.25 ppm, the highest daily average concentration value, was used to calculate the generated carbon monoxide. About 27.0 ppm of carbon monoxide was measured in S3 after the initial spontaneous ignition, which rose to 60.0 ppm after four days. At that time, the average concentration of carbon monoxide in the indoor coal storage shed was 40.3 ppm, exceeding the optimum internal concentration of 30.0 ppm. The generated carbon monoxide at the maximum concentration of 100 ppm in the S3 region was derived when spontaneous ignition occurred. Therefore, computational analysis was performed in this study, assuming 16 kg/s of carbon monoxide generation in the natural ignition generation area.

Numerical Method
The simulation boundary conditions applied in this study are described in Table 3, as follows. The simulation of the flow analysis in CFD was significant. As described above, the standard k − ε model was used. The louver on the first floor applied the flow rate measurement result, and set it as a velocity inlet. The monitor louver is an outlet through which the introduced air was discharged. Therefore, it was set as a pressure outlet. The most important aspect was the location of spontaneous ignition; in fact, the point where spontaneous ignition occurred in the coal storage shed was measured using thermal images. It was selected by referring to the measured results; therefore, the location where spontaneous ignition occurred most frequently was applied. At the point of the spontaneous ignition of coal, 16.0 kg/s of carbon monoxide was generated. The method of selecting the amount of carbon monoxide generated was as follows. Figure 3 below shows the measurement results of carbon monoxide concentration. Carbon monoxide was measured at four points and the simulation was repeated dozens of times, until the results measured at the same four points were obtained using the simulation. The derived CO concentration was applied to the analysis. The coal inside the indoor coal storage shed was modeled at a slope of 40 degrees. Since air flows into the coal pile, the coil was set to a porous zone. This study assumed that the diameter of the coal was 0.01 m, the porosity was 0.2, and the permeability and inertial resistance coefficient were 35,000. ages. It was selected by referring to the measured results; therefore, the location where spontaneous ignition occurred most frequently was applied. At the point of the spontaneous ignition of coal, 16.0 kg/s of carbon monoxide was generated. The method of selecting the amount of carbon monoxide generated was as follows. Figure 3 below shows the measurement results of carbon monoxide concentration. Carbon monoxide was measured at four points and the simulation was repeated dozens of times, until the results measured at the same four points were obtained using the simulation. The derived CO concentration was applied to the analysis. The coal inside the indoor coal storage shed was modeled at a slope of 40 degrees. Since air flows into the coal pile, the coil was set to a porous zone. This study assumed that the diameter of the coal was 0.01 m, the porosity was 0.2, and the permeability and inertial resistance coefficient were 35,000. Coal pile  Figure 4 shows the velocity contours that appeared from the CFD analysis results of the outdoor air-measurement data, used to analyze the flow characteristics of shed-type  Figure 4 shows the velocity contours that appeared from the CFD analysis results of the outdoor air-measurement data, used to analyze the flow characteristics of shed-type coal storage. When the inflow velocity was V Max , the outside air from the first-floor louver and window rose by the coal pile and the central wall, and flowed out to the monitor louver. Moreover, a recirculation area generated in the upper part of the outside air inflow direction. For V low , the velocity of the inflow reduced, and the upper recirculation area gradually reduced. The discharge to the monitor louver also reduced rapidly.  Figure 4 shows the velocity contours that appeared from the CFD analysis results of the outdoor air-measurement data, used to analyze the flow characteristics of shed-type coal storage. When the inflow velocity was , the outside air from the first-floor louver and window rose by the coal pile and the central wall, and flowed out to the monitor louver. Moreover, a recirculation area generated in the upper part of the outside air inflow direction. For , the velocity of the inflow reduced, and the upper recirculation area gradually reduced. The discharge to the monitor louver also reduced rapidly.  The coal storage shed did not have mechanical ventilation. The discharge of pollutants was not smooth, due to the structural characteristics of generating a large amount of coal dust and harmful gas in the coal pile. Therefore, to improve the indoor working environment of the field workers inside the indoor coal yard, the amount of ventilation must be analyzed for each outdoor air inlet and outlet. The mass flow rate that flows in and out of the natural ventilation system due to changes in wind speed is illustrated in Figure 5. When the inflow velocity of the outside air was 1.0 m/s, 1634.1 m/s of the outside air was discharged from the first-floor louver. In addition, 1084.4 m/s of the outside air flowed out to the upper monitor louver. The amount of ventilation for each natural ventilation device The coal storage shed did not have mechanical ventilation. The discharge of pollutants was not smooth, due to the structural characteristics of generating a large amount of coal dust and harmful gas in the coal pile. Therefore, to improve the indoor working environment of the field workers inside the indoor coal yard, the amount of ventilation must be analyzed for each outdoor air inlet and outlet. The mass flow rate that flows in and out of the natural ventilation system due to changes in wind speed is illustrated in Figure 5. When the inflow velocity of the outside air was 1.0 m/s, 1634.1 m/s of the outside air was discharged from the first-floor louver. In addition, 1084.4 m/s of the outside air flowed out to the upper monitor louver. The amount of ventilation for each natural ventilation device is described in Figure 6. When the total outdoor air outflow was 100%, 51.9% of the outdoor air flowed through the monitor louver. Additionally, 33.8% was emitted by the first-floor louver, and 5.0% was by the window. When the inflow velocity was 4.8 m/s, 79.0% of the total outdoor air inflow flowed into the first-floor louver. About 54.3% of the outflow flowed to the upper monitor louver, and 31.9% flowed out of the first-floor louver.

Analysis of Internal Flow and Ventilation
In addition, the air change rate per hour (ACH) in coal storage was analyzed; at the maximum speed, the ventilation volume was 13.1 ACH. At the minimum speed, the ventilation volume was 4.4 ACH. Even at a relatively low wind speed, more than 4.4 ACH were secured. However, it may be difficult to ensure sufficient ventilation because the amount of ventilation decreased sharply if the inflow velocity was further reduced, due to the nature of the indoor coal mine, where substantial harmful gas and dust is generated. Therefore, additional analysis is required on the concentration characteristics of local pollutants when spontaneous ignition occurs.
is described in Figure 6. When the total outdoor air outflow was 100%, 51.9% of the outdoor air flowed through the monitor louver. Additionally, 33.8% was emitted by the firstfloor louver, and 5.0% was by the window. When the inflow velocity was 4.8 m/s, 79.0% of the total outdoor air inflow flowed into the first-floor louver. About 54.3% of the outflow flowed to the upper monitor louver, and 31.9% flowed out of the first-floor louver.  In addition, the air change rate per hour (ACH) in coal storage was analyzed; at the maximum speed, the ventilation volume was 13.1 ACH. At the minimum speed, the ventilation volume was 4.4 ACH. Even at a relatively low wind speed, more than 4.4 ACH were secured. However, it may be difficult to ensure sufficient ventilation because the amount of ventilation decreased sharply if the inflow velocity was further reduced, due to the nature of the indoor coal mine, where substantial harmful gas and dust is generated. Therefore, additional analysis is required on the concentration characteristics of local pollutants when spontaneous ignition occurs. is described in Figure 6. When the total outdoor air outflow was 100%, 51.9% of the outdoor air flowed through the monitor louver. Additionally, 33.8% was emitted by the firstfloor louver, and 5.0% was by the window. When the inflow velocity was 4.8 m/s, 79.0% of the total outdoor air inflow flowed into the first-floor louver. About 54.3% of the outflow flowed to the upper monitor louver, and 31.9% flowed out of the first-floor louver.  In addition, the air change rate per hour (ACH) in coal storage was analyzed; at the maximum speed, the ventilation volume was 13.1 ACH. At the minimum speed, the ventilation volume was 4.4 ACH. Even at a relatively low wind speed, more than 4.4 ACH were secured. However, it may be difficult to ensure sufficient ventilation because the amount of ventilation decreased sharply if the inflow velocity was further reduced, due to the nature of the indoor coal mine, where substantial harmful gas and dust is generated. Therefore, additional analysis is required on the concentration characteristics of local pollutants when spontaneous ignition occurs.

Concentration of Carbon Monoxide
The boundary conditions for carbon monoxide concentration analysis appear in Table 4. Case 2-1 assumes the conditions in which spontaneous ignition occurs in Cell 4: the wind direction being west, and the inflow velocity being 6 m/s. Under the same conditions in Case 2-2, the inflow velocity is 2.0 m/s. These conditions assume that both the inlet and outlet of the coal storage tank are open, and the coal pile is 100% stored.
In the case of spontaneous ignition, the concentration distribution analysis of carbon monoxide, a harmful gas in indoor coal storage sheds, was conducted, and the results are as follows. Figure 7 illustrates the results of the CFD analysis of carbon monoxide for spontaneous coal combustion in an indoor coal storage shed. For the inflow rate of 6.0 m/s, the ambient air flowed through the louver, and the flow circulated on the left side of the shed and inclined coal surfaces. In addition, carbon monoxide generated from the coal pile surface was only observed at the central wall and the point of spontaneous ignition. About 10.5 ppm of carbon monoxide was found in the upper part of the self-igniting cell. The ventilation volume was secured due to the increase in the inflow rate, and there was no area over 30 ppm (the hazardous standard concentration) in the workspace. As a result of checking the inflow rate of 2.0 m/s, it is possible to check the concentration of carbon monoxide in the upper part of the central shed. As the ventilation rapidly decreased, the accumulated carbon monoxide increased. An area where carbon monoxide exceeded 30 ppm occurs in the workspace was on the second floor, adjacent to the spontaneous ignition cell.

Concentration of Carbon Monoxide
The boundary conditions for carbon monoxide concentration analysis appear in Table 4. Case 2-1 assumes the conditions in which spontaneous ignition occurs in Cell 4: the wind direction being west, and the inflow velocity being 6 m/s. Under the same conditions in Case 2-2, the inflow velocity is 2.0 m/s. These conditions assume that both the inlet and outlet of the coal storage tank are open, and the coal pile is 100% stored. In the case of spontaneous ignition, the concentration distribution analysis of carbon monoxide, a harmful gas in indoor coal storage sheds, was conducted, and the results are as follows. Figure 7 illustrates the results of the CFD analysis of carbon monoxide for spontaneous coal combustion in an indoor coal storage shed. For the inflow rate of 6.0 m/s, the ambient air flowed through the louver, and the flow circulated on the left side of the shed and inclined coal surfaces. In addition, carbon monoxide generated from the coal pile surface was only observed at the central wall and the point of spontaneous ignition. About 10.5 ppm of carbon monoxide was found in the upper part of the self-igniting cell. The ventilation volume was secured due to the increase in the inflow rate, and there was no area over 30 ppm (the hazardous standard concentration) in the workspace. As a result of checking the inflow rate of 2.0 m/s, it is possible to check the concentration of carbon monoxide in the upper part of the central shed. As the ventilation rapidly decreased, the accumulated carbon monoxide increased. An area where carbon monoxide exceeded 30 ppm occurs in the workspace was on the second floor, adjacent to the spontaneous ignition cell.
The coal storage shed has three floors of workspace. The characteristics of the carbon monoxide concentration and exposure hazard areas were identified in each workplace. Figure 8 depicts the carbon monoxide concentration contour for each height. The result when the wind direction is a westerly wind of 1.0 m/s, which is the worst condition, must be checked to analyze the risk of carbon monoxide.    It was assumed that the inlets and outlets for outside air were all open, such as the doors and windows. The analysis was conducted assuming that spontaneous ignition occurred in Cell 4. The first floor has many louvers and windows where outdoor air flows in. Therefore, the working space on the first floor did not have a dangerous space of 30 ppm or more carbon monoxide, due to the rise of carbon monoxide at the firing point. In It was assumed that the inlets and outlets for outside air were all open, such as the doors and windows. The analysis was conducted assuming that spontaneous ignition occurred in Cell 4. The first floor has many louvers and windows where outdoor air flows in. Therefore, the working space on the first floor did not have a dangerous space of 30 ppm or more carbon monoxide, due to the rise of carbon monoxide at the firing point. In the second-floor workspace, carbon monoxide was relatively high, compared with the surrounding area, because it was adjacent to the point of spontaneous ignition. In particular, up to 48.5 ppm of carbon monoxide concentration was identified on the two-layer central wall adjacent to the ignition point. As this increased, the carbon monoxide concentration gradually diluted. On the third floor, carbon monoxide was discharged into the monitor louver, and elevated carbon monoxide was diluted outside the inflow and outflow air, so no carbon monoxide concentration greater than 20 ppm was identified. However, this is the interpretation of spontaneous ignition conditions in one cell. Therefore, if spontaneous ignition occurred in multiple cells in combination, the risk zone of the second layer would be likely to expand.

Scattering Coal Dust Emissions
Considerable scattered dust occurs when coal drops in the coal storage shed. The coal storage shed was built to prevent scattering dust, but the indoor field work environment is not safe for workers due to fine dust. An analysis of the behavior and emission characteristics of scattering dust, according to the surrounding weather conditions, is required. Therefore, the amount of natural ventilation of scattered dust, according to the wind direction and speed, for the coal storage was analyzed. Tables 5 and 6 list the boundary conditions for analyzing coal dust emission characteristics, according to wind direction and speed. Cases 3-1 through 3-4 changed the wind direction in the east, west, south and north, under 2.0 m/s wind conditions. Cases 3-5 to 3-8 were analyzed by increasing the wind speed to 1 m/s, 2 m/s, 4 m/s, and 6 m/s under western wind conditions. Coal dust was equally generated in Cell 4, and natural ventilation was assumed to be fully open. In addition, 152 particle tracks were created at the coal storage shed to quantify the natural emission of dust generated when coal fell inside the coal storage shed. By checking the amount discharged to the outside, the dust generated in the indoor low-carbon field was tracked, and the natural emissions were reviewed according to the variables. Modeling is not safe for workers due to fine dust. An analysis of the behavior and emission characteristics of scattering dust, according to the surrounding weather conditions, is required. Therefore, the amount of natural ventilation of scattered dust, according to the wind direction and speed, for the coal storage was analyzed. Tables 5 and 6 list the boundary conditions for analyzing coal dust emission characteristics, according to wind direction and speed. Cases 3-1 through 3-4 changed the wind direction in the east, west, south and north, under 2.0 m/s wind conditions. Cases 3-5 to 3-8 were analyzed by increasing the wind speed to 1 m/s, 2 m/s, 4 m/s, and 6 m/s under western wind conditions. Coal dust was equally generated in Cell 4, and natural ventilation was assumed to be fully open. In addition, 152 particle tracks were created at the coal storage shed to quantify the natural emission of dust generated when coal fell inside the coal storage shed. By checking the amount discharged to the outside, the dust generated in the indoor low-carbon field was tracked, and the natural emissions were reviewed according to the variables. is not safe for workers due to fine dust. An analysis of the behavior and emission characteristics of scattering dust, according to the surrounding weather conditions, is required. Therefore, the amount of natural ventilation of scattered dust, according to the wind direction and speed, for the coal storage was analyzed. Tables 5 and 6 list the boundary conditions for analyzing coal dust emission characteristics, according to wind direction and speed. Cases 3-1 through 3-4 changed the wind direction in the east, west, south and north, under 2.0 m/s wind conditions. Cases 3-5 to 3-8 were analyzed by increasing the wind speed to 1 m/s, 2 m/s, 4 m/s, and 6 m/s under western wind conditions. Coal dust was equally generated in Cell 4, and natural ventilation was assumed to be fully open. In addition, 152 particle tracks were created at the coal storage shed to quantify the natural emission of dust generated when coal fell inside the coal storage shed. By checking the amount discharged to the outside, the dust generated in the indoor low-carbon field was tracked, and the natural emissions were reviewed according to the variables. Fully open Table 6. Boundary conditions for coal-dust behavior analysis according to wind speed.

Modeling Ignition point Cell No.4 Coal pile West
is not safe for workers due to fine dust. An analysis of the behavior and emission characteristics of scattering dust, according to the surrounding weather conditions, is required. Therefore, the amount of natural ventilation of scattered dust, according to the wind direction and speed, for the coal storage was analyzed. Tables 5 and 6 list the boundary conditions for analyzing coal dust emission characteristics, according to wind direction and speed. Cases 3-1 through 3-4 changed the wind direction in the east, west, south and north, under 2.0 m/s wind conditions. Cases 3-5 to 3-8 were analyzed by increasing the wind speed to 1 m/s, 2 m/s, 4 m/s, and 6 m/s under western wind conditions. Coal dust was equally generated in Cell 4, and natural ventilation was assumed to be fully open. In addition, 152 particle tracks were created at the coal storage shed to quantify the natural emission of dust generated when coal fell inside the coal storage shed. By checking the amount discharged to the outside, the dust generated in the indoor low-carbon field was tracked, and the natural emissions were reviewed according to the variables. Fully open Table 6. Boundary conditions for coal-dust behavior analysis according to wind speed.

Modeling Ignition point Cell No.4 Coal pile West
is not safe for workers due to fine dust. An analysis of the behavior and emission characteristics of scattering dust, according to the surrounding weather conditions, is required. Therefore, the amount of natural ventilation of scattered dust, according to the wind direction and speed, for the coal storage was analyzed. Tables 5 and 6 list the boundary conditions for analyzing coal dust emission characteristics, according to wind direction and speed. Cases 3-1 through 3-4 changed the wind direction in the east, west, south and north, under 2.0 m/s wind conditions. Cases 3-5 to 3-8 were analyzed by increasing the wind speed to 1 m/s, 2 m/s, 4 m/s, and 6 m/s under western wind conditions. Coal dust was equally generated in Cell 4, and natural ventilation was assumed to be fully open. In addition, 152 particle tracks were created at the coal storage shed to quantify the natural emission of dust generated when coal fell inside the coal storage shed. By checking the amount discharged to the outside, the dust generated in the indoor low-carbon field was tracked, and the natural emissions were reviewed according to the variables. Fully open Table 6. Boundary conditions for coal-dust behavior analysis according to wind speed.

Case 3-5 Case 3-6 Case 3-7 Case 3-8 Inlet Wind Speed 1 m/s 2 m/s 4 m/s 6 m/s
Modeling Considerable scattered dust occurs when coal drops in the coal storage shed. The coal storage shed was built to prevent scattering dust, but the indoor field work environment is not safe for workers due to fine dust. An analysis of the behavior and emission characteristics of scattering dust, according to the surrounding weather conditions, is required. Therefore, the amount of natural ventilation of scattered dust, according to the wind direction and speed, for the coal storage was analyzed. Tables 5 and 6 list the boundary conditions for analyzing coal dust emission characteristics, according to wind direction and speed. Cases 3-1 through 3-4 changed the wind direction in the east, west, south and north, under 2.0 m/s wind conditions. Cases 3-5 to 3-8 were analyzed by increasing the wind speed to 1 m/s, 2 m/s, 4 m/s, and 6 m/s under western wind conditions. Coal dust was equally generated in Cell 4, and natural ventilation was assumed to be fully open. In addition, 152 particle tracks were created at the coal storage shed to quantify the natural emission of dust generated when coal fell inside the coal storage shed. By checking the amount discharged to the outside, the dust generated in the indoor low-carbon field was tracked, and the natural emissions were reviewed according to the variables.

Scattering Coal Dust Emissions
Considerable scattered dust occurs when coal drops in the coal storage shed. The coal storage shed was built to prevent scattering dust, but the indoor field work environment is not safe for workers due to fine dust. An analysis of the behavior and emission characteristics of scattering dust, according to the surrounding weather conditions, is required. Therefore, the amount of natural ventilation of scattered dust, according to the wind direction and speed, for the coal storage was analyzed. Tables 5 and 6 list the boundary conditions for analyzing coal dust emission characteristics, according to wind direction and speed. Cases 3-1 through 3-4 changed the wind direction in the east, west, south and north, under 2.0 m/s wind conditions. Cases 3-5 to 3-8 were analyzed by increasing the wind speed to 1 m/s, 2 m/s, 4 m/s, and 6 m/s under western wind conditions. Coal dust was equally generated in Cell 4, and natural ventilation was assumed to be fully open. In addition, 152 particle tracks were created at the coal storage shed to quantify the natural emission of dust generated when coal fell inside the coal storage shed. By checking the amount discharged to the outside, the dust generated in the indoor low-carbon field was tracked, and the natural emissions were reviewed according to the variables. Considerable scattered dust occurs when coal drops in the coal storage shed. The coal storage shed was built to prevent scattering dust, but the indoor field work environment is not safe for workers due to fine dust. An analysis of the behavior and emission characteristics of scattering dust, according to the surrounding weather conditions, is required. Therefore, the amount of natural ventilation of scattered dust, according to the wind direction and speed, for the coal storage was analyzed. Tables 5 and 6 list the boundary conditions for analyzing coal dust emission characteristics, according to wind direction and speed. Cases 3-1 through 3-4 changed the wind direction in the east, west, south and north, under 2.0 m/s wind conditions. Cases 3-5 to 3-8 were analyzed by increasing the wind speed to 1 m/s, 2 m/s, 4 m/s, and 6 m/s under western wind conditions. Coal dust was equally generated in Cell 4, and natural ventilation was assumed to be fully open. In addition, 152 particle tracks were created at the coal storage shed to quantify the natural emission of dust generated when coal fell inside the coal storage shed. By checking the amount discharged to the outside, the dust generated in the indoor low-carbon field was tracked, and the natural emissions were reviewed according to the variables. Considerable scattered dust occurs when coal drops in the coal storage shed. The coal storage shed was built to prevent scattering dust, but the indoor field work environment is not safe for workers due to fine dust. An analysis of the behavior and emission characteristics of scattering dust, according to the surrounding weather conditions, is required. Therefore, the amount of natural ventilation of scattered dust, according to the wind direction and speed, for the coal storage was analyzed. Tables 5 and 6 list the boundary conditions for analyzing coal dust emission characteristics, according to wind direction and speed. Cases 3-1 through 3-4 changed the wind direction in the east, west, south and north, under 2.0 m/s wind conditions. Cases 3-5 to 3-8 were analyzed by increasing the wind speed to 1 m/s, 2 m/s, 4 m/s, and 6 m/s under western wind conditions. Coal dust was equally generated in Cell 4, and natural ventilation was assumed to be fully open. In addition, 152 particle tracks were created at the coal storage shed to quantify the natural emission of dust generated when coal fell inside the coal storage shed. By checking the amount discharged to the outside, the dust generated in the indoor low-carbon field was tracked, and the natural emissions were reviewed according to the variables. Computational fluid dynamics were used to analyze the dust emission according to the wind direction and speed when coal dust was generated in a coal storage shed.
When the wind speed is 2.0 m/s, the dust behavior according to the wind direction during coal storage in cell No. 4 must be checked. In Cases 4-1 and 4-2, which were the east and west wind conditions, the scattered coal dust was distributed in large quantities on the top of the center retaining wall of the cell, where the drop operation occurs. The scattered dust was discharged to the monitor louver. In Cases 4-3 and 4-4, which were the conditions of southerly and northerly winds, dust was distributed in the upper part of the cell, and the horizontal spread of dust was active due to the north-south winds. Regarding the dust emission ratio, 50.6% of the dust was emitted if outside air flowed in from the direction of the coal fall operation. For east wind inflow conditions, the airflow was blocked by the central wall, and 19.1% was discharged to the outside. Therefore, the emission of dust was reduced.
Results of simulating the scattering dust behavior characteristics are described in Figure 9. Regarding the analysis results of the behavioral characteristics of scattered dust, according to the inflow flow rate of the coal storage shed, when the wind speed is the lowest at 1.0 m/s, about 14.5% of the dust is discharged outside. As the flow rate increases, the amount of scattered dust also increases. For 2.0 m/s and 6.0 m/s flow velocities, 50.6% and 92.1% of scattered dust are discharged to the outside, respectively. If the flow rate is slow, it stagnates at the top of the dust point. However, if the flow rate is high, the emissions increase over the central retaining wall, and most dust is emitted outside.
Results of simulating the scattering dust behavior characteristics are described in Figure 9. Regarding the analysis results of the behavioral characteristics of scattered dust, according to the inflow flow rate of the coal storage shed, when the wind speed is the lowest at 1.0 m/s, about 14.5% of the dust is discharged outside. As the flow rate increases, the amount of scattered dust also increases. For 2.0 m/s and 6.0 m/s flow velocities, 50.6% and 92.1% of scattered dust are discharged to the outside, respectively. If the flow rate is slow, it stagnates at the top of the dust point. However, if the flow rate is high, the emissions increase over the central retaining wall, and most dust is emitted outside.

Verification of Results
In order to verify the results of the CFD analysis of the indoor coal pit, it is necessary to check the flow field visually. The flow visualization experiment was used to obtain flow information by visualizing transmission phenomena such as speed, pressure, and density. Among various flow visualization experiments, the tomographic technique is an experiment that acquires flow information from a cross-section formed by a laser. In this study,

Verification of Results
In order to verify the results of the CFD analysis of the indoor coal pit, it is necessary to check the flow field visually. The flow visualization experiment was used to obtain flow information by visualizing transmission phenomena such as speed, pressure, and density. Among various flow visualization experiments, the tomographic technique is an experiment that acquires flow information from a cross-section formed by a laser. In this study, flow information was acquired using the tomographic method. Then, using the visualization result, it was compared qualitatively with the CFD simulation result. The experimental visualization device is manufactured to visualize the flow field that occurs according to the change in flow rate. Figures 10 and 11 below explain the experimental setup and photos. Using acrylic, we made a scaled model of the indoor coal yard with a scale of 1/180, implementing natural ventilation (window, coal transfer port, monitor louver). We installed a wind fan in front of the experimental device to realize the external wind, and changed the wind speed by adjusting the fan's RPM and installing a flow stabilizer in front of the fan. Then, a smoke generator was installed at the louver entrance on the first floor of the indoor coal storage shed. Smoke from a smoke generator passed through a cross-section formed by a laser. At this time, the formed flow field was visualized, and compared with the CFD result.
1/180, implementing natural ventilation (window, coal transfer port, monitor louver). We installed a wind fan in front of the experimental device to realize the external wind, and changed the wind speed by adjusting the fan's RPM and installing a flow stabilizer in front of the fan. Then, a smoke generator was installed at the louver entrance on the first floor of the indoor coal storage shed. Smoke from a smoke generator passed through a cross-section formed by a laser. At this time, the formed flow field was visualized, and compared with the CFD result.   front of the fan. Then, a smoke generator was installed at the louver entrance on the first floor of the indoor coal storage shed. Smoke from a smoke generator passed through a cross-section formed by a laser. At this time, the formed flow field was visualized, and compared with the CFD result.   The Reynolds number must be compared to verify the two results. M. Vallikivi et al. [32] analyzed a very high Reynolds number's turbulent flow study; statistically similar results were derived at 20,000 or more. As a result of both comparisons, a qualitative comparison was possible, because both were flow fields with Reynolds numbers of 20,000 or more. The experimental conditions and analysis boundary conditions are described in Table 7 below. The experiment was a reduced model of 1/180 ratio, and the inflow flow rate was 6.2 m/s. The inflow flow rate of the analysis result was 2.0 m/s. The results of analyzing the flow field derived from the experiment are as follows. The air introduced from the louver on the first floor rose through the coal slope, and was discharged to the monitor louver. A recirculation area was generated above the louver on the first floor, and a stagnant area was developed above the central wall. These results were qualitatively consistent with the simulation results. According to the simulation results, the concentration of carbon monoxide was high in the stagnant area above the central wall. Therefore, in order to improve the ventilation system, it was necessary to increase the amount of ventilation or consider the central wall flow dead area. Results louver on the first floor rose through the coal slope, and was discharged to the monitor louver. A recirculation area was generated above the louver on the first floor, and a stagnant area was developed above the central wall. These results were qualitatively consistent with the simulation results. According to the simulation results, the concentration of carbon monoxide was high in the stagnant area above the central wall. Therefore, in order to improve the ventilation system, it was necessary to increase the amount of ventilation or consider the central wall flow dead area.

Improvement of Ventilation System
In this section, a plan to improve the ventilation system is proposed by synthesizing the simulation results. The effect of the improvement plan was analyzed using CFD simulation. First, in order to further secure the amount of ventilation, the plan to install an additional natural ventilation device was analyzed. Solar power generation panels were installed on the roof of the indoor coal yard. Therefore, the area where additional louvers could be installed was limited. In this study, an additional louver was applied to the ceiling; it was 23.0 m long and 1.8 m wide. A total of 22 additional louvers were applied, and the plan to use a mobile blower was analyzed. The flow rates of the mobile blower were 10 m/s and 20 m/s. If additional oxygen is supplied to the fire point, the fire will likely expand. Therefore, the blower applied a plan to avoid the spontaneous ignition occurrence point. The boundary conditions for analyzing the improvement plan of the ventilation system are described in Table 8. louver on the first floor rose through the coal slope, and was discharged to the monitor louver. A recirculation area was generated above the louver on the first floor, and a stagnant area was developed above the central wall. These results were qualitatively consistent with the simulation results. According to the simulation results, the concentration of carbon monoxide was high in the stagnant area above the central wall. Therefore, in order to improve the ventilation system, it was necessary to increase the amount of ventilation or consider the central wall flow dead area.

Improvement of Ventilation System
In this section, a plan to improve the ventilation system is proposed by synthesizing the simulation results. The effect of the improvement plan was analyzed using CFD simulation. First, in order to further secure the amount of ventilation, the plan to install an additional natural ventilation device was analyzed. Solar power generation panels were installed on the roof of the indoor coal yard. Therefore, the area where additional louvers could be installed was limited. In this study, an additional louver was applied to the ceiling; it was 23.0 m long and 1.8 m wide. A total of 22 additional louvers were applied, and the plan to use a mobile blower was analyzed. The flow rates of the mobile blower were 10 m/s and 20 m/s. If additional oxygen is supplied to the fire point, the fire will likely expand. Therefore, the blower applied a plan to avoid the spontaneous ignition occurrence point. The boundary conditions for analyzing the improvement plan of the ventilation system are described in Table 8.

Result of comparison results
louver on the first floor rose through the coal slope, and was discharged to the monitor louver. A recirculation area was generated above the louver on the first floor, and a stagnant area was developed above the central wall. These results were qualitatively consistent with the simulation results. According to the simulation results, the concentration of carbon monoxide was high in the stagnant area above the central wall. Therefore, in order to improve the ventilation system, it was necessary to increase the amount of ventilation or consider the central wall flow dead area.

Improvement of Ventilation System
In this section, a plan to improve the ventilation system is proposed by synthesizing the simulation results. The effect of the improvement plan was analyzed using CFD simulation. First, in order to further secure the amount of ventilation, the plan to install an additional natural ventilation device was analyzed. Solar power generation panels were installed on the roof of the indoor coal yard. Therefore, the area where additional louvers could be installed was limited. In this study, an additional louver was applied to the ceiling; it was 23.0 m long and 1.8 m wide. A total of 22 additional louvers were applied, and the plan to use a mobile blower was analyzed. The flow rates of the mobile blower were 10 m/s and 20 m/s. If additional oxygen is supplied to the fire point, the fire will likely expand. Therefore, the blower applied a plan to avoid the spontaneous ignition occurrence point. The boundary conditions for analyzing the improvement plan of the ventilation system are described in Table 8.

Improvement of Ventilation System
In this section, a plan to improve the ventilation system is proposed by synthesizing the simulation results. The effect of the improvement plan was analyzed using CFD simulation. First, in order to further secure the amount of ventilation, the plan to install an additional natural ventilation device was analyzed. Solar power generation panels were installed on the roof of the indoor coal yard. Therefore, the area where additional louvers could be installed was limited. In this study, an additional louver was applied to the ceiling; it was 23.0 m long and 1.8 m wide. A total of 22 additional louvers were applied, and the plan to use a mobile blower was analyzed. The flow rates of the mobile blower were 10 m/s and 20 m/s. If additional oxygen is supplied to the fire point, the fire will likely expand. Therefore, the blower applied a plan to avoid the spontaneous ignition occurrence point. The boundary conditions for analyzing the improvement plan of the ventilation system are described in Table 8.
The results for the improvement plans of ventilating the coal storage shed were analyzed. And the simulation results are shown in Figure 12. Case 4-1 was a comparative case in which the ventilation system improvement plan was not applied. When the louver was additionally installed, there was no significant difference in the concentration result of carbon monoxide inside. Additional ventilation could be secured, but carbon monoxide on the central wall could not be emitted. The result of applying the mobile blower was very effective. In particular, the concentration of carbon monoxide in the workspace on the second floor decreased sharply. The blower could dilute carbon monoxide and further secure the amount of ventilation; when the speed of the blower was 20 m/s, the concentration of carbon monoxide in the workspace on the second floor was insignificant, and the concentration of carbon monoxide was less than 10 ppm on the third floor. As a result, in order to improve the ventilation performance of the coal storage shed, a method of using a mobile blower was the most effective.  The results for the improvement plans of ventilating the coal storage shed were analyzed. And the simulation results are shown in Figure 12. Case 4-1 was a comparative case in which the ventilation system improvement plan was not applied. When the louver was additionally installed, there was no significant difference in the concentration result of carbon monoxide inside. Additional ventilation could be secured, but carbon monoxide on the central wall could not be emitted. The result of applying the mobile blower was very effective. In particular, the concentration of carbon monoxide in the workspace on the second floor decreased sharply. The blower could dilute carbon monoxide and further secure the amount of ventilation; when the speed of the blower was 20 m/s, the concentration of carbon monoxide in the workspace on the second floor was insignificant, and the concentration of carbon monoxide was less than 10 ppm on the third floor. As a result, in order to improve the ventilation performance of the coal storage shed, a method of using a mobile blower was the most effective.

Conclusions
This study analyzed the internal flow and ventilation characteristics of the indoor coal storage shed of a coal-fired power plant using CFD. In addition, the behavior of a large amount of harmful gas generated during spontaneous coal combustion in a coal storage shed was analyzed. The results were combined to identify the hazardous areas of a field workspace.
In conclusion, an analysis was conducted of the internal flow characteristics and ventilation volume considering the location of the coal storage shed. As the flow rate of the outside air increased, the upper recirculation strength increased, and a stagnant area was  The results for the improvement plans of ventilating the coal storage shed were analyzed. And the simulation results are shown in Figure 12. Case 4-1 was a comparative case in which the ventilation system improvement plan was not applied. When the louver was additionally installed, there was no significant difference in the concentration result of carbon monoxide inside. Additional ventilation could be secured, but carbon monoxide on the central wall could not be emitted. The result of applying the mobile blower was very effective. In particular, the concentration of carbon monoxide in the workspace on the second floor decreased sharply. The blower could dilute carbon monoxide and further secure the amount of ventilation; when the speed of the blower was 20 m/s, the concentration of carbon monoxide in the workspace on the second floor was insignificant, and the concentration of carbon monoxide was less than 10 ppm on the third floor. As a result, in order to improve the ventilation performance of the coal storage shed, a method of using a mobile blower was the most effective.

Conclusions
This study analyzed the internal flow and ventilation characteristics of the indoor coal storage shed of a coal-fired power plant using CFD. In addition, the behavior of a large amount of harmful gas generated during spontaneous coal combustion in a coal storage shed was analyzed. The results were combined to identify the hazardous areas of a field workspace.
In conclusion, an analysis was conducted of the internal flow characteristics and ventilation volume considering the location of the coal storage shed. As the flow rate of the outside air increased, the upper recirculation strength increased, and a stagnant area was  The results for the improvement plans of ventilating the coal storage shed were analyzed. And the simulation results are shown in Figure 12. Case 4-1 was a comparative case in which the ventilation system improvement plan was not applied. When the louver was additionally installed, there was no significant difference in the concentration result of carbon monoxide inside. Additional ventilation could be secured, but carbon monoxide on the central wall could not be emitted. The result of applying the mobile blower was very effective. In particular, the concentration of carbon monoxide in the workspace on the second floor decreased sharply. The blower could dilute carbon monoxide and further secure the amount of ventilation; when the speed of the blower was 20 m/s, the concentration of carbon monoxide in the workspace on the second floor was insignificant, and the concentration of carbon monoxide was less than 10 ppm on the third floor. As a result, in order to improve the ventilation performance of the coal storage shed, a method of using a mobile blower was the most effective.

Conclusions
This study analyzed the internal flow and ventilation characteristics of the indoor coal storage shed of a coal-fired power plant using CFD. In addition, the behavior of a large amount of harmful gas generated during spontaneous coal combustion in a coal storage shed was analyzed. The results were combined to identify the hazardous areas of a field workspace.
In conclusion, an analysis was conducted of the internal flow characteristics and ventilation volume considering the location of the coal storage shed. As the flow rate of the outside air increased, the upper recirculation strength increased, and a stagnant area was The results for the improvement plans of ventilating the coal storage shed were analyzed. And the simulation results are shown in Figure 12. Case 4-1 was a comparative case in which the ventilation system improvement plan was not applied. When the louver was additionally installed, there was no significant difference in the concentration result of carbon monoxide inside. Additional ventilation could be secured, but carbon monoxide on the central wall could not be emitted. The result of applying the mobile blower was very effective. In particular, the concentration of carbon monoxide in the workspace on the second floor decreased sharply. The blower could dilute carbon monoxide and further secure the amount of ventilation; when the speed of the blower was 20 m/s, the concentration of carbon monoxide in the workspace on the second floor was insignificant, and the concentration of carbon monoxide was less than 10 ppm on the third floor. As a result, in order to improve the ventilation performance of the coal storage shed, a method of using a mobile blower was the most effective.

Conclusions
This study analyzed the internal flow and ventilation characteristics of the indoor coal storage shed of a coal-fired power plant using CFD. In addition, the behavior of a large amount of harmful gas generated during spontaneous coal combustion in a coal storage shed was analyzed. The results were combined to identify the hazardous areas of a field workspace.
In conclusion, an analysis was conducted of the internal flow characteristics and ventilation volume considering the location of the coal storage shed. As the flow rate of the outside air increased, the upper recirculation strength increased, and a stagnant area was

Conclusions
This study analyzed the internal flow and ventilation characteristics of the indoor coal storage shed of a coal-fired power plant using CFD. In addition, the behavior of a large amount of harmful gas generated during spontaneous coal combustion in a coal storage shed was analyzed. The results were combined to identify the hazardous areas of a field workspace.
In conclusion, an analysis was conducted of the internal flow characteristics and ventilation volume considering the location of the coal storage shed. As the flow rate of the outside air increased, the upper recirculation strength increased, and a stagnant area was generated around the central wall. Fluid stagnation occurred near the central wall in the same flow visualization test result to verify the simulation. In the same way as the flow visualization experiment to verify the simulation, flow stagnation occurred in the area near the central wall. Based on these results, when a louver is additionally installed to increase the ventilation amount, it is necessary to consider erasing the flow congestion area of the two-story workspace.
According to the analysis of the ventilation per hour in the low-carbon field, at the maximum speed, the ventilation volume was 13.1 ACH, and at the minimum speed, the ventilation volume was 4.4 ACH. About 51.9% of the natural ventilation emissions of the coal storage shed were discharged to the upper monitor louver. Therefore, the additional installation of the upper monitor louver effectively increased the natural ventilation in the coal storage shed.
Next, the characteristics of the concentration distribution of carbon monoxide generated during spontaneous coal ignition were analyzed. When the inflow velocity was 6 m/s, sufficient ventilation was secured, and carbon monoxide was diluted inside through the inflow of outside air. In this case, no area exceeded the dangerous standard concentration, except the point where spontaneous ignition occurred and the point near the coal pile. However, for an inflow velocity of 2.0 m/s, considering the previously derived ventilation rate of 4.4 ACH, it was possible to identify hazardous areas of 30 ppm or more in the workspace on the second floor, and the area near the central wall.
This study assumed that spontaneous ignition occurred in one specific cell. If spontaneous ignition occurs in multiple cells simultaneously, the risk area of more than 30 ppm of carbon monoxide is highly likely to expand. Therefore, it is essential to prepare for the case in which ventilation is sharply decreased due to decreased outdoor air inflow and spontaneous ignition occurring in many cells. In addition, it is deemed necessary to secure the ventilation volume by installing additional natural ventilation facilities.
The behavioral characteristics of the scattered coal dust in the coal storage shed were analyzed. The discharge characteristics of scattered coal dust in the coal storage shed changed according to the wind direction and speed. If outside air flowed in from the direction in which the coal dust was generated, the coal dust discharged to the monitor louver by the rising airflow, which also increased. However, the emissions of scattered dust were reduced due to the central wall when ambient air was introduced in the opposite direction of the coal drop point. In addition, 19.1% of the coal dust was emitted with an incoming wind speed of 1.0 m/s, and most dust was discharged at 6.0 m/s. A method for improving the ventilation performance of the coal storage shaded was analyzed. The plan to additionally install louvers had little effect in areas where carbon monoxide was high, and it was confirmed that the plan to use a mobile blower was very effective. Carbon monoxide generated from coal can be diluted, and it is effective to emit carbon monoxide by increasing the amount of natural ventilation. One thing to note is that using a blower at the point of spontaneous ignition is likely to supply oxygen and expand the fire. Therefore, it is necessary to consider operating the blower to avoid spontaneous ignition points.