Research on Hierarchical Control Strategy of AC / DC Hybrid Microgrid Based on Power Coordination Control

: The AC / DC hybrid microgrid has a large-scale and complex control process. It is of great signiﬁcance and value to design a reasonable power coordination control strategy to maintain the power balance of the system. Based on hierarchical control, this paper designs a reasonable power coordination control strategy for AC / DC hybrid microgrid. For lower control, this paper designs a variety of control modes for each converter in di ﬀ erent application scenarios. For the higher control, this paper analyzes the working mode of the system and designs the power coordination control strategy under the grid-connected and isolated island mode. In grid-connected operation, the DC bus voltage can be stabilized by adjusting the operation mode of the DC energy storage and the on-o ﬀ of the secondary load. In isolated island operation, the DC sub-microgrid is the main microgrid, and the DC energy storage is the main power regulating equipment. This is based on the principle of “energy is in short supply in the system, DC energy storage ﬁnally discharge, energy supply exceeds demand in the system, DC energy storage gives priority to charging” of DC energy storage. By adjusting the control strategy of the micro-source, the reference power, and the on-o ﬀ of the secondary load, the overall power balance is maintained. The Matlab / Simulink simulation software was used to build the AC / DC hybrid microgrid simulation model, which veriﬁed the e ﬀ ectiveness and stability of the proposed power coordination control strategy under various operating conditions.


Introduction
With the continuous update and development of science and technology, especially the continuous improvement of power electronic interface technology and modern automatic control theory, a small power generation, distribution, and electricity system "microgrid" has been formed, which integrates distributed generation (DG), energy management system, and load [1]. Whether it is AC microgrid or DC microgrid, when AC load and DC load coexist, a large number of converters are needed in the microgrid for electrical energy conversion, which will cause a certain amount of energy waste and increase economic costs [2]. The typical AC/DC hybrid microgrid is composed of AC subsystem, DC subsystem, and interlinking converter (ILC) [3]. The AC load and DC load can be connected to AC bus and DC bus, respectively, which can greatly reduce the number of power electronic converters and reduce unnecessary power loss. It is considered to be the mainstream structure of microgrid in the future.
The AC/DC hybrid microgrid can solve the problem of power conversion of the load because it contains one or more interlinking converters, various forms of DG, and energy storage units. How to reasonably control each power electronic converters to ensure the stability of the microgrid system has always been the research focus of experts and scholars.
The rest of the article is shown below. Section 2 introduces the topology and control framework of the AC/DC hybrid microgrid studied in this paper. Section 3 establishes each unit model and analyzes the control strategy of the lower converter. Section 4 describes the power coordination control strategy of the AC/DC hybrid microgrid designed in this paper under the condition of gridconnection and isolated island. Section 5 describes related experiments and analyzes the experimental results. Finally, Section 6 concludes.

System Topology of AC/DC Hybrid Microgrid
The AC/DC hybrid microgrid system studied in this paper belongs to a typical topology structure [15], including AC sub-microgrid, DC sub-microgrid, and interlinking converter, and the system is incorporated into the public grid by the AC bus. Its topology is shown in Figure 1. It can be seen from Figure 1 that in the DC sub-microgrid, a group of photovoltaic units is connected to the DC bus by Boost converter, and the other group of batteries is connected to the DC bus by Boost/Buck converter as DC energy storage. In the AC sub-microgrid, a group of photovoltaic units is connected to the AC bus through the Boost converter and DC/AC converter, and a group of batteries is connected to the AC bus as AC storage energy through Boost/Buck converter and bidirectional AC/DC converter. In order to increase the capacity of power flow between submicrogrids, two parallel bidirectional AC/DC interlinking converters are placed in the middle of the system as a bridge to connect the two sub-microgrids.

Hierarchical Control Architecture of AC/DC Microgrid
Hierarchical control refers to the microgrid control technology that uniformly manages the lower converter and load through the higher central controller [16]. Based on this, for AC/DC hybrid microgrid systems, the factors to be considered in isolate mode and grid-connected mode are often different. For example, in grid-connected operation, due to the support of the public power grid, it is not necessary to consider the voltage and frequency regulation of the AC bus. However, the voltage and frequency of the AC bus must be kept stable when performing isolated island operation. Furthermore, the lower converter often needs to prepare multiple control modes to switch or adjust in different situations. The control architecture adopted in this paper is shown in Figure 2. It can be seen from Figure 1 that in the DC sub-microgrid, a group of photovoltaic units is connected to the DC bus by Boost converter, and the other group of batteries is connected to the DC bus by Boost/Buck converter as DC energy storage. In the AC sub-microgrid, a group of photovoltaic units is connected to the AC bus through the Boost converter and DC/AC converter, and a group of batteries is connected to the AC bus as AC storage energy through Boost/Buck converter and bidirectional AC/DC converter. In order to increase the capacity of power flow between sub-microgrids, two parallel bidirectional AC/DC interlinking converters are placed in the middle of the system as a bridge to connect the two sub-microgrids.

Hierarchical Control Architecture of AC/DC Microgrid
Hierarchical control refers to the microgrid control technology that uniformly manages the lower converter and load through the higher central controller [16]. Based on this, for AC/DC hybrid microgrid systems, the factors to be considered in isolate mode and grid-connected mode are often different. For example, in grid-connected operation, due to the support of the public power grid, it is not necessary to consider the voltage and frequency regulation of the AC bus. However, the voltage and frequency of the AC bus must be kept stable when performing isolated island operation. Furthermore, the lower converter often needs to prepare multiple control modes to switch or adjust in different situations. The control architecture adopted in this paper is shown in Figure 2. Appl. Sci. 2020, 10, x FOR PEER REVIEW 4 of 24 In the DC sub-microgrid, when the DC side photovoltaic #1 is connected to the grid, in order to provide more power and make full use of solar energy resources, it generally works at maximum power point tracking (MPPT) mode [17]. During isolate island operation, the DC side photovoltaic #1 can be controlled by MPPT. However, when the generating power of the system is greater than the limit of its own consumable power, it is not suitable to work at the maximum power point. Therefore, the power-DC bus voltage ( dc P U − ) droop control is adopted to limit its power output [18]. When the DC side battery #1 is connected to the grid, the method of bus constant voltage control can be adopted to maintain the DC bus voltage stability with the interlinking converter, or it can also be charged at a constant voltage within its own tolerance. When isolating island operation, in addition to constant voltage control, the DC side battery #1 usually adopts droop control and photovoltaic #1 to regulate DC bus voltage and increase system autonomy. In addition, the state of charge ( SOC ) of the battery is also a key factor to be considered in the design of control strategy and to avoid overcharge or overdischarge [19].
In the AC sub-microgrid, when connected to the grid, the AC side photovoltaic #2 needs to be controlled by MPPT as well as the DC side photovoltaic #1, and the AC side battery #2 can be control charging according to its SOC constant power (P/Q). In isolated island, when the overall power consumption of the system is low, the AC side photovoltaic #2 and battery #2 can adopt P/Q control to achieve the supply and demand balance of AC side power and reduce the working frequency of the interlinking converter.
In this paper, two parallel interlinking converters are used to exchange power between the AC and DC sub-microgrids. In the grid-connected mode, constant voltage control and DC side energy storage units are used to maintain the DC bus voltage stability. In isolated island mode, constant voltage and constant frequency (V/F) control is adopted to regulate the AC bus voltage and frequency.

Photovoltaic Power Generation Unit Model and Control Strategy
The photovoltaic cell is the smallest unit of a photovoltaic array. It is a kind of semiconductor device that uses the photovoltaic effect to convert light energy into electric energy directly [20]. When the light intensity is constant, the photo-generated current is basically constant, so it can be equivalent to a constant current source. When the photo-generated current passes through the load, the terminal voltage will be formed on the load. This voltage will cause the positive-negative (PN) junction to be forward-biased and generate the dark current that is opposite to the photo-generated current. At the In the DC sub-microgrid, when the DC side photovoltaic #1 is connected to the grid, in order to provide more power and make full use of solar energy resources, it generally works at maximum power point tracking (MPPT) mode [17]. During isolate island operation, the DC side photovoltaic #1 can be controlled by MPPT. However, when the generating power of the system is greater than the limit of its own consumable power, it is not suitable to work at the maximum power point. Therefore, the power-DC bus voltage (P − U dc ) droop control is adopted to limit its power output [18]. When the DC side battery #1 is connected to the grid, the method of bus constant voltage control can be adopted to maintain the DC bus voltage stability with the interlinking converter, or it can also be charged at a constant voltage within its own tolerance. When isolating island operation, in addition to constant voltage control, the DC side battery #1 usually adopts droop control and photovoltaic #1 to regulate DC bus voltage and increase system autonomy. In addition, the state of charge (SOC) of the battery is also a key factor to be considered in the design of control strategy and to avoid overcharge or overdischarge [19].
In the AC sub-microgrid, when connected to the grid, the AC side photovoltaic #2 needs to be controlled by MPPT as well as the DC side photovoltaic #1, and the AC side battery #2 can be control charging according to its SOC constant power (P/Q). In isolated island, when the overall power consumption of the system is low, the AC side photovoltaic #2 and battery #2 can adopt P/Q control to achieve the supply and demand balance of AC side power and reduce the working frequency of the interlinking converter.
In this paper, two parallel interlinking converters are used to exchange power between the AC and DC sub-microgrids. In the grid-connected mode, constant voltage control and DC side energy storage units are used to maintain the DC bus voltage stability. In isolated island mode, constant voltage and constant frequency (V/F) control is adopted to regulate the AC bus voltage and frequency.

Photovoltaic Power Generation Unit Model and Control Strategy
The photovoltaic cell is the smallest unit of a photovoltaic array. It is a kind of semiconductor device that uses the photovoltaic effect to convert light energy into electric energy directly [20]. When the light intensity is constant, the photo-generated current is basically constant, so it can be equivalent to a constant current source. When the photo-generated current passes through the load, the terminal voltage will be formed on the load. This voltage will cause the positive-negative (PN) junction to be forward-biased and generate the dark current that is opposite to the photo-generated current. At the same time, because the material of the photovoltaic panel itself has a certain resistivity, it is equivalent to a resistor R s connected in series with a constant current source. In the manufacturing process, process defects will cause leakage current of photovoltaic panels. In order to eliminate errors, parallel resistance R sh is introduced [21]. Combined with the above analysis, the equivalent physical circuit model of the photovoltaic cell is shown in Figure 3.
Appl. Sci. 2020, 10, x FOR PEER REVIEW 5 of 24 same time, because the material of the photovoltaic panel itself has a certain resistivity, it is equivalent to a resistor s R connected in series with a constant current source. In the manufacturing process, process defects will cause leakage current of photovoltaic panels. In order to eliminate errors, parallel resistance sh R is introduced [21]. Combined with the above analysis, the equivalent physical circuit model of the photovoltaic cell is shown in Figure 3. In practical application, it is difficult to determine some parameters in the physical circuit model shown in Figure 3. Therefore, the engineering model is generally adopted [22]. Equation (1) is shown as follow: where s N and p N are the series and parallel number of photovoltaic cells.
In this paper, both photovoltaic #1 and photovoltaic #2 use perturbation and observation method (Perturbation and Observation, P&O) to realize MPPT control [23]. This method uses a fixed step size to reduce or increase the input reference voltage of the converter, thereby moving the operating point In practical application, it is difficult to determine some parameters in the physical circuit model shown in Figure 3. Therefore, the engineering model is generally adopted [22]. Equation (1) is shown as follow: where C 1 and C 2 are defined as: where I sc is the short-circuit current of the photovoltaic cell under standard test conditions, U oc is the open-circuit voltage, I m is the maximum power point current, and U m is the maximum power point voltage.
The voltage of a single photovoltaic cell is relatively low. So, in practice application, it is often necessary to connect multiple photovoltaic units in series to form a photovoltaic array. When the output voltage and current of the photovoltaic cell are U and I, respectively, the output voltage U pv_array and I pv_array current of the photovoltaic array are expressed as: where N s and N p are the series and parallel number of photovoltaic cells.
In this paper, both photovoltaic #1 and photovoltaic #2 use perturbation and observation method (Perturbation and Observation, P&O) to realize MPPT control [23]. This method uses a fixed step size to reduce or increase the input reference voltage of the converter, thereby moving the operating point closer to the maximum power point. Compared with other MPPT methods, the P&O method requires fewer sensors, has lower calculation complexity, and is simple to implement. The control strategy of DC side photovoltaic unit photovoltaic #1 is shown in Figure 4.
Appl. Sci. 2020, 10, x FOR PEER REVIEW 6 of 24 closer to the maximum power point. Compared with other MPPT methods, the P&O method requires fewer sensors, has lower calculation complexity, and is simple to implement. The control strategy of DC side photovoltaic unit photovoltaic #1 is shown in Figure 4.  Figure 4. The DC side photovoltaic #1 control strategy.
As can be seen from Figure 4 that in photovoltaic #1, in addition to MPPT control, in order to improve the autonomous ability or power-limited operation during isolated island operation, this paper adds droop control pv dc dc P U − , which can be expressed as: When MPPT is controlled, it may happen that the power generated by the system is greater than the maximum consumable power. In this paper, P/Q control is considered as an alternative control in the control of photovoltaic #2. The control strategy of photovoltaic power generation unit photovoltaic #2 on the AC side is shown in Figure 5.  Figure 4. The DC side photovoltaic #1 control strategy.
As can be seen from Figure 4 that in photovoltaic #1, in addition to MPPT control, in order to improve the autonomous ability or power-limited operation during isolated island operation, this paper adds droop control P pv dc − U dc , which can be expressed as: where U dc is the DC bus measurement voltage, U ref dc is the reference voltage of the DC bus, P pv dc is the measured output power of the DC side photovoltaic #1, P pv_ref dc is the reference output power of the DC side photovoltaic #1, k 1 is the voltage-power droop coefficient, When MPPT is controlled, it may happen that the power generated by the system is greater than the maximum consumable power. In this paper, P/Q control is considered as an alternative control in the control of photovoltaic #2. The control strategy of photovoltaic power generation unit photovoltaic #2 on the AC side is shown in Figure 5.
closer to the maximum power point. Compared with other MPPT methods, the P&O method requires fewer sensors, has lower calculation complexity, and is simple to implement. The control strategy of DC side photovoltaic unit photovoltaic #1 is shown in Figure 4.  Figure 4. The DC side photovoltaic #1 control strategy.
As can be seen from Figure 4 that in photovoltaic #1, in addition to MPPT control, in order to improve the autonomous ability or power-limited operation during isolated island operation, this paper adds droop control pv dc dc P U − , which can be expressed as: When MPPT is controlled, it may happen that the power generated by the system is greater than the maximum consumable power. In this paper, P/Q control is considered as an alternative control in the control of photovoltaic #2. The control strategy of photovoltaic power generation unit photovoltaic #2 on the AC side is shown in Figure 5. Figure 5. The AC side photovoltaic #2 control strategy.

Battery Energy Storage Unit Model and Control
The relationship between the internal parameters of the battery is complex, and there is a nonlinear relationship between these parameters. So, the modeling of the storage battery is also the research Appl. Sci. 2020, 10, 7603 7 of 22 focus of relevant experts. For the convenience of modeling, the general basic model is selected in this paper. Its physical circuit model is shown in Figure 6, which is formed by the controlled voltage source and an equivalent internal resistance in series [24].

Battery Energy Storage Unit Model and Control
The relationship between the internal parameters of the battery is complex, and there is a nonlinear relationship between these parameters. So, the modeling of the storage battery is also the research focus of relevant experts. For the convenience of modeling, the general basic model is selected in this paper. Its physical circuit model is shown in Figure 6, which is formed by the controlled voltage source and an equivalent internal resistance in series [24]. In this paper, the "Battery" module in Matlab/Simulink is selected as the model of battery energy storage unit, and the lithium-ion (Lithium-Ion) battery model is used. When the controlled voltage source is discharged, the unload voltage is: When the controlled voltage source is charged, the unload voltage is: where b attery R is the equivalent internal resistance of the battery.
In this paper, the battery energy storage units are connected to the AC and DC sub-microgrids. When connected to the public grid, the DC side battery mainly works with the interlinking converter to maintain the DC bus voltage stability, and the constant voltage charging is used when the battery charge is low. In the isolated island, the droop discharge is used to stabilize the DC bus voltage within a certain range. If the photovoltaic unit power generation power is greater than the power In this paper, the "Battery" module in Matlab/Simulink is selected as the model of battery energy storage unit, and the lithium-ion (Lithium-Ion) battery model is used. When the controlled voltage source is discharged, the unload voltage is: When the controlled voltage source is charged, the unload voltage is: where, I * battery = I battery dt is the actual charge and discharge capacity of the battery, U 0 is the rated voltage of the battery, k is the polarization voltage, Q is the battery capacity, A is the voltage drop in the exponential domain, B is the reciprocal of the time constant in the exponential domain.
The output voltage and SOC are two important variables of the battery. For the general basic model, they are defined as: SOC= 100 where R battery is the equivalent internal resistance of the battery. In this paper, the battery energy storage units are connected to the AC and DC sub-microgrids. When connected to the public grid, the DC side battery mainly works with the interlinking converter to maintain the DC bus voltage stability, and the constant voltage charging is used when the battery charge is low. In the isolated island, the droop discharge is used to stabilize the DC bus voltage within a certain range. If the photovoltaic unit power generation power is greater than the power consumption, the constant voltage control charging of the DC bus is required. In addition, to protect the battery, the SOC charge and discharge threshold should be set.
The battery #1 of the DC side battery energy storage unit is connected to the DC bus through a Boost/Buck circuit, and its control strategy is shown in Figure 7.
Appl. Sci. 2020, 10, x FOR PEER REVIEW 8 of 24 consumption, the constant voltage control charging of the DC bus is required. In addition, to protect the battery, the SOC charge and discharge threshold should be set. The battery #1 of the DC side battery energy storage unit is connected to the DC bus through a Boost/Buck circuit, and its control strategy is shown in Figure 7. Figure 7. The DC side battery #1 control strategy.
In Figure 7, the droop control of battery #1 can be expressed as: where, dc The control strategy of battery #2 in the AC side battery energy storage unit is shown in Figure  8. The voltage is boosted by the Boost/Buck circuit, then connected to the AC bus through a bidirectional DC/AC converter and filter circuit. The power instruction of the central controller is received during operation, adopting P/Q control to absorb or output power. In Figure 7, the droop control of battery #1 can be expressed as: where, U dc is the DC bus measurement voltage, U ref dc is the DC bus reference voltage, P bat dc is the measured output power of the DC side battery #1, P bat_ref dc is the reference output power of the DC side battery #1, k 2 is the voltage-power droop coefficient. When battery #1 is in rechargeable and dischargeable mode, P bat_ref When battery #1 can only be discharged, P bat_ref The control strategy of battery #2 in the AC side battery energy storage unit is shown in Figure 8. The voltage is boosted by the Boost/Buck circuit, then connected to the AC bus through a bidirectional DC/AC converter and filter circuit. The power instruction of the central controller is received during operation, adopting P/Q control to absorb or output power.

Interlinking Converter Model and Control
The interlinking converter is a key module to connect AC sub-microgrid and DC sub-microgrid. In this paper, the interlinking converter adopts a three-phase pulse width modulation (PWM) converter. In order to increase the power exchange capacity, the two converters are connected in parallel. The main circuit topology of the interlinking converter used in this paper is shown in Figure   Figure 8. The AC side battery #2 control strategy.

Interlinking Converter Model and Control
The interlinking converter is a key module to connect AC sub-microgrid and DC sub-microgrid. In this paper, the interlinking converter adopts a three-phase pulse width modulation (PWM) converter. In order to increase the power exchange capacity, the two converters are connected in parallel. The main circuit topology of the interlinking converter used in this paper is shown in Figure 9 [25].

Interlinking Converter Model and Control
The interlinking converter is a key module to connect AC sub-microgrid and DC sub-microgrid. In this paper, the interlinking converter adopts a three-phase pulse width modulation (PWM) converter. In order to increase the power exchange capacity, the two converters are connected in parallel. The main circuit topology of the interlinking converter used in this paper is shown in Figure  9 [25].
In this paper, the interlinking converter adopts different control strategies in grid-connected and island modes. When connected to the grid, the voltage and frequency of the AC bus are stable, so constant voltage control (unit power factor control) is adopted to maintain the DC bus voltage. In isolated island, V/F control is used to control and stabilize the voltage and frequency of the AC bus. The control strategy of a single interlinking converter in this paper is shown in Figure 10. In this paper, the interlinking converter adopts different control strategies in grid-connected and island modes. When connected to the grid, the voltage and frequency of the AC bus are stable, so constant voltage control (unit power factor control) is adopted to maintain the DC bus voltage. In isolated island, V/F control is used to control and stabilize the voltage and frequency of the AC bus. The control strategy of a single interlinking converter in this paper is shown in Figure 10. Figure 10. Interlinking converter control strategy diagram.

Multi-System Mode Power Coordination Control Strategy in Grid-Connected Operation
In grid-connected operation, the AC bus is directly connected to the public power grid, and its voltage and frequency will remain stable. Therefore, this section focuses on adjusting the DC bus voltage. For the DC sub-microgrid, it is necessary to maintain the power balance together with the photovoltaic power generation unit photovoltaic #1, the energy storage unit battery #1, and the interlinking converter on the DC side. In order to maximize the utilization of solar energy resources, photovoltaic power generation units will operate in MPPT mode. Besides, to maintain the DC bus voltage stability, the interlinking converter adopts DC bus constant voltage control.
To maintain the DC bus voltage, the DC side battery #1 and the interlinking converter need to work together, and the state of charge is an important factor to determine whether the battery can be charged or discharged. Therefore, the state of charge SOC of battery #1 is taken as an important

Multi-System Mode Power Coordination Control Strategy in Grid-Connected Operation
In grid-connected operation, the AC bus is directly connected to the public power grid, and its voltage and frequency will remain stable. Therefore, this section focuses on adjusting the DC bus voltage. For the DC sub-microgrid, it is necessary to maintain the power balance together with the photovoltaic power generation unit photovoltaic #1, the energy storage unit battery #1, and the interlinking converter on the DC side. In order to maximize the utilization of solar energy resources, photovoltaic power generation units will operate in MPPT mode. Besides, to maintain the DC bus voltage stability, the interlinking converter adopts DC bus constant voltage control.
To maintain the DC bus voltage, the DC side battery #1 and the interlinking converter need to work together, and the state of charge is an important factor to determine whether the battery can be charged or discharged. Therefore, the state of charge SOC dc of battery #1 is taken as an important basis for the division of system mode; the maximum value is SOC max dc and the minimum value is SOC min dc . At the same time, since the photovoltaic power generation unit operates in MPPT mode, the power P pv dc emitted by the DC side photovoltaic #1 is constant under steady-state, and the power P load dc absorbed by the DC load when the voltage is stable and also constant. Therefore, the balance between the two is also one of the bases for the division of system mode. The power P net dc of the DC sub-microgrid is defined as: In addition, for the interlinking converters, the transmission direction from the AC side to the DC side is set to be positive, the maximum conversion power of a single interlinking converter is P max ILC , and the maximum conversion power of two parallel converters is P max ILCs = 2 × P max ILC . Therefore, the actual conversion power P ILCs of the two interlinking converters will also be referred to in the system mode division. In summary, the operation mode is analyzed according to the situation: (1) SOC dc ≥ SOC max dc At this time, the DC side battery #1 has reached the maximum charged state, can only discharge. When P net dc ≥ 0, the DC load is not enough to consume the power generated by the DC side photovoltaic #1. In order to protect the battery, battery #1 should be in a standby state, and the excess power generated by photovoltaic #1 should be transmitted to the public grid by an interlinking converter. The power balance relationship can be expressed as: where P ILCs ≤ 0, the interlinking converter is in the inverter state. When P net dc < 0, the generation power of photovoltaic #1 on the DC side is greater than the consumption power of the load, resulting in the DC bus voltage drop. For faster adjustment to stabilize the DC bus voltage, battery #1 should be in the DC bus constant voltage mode and adjust the DC bus voltage to the rated value together with the interlinking converter. The power relationship at balancing is as follow: P pv dc + P ILCs + P bat dc = P load dc , where P bat dc > 0 indicates the output power of battery #1 and P ILCs > 0 indicates that the interlinking converter is in a rectified state.
In addition, even in the situation of grid-connection, the load power on the DC bus cannot be allowed to increase indefinitely because the interlinking converter capacity is constant. Therefore, when P net dc < 0 and P ILCs > P max ILCs , the secondary load on the DC side should be cut off to protect the normal operation of the converter.
(2) SOC dc ≤ SOC min dc This situation indicates that the DC side battery #1 has reached the minimum charged state and cannot continue discharging, but it can be charged. The battery should be switched to a constant voltage charging state, limiting its maximum current to be no greater than 0 and charging at rated voltage, and the power balance relationship can be expressed as: where P bat dc < 0 indicates that the DC side battery #1 absorbs power. Although the DC side battery #1 is in constant voltage charging mode at this time, the power source is different. When P net dc > 0, it means that although the battery power is low, the output power of the photovoltaic unit is sufficient to meet the demand of the DC load. Therefore, on the premise that the interlinking converter maintains the DC bus voltage, battery #1 can absorb the excess power generated by the photovoltaic unit at a constant voltage. When P net dc < 0, the internal power supply of the DC sub-microgrid is scarce, but the capacity of the interlinking converter does not reach the rated value and battery #1 can still absorb power from the public grid in a constant voltage charging state. If P ILCs > P max ILCs , first put battery #1 in the standby state, and then continue to determine whether the interlinking converter is overloaded. If so, remove the DC load, otherwise, it will operate normally. ( In this mode, the DC side battery #1 is in the normal range of charging and discharging. When P net dc > 0, the running state at this time is the same as SOC dc ≤ SOC min dc . Because battery #1 is charged at a constant voltage. Then SOC dc will be greater than the minimum threshold, the power balance relationship can also be expressed as (13). When P net dc < 0, the system running state under this condition is the same as SOC dc ≥ SOC max dc . Because battery #1 constant DC bus voltage discharge, after a period of time, SOC dc will fall below the maximum threshold, and the power balance relationship can also be expressed as (12).
Based on the above analysis, this paper divides the control strategy of the whole AC/DC hybrid microgrid system into multiple modes during grid-connected operation. The central controller needs to send commands to the lower converter in accordance with the power coordination control strategy to ensure the normal flow of power, as shown in Figure 11.
Appl. Sci. 2020, 10, x FOR PEER REVIEW 12 of 24 discharge, after a period of time, dc SOC will fall below the maximum threshold, and the power balance relationship can also be expressed as (12). Based on the above analysis, this paper divides the control strategy of the whole AC/DC hybrid microgrid system into multiple modes during grid-connected operation. The central controller needs to send commands to the lower converter in accordance with the power coordination control strategy to ensure the normal flow of power, as shown in Figure 11.

Multi-System Mode Power Coordination Control Strategy in Isolated Island Operation
In isolated island operation, the whole AC/DC hybrid microgrid system does not have the support of the public power grid, and the power balance of the entire system needs to be considered during control, so the control process is more complex than when it is connected to the grid. This paper adopts the mode of DC sub-microgrid as the main micro-grid, and the interlinking converter needs to work in the V/F control mode to maintain the voltage and frequency stability of the AC bus. In order to improve the utilization rate of solar energy, the DC side photovoltaic #1 will be in MPPT mode at the initial moment. The AC side photovoltaic #2 can work in MPPT or P/Q control mode. Moreover, the AC side energy storage unit battery #2 works in P/Q control mode. At the same time, battery #2 is regarded as an energy storage device with rated charging and discharging power, regardless of its SOC. During operation, the control mode of battery #1 should be switched according to the power balance state. Meanwhile, the reference power of photovoltaic #2 and battery #2 should

Multi-System Mode Power Coordination Control Strategy in Isolated Island Operation
In isolated island operation, the whole AC/DC hybrid microgrid system does not have the support of the public power grid, and the power balance of the entire system needs to be considered during control, so the control process is more complex than when it is connected to the grid. This paper adopts the mode of DC sub-microgrid as the main micro-grid, and the interlinking converter needs to work in the V/F control mode to maintain the voltage and frequency stability of the AC bus. In order to improve the utilization rate of solar energy, the DC side photovoltaic #1 will be in MPPT mode at the initial moment. The AC side photovoltaic #2 can work in MPPT or P/Q control mode. Moreover, the AC side energy storage unit battery #2 works in P/Q control mode. At the same time, battery #2 is regarded as an energy storage device with rated charging and discharging power, regardless of its SOC. During operation, the control mode of battery #1 should be switched according to the power balance state. Meanwhile, the reference power of photovoltaic #2 and battery #2 should be adjusted. When the system is overloaded, the secondary load should be cut off.
Since the DC sub-microgrid is the main microgrid, the charging state of DC side battery #1 is still an important basis for operation mode analysis. The power P net island of the hybrid AC/DC microgrid in isolated island is defined as: where P load ac is the absorbed power of the AC load and P pv ac is the output power of the AC side photovoltaic #2.
According to the SOC operating mode in isolated island, the analysis is as follow: The DC side battery #1 reaches the maximum power and cannot continue to charge. If P net island ≥ 0, the power generated by DG in the whole microgrid system is greater than the total power consumed by the AC and DC side loads, so measures need to be taken to reduce the power generated. First, we should consider whether AC side battery #2 can be used for charging to maintain power balance. If the rated output power of battery #2 is P bat_N ac > P net island , then battery #2 can be used to absorb excess power. At this time, set the reference power P bat_ref ac of battery #2 as: If the AC side battery #2 cannot absorb excess power, consider adjusting the output power of the photovoltaic unit. If photovoltaic #2 is in P/Q control mode at this time, then the reference power P pv_ref ac needs to be adjusted as: If the AC side photovoltaic #2 is in MPPT mode, then adjust the DC side photovoltaic #1 to limit power droop control. The final power balance relationship is: P pv ac + P pv dc + P bat ac = P load ac + P load dc .
When P net island < 0, it means that the generating power of the system micro source is not enough to maintain the normal operation of the system load. Therefore, first, the DC-side battery needs to be in P bat dc − U dc droop control output power. Then, judge whether the AC side battery #2 can meet the system vacant power. If so, in order to reduce the output of battery #1, set P bat_ref ac reference (15). If the rated power of the AC side battery #2 is P bat_N ac < −P net island , then the DC side battery #1 output power is required and its rated power is set to P bat_N dc . If the combined output of battery #1 and battery #2 can meet the vacant power, then the system can remain stable. When P bat_N ac + P bat_N dc + P net island ≥ 0, the system will be in a new equilibrium state, and the power balance relationship is: If the joint output of the AC and DC batteries cannot meet the vacant power, the system is overloaded and the secondary load needs to be cut off.
(2) SOC dc ≤ SOC min dc In this state, the DC side battery #1 cannot continue to discharge. When P net island ≥ 0, set battery #1 to constant voltage control mode. Due to the system power redundancy, the DC bus voltage will increase, so battery #1 will start charging. If P net island − P bat_N dc ≤ 0, it means that the excess power can be absorbed into the battery within the rated power of battery #1. At this time, the power balance state can be expressed as: In the situation of P net island − P bat_N dc > 0, the AC side battery #2 is also required to absorb power.
When P net island − P bat_N ac − P bat_N dc ≤ 0, it means that when the batteries on the AC and DC sides absorb the excess power together, the system can reach a new balance. At this time, P bat_ref ac should be set to: where the minimum value of P bat_ref ac is 0. When P net island − P bat_N ac − P bat_N dc > 0, it means that the power generated by the micro-source is too much. At this time, the processing method is the same as when SOC dc ≥ SOC max dc . The AC side battery #2 absorbs power at rated power. When the AC side photovoltaic #2 is in P/Q mode, P pv_ref ac should be set to: P pv_ref ac If P net island < 0, then the DC side battery #1 cannot continue to discharge. Therefore, it is necessary to refer to whether the AC side battery #2 can meet the vacant power of the system. If so, then set its reference power as shown in (15). If not, the secondary load needs to be cut off. ( In this mode, the DC side battery #1 can both charge and discharge. When P net island > 0, the system running state is the same as SOC dc ≤ SOC min dc . Conversely, when P net island < 0, the system running state is the same as SOC dc ≥ SOC max dc . In summary, the power coordination control strategy of the AC/DC hybrid microgrid when off-grid is formulated is shown in Figure 12.
Appl. Sci. 2020, 10 where the minimum value of b a t_ re f a c P is 0.
If net islan d 0 P < , then the DC side battery #1 cannot continue to discharge. Therefore, it is necessary to refer to whether the AC side battery #2 can meet the vacant power of the system. If so, then set its reference power as shown in (15). If not, the secondary load needs to be cut off. In summary, the power coordination control strategy of the AC/DC hybrid microgrid when offgrid is formulated is shown in Figure 12.

Simulation Analysis
In order to verify the effectiveness of the power control strategy designed in this paper in the hybrid microgrid, the simulation control model as shown in Figure 1 was built in Matlab/Simulink. The basic parameters in the simulation system are shown in Table 1, in which the power is active power.

Simulation of Power Control Strategy in Grid-Connected Operation
Since the AC bus is directly connected to the public power grid during the grid-connected operation, the changes of the power, voltage, frequency, and other values of the AC side microgrid are not analyzed.
(1) Case 1 When the system works in grid-connected mode, the DC side photovoltaic #1 and the AC side photovoltaic #2 work in MPPT mode. The initial SOC of the DC side battery #1 is set to 10%, the AC side battery #2 works in P/Q control mode, and the initial SOC is 90%. The active power of the AC load is 50 kW and remains unchanged. The interlinking converter works in the DC bus constant voltage control mode.
During the operation of the system, the ambient temperature remains unchanged at 25 • C, the initial light intensity is 1000 W/m 2 , and the DC load power is 2 kW. At 2 s, the light intensity was reduced to 800 W/m 2 . At 3 s, the DC load power increased to 8 kW, and at 6 s, the light intensity continued to decrease to 600 W/m 2 , while the DC load power continued to increase to 14 kW. The simulation results are shown in Figure 13.
As can be seen from Figure 13c, at the beginning of the system operation, if the DC side battery #1 is discharged, and the state of charge will instantly fall below the minimum threshold of 10%. Therefore, the system will operate according to the situation of SOC dc ≤ SOC min dc in Figure 11, where battery #1 will be charged at a constant voltage. Appl. Sci. 2020, 10  As can be seen from Figure 13c, at the beginning of the system operation, if the DC side battery #1 is discharged, and the state of charge will instantly fall below the minimum threshold of 10%. Therefore, the system will operate according to the situation of min dc dc SOC SOC ≤ in Figure 11, where battery #1 will be charged at a constant voltage.
According to Figure 13a, form 0 s to2 s, the DC side photovoltaic #1 will work in the standard environment with an output power reaching 18 k W and the DC load power reaching 2 k W , resulting in net dc 0 P > . The excess power of the DC sub-microgrid will be absorbed by the DC side battery #1, but its charging power will not reach the maximum value soon, and the battery charging current will increase slowly. Therefore, the power flowing to the large power grid through the According to Figure 13a, form 0 s to2 s, the DC side photovoltaic #1 will work in the standard environment with an output power reaching 18 kW and the DC load power reaching 2 kW, resulting in P net dc > 0. The excess power of the DC sub-microgrid will be absorbed by the DC side battery #1, but its charging power will not reach the maximum value soon, and the battery charging current will increase slowly. Therefore, the power flowing to the large power grid through the interlinking converter gradually decreases. From 2 s to 3 s, the light intensity decreases, and the output power of DC side photovoltaic #1 is about 14 kW. At this time, the load power remains unchanged, and the charging power of DC side battery #1 continues to increase, so the power transmitted from the interlinking converter to the public grid is getting less and less. At 2.5 s, the power of the interlinking converter changes from negative to positive, and the power generated by DC side photovoltaic #1 is not enough to maintain battery #1 charging and load consumption. From 3 s to 6 s, the light intensity is unchanged, and the load power is increased to 8 kW. At 3.2 s, the charging power of battery #1 on the DC side reaches the maximum value, about 21 kW, so the power of the interlinking converter is also stable at about 15 kW. From 6 s to 8 s, the DC load power continues to increase to 14 kW, while the DC side photovoltaic #1 output power decreases to 10 kW, resulting in P net dc < 0. Furthermore, the power of DC side battery #1 is still below the minimum threshold and continues to be charged at a constant voltage. At this time, the absorbed power of the DC sub-microgrid is mainly provided by the interlinking converter from the public power grid, and about 25 kW, which does not reach its maximum transmission power. Figure 13b shows the DC bus voltage fluctuations, from which it can be seen that the voltage is stable at the rated value of 650 V at about 0.8 s. Due to the change of system power, there is a slight fluctuation at 2 s, 3 s, and 6 s, but the rated value is quickly restored.
(2) Case 2 When the temperature is kept at 25 • C and the light intensity is kept at 1000 W/m 2 , the system is connected to the grid, and the DC side photovoltaic #1 and AC side photovoltaic #2 work in MPPT mode. The initial SOC of DC side battery #1 is set to 95%. The initial conditions of AC side battery #2, interlinking converter, and AC load are the same as in case 1. At the initial moment of the system, the DC load power is 10 kW. At 3 s, the DC load power increases to 18 kW. At 6 s, the DC load continues to increase, and the power reaches 28 kW. According to the system setting, the charge state of DC side battery #1 is above the maximum threshold of 90% at this time, so the system will operate as SOC dc ≥ SOC max dc when connected to the grid. The simulation results are shown in Figure 14.
Appl. Sci. 2020, 10, x FOR PEER REVIEW 17 of 24 interlinking converter gradually decreases. From 2 s to 3 s, the light intensity decreases, and the output power of DC side photovoltaic #1 is about 14 k W . At this time, the load power remains unchanged, and the charging power of DC side battery #1 continues to increase, so the power transmitted from the interlinking converter to the public grid is getting less and less. At 2.5 s, the power of the interlinking converter changes from negative to positive, and the power generated by DC side photovoltaic #1 is not enough to maintain battery #1 charging and load consumption. From 3 s to 6 s, the light intensity is unchanged, and the load power is increased to 8 k W . At 3.2 s, the charging power of battery #1 on the DC side reaches the maximum value, about 21 k W , so the power of the interlinking converter is also stable at about 15 k W . From 6 s to 8 s, the DC load power continues to increase to 14 k W , while the DC side photovoltaic #1 output power decreases to 10 k W , resulting in net dc 0 P < . Furthermore, the power of DC side battery #1 is still below the minimum threshold and continues to be charged at a constant voltage. At this time, the absorbed power of the DC sub-microgrid is mainly provided by the interlinking converter from the public power grid, and about 25 k W , which does not reach its maximum transmission power. Figure 13b shows the DC bus voltage fluctuations, from which it can be seen that the voltage is stable at the rated value of 650 V at about 0.8 s. Due to the change of system power, there is a slight fluctuation at 2 s, 3 s, and 6 s, but the rated value is quickly restored.
(2) Case 2 When the temperature is kept at 25 °C and the light intensity is kept at 1000 2 W/m , the system is connected to the grid, and the DC side photovoltaic #1 and AC side photovoltaic #2 work in MPPT mode. The initial S O C of DC side battery #1 is set to 95%. The initial conditions of AC side battery #2, interlinking converter, and AC load are the same as in case 1. At the initial moment of the system, the DC load power is 10 k W . At 3 s, the DC load power increases to 18 k W . At 6 s, the DC load continues to increase, and the power reaches 28 k W . According to the system setting, the charge state of DC side battery #1 is above the maximum threshold of 90% at this time, so the system will operate as  As can be seen from Figure 14a that form 1 s to 3 s, the DC side photovoltaic #1 works under standard conditions, the output power reaches a maximum value of 18 k W , while the DC load power remains unchanged at 10 k W , that is, net dc 0 P > . However, the internal of the DC side battery #1 has exceeded the maximum threshold, so it cannot continue to charging, that is, it is in a standby state and the output power of 0 k W . All the excess power in the DC sub-microgrid is transmitted from the interlinking converter to the AC side, and the transmission power is −8 k W . From 3 s to 6 s, when the DC load power is increased to 18 k W , the power generation of DG in the DC sub-micro grid is just enough to meet the power consumption of the load,  As can be seen from Figure 14a that form 1 s to 3 s, the DC side photovoltaic #1 works under standard conditions, the output power reaches a maximum value of 18 kW, while the DC load power remains unchanged at 10 kW, that is, P net dc > 0. However, the internal of the DC side battery #1 has exceeded the maximum threshold, so it cannot continue to charging, that is, it is in a standby state and the output power of 0 kW. All the excess power in the DC sub-microgrid is transmitted from the interlinking converter to the AC side, and the transmission power is −8 kW. From 3 s to 6 s, when the DC load power is increased to 18 kW, the power generation of DG in the DC sub-micro grid is just enough to meet the power consumption of the load, P net dc = 0. So, the transmission power of DC side battery #1 and the interlinking converter is 0 kW. From 6 s to 8 s, the DC load power continues to increase by 10 kW to 28 kW. At this time, the output power of DC side photovoltaic #1 cannot meet the DC load, then P net dc < 0. The DC side battery #1 switches from standby mode to constant voltage mode to maintain the DC bus voltage with the interlinking converter and the output power is 2 kW. The transmitted power of the interlinking converter is 8 kW.
According to Figure 14b, the DC load power will increase at 3 s and 6 s, and the DC bus will decrease slightly. However, due to the constant voltage control of DC side battery #1 and the interlinking converter, the system quickly reaches a power balance state. As a result, the DC bus voltage will quickly stabilize to the rated value.

Simulation of Power Control Strategy in Isolate Island Operation
During the island operation, the overall power balance should be considered. At this time, the interlinking converter works in V/F control mode to provide voltage and frequency support for the AC bus.
(1) Case 1 The system works in island mode with a constant temperature of 25 • C, the DC side photovoltaic #1 works in MPPT mode, and the AC side photovoltaic #2 works in P/Q mode. The AC side photovoltaic #2 active power reference value is set to 16 kW, and the reactive output is set to 0 kVar. The SOC of DC side battery #1 and AC side battery #2 are both 85%, they operate in SOC min dc ≤ SOC dc ≤ SOC max dc mode in Figure 12. The DC load power is 10 kW, and the AC load active power is 20 kW. At the initial moment, the light intensity was 1000 W/m 2 . At 5 s, the light intensity decreased to 800 W/m 2 . The simulation results of active power flow in the system are shown in Figure 15.  As can be seen from Figure 15a that at the beginning of the system operation, the output power of DC side photovoltaic #1 reached 18 k W under standard conditions, and the output power of AC side photovoltaic #2 is 16 k W , which is 34 k W in total. At this time, the sum of the active power of AC load and DC load is 30 k W , then net island 0 P > . According to Figure 12, the DC side battery #1 works in constant voltage mode and can absorb the excess power of the system. Therefore, the active power reference value of AC side battery #2 is 0 k W , and the absorbed power of DC side battery #1 is about 3 k W . Form 5s to 8 s, the light intensity is reduced, and the output of DC side As can be seen from Figure 15a that at the beginning of the system operation, the output power of DC side photovoltaic #1 reached 18 kW under standard conditions, and the output power of AC side photovoltaic #2 is 16 kW, which is 34 kW in total. At this time, the sum of the active power of AC load and DC load is 30 kW, then P net island > 0. According to Figure 12, the DC side battery #1 works in constant voltage mode and can absorb the excess power of the system. Therefore, the active power reference value of AC side battery #2 is 0 kW, and the absorbed power of DC side battery #1 is about 3 kW. Form 5 s to 8 s, the , and the output of DC side photovoltaic #1 is reduced to 14 light intensity is reducedkW, then P net island = 0. Therefore, the active power reference value of AC side battery #2 is still 0 kW. However, due to system losses, DC side battery #1 still needs to maintain a power output of approximately 1 kW to stabilize the system.
The AC bus voltage and frequency curves are shown in Figure 16a,b, and the DC bus voltage curve is shown in Figure 16c.  According to Figure 16a,b, the voltage and frequency of the AC bus do no obviously fluctuate during 5 s, and the rated value is always maintained during system operation. As can be seen from Figure 16c, the DC bus voltage is maintained at the rated value of 650 V from 1 s to 5 s. At 5 s, due to the sudden decrease in light intensity, the output of DC side photovoltaic #1 will immediately decrease, while the DC side battery #1 will not immediately reduce its absorbed power. Therefore, the DC bus voltage will have a downward trend. When it falling to 622 V, the DC side battery #1 no longer absorbs power, so the DC bus voltage immediately returns to the rated value.
(2) Case 2 The system works in island mode, the ambient temperature is 25 °C, the light intensity is 1000 2 W/m , and the DC side photovoltaic #1 runs in MPPT mode. Moreover, the AC side photovoltaic #2 runs in P/Q mode, with the active power constant at 16 k W and reactive power output at 0 k V ar . The settings of the DC side battery #1 and the AC side battery #2 are the same as that of isolated island in case 1. At the initial moment, the DC load power is 20 , the AC load active power is According to Figure 16a,b, the voltage and frequency of the AC bus do no obviously fluctuate during 5 s, and the rated value is always maintained during system operation. As can be seen from Figure 16c, the DC bus voltage is maintained at the rated value of 650 V from 1 s to 5 s. At 5 s, due to the sudden decrease in light intensity, the output of DC side photovoltaic #1 will immediately decrease, while the DC side battery #1 will not immediately reduce its absorbed power. Therefore, the DC bus voltage will have a downward trend. When it falling to 622 V, the DC side battery #1 no longer absorbs power, so the DC bus voltage immediately returns to the rated value.
(2) Case 2 The system works in island mode, the ambient temperature is 25 • C, the light intensity is 1000 W/m 2 , and the DC side photovoltaic #1 runs in MPPT mode. Moreover, the AC side photovoltaic #2 runs in P/Q mode, with the active power constant at 16 kW and reactive power output at 0kVar. The settings of the DC side battery #1 and the AC side battery #2 are the same as that of isolated island in case 1. At the initial moment, the DC load power is 20 kW, the AC load active power is 50 kW, and the reactive power is 0 kVar. At 3 s, the active power of the AC load increases to 55 kW. At 6 s, the active power of the AC load continues to increase until it reaches 60 kW. The system active power flow simulation waveform is shown in Figure 17.  As can be seen from Figure 17a that at the initial moment of the system, the output power of the DC side photovoltaic #1 reaches a maximum value of 18 k W , and the actual output power of the AC side photovoltaic #2 is lower than the theoretical value, which is about 29 k W . The sum of the active power of the DC load and the AC load reaches 70 k W , that is, net island 0 P < . So, the DC side battery #1 is bat dc dc P U − droop control. At the same time, the active power deficit exceeds the rated power of AC side battery #2, so battery #2 maintains the rated power output of 10 k W , and the AC side is still unbalanced. As shown in Figure 17b, about 11 k W of active power is transmitted from the DC side to the AC side through the interlinking converter. At this time, in order to balance the power balance of the DC sub-microgrid and the AC sub-microgrid, the DC side battery #1 power output is about 14 k W .
At 3 s, the active power of the AC load increases to 55 k W , net island 0 P < remains unchanged, and the active power deficit increases. However, the DC side battery #1 and the AC side battery #2 still do not reach their rated output power, so they can continue to maintain the system balance. At this time, the DC side battery #1 output power is about 19 k W . As can be seen from Figure 17a that at the initial moment of the system, the output power of the DC side photovoltaic #1 reaches a maximum value of 18 kW, and the actual output power of the AC side photovoltaic #2 is lower than the theoretical value, which is about 29 kW. The sum of the active power of the DC load and the AC load reaches 70 kW, that is, P net island < 0. So, the DC side battery #1 is P bat dc − U dc droop control. At the same time, the active power deficit exceeds the rated power of AC side battery #2, so battery #2 maintains the rated power output of 10 kW, and the AC side is still unbalanced. As shown in Figure 17b, about 11 kW of active power is transmitted from the DC side to the AC side through the interlinking converter. At this time, in order to balance the power balance of the DC sub-microgrid and the AC sub-microgrid, the DC side battery #1 power output is about 14 kW. At 3 s, the active power of the AC load increases to 55 kW, P net island < 0 remains unchanged, and the active power deficit increases. However, the DC side battery #1 and the AC side battery #2 still do not reach their rated output power, so they can continue to maintain the system balance. At this time, the DC side battery #1 output power is about 19 kW.
At 6 s, the active power of the AC load continues to increase by 5 kW and the DC side battery #1 reaches the rated output power is still not enough to maintain the system balance. Therefore, it is necessary to cut off the secondary load of 10 kW on the DC side. The load power on the DC side is reduced to 10 kW, and the DC side battery #1 output power is about 14 kW. Meanwhile, according to Figure 17b, the power entering the AC sub-microgrid is about 21 kW. The DC bus voltage in this mode is shown in Figure 18. As can be seen from Figure 17a that at 3 s, the active power of the AC load increases, and the DC side battery #1 will not be discharged to the power balance state immediately. Therefore, at 3 s in Figure 18, the DC bus will drop to about 620 V and then rise back to the rated voltage of 650 V, the system power balance. At 6 s, the DC bus voltage will decrease due to the continuous increase of AC load active power. However, when the whole AC/DC microgrid system is overloaded, the secondary load of 10 kW on the DC side will be cut off. At this time, because the output of DC side battery #1 will not change immediately, the DC bus voltage will rise to 705 V, and then it will drop to the rated voltage. In the whole process, the deviation of the DC bus voltage is within ±10%, which meets the requirements of allowable deviation of power quality supply voltage [26].

Conclusions
In this paper, the operation mode of the AC/DC hybrid microgrid is analyzed in detail, and the power coordinated control strategy of grid-connected operation and island operation is designed. In grid-connected operation, it is based on the control of the interlinking converter of the DC bus constant voltage. To stabilize the DC bus voltage, adjust the operating mode of DC energy storage and control the on-off of secondary loads by referring to the charged state of DC energy storage, the power balance state of DC microgrid, and the maximum transmitted power of interlinking converters. In the island operation, DC sub-microgrid is the main microgrid, DC energy storage is the main power regulation equipment, and based on the principle of "energy is in short supply in the system, DC energy storage finally discharge, energy supply exceeds demand in the system, DC energy storage gives priority to charging" of DC energy storage. In order to maintain the balance of the overall power, the control strategy of the micro-source, the reference power, and the on-off of the secondary load should be adjusted by referring to the charged state of DC energy storage, the overall power balance state of the system, and the operation mode of each micro-source. Finally, the higher control, analysis, and integration of system data and reasonable control of each converter control strategy change make the reliable and stable operation of the system. The lower control integrates various control strategies of the converter, improves the flexibility of the system, realizes the reasonable distribution of power under different modes, and reduces the consumption of energy.
In this paper, the switching mode of the bidirectional converter mode is carried out under ideal conditions without considering the switching dynamics. At the same time, system design is a steadystate process, and the study of the transient process will become our research direction in the following steps. As can be seen from Figure 17a that at 3 s, the active power of the AC load increases, and the DC side battery #1 will not be discharged to the power balance state immediately. Therefore, at 3 s in Figure 18, the DC bus will drop to about 620 V and then rise back to the rated voltage of 650 V, the system power balance. At 6 s, the DC bus voltage will decrease due to the continuous increase of AC load active power. However, when the whole AC/DC microgrid system is overloaded, the secondary load of 10 kW on the DC side will be cut off. At this time, because the output of DC side battery #1 will not change immediately, the DC bus voltage will rise to 705 V, and then it will drop to the rated voltage. In the whole process, the deviation of the DC bus voltage is within ±10%, which meets the requirements of allowable deviation of power quality supply voltage [26].

Conclusions
In this paper, the operation mode of the AC/DC hybrid microgrid is analyzed in detail, and the power coordinated control strategy of grid-connected operation and island operation is designed. In grid-connected operation, it is based on the control of the interlinking converter of the DC bus constant voltage. To stabilize the DC bus voltage, adjust the operating mode of DC energy storage and control the on-off of secondary loads by referring to the charged state of DC energy storage, the power balance state of DC microgrid, and the maximum transmitted power of interlinking converters. In the island operation, DC sub-microgrid is the main microgrid, DC energy storage is the main power regulation equipment, and based on the principle of "energy is in short supply in the system, DC energy storage finally discharge, energy supply exceeds demand in the system, DC energy storage gives priority to charging" of DC energy storage. In order to maintain the balance of the overall power, the control strategy of the micro-source, the reference power, and the on-off of the secondary load should be adjusted by referring to the charged state of DC energy storage, the overall power balance state of the system, and the operation mode of each micro-source. Finally, the higher control, analysis, and integration of system data and reasonable control of each converter control strategy change make the reliable and stable operation of the system. The lower control integrates various control strategies Appl. Sci. 2020, 10, 7603 21 of 22 of the converter, improves the flexibility of the system, realizes the reasonable distribution of power under different modes, and reduces the consumption of energy.
In this paper, the switching mode of the bidirectional converter mode is carried out under ideal conditions without considering the switching dynamics. At the same time, system design is a steady-state process, and the study of the transient process will become our research direction in the following steps.