The Passivhaus Standard in the Spanish Mediterranean: Evaluation of a House’s Thermal Behaviour of Enclosures and Airtightness

: Few houses have been built in the Spanish Mediterranean in accordance with the Passivhaus (PH) standard. This standard is adapted to the continental climates of Central Europe and thorough studies are necessary to apply this standard in Spain, especially in the summer. High relative air humidity levels in coastal areas and solar radiation levels of west-facing façades require adapted architectural designs, as well as greater control of air renewal and dehumidiﬁcation. A priori, energy consumptions undergo big variations. In this study, the construction of a single-family house in the Spanish Levante was analysed. All enclosure layers were monitored using sensors of surface temperature, solar radiation, indoor and outdoor air temperature, relative humidity, and air speed. The thermal behaviour of the façade enclosure and air inﬁltration through the enclosure were examined using the blower door test and impacts on annual energy demand were quantiﬁed. Using simulation tools, improvements are proposed, and the results are compared with examples of PH housing in other geographical areas. The annual energy demand of PH housing was 69.19% below the usual value for buildings in the Mediterranean region. Very thick thermal insulation and low values of airtightness could be applied to the envelope, which would work very well in the winter. These technique solutions could provide optimal comfort conditions with a well-designed air conditioning system in summer and low energy consumption.


Introduction
Within the European Union, the energy consumption of buildings represents 40% of final energy consumption. Buildings are responsible for 36% of CO 2 emissions. A total of 85% of the energy consumed is used to heat or cool rooms, illuminate them, and heat sanitary water. In December 2002, the European Parliament approved the Energy Performance Building Directive, EPBD 2002/91/EC, with the aim of improving energy efficiency [1]. Long-term strategies have been established to decrease energy consumption and to reduce CO 2 emissions, based on the Kyoto Protocol. Both exterior and local weather conditions are taken into account, as well as internal climatic conditions and the cost-effectiveness ratio. A few years later, a revised text was approved, Directive 2010/31/EU, known as the EPDB Recast [2]. Thus, the regulations on Nearly Zero Energy Buildings, known as NZEBs, were introduced for all new buildings from year 2020 onwards [3]. This text was revised in 2012 and has now become Directive 2012/27/EU [4].
as Mihai et al. in Bucharest, with earth-to-air heat exchange technology (EAHX) with photovoltaic panels, generating 1,556.5 kWh/year, and a drop in annual energy demand to 13 kWh/m 2 yr [27]. Harkouss, Fardoun, and Biwole, through multi-criteria decision making (MCDM), further refined the technical quantification of thermal insulation and thermal transmittance U values in warm climates at 0.6 W/m 2 K for walls, 0.6 W/m 2 K for ceilings, and 0.5 W/m 2 K for floors [28]. In mixed climates, the walls and ceiling should be well insulated (U= 0.2 W/m 2 K), while the floor's thermal transmittance should not be minimised so as to allow the heat to escape through the floor in summer. A low window/surface area ratio value (10%) is necessary to improve buildings' energy performance.
From this review of the state-of-the-art, we can conclude that, to date, few PH dwellings have been built on the Spanish Mediterranean coast. Some of the research has focused on applying bioclimatic techniques in order to comply with the PH standard and to improve climatic conditions in summer, while others have limited themselves to quantifying energy demand in summer and winter. However, the absence of more detailed quantifications, according to the different parameters and intervening agents, of the energy consumption produced in these PH dwellings is detected. The novelty of this research is the quantification of energy consumption due to the transmission of heat through the various elements of the enclosures and of the actual infiltration of air through the enclosure by means of the analysis of a representative PH case study.

Aims and Objectives
The present study examined the implementation of the Passivhaus standard in the Spanish Mediterranean. It focused on the impact that building envelope heat flows and air infiltration have on annual energy demand [29]. To this end, the construction of an isolated detached house in Molina de Segura (Spain), located 40 km away from Spain's Eastern coast was studied. The house was designed with the aim of complying with the Passivhaus standard. The façade enclosures were monitored and thermal transmittance measurements were made in situ. The Blower Door air infiltration test was also conducted. Subsequently, using the Design Builder simulation tool [30], results on the quantification of the impact on energy demand were obtained for both parameters, both in the studied house and in the hypothetical case that it would have been built in the city of Alicante, on the coast [18]. Since the standard was designed to improve energy efficiency under a continental climate, the intention was to draw a conclusion on whether the standard could also be appropriate for coastal climate situations. Relative air humidity in the months of summer and autumn is much higher than that experienced in Central European countries, as well as wall and indoor air overheating by solar gains through glazing [31]. The thermal gaps between indoor air temperature and outdoor air temperature during the winter and spring months are more moderate. These big differences call into question, a priori, the validity of initial investments in the construction quality and the control devices for air renewal installations with heat recovery.
In addition to the tests mentioned previously, we proceeded to evaluate the parameters selected in this study in other houses in the area, according to local construction culture. First, we examined houses built before 1979 (without thermal insulation), then buildings built after the NBE CT-79 standard came into force [32], and finally, buildings constructed after 2006, after the CTE was implemented [5]. The enclosures of the latter buildings are resolved using two sheets with an air chamber and 6 cm of thermal insulation, an inverted flat roof with 6 cm of thermal insulation finished with gravel, and air permeable class 2 joineries (27 m 3 /hm 2 ), with silicone-based sealing and double hollow brick walls, and high air infiltration standards according to the n 50 index. In this way, results obtained in the present study can be compared with other construction systems and installations, allowing further studies to conclude on the suitability of the Passivhaus (PH) standard for Spanish Mediterranean coast buildings.

Description of the Case Study
The isolated detached house under study is located in Molina de Segura (Spain), 40 km from the coast (Figure 1). It is composed of two volumes. The lower volume has day areas (living room, laundry room, pantry, toilet, and office) and a floor area of 100 m 2 . The first floor corresponds to the night area (3 bedrooms, 2 bathrooms, and a study) and has a constructed surface area of 95 m 2 . There are covered porches on the outside with a constructed area of 43 m 2 , which help to protect the house from solar radiation, resulting in a total floor area of 216.15 m 2 . The bedrooms are south-facing to capture the largest possible amount of solar radiation in winter, while the living room and kitchen face a north-south axis, obtaining an axis of natural ventilation that passes through the house. Overheating in summer can thus be avoided ( Figure 2). The gaps in the exterior façade have been planned in such a way as to capture a maximum amount of natural light. Overhangs and solar protections based on adjustable blades were designed to avoid direct solar radiation in summer.
Flat roofs with small punctual overhangs protect the gaps from the impact of sunlight in summer.    The façade on the ground floor is resolved with a thermal insulation system on the outside (SATE), thus constituting a ventilated façade made with a stucco lime mortar coating with flexible silicate on vertically modulated 32 × 100 mm mullions, a waterproof EPDM sheet, 15 mm Superpan Tech board, on a structure of modulated wooden posts every 60 cm and filled with natural 160 mm mineral wool, Micro USB barrier 230/20 Riwega, and laminated wood board on a self-supporting 73 × 48 structure (Figure 3). On the first floor, the exterior enclosure is a ventilated façade formed by larch wood slats, a 32 × 100 mm ventilation strip, Riwega waterproof sheet, 15 mm Superpan Tech board on a structure of modulated wooden mullions every 60 cm and filled with 148 mm natural mineral wool, and Micro USB 230/20 Riwega vapour barrier, with laminated wood board on a 73 × 48 self-supporting structure ( Figure 4). All joineries between elements are solved with an adhesive tape seal, Riwega USB Tape 1 PE (60mm wide, professional and universal polyethylene with mesh reinforcement coated with high adhesive strength acrylic adhesive), which guarantees perfect air-tightness ( Figure 5), as later verified with the results of the Blower Door test. The joinery is made of wood with thermal bridge break, elastic joint, Guardian-Sun type laminated glass (6 + 16 + 3 + 3), and Guardian-Sun type glass (6 + 16 + 4) for the non-laminated glazing.   The roof is flat, not passable, and is made with slopes, a SuperPan Tech P5 21 mm board, 200 gr/m 2 geotextile separating layer plus EPDM membrane waterproofing 1 mm thick, and a finishing layer of 5 cm-thick clean gravel, on a 198 × 48 wooden beam structure, 2 SuperPan Tech P4 25 mm wooden boards containing a 200 mm natural mineral wool thermal insulation layer, and a continuous suspended ceiling with a metal structure, formed by a laminated plaster plate. The foundation is based on a reinforced concrete slab, with a thermal insulation of XPS, 100 mm thick, and an EPDM waterproofing sheet, as well as self-levelling mortar and a class 3 microcement pavement.

233
The house has a low-temperature solar collector system for domestic hot water demand (DHW),

234
in addition to auxiliary aerothermal equipment [33], located in the laundry room, which intervenes  The house has a low-temperature solar collector system for domestic hot water demand (DHW), in addition to auxiliary aerothermal equipment [33], located in the laundry room, which intervenes when there is insufficient solar radiation collection. In addition to natural ventilation, mechanical ventilation was installed with heat recovery with a contribution of 5 l/s per person in the bedrooms, 2 l/s per person in the living and dining rooms, and 2 l/s per m 2 in the kitchen, as specified in the CTE-DB-HS3. One air conditioning system is included, coupled to the ventilation system, and composed of an exterior machine as well as an indoor one, with a direct expansion cold-only air-air system. The EER value is 5.93 and the COP is 4.27. Sustainability 2017, 9,

261
The two domains of evaluation of the house's energy demand are linked to the materials used 262 as well as the technical characteristics of the enclosures, although they are of a very different nature.

263
Evaluating the actual heat flow through the enclosures throughout the year's entire cycle is a complex 264 matter [36]. This evaluation requires simulation models that take into account construction faults, the 265 impact of thermal inertia, real thermal bridges, as well as the incidence of solar radiation on the 266 Figure 5. Lacquered aluminium carpentry joined to the exterior pavement. Airproof sealing and waterproofing with EPDM (left). Interior partitions and enclosure with tape sealing, type Riwega USB Tape 1 PE (right).

Climatic and Normative Conditions
The house location is under a Mediterranean climate. According to the Köpen-Geiger classification [34], it is classified as BSh, a warm semi-arid climate with hot or very hot summers and mild winters with very little rainfall [35]. The average annual temperature is 18.1 • C, the coldest month being January, with an average of 10.3 • C, and the hottest month being August, with an average of 26.3 • C.
According to the Spanish regulations in force at the time of building the CTE house (2013 modification), it is located in a B3 climatic zone with an altitude of 240 m above sea level, letter B in winter and 3 in summer, according to the CTE-DB-HE table B1 classification (Climate Zones).

Energy Demands Obtained in the Project Phase
According to the current calculation procedure in Spain, CTE DB-HE-2013, using the Unified Tool Lider-Calener (HULC), the demand for renewable energy consumption was 29.7 kWh/m 2 ·year. The annual heating demand was 6.41 kWh/m 2 ·year, below the demand level required by the CTE (26.29 kW·h/m 2 ·year). Cooling energy demand was 4.17 kWh/m 2 ·year, i.e., below that required by the CTE (15 kWh/m 2 ·year).

Materials and Methods
The two domains of evaluation of the house's energy demand are linked to the materials used as well as the technical characteristics of the enclosures, although they are of a very different nature. Evaluating the actual heat flow through the enclosures throughout the year's entire cycle is a complex matter [36]. This evaluation requires simulation models that take into account construction faults, the impact of thermal inertia, real thermal bridges, as well as the incidence of solar radiation on the exterior surfaces and the air conditioning systems used. Air infiltration through the enclosures varies according to the external environment's climatic conditions, the air pressure at each moment, as well as how occupants maintain and use certain mobile elements such as joinery, adjustable slats, or grids. All this means that estimating the energy impact due to air infiltration is complex.

U Thermal Transmittance of the Enclosures
Fourier's law, which applies to parallel layers of materials, of an unlimited surface, in steady state indoor T i and exterior T e air temperatures, establishes the temperature gradient reached by multi-layer enclosures when there is a thermal gap between outdoor and indoor air temperatures (Equation (1)). Thermal transmission by conduction and convection intervene according to values of resistance to the passage of heat or superficial thermal resistance due to the convection currents generated. (1) However, this law is valid only for ideal situations and steady states. Walls have limited surfaces, they present discontinuities due to joineries and glazing, thermal bridges due to construction faults [37,38], etc. In addition, the various layers are made up of different types of materials with different values of physical parameters of resistance to the passage of the heat [39]. Furthermore, outdoor air conditions are altered by solar radiation, air speed, water vapour pressure in the air, etc. Solar radiation also often has an impact on the outer surfaces, substantially increasing their temperature. Indoors, thermal loads and the air conditioning systems used alter the physical parameters of interior air temperature and relative humidity, as well as the surface temperatures of the walls [40]. Finally, the thermal inertia of the materials making up the enclosure alters the linear Fourier process as a function of time, since the thermal gap between exterior and interior air temperature, the solar radiation that affects the exterior surface, or the interior air conditioning systems vary according to the weather. Heat flow thus becomes a dynamic and complex process [41].

Theoretical Calculation of the U Transmittances of the Enclosures
In this study, we measured the house's thermal transmittance U value, but we did not analyse the effect of the parameters affecting the dynamic regime of the heat flow through the enclosures, such as thermal admittance, Y, and thermal wave lag [42], df, or the damping factor of the thermal wave, f a . The thermal transmittance U values were obtained according to the method established by the current regulations, the Technical Building Code (CTE) [43].
The usual values of thermal conductivity, λ, of the materials used in the enclosure, according to UNE EN ISO 10456: 2012 [44,45], were compared to the measurements obtained from real samples by means of the thermal conductivity analyser C-Therm TCi by Mathis Instrumentos Ltd., using a universal sensor, made at the University of Alicante. We proceeded with a theoretical calculation of the heat flow resistance of the enclosure's different layers, under ideal conditions, according to Fourier's law.
To simulate this behaviour in a steady state, we overlooked the impact of other energy sources, such as solar radiation, the indoor conditioning system, or the effect of material effusiveness or thermal inertia [46], and decided to apply the maximum outdoor air temperature in summer (39.57 • C) and the minimum outdoor temperature in winter (7.87 • C), collected by PT 100 monitoring sensors, and an indoor air temperature of 28.62 • C in summer and 17.74 • C in winter, without the air conditioning system operating. To do this, we considered, in accordance with the CTE [47], that surface thermal resistance was 1/h i of 0.13 m 2 K/W, surface thermal resistance was 1/h e of 0.04 m 2 K/W, and thermal resistance, R c , of the ventilated façade chamber was 0.0176 m 2 K/W.

In-Situ Measurements of U Transmittance
Subsequently, a thermoflumetric study of the opaque enclosures was conducted to measure U thermal transmittance [48,49]. It was measured in the two rooms on the southeast façade (the kitchen at a height of 0.70 m and the dining room), in the northwest façade (the living room), as well as in the bedrooms on the first floor in the northeast and southwest façades. For this, the ISO 9869-1: 2014 [50] standard was followed. The equipment consisted of a heat flow plate; a transducer that generates an electrical signal proportional to the total heat rate applied to the sensor surface. Two indoor and outdoor air temperature probes were attached to this plate, as well as two surface temperature sensors for the exterior and interior surfaces. These were connected to the analyser directly with cables or through the window. The trial lasted one week for each of the three measurements. The data was analysed using the module that calculates thermal transmittance, part of the AMR WinControl software developed by Ahlborn for ALMEMO measuring equipment. The method used was the "average method", which assumes that thermal transmittance or thermal conductivity can be calculated by dividing the average density of the thermal flow by the average temperature difference [51].
This analysis was completed with the thermal imaging and detection of possible thermal bridges, helping to determine the outer envelope's ventilated chamber behaviour [52,53], though quantifying thermal bridges was not the subject of this study [54].

Air Infiltration Through the Envelope
The air infiltration value through the enclosure was forecast to be very low thanks to the construction's quality, the seals used, and the joinery quality. It was evaluated by means of the Blower Door test conducted in accordance with the European Standard EN 13829, using the Blower Door GMBH MessSysteme für Luftdichtheit equipment. The corresponding graphs were obtained and there was an n 50 air infiltration value of 50 Pa. To characterise the information obtained, the Minneapolis Blower Door Model 3 software (TEC-TITE 5.0) was used. This tool was developed specifically to describe 140 parameters that possibly intervene in the filtration phenomenon [55]. These parameters were collected in a database used to perform a general evaluation of the results.
To obtain the average value of air infiltration in the building, a parameter difficult to quantify, and to be able to perform the energy impact simulations using the Design Builder tool, thus obtaining the values of annual energy demand, the protocol established in the UNE-EN-ISO 13790: 2003 standard was followed, which it allows for converting the value of n 50 to renewals/hour under normal pressure conditions by means of Equation (2): where: n 50 renewals/hour at 50 pascals; e i wind protection coefficient = 0.05; and ε i height corrector factor = 1.
The Blower Door test was the tool used to detect thermal bridges through images using a ThermaCam P 25 thermographic camera from Flyr. It was quantified using the AnTherm program. Load losses or gains due to thermal bridges were estimated at 3.5% of the total thermal loads by U thermal transmittance of the enclosures. These values are similar to values obtained in previous studies [56,57].

Energy Impact Assessment
As mentioned, the main objective of the present study was to quantify the energetic impact of the heat flow through the envelope and air infiltration. Both values were obtained using different tools and methodologies.

Energy Losses due to U Transmittance Values
To quantify the energetic impact, the transmittance U values of all the enclosures obtained in-situ were introduced into the Design Builder tool. To perform building behaviour simulations in terms of energy demand and interior comfort parameters, the data and parameter values that follow were introduced into the Design Builder tool. The winter period covered 1 December to 30 April and the summer period covered from 1 May to 30 November. This decision was based on results from previous studies, contrasted with the experience of various calibrations of models in the same geographical location. The interior air setpoint temperatures were 21 • C in winter and 24 • C in summer. For the standard calculation of air renewal, occupancy was 5 people. To comply with regulations, a value of 0.63 air changes per hour (ACH) of air renewal was established, in accordance with the Technical Building Code (CTE) currently in force. The air infiltration values introduced in the tool were those obtained from the Blower Door test. Table 1 shows the parameters introduced in Design Builder's simulation model. Estimating the air infiltration's energy impact is a complex issue. It depends not only on the sealing of the building envelope, but also on weather conditions, which are sometimes very difficult to predict. No common criterion exists regarding the right model to evaluate the energetic impact of infiltrations. Until now, different calculation models have been developed with varying degrees of complexity and reliability. The simplest models presuppose a uniform distribution of leak paths and average constant leaks over time. In the present study, this impact was evaluated using a simplified model (Equation (3)), applying the concept of degree-day, which relates the average temperature outside the house under study and the interior comfort temperature (21 • C for heating and 24 • C for cooling) [7]. This estimate is theoretical and actual energy consumption depends on the particular conditions of the houses' internal air temperature setpoint, T i . This calculation procedure allows evaluating the energetic impact, taking into account the climatic data specific to the area around the house. The air infiltration flow, specific air capacity, and the air temperature difference between the interior and the exterior of the house were all taken into consideration [58]. where: Q inf is annual energy loss (kWh/yr) due to air infiltration for heating Q inf-H and cooling Q inf-C .; C p is the air's specific heat capacity, which is 0.34 Wh/m 3 K; G t are annual degrees-days (kKh/yr); and V inf is the air leak rate (m 3 /h).
The Persily-Kronvall estimate is simple and the model is widespread in the scientific community [59]. It assumes a linear relationship between permeability at 50 Pa and average annual infiltration (Equation (4)).
where q inf is the air permeability (m 3 /(h m 2 )). Subsequently, this linear relationship between leakage and infiltration evolved [59] and incorporated coefficients according to the characteristics of the location of the Equations (5) and (6). where: N is a constant; C is the climatic factor; cf 1 is the building's height correction factor, 1 (cf 1 = 1) to 3 (cf 1 = 0.7) floors; cf 2 is the site screening correction factor, for well shielded cases (cf 2 = 1,2), (cf 2 = 1) (cf 2 = 1) or exposed dwellings (cf 2 = 0.9); and cf 3 is the sealing correction factor, which depends on the value of the exponent of leak n. This simplified extended model has been adopted to calculate the average infiltration flow in Spain's Mediterranean area, obtaining the value of climatic factor C via equivalence with US climates, based on average temperature and wind speed. For the coefficients cf 1 , cf 2 , and cf 3 , a value equal to 1 was adopted in all three cases. The type of infiltration opening was obtained from the mean value of the flow exponent n = 0.59. The V inf air leak rate, necessary to calculate the energy impact, was calculated based on the air permeability rate and the envelope surface area, as follows (Equation (7)): where A E is the envelope area.
Once the value of the volume of air infiltration through the envelope or air leak rate V inf was obtained to calculate the energetic impact, according to the annual average corrected by means of equations (3-7), sensible and latent heats were quantified by means of the following Equations (8) and (9): where: Q s is the energy impact value of the sensible heat of the air leak rate V inf (W); V inf is the air leak rate (m 3 /h); C e is the specific heat of the air under normal conditions 0.349 Wh/kgK; ρ is the density of air (kg/m 3 ); T e is the outside air temperature in degrees Kelvin (K), considered as the average annual value; and T i is the air temperature inside the house (21 • C in winter and 24 • C in summer). where: Q l is the energetic impact value of the latent heat of the air leak rate V inf (W); C v is the heat of water vaporization (0.628 W/g vapour ); W e is the specific humidity of the external air taken as the annual average value (g vapour /kg); W i is the specific humidity of the indoor air (g vapour /kg).

Results
The measurements of some thermal behaviour parameters of the materials used in the house's enclosures are presented in Table 2. They do not differ substantially from those obtained in other similar publications [40]. In this way, the thermal transmittance U values of a typical enclosure, according to Fourier or in steady state, were obtained following the values of surface thermal resistance and air chambers established by the CTE. With these values, we proceeded to make a theoretical calculation according to Fourier and λ values extracted from the UNE EN ISO 10456: 2012 standard, of the U thermal transmittances of conventional enclosures. Table 3 shows the calculation for the opaque enclosure. The U thermal transmittance measurements made using the sensors and Testo equipment ( Figure 6) are shown in Table 4, together with the comparison of the theoretical calculation results in a steady state [36]. As shown, deviations ranging between 1% and 7% were detected. They are also compared with the usual measurement results of enclosures in standard building types in the Spanish Mediterranean area over the periods 1979-2006 and 2006-2019 [60].  Figure 6) are shown in Table 4, together with the comparison of the theoretical calculation results in 439 a steady state [36]. As shown, deviations ranging between 1% and 7% were detected. They are also    (Figure 7), the results are shown in Table 5. As can be seen, the   (Figure 7), the results are shown in Table 5. As can be seen, the average value is 0.51 air changes per hour (ACH) at 50 Pa, a lower value than the maximum allowed by the PH standard ( Figure 8). In comparison with the values obtained for other buildings in the area, and in other geographical parts of Spain, the value is significantly lower. It is between 600% and 1200% below that of isolated single-family homes in the area built between 1979 and 2019, whose n 50 values are between 3 and 6 ACH [61]. and in other geographical parts of Spain, the value is significantly lower. It is between 600% and 453 1,200% below that of isolated single-family homes in the area built between 1979 and 2019, whose n50 454 values are between 3 and 6 ACH [61].

473
The schematic diagram of the air conditioning system and the aerothermal system, as well as

Energetic Impact of Heat Flow Through the Envelope
Once we obtained the enclosures' U values of thermal transmittance, the values of indoor air renewal rate according to CTE, air infiltration through the envelope, surface temperatures of the walls, house occupancy, etc., we proceeded to simulate the house's thermal behaviour using the Design Builder tool (Figure 9) [29]. It was thus possible to analyse users' feeling of comfort, the temperature gradients in the rooms, and to compare the summer and winter energy demands depending on the characteristics of the enclosures and the Blower Door test. Simulations could also be made by modifying the technical characteristics of the enclosures [62], modifying the air infiltration rate factor n 50 , and other parameters [42]. As indicated, the interior air setpoint temperatures applied were 21 • C in winter and 24 • C in summer.

473
The schematic diagram of the air conditioning system and the aerothermal system, as well as 474 solar thermal panels to produce ACS, were also introduced into Design Builder. To adjust the 475 simulation parameters to the real data, or to calibrate the model, they were compared with indoor air 476 temperature and surface temperature values that had been obtained through monitoring. The The schematic diagram of the air conditioning system and the aerothermal system, as well as solar thermal panels to produce ACS, were also introduced into Design Builder. To adjust the simulation parameters to the real data, or to calibrate the model, they were compared with indoor air temperature and surface temperature values that had been obtained through monitoring. The monitoring system was designed using a wireless system. Temperature sensors were connected to small analysers ("EL-WiFi-TC. Thermocouple Probe Data logger"). The "EL-WiFi-TH, temperature and humidity data logger" analysers, with built-in sensors of temperature and relative humidity, interpreted the recorded data and sent Wi-Fi signals to a "RouterOS" router, connected to a laptop [40]. By installing the software "EasyLog Wi-Fi Software", the data was received and stored in the computer. The climate file, including external air temperatures, relative humidity, and solar radiation levels by means of a pyranometer throughout the complete one-year cycle was obtained for the house in Molina de Segura and was also introduced. Figures 10-13 show Computational Fluid Dynamics (CFD) results obtained through the Design Builder tool for 1 August 2018 at 3 p.m. and 1 February 2019 at 9 am. The climate differences between summer and winter are remarkable. To perform the simulations, the summer period was established from 1 May to 30 November and the winter regime from 1 December to 30 April. This division was based on prior simulation results, with the resulting model calibrated according to data obtained by monitoring the complete one-year cycle [63].

499
Based on the Design Builder simulations, impact results on annual energy demand were 500 obtained for each housing type enclosure (

499
Based on the Design Builder simulations, impact results on annual energy demand were 500 obtained for each housing type enclosure ( Table 6). The climate file obtained in situ, by monitoring,

501
was applied to obtain more accurate simulation results. Heat flows through the window openings 502 accounted for almost 60% of the energy demand due to enclosure transmittance and 15% of the 503 annual energy demand.  Based on the Design Builder simulations, impact results on annual energy demand were obtained for each housing type enclosure ( Table 6). The climate file obtained in situ, by monitoring, was applied to obtain more accurate simulation results. Heat flows through the window openings accounted for almost 60% of the energy demand due to enclosure transmittance and 15% of the annual energy demand.
If we compare these results with those obtained for conventional housing constructions in the area (Table 7), the annual energy demand reduction is reduced by 39%, a high value that is mainly due to the breakage of thermal bridges and the increase in thickness of thermal insulation; 14.8 cm instead of the usual 4-6 cm [64]. The usual impact values of thermal bridges in conventional houses account for 3%-5% of the energy loss through the enclosure, while in the case of the house under study, this figure was reduced to 0.5% [65]. Simply by improving the enclosures' thermal insulation and thermal bridges, the application of the PH standard to the constructions on the Spanish Murcia-Alicante Mediterranean coast would bring about annual energy demand reductions of around 5 to 8 kWh/m 2 year. This represents between 10% to 14% annual energy savings and this latter percentage would increase in the case of buildings built before the enforcement of the CTE.

Energetic Impact of Air Infiltration
The energetic impact of air infiltration was obtained by applying the methodology described in Section 3.3. The values obtained are shown in Table 8. These values were also obtained in the Design Builder tool, once the value obtained in the Blower Door test was entered in the model and calibrated using the Persily-Kronvall estimate [59]. The table shows the values of the impact on annual energy demand of the air infiltration through the envelope, which alters the interior air temperature and its specific humidity [66]. The results for other conventional houses built in the same area have also been introduced. The energy impact percentages obtained are significant. The energy losses due to the air infiltration in the PH house analysed were between 5 and 7 times lower, leading to significant reductions in the percentage of impact on annual energy demand. The annual energy demand was reduced between 14 and 32 kWh/m 2 yr, in percentage terms that is between 72.38% and 85.57%. This represents a major percentage drop compared to the conventional houses on the Mediterranean Murcia-Alicante coast.

Impact of Improvements of Thermal Transmittances and Air Infiltration on Annual Energy Demand
Once the results of thermal transmission (4.1) and air infiltration (4.2) were analysed, we could lay them out in a table together with the energy demand values for summer, winter, and a year, obtained from the Design Builder tool, for each of the three types studied (Table 9). Most notably, the annual energy demand of the PH house accounted for 30.81% of the usual value for buildings in the Mediterranean region under study. Regarding the most recent buildings built under the CTE umbrella, this percentage is 39.73% [57]. A drastic drop in energy consumption can be observed. The energy losses due to enclosure transmittance and air infiltration in the PH house were much lower, i.e., between 21.5 and 46 kWh m 2 yr. They represent major annual energy demand drops for conventional housing on the Mediterranean Murcia-Alicante coast. The energy losses by infiltration were also found to be around 30%-40% of conventional housing energy demands, while this value was reduced to 20% in the case of the PH.
If we consider the values obtained in other studies, according to which the average impact of air infiltration on annual energy demand is around 12 kWh/m 2 yr for Alicante, 10 kWh/m 2 yr for Malaga, or 17 kWh/m 2 yr for Barcelona [61], we can conclude that by applying the PH standard and its technical construction requirements, annual energy demand due to infiltration could be reduced by between 100% and 300%.

Conclusions
Quantifying the energetic impact of thermal transmission through enclosures and air infiltration is decisive to adapt the Passivhaus standard to the Spanish Mediterranean region. When gaps and glazing are designed to protect against solar radiation, overheating of indoor air and interior surfaces can be avoided, making it easier to implement the standard. This design layout leads to significant reductions in annual energy demand. Very thick thermal insulation could thus be applied to the envelope, which would work very well in winter, with energy demands below 15 kWh/m 2 year and optimal comfort conditions with a well-designed air conditioning system in summer. The annual energy demand would not be too high, below 30 kW/m 2 yr, a much lower value than the usual standards. Heat recovery systems relating to air renewal in summer, combined with the VRV system's air dehumidification, allow us to conclude the implementation of the standard could be generalised in the area, with low energy consumption. Low air infiltration implies low dehumidification system consumption, maintaining 50% of RH.
Highly satisfactory energy savings were obtained for the PH house under study, as follows: • Energy losses through enclosure transmittance were 11.324 kWh/m 2 yr, between 32% and 40% lower than those obtained in the usual homes in the region; • Losses due to air infiltration were very low, of 5.393 kWh/m 2 yr, given that the Blower Door test produced a very low n 50 value of 0.49 ACH. They were between 5 and 7 times lower than in conventional homes in the area; • The annual energy demand of PH housing was 69.19% below the usual value for buildings in the Mediterranean region. Regarding the most recent buildings built under the CTE umbrella, the reduction was 60.27%.
In future studies, investments necessary to build the house will be quantified and compared to conventional Murcia-Alicante coast standards. The energy saving values obtained in this study will be applied and the investments' amortisation period will be calculated. It will be possible to demonstrate the adequacy of the Passivhaus standard to the Administrations and the necessary corrections to apply the standard under the Spanish Mediterranean region climate. Policies proposing incentives to implement these construction systems and specific installations would undoubtedly lead to significant energy savings and thus reduce the environmental impacts deriving from the building and use of residential developments.