Application of Composite Pre-Polymerized Coagulants for the Treatment of High-Strength Industrial Wastewaters

The aim of this study was the investigation of alternative pre-polymerized coagulants for the treatment of high-strength industrial wastewaters, such as those created by tanneries, or by yeast production industries. The novel inorganic composite coagulant examined in this study (as well as variations of it) was denoted as PSiFAC1.5-10-15. The contribution of a typical polyelectrolyte to improve the effectiveness of the coagulation/flocculation (C/F) process was additionally studied, either by adding it separately (i.e., as a flocculant aid) or by co-polymerizing it within the structure of inorganic coagulant (denoted as PAPEFAC1.5-10-15). It was found that the PSiFAC1.5:10:15 coagulant, either with or without the addition of polyelectrolyte, can provide better efficiency for the C/F process than the conventional coagulants. For example, the addition of 80 mg Al/L in yeast production wastewater samples resulted in a 56% reduction of COD, 40% of turbidity, and 43% of phosphates, regarding the pre-treated anaerobically wastewater samples and reduced by an extra 22%, 14%, and 38% for the pre-treated anaerobically plus aerobically wastewater samples, respectively. The residual aluminum concentration in the treated wastewaters was found to be below the legislation limit of 200 μg Al/L. The characterization of coagulants showed the relatively higher Al13 content of 51% and 43% for the cases of PSiFAC1.5-10-15 and PAPEFAC1.5-10-15, respectively, accompanied by the high zeta-potential measurements (50.5 and 39.5 mV).


Introduction
Domestic and industrial wastewaters can contain large concentrations of recalcitrant compounds, whereas their treatment by the application of biological processes in several cases was not found to be adequately effective, resulting in a treated effluent of rather low quality, e.g., causing severe eutrophication problems after disposal due to the remaining quite high nutrient concentrations (among others). For this case, particularly important is the presence of phosphorous (usually in the form of orthophosphates), which has to be efficiently removed (or recovered), especially from certain industrial wastewaters [1][2][3], noting that phosphorus can be removed from waters/wastewaters either biologically or (more effectively) by the addition of appropriate chemical agents [4].
In several wastewater treatment installations, the supplementary post-chemical treatment is commonly required to meet the respective strict effluent quality standards, especially regarding the discharge (i.e., the final permissible/legislative concentrations) of phosphorus. Membrane filtration is an attractive option to remove the chemically precipitated phosphorus, but this process can be impeded by the commonly encountered fouling of the membrane surface, mainly due to the usual Al (III), Fe (III), and poly-silicic acid solution (pSi), whereas the coagulation efficiency of produced composite poly-aluminum-ferric-silicate-chloride is mainly affected by the Al/Fe/Si ratio and the respective preparation (i.e., inorganic polymerization) techniques.
Additionally, synthetic organic polyelectrolytes have already been utilized to enhance the C/F process for water or wastewater treatment applications for more than four decades already. Due to the fact of their wide usage, they are considered also as alternative additives in the pre-polymerized coagulants for the production of new, modified composite coagulation reagents [24]. In previous studies, the use of pre-polymerized coagulants, based on iron or aluminum, was examined and found quite efficient for several water or wastewater applications, regarding, for example, the removal of turbidity [29,30], arsenic [31], fluoride [32], and the reduction of membrane fouling in MBR systems [33], producing also very low residual metal concentrations; this is also the case of PSiFAC product which is an aluminum-based pre-polymerized coagulant.
The aim of this study was the improvement of the effectiveness of C/F process, using the composite poly-aluminum-ferric-silicate-chloride coagulants and a common anionic polyelectrolyte (Magnafloc-LT 25) as the flocculant aid for the treatment of certain high-strength industrial wastewater samples. Furthermore, the combination of coagulant and polyelectrolyte in one reagent was also examined for comparison reasons in order to increase further their flocculation efficiency by replacing the inorganic poly-silicate additive with the organic polyelectrolyte in their structure. To the best of our knowledge, there are no published data regarding the use of composite pre-polymerized coagulants, considering the treatment of high-strength wastewaters, and this study is an alternative and possibly promising approach for the effective processing of such kind of wastes [29][30][31][32][33].
The specific properties of novel coagulants were investigated by examining the aluminum species distribution, employing the ferron technique. The structure and the morphology of composite coagulants were studied in detail by the application of FTIR, XRD, and SEM techniques and by z-potential measurements. To the best of our knowledge, these coagulants have never been applied for the treatment of high-strength industrial wastewaters, while the use of PAPEFAC (i.e., coagulant and polyelectrolyte co-polymerized and producing a new composite reagent) is reported for the first time in the literature.

Laboratory Procedure for the Preparation of Novel Composite Coagulants
Composite poly-aluminum-ferric-silicate-chloride (PSiFAC) coagulants were produced at room temperature (22 • C), according to the procedure proposed by   [30] under various experimental conditions and by applying different mixing orders of the used chemicals. All chemical reagents were of analytical pure chemical grade. The used initial solutions were: 0.5 M AlCl 3 ·6H 2 O (Merck), 0.5 M FeCl 3 ·6H 2 O (Merck), 0.5 M NaOH (Merck)-as the added base-and the prepared poly-silicic acid solution (pSi), according to Tzoupanos et al. (2009) [34]. The most effective coagulants and molar ratios obtained during preliminary experiments [30], such as PSiFAC 1.5-10-15 , were further examined in this study.
A solution of poly-acrylamide co-polymer (Magnafloc LT-25, Ciba SC LTD, commercially available), as a commonly used anionic polyelectrolyte (APE), was prepared (0.01% w/v) and used both as a separate flocculant aid (with [Al]/[APE] = 10, molar ratios) as well as the organic additive for the synthesis of new composite (inorganic-organic) coagulants (PAPEFAC). This specific polyelectrolyte is already widely applied as a flocculant aid in several water or wastewater treatment installations [35,36]. Table 1 presents the preparation conditions of all prepared and examined coagulants in this study.

Coagulation Experiments Performed by Jar-Tests
The experimental procedure was conducted using a jar-test apparatus (Aqualytic) equipped with six paddles, employing 1 L glass beakers. Under rapid stirring of 200 rpm, a predetermined amount of coagulants was dosed. After 3 min, the speed was changed to a slow stirring speed of 40 rpm for 30 min; after quiescent settling of 45 min, samples were collected from 5 cm below the surface. Three types of industrial high-strength wastewater samples were examined: (1) a tannery wastewater; (2) a yeast manufacturing wastewater, subjected to preliminary anaerobic treatment; (3) a (similar) yeast manufacturing wastewater which was also subjected to aerobic treatment (besides anaerobic). The major parameters of the examined samples are presented in Table 2. After the C/F treatment, samples were collected from the supernatant of each beaker and were analyzed for the determination of major pollution parameters, i.e, (a) turbidity (NTU), by using a HACH RATIO/XR Turbidimeter; (b) COD (mg/L) spectrophotometrically after the appropriate oxidation pre-treatment by using the Lange spectrophotometer; and (c) phosphates (mg/L) by the ascorbic acid method [37].

Physico-Chemical Properties
All prepared composite coagulants were characterized by measuring: (a) the pH value using a Metrohm Herisau pH-Meter; (b) the turbidity using a Hach ratio/XR Turbidity-meter; and (c) the conductivity using a Crison CM 35 conductivity meter.

Aluminum Species Distribution
The distribution of aluminum species was determined with the application of Al-ferron timed spectrophotometric method which was based on the different reaction time of aluminum species with ferron reagent (8-hydroxy-7-iodoquinoline-5-sulphonic acid) to form water soluble complexes. These complexes can absorb light (maximum at 370 nm); hence, the kinetic absorbance measurements at this wavelength may allow the calculation of three different (major) aluminum species (i.e., Al a -monomers, Al b -Al 13 and Al c -Al(OH) 3 ); a Hitachi UV/vis spectrophotometer was used for this purpose.

Scanning Electron Microscopy (SEM)
Small portions of coagulant powders were obtained after drying in an oven (~40 • C) and used to observe the morphology of respective products, by employing a ZEISS EVO 50 scanning microscope.

Fourier-Transform-Infrared Spectroscopy (FTIR)
The FTIR spectra of prepared composite products were recorded in the range of 4000-400 cm −1 using a Nicolet 380 FTIR Spectrometer-Thermo Scientific spectrophotometer to allow the observation of surface species and the possible polymeric interactions among the components.

X-ray Diffraction Spectroscopy (XRD)
X-ray diffraction spectroscopy (XRD) is an important tool for the identification of crystalline compounds, and it was applied to identify the possibly formed crystalline phases which are likely to be present in the prepared coagulants (such as Al 13 ). The Malvern Panalytical Xpert instrument (Cu-K radiation) was used, and the solid samples were analyzed in the range of 5-80 • 2θ with a scan rate of 1 • /min.

Zeta-Potential and Particle Size Measurements
The zeta-potential measurements were conducted with the ZETASIZER Nano-ZS (Malvern). For each (adjusted) pH value, three measurements of zeta-potential and the respective particle sizes were measured. The temperature was set at 20 • C. The particle sizes' distribution produced by each coagulant sample was calculated by assuming that their refractive index was equal to the refractive index of aluminum silicate. Dynamic light scattering (DLS) was used to measure the particle sizes of coagulants under different experimental conditions. This technique measures the diffusion of particles, moving under Brownian motion and converts this measurement to particle size and size distribution using the Stokes-Einstein relationship. Non-invasive back scatter technology (NIBS) was incorporated to give the highest sensitivity, simultaneously, with the highest size and concentrations range. The pH adjustments were conducted by using the MPT-2 Multi-Purpose Titrator (Malvern). The titration was necessary in order to scan (and maintain) the desirable pH range.
The z-potential measurements were performed by inserting a certain quantity of coagulant in deionized water and the instrument firstly is setting the pH value and then does the measurement. Then, the instrument sets a different pH value and measures again. It was not possible to insert actual wastewaters after the treatment in this instrument because all pipes, filters, etc., may be clogged and there would be several problems with the repeatability of measurements.
Furthermore, since the measurements were taking place using aqueous solutions of the examined coagulants, the obtained values were considered to be quite similar with the respective values expected if industrial wastewaters coagulation experiments were used for the specifically set (final) pH values.

Residual Aluminum Concentration
The residual aluminum concentration was determined by the Eriochrome cyanine R standard method [37]; dissolved aluminum ions react with Eriochrome cyanine R dye at pH 6, resulting in a colored compound with maximum absorbance at 535 nm. The detection limit of this method (MDL) was 6 µg/L. Table 3 displays the major physicochemical properties of laboratory prepared composite coagulants. It can be observed that the addition of poly-silicic acid (pSi) in the Al-Fe solution (denoted as FpA), when performed to induce the formation of composite coagulants, resulted in the increase of turbidity in comparison with the addition of anionic polyelectrolyte (APE) in the same FpA solution, i.e., the PSiFAC 1.5-10-15 and PAPEFAC 1.5-10-15 products had 211 and 137 NTU values, respectively. The mixing order of Al/Fe/Si components was also found to affect significantly the turbidity of products. Specifically, when Al was firstly added to pSi, i.e., to prepare the PSiFAC 1.5-10-15 product, the turbidity value was quite high (211 NTU), most likely due to the interaction between the chemical forms of Al and Si, as Duan and Gregory (1998) [38] suggested, arguing that in aqueous solutions, silicic acid can interact with the chemical forms of Al to form hydroxy-alumino-silicate complexes (HAS). Unlike the aforementioned case (i.e., regarding the product PSiFAC 1.5-10-15 ), when the mixing sequence was different (i.e., (Fe+pSi)+Al), as in the PAFSiC 1.5-15-10 product, the respective turbidity was found to be much lower (117 NTU), possibly because Si is firstly bound with Fe.

Major Physico-Chemical Properties of Prepared Coagulation Agents
From the results presented in Table 3, it appears that the mixing order of components may also affect the percentage of medium-sized forms of polymerized aluminum (i.e., Al b ), and the (desired) Al 13 content (specifically in the case of PSiFAC 1.5-10-15 ) was found to increase (i.e., Al 13 51%) as compared with the corresponding value of Al 13 (29%-32%) found in the laboratory-prepared PACl lab product (also confirmed by Yan et al. (2008) [39]); therefore, an improved product was obtained.
Finally, by studying the effect of polyelectrolyte addition on the composition of obtained product, it was found that the degree of polymerization and the content (%) of Al b , when using an anionic polyelectrolyte instead of poly-silicic acid, presented relatively higher values. Particularly, the two products, PAPEFAC 1.5-10-15 and PSiFAC 1.5-10-15 , based on the values in Table 3, exhibited the (desirable) highest percentage of medium-sized polymerized forms of aluminum (Al b ), favoring the formation of higher Al 13 content.

Structure Analysis
The possible chemical bonds, being present in the produced composite coagulants, were examined. Figure 1 illustrates the FTIR spectra of selected products, regarding the different mixing order of Al/Fe/Si components. All these spectra were found to exhibit two characteristic bonds at different wavelengths (i.e., at 3500-3300 cm −1 ) attributed to the stretching vibration of -OH and at 1641-1638 cm −1 , which can be attributed to the bending vibration of water absorbed, polymerized, and crystallized in the coagulant structure. The spectra of composite coagulants, corresponding to the stretching vibration of -OH bonds, was almost identical with the case PACl 1.5(lab) , (see the comparison in Figure S1).
As shown in Figure 1, the band at 1038 cm −1 was assigned to the asymmetric Si-O stretching vibrations of Si-O-Si bonds [40] which is indicative of the high polymerization degree of silica. In addition, there were two characteristic peaks: (a) at 1100 cm −1 that could be attributed to the asymmetric stretching vibration of Fe-O-Fe or Al-O-Al bonds [25] and (b) at 1080-980 cm −1 that can be assigned to symmetrical stretching vibrations of Si-O-Fe and Si-O-Al bonds [41,42], respectively. Moreover, the existence of stretching and bending vibrations of the Fe-OH-Fe or Al-OH-Al bonds, may indicate the presence of the respective polymers, formed in the samples, which can be proved also by the two strong absorption peaks at 1098-1100 and 831-833 cm −1 wavelengths (see also References [41,42]). It is obvious from Figure 1 that the mixing order had no effect on the relevant FTIR spectra, as rather similar peaks were detected. In Figure 2, the corresponding FTIR spectra comparing PSiFAC 1.5-10-15 with PAPEFAC 1.5-10-15 (which is the material containing the anionic polyelectrolyte in its structure, instead of poly-silicic acid) are presented. As it can be noticed, the latter material was found to present similar absorption bands with PSiFAC 1.5-10-15 and PACl 1.5(lab) , although the corresponding peaks were found to be more intensive.

Morphological Analysis
The comparison of the surface of the solid residue, which remains after drying of coagulants' solutions, could give useful information about the structural changes that possibly take place due to the addition of polysilicates and/or iron on the surface of PACl. Additionally, the further elemental analysis with the application of SEM/EDS of these samples, focusing on specific areas on the surface of the solid residues, is expected to contribute significantly to the better understanding of the nature (composition) and structure of the new coagulants. It is for this reason that the SEM images are presented in this article, i.e., contributing to the SEM/EDS atomic analysis of the obtained cubic crystals. Figure 3a illustrates the SEM images of dried samples, regarding the different mixing order of Al/Fe/Si components, whereas, for comparison reasons, the corresponding SEM image for PACl 1.5(lab) at Figure 3d is also presented. Several different morphologies were observed, the most predominant being a cubic-like morphology and a separate compact solid surface. Initially, these cubes were considered to be NaCl crystals, separated from the other constituents. However, further atomic analysis with the application of SEM/EDS, as presented in Table 4, revealed that these cubes consist from the sum of elements Na, Al, Si, O, Cl, and Fe (expressed as % w/w of the relative content). The low relative Na content and the significantly higher Cl content indicate that in addition to NaCl, other chemical forms can also be involved in the formation of these cubes such as various Al forms and perhaps alumino-silicates. In the case of PACl 1.5(lab) (prepared with [OH]/[Al] = 1.5 ratio), generally similar configurations were observed, i.e., cubic-shaped crystals and a distinct amorphous surface. According to the obtained results, PSiFAC 1.5-10-15 had the most compact form of all the materials examined in this case. It also had the highest content of Al, Fe, and Si and the lowest of Na compared to all other materials as defined by the application of chemical analysis with SEM/EDS (applied locally, i.e., in specific sites of the respective surfaces) which may indicate that the new coagulant PSiFAC 1.5-10-15 is a stable material, even after drying at 40 • C without any particular loss or change of its components. The presence of aluminum in the branches observed in the relevant SEM image can be considered an indication of the interactions between the chemical forms of aluminum, iron, and silicates.

X-ray Diffraction Spectroscopy (XRD)
From the XRD diagram of the PSiFAC 15-10-15 sample containing 51% Al b (after drying) and considered to be the relatively best product, three specific compounds were identified according to the respective database, i.e., sodium chloride (NaCl), aluminum chloride hexahydrate (AlCl 3 .6H 2 O), and a compound with 13 aluminum atoms (i.e., Al 13 Cl 15 (OH) 24 .37.5H 2 O) as illustrated in Figure 4. The crystallinity of this sample was scarcely apparent when observing the nature of the respective peaks. The high-intensity peaks showed relatively narrow widths which indicate a high degree of crystallinity, whereas the other, lower intensity peaks appeared to be wider. Particularly, NaCl is formed as a by-product during the reaction of neutralizing the aluminum solution by the addition of the alkaline solution. The XRD technique is particularly sensitive to crystalline NaCl formation due to the fact of its crystal size and structure which explains the high intensity peaks at 2θ angles 27 • , 32 • , 46 • , and 57 • . Aluminum chloride was also detected at very low concentrations as shown by the intensity of respective peaks. This particular coagulant, PSiFAC 15-10-15 , produced by a molecular ratio [OH]/[Al] = 1.5, means that the neutralization of aluminum solution was not complete. Therefore, a certain amount of the original AlCl 3 solution would not react as shown in the XRD diagram. Two of the three aforementioned compounds (i.e., NaCl and AlCl 3 ) were also identified by other researchers in the pre-polymerized aluminum-based coagulants [25], whereas the compound with 13 aluminum atoms was previously identified by Tzoupanos et al. (2009) [34].
A specific characteristic of Al 13 noticed during the XRD analysis was the appearance of relatively sharp peaks at low angles (5-35 • 2θ) with the respective chemical formula identified as Al 13 Cl 15 (OH) 24 ·37.5H 2 O. This identification was carried out after several tests, noting that the sensitivity of detection by the XRD technique was significantly affected by the presence of formed NaCl.

Z-Potential and Size Measurements
In Figure 4, the relevant comparison diagrams of the zeta-potential and particle size measurements of certain examined coagulants were presented; the values of initial pH samples, zeta-potential, particle sizes, and iso-electric points (IEPs) are displayed in Table 5. The applied coagulant dosage was the same (i.e., 10 mg Al/L in deionized water) for each coagulant. Figure 4 shows also that an increase in pH values can cause a reduction of z-potential values of the samples but an increase in the respective particle size. This is most likely attributed to the fact that the pH difference can result in the decrease of the positive charge of the formed particles which tend to be neutralized at the respective IEPs. Consequently, the overall negative charge is prevailing at pH values higher than IEP, causing the (desirable) destabilization of colloidal system. The PSiFAC 1.5-10-15 is the coagulant that presented the highest initial positive value of zeta-potential (i.e., 50.5 mV) [32], followed by PAPEFAC 1.5-10-15 (39.2 mV), and by PASiC 1.5-15 (similar 35.9 mV). The IEP values for these coagulants were 9.10, 9.56, and 9.40, respectively. Figure 5a shows that for all these coagulants, the IEP values were found to be greater than eight, which means that at lower pH values, an overall positive charge prevails, favoring the interaction of aluminum species with the (mainly) negatively charged components (e.g., phosphates) in wastewaters. The initial particle size of PSiFAC 1.5-10-15 [32] was approximately 189 nm, while the relative size of PAPEFAC 1.5-10-15 and PASiC 1.5-15 products was higher, i.e., 245 and 216 nm, respectively, and increased substantially as the pH value further rose. The results depict that all these chemical agents can be classified as nano-scale coagulants. Figure 5b shows that the size of PSiFAC 1.5-10-15 and PAPEFAC 1.5-10-15 particles/flocs increased drastically at pH values around 7.0 which is most likely attributed to the formation of Al(OH) 3 and Fe(OH) 3 precipitates, in comparison with PASiC 1.5-15 , which does not contain Fe, and its relevant size increased at (around) pH 9.

Tannery Wastewater
Initially, the poly-aluminum-ferric-silicate-chloride coagulants were compared in terms of turbidity removal ( Figure S2) in order to obtain the optimum mixing order of the component's Al/Fe/pSi. As it is shown, all these coagulants reduced the turbidity of the tannery wastewater sample for doses greater than 60 mg Al/L.
The most effective coagulant obtained, namely, PSiFAC 1.5-10-15 was further applied to tannery wastewater treatment, aiming to evaluate its efficiency for the treatment of a typical high-strength industrial wastewater. The results of coagulation experiments for the removal (%) of turbidity (expressed as NTU units), COD, and phosphates are shown in Figure S3. As it can be observed, PSiFAC 1.5-10-15 significantly reduced turbidity, COD, and phosphates for doses above 30 mg Al/L.
The main goal of this study was to examine the effectiveness of the coagulation/flocculation (C/F) process using the new composite poly-aluminum-ferric-silicate-chloride coagulants. Then, in an attempt to optimize the treatment, a flocculant aid, such as the typical anionic polyelectrolyte-APE, was also used to improve the treatment of this wastewater sample. The new material synthesized in this study, PAPEFAC 1.5-10-15 , which contains the anionic polyelectrolyte in its structure and is a combination of coagulant and polyelectrolyte in a single reagent, by replacing the inorganic poly-silicate additive with the organic polyelectrolyte, was also studied for comparative reasons.
In Figure 6, the results of the application of these materials to the removal of turbidity, COD, and phosphates, applying a coagulant dose of 30 mg Al/L, are shown. However, from the presented results, the addition of a common anionic polyelectrolyte, either as a separate flocculation aid/enhancer (i.e., PSiFAC 1.5-10-15 + APE) or as an additive in the respective product structure (i.e., as PAPEFAC 1.5-10-15 ) did not produce any specific improvement on PSiFAC 1.5-10-15 performance, except the additional benefit from the use of a single material which avoids the use of special equipment to handle separately the polyelectrolyte (e.g., weighting, dissolution, pumping, etc.). The results of this study present certain advantages over the relevant literature data, where substantially higher dosages are usually required, e.g., 800 mg/L [43] of aluminum sulfate for the treatment of tannery wastewater samples, providing 30%-37% removal of total COD, and more recently [44], when using (again) aluminum sulfate, the maximum removal (60%) was observed for the dose 350 mg/L; also, for the case of PACl, when using an initial concentration of 600 mg/L, turbidity and COD removals of 99.3% and 83.3% were found, respectively [45]. Finally, there are no data in the scientific literature for the use of composite pre-polymerized coagulants regarding the treatment of high-strength wastewaters.

Yeast Production Wastewater
The optimum coagulant obtained during the treatment of tannery wastewater sample as well as during previous relevant studies [30,32] (i.e., the PSiFAC 1.5-10-15 ) was also applied to treat the yeast production wastewater, examining two different samples (i.e., a yeast manufacturing wastewater, subjected to preliminary anaerobic treatment, and another sample which was supplementary subjected to aerobic treatment (besides the previous anaerobic)) aiming to evaluate its efficiency for the treatment of a typical high-strength difficult to be treated industrial wastewater. The results of coagulation experiments, regarding the removal (%) of turbidity (NTU), COD, and phosphates, are shown in Figure 7 for the sample subjected to preliminary anaerobic/aerobic treatment. As it can be observed from these results, PSiFAC 1.5-10-15 was found to enhance the removal rate, particularly of turbidity and orthophosphates, at doses greater than 50 mg Al/L. Attempting to optimize further the treatment of this wastewater (improve efficiency) and for comparison purposes, an anionic polyelectrolyte-APE was separately applied as flocculant aid together with the same coagulant, as well as: (a) the PAPEFAC 1.5-10-15 coagulant, which contained the anionic polyelectrolyte in its structure, (b) the PASiC 1.5-15 , which did not contain iron in its structure, and (c) the PACl 1.5(lab) , i.e., a pre-polymerized coagulant containing only aluminum, resembling a commercially available relevant product. In Figure S4, the results of the application of these materials for the removal of turbidity, COD, and phosphates with a coagulant dose of 80 mg Al/L are shown, regarding the treatment of both yeast production wastewater samples.
As depicted from the results of Figure S4, the addition of polyelectrolyte as a flocculant enhancer/aid was found to improve the efficiency of all applied coagulants, especially in the case of PASiC 1.5-15 . However, it is quite remarkable the fact that the addition of the PAPEFAC 1.5-10-15 coagulant, i.e., that incorporating also the polyelectrolyte into its structure, exhibited satisfactory removal rates, which suggests that it could also be used as a single reagent during wastewater treatment, i.e., without the need for special additional equipment for the handling the polyelectrolyte, thereby reducing the overall treatment costs.

Comparison of Industrial Wastewater Treatment Results
The comparative diagrams of industrial wastewater treatment using 80 mg Al/L of the best PSiFAC 1.5-10-15 coagulant product as well as of the PSiFAC 1.5-10-15 coagulant plus the separate APE addition and of the composite PAPEFAC 1.5-10-15 are shown in Figure 8, regarding the removal (%) of (a) turbidity, (b) COD, and (c) phosphates. The results showed that the addition of 80 mg Al/L of PSiFAC 1.5-10-15 to tannery wastewater sample, either with or without the supplement of a common anionic polyelectrolyte, acting as flocculant aid or incorporated in its structure, resulted in substantial reductions of COD (67%), turbidity (96%), and phosphates (62%). In addition, by applying these coagulants to the yeast production wastewater samples, the same dose resulted in a relatively lower reduction of COD (56%), turbidity (40%), and phosphates (43%) for the anaerobically pre-treated wastewater samples, whereas an even smaller reduction (i.e., COD 22%, turbidity 14%, and phosphate 38%), was noticed for the anaerobically and aerobically pre-treated wastewater samples. However, it is evident (Figure 8) that higher rates of turbidity removal, approaching 45%-50%, were obtained when the coagulant and the polyelectrolyte were combined in a single reagent (PAPEFAC 1.5-10-15 ), although regarding the reduction of COD, the use of PSiFAC 1.5-10-15 without the addition of the polyelectrolyte enhancer/flocculant aid showed better results.

Residual Aluminum Concentration
The residual aluminum concentration is considered as particularly important parameter from the perspective of human health and should be carefully considered when an aluminum coagulant is applied, especially for drinking water treatment. According to Figure 9, it can be seen that the residual Al concentration remained well under the respective legislation limit of 200 µg Al/L, according to the EU Directive 98/83/EC, for the examined coagulants, and for all the examined wastewater samples.

Conclusions
In this study, different composite poly-aluminum-ferric-silicate-chloride (PSiFAC) coagulants were prepared in the laboratory, and their efficiency was examined for the treatment of high-strength industrial wastewaters, such as those originating in tanneries, or in yeast-production (fermentation) plants. The contribution of polyelectrolyte during the coagulation/flocculation process was additionally studied by two different types of process application, i.e., either the polyelectrolyte was separately added in the sample as a supplementary flocculation aid or the coagulant and the polyelectrolyte were combined in one single reagent (PAPEFAC) in order to increase further the flocculation efficiency.
The properties and characteristics of commonly applied poly-aluminum-chloride (PACl) were affected by the introduction of poly-silicates or polyelectrolyte, simultaneously with ferric cations in its structure. According to the presented results, the new composite coagulants, i.e., PSiFAC 1.5-10-15 and PAPEFAC 1.5-10-15 showed the relatively higher Al 13 content, i.e., 51% and 43%. Consequently, the FTIR and SEM analyses of these composite coagulants indicated a similarity in their structure and morphology which were not affected by the different preparation methods (addition order of the chemicals) of the samples. Furthermore, polymerization was noticed for both coagulants by observing the existence of intensive peaks in the FTIR spectra which can be attributed to the stretching and bending vibration of Fe-OH-Fe and Al-OH-Al bonds, respectively. The SEM micrographs showed the resulting amorphous structures on the surface of all prepared composite coagulants, pointing at the same time to the formation of NaCl as clinging block-shaped crystals.
The coagulants proved to be quite effective, depending upon their specific properties; the addition of 80 mg Al/L in yeast production wastewater samples resulted in a sufficient reduction of COD (56%), turbidity (40%), and phosphates (43%) for the anaerobically pre-treated wastewater sample; an extra reduction of COD (22%), turbidity (14%), and phosphates (38%) was noticed for the pre-treated anaerobically/aerobically wastewater treatment samples, respectively. Compared to these results, higher removal rates were obtained for the treatment of tannery wastewater (i.e., COD 67%, turbidity 96%, phosphates 62%).
Conclusively, it was found that the PSiFAC 1.5:10:15 coagulant, either with or without the addition of a common flocculant aid (polyelectrolyte), can provide better effectiveness of the C/F process, especially regarding COD removal. The residual aluminum concentration in the treated wastewaters was found to be below the maximum concentration limit of Al even for drinking water (200 µg/L). Certain additional cost benefits may arise by the utilization of this material in specific wastewater treatment cases, including the possible avoidance of equipment for handling the organic polyelectrolyte reagent (e.g., dissolution, pumping). In this way, the overall treatment procedure is simplified, and the overall cost-effectiveness can be improved.