Optimization and Scheduling Method for Power Systems Considering Wind Power Forward/Reverse Peaking Scenarios

: With the promotion of the dual carbon target, the scale of the wind power grid connection will significantly increase. However, wind power has characteristics such as randomness and volatility, and its grid connection challenges the pressure of system peak shaving, making it increasingly difficult to regulate the power system. To solve the problem of wind power abandonment, the positive and negative peak shaving characteristics of wind power were first analyzed. Based on this, it is proposed that demand response resources and energy storage with adjustable characteristics are used as the new means of wind power consumption. Together with the thermal power units, they participate in the optimization and scheduling of the power grid, forming a coordinated and optimized operation mode of source load storage. With the goal of minimizing system operating costs, a two-stage economic scheduling model was formed for the day-ahead and intra-day periods. Finally, optimization software was used to solve the problem, and the simulation results showed the effectiveness of the proposed economic scheduling model, which can improve the system’s new energy consumption and reduce the system’s operating costs.


Introduction
A new power system characterized by equipment for renewable energy power generation and new energy grid-connecting technologies, has gradually emerged with rapid development [1][2][3][4][5].According to the national electricity industry statistics released by the National Energy Administration of China [6], China's installed wind power capacity is increasing year on year, and its volatility and the need for anti-peak regulation will cause electricity costs to rise in proportion to this trend.If only traditional dispatching methods are used to smooth out system fluctuations, it will have an impact on the stable operation of thermal power units, and will also lead to serious abandoned wind and light problems [7][8][9][10][11].Enhancing the consumption level of wind power is a pivotal issue within modern power systems.This problem requires urgent attention and resolution due to the presence of large-scale wind power integration.
With the reform of electricity marketization, demand response (DR) resources have been involved in the dispatching operation as adjustable resources of the power system [12][13][14].In recent years, the Northeast Energy Regulatory Bureau and relevant departments have formulated implementation plans regarding power demand response, aiming to further implement the work of the National Energy Board to comprehensively promote the development of the electricity market and improve the electricity market rules system.The ability of DR resources to absorb wind power has been paid more and more attention by experts.The literature [15,16] investigated the impact of price-based demand response resources on the disruption of wind power consumption and highlighted their growing significance; these resources play an increasingly crucial role in maintaining the equilibrium between the short-term power supply and demand, considering the cross-price elasticity coefficient of load changes between hours to adjust the demand situation in response to price changes.The literature [17] analyzed the results of PDR and IDR participation in peaking, and the results showed that the two are interrelated and independent, and could be coordinated according to the system's requirements for economy and reliability.The literature [18] established a model for demand response resource agents to provide DR standby resources, and a two-stage stochastic model was used to achieve optimal scheduling of the DR standby resources.The literature [19] established a centralized control and tariff response-based wind power consumption strategy, which considered different users to develop different strategies.The studies included only considered the scheduling of the demand response resources, so the paper added energy storage resources as a means of wind power consumption, making the system more flexible in the use of regulatory resources.
The literature [20,21] proposed that DR resources are involved at the planning level to improve the system flexibility, reduce the capacity demand of the wind power access system peaking units, and improve the system operation efficiency.The literature [22][23][24][25][26] established a stochastic unit combination model to analyze the impact of wind power uncertainty on the system.It was somewhat better than the deterministic model [8] in terms of economy and reliability.The literature [27] considered the combination of both uncertainty optimization methods and the DR consumption of wind power, and the results demonstrated that both can work synergistically to reduce the cost incurred by the uncertainty of wind power.The literature further improved the grid-connected consumption of new energy generation in practical applications, while also reducing carbon emissions to improve the operational performance of comprehensive energy.This article also provides inspiration for future research to introduce the goal of reducing carbon emissions in integrated energy systems, while balancing the low-carbon and economic benefits.However, there are the following shortcomings: one is the volatility and randomness of the new energy output, and the uncertainty regarding how the demand response load will affect the accuracy of the day-ahead dispatching plan formulated by the grid.Another point is that most of the research in the literature only considers the scheduling situation of the power grid in the day ahead, and only considers the scheduling of the demand response resources at the day-ahead timescale.The advantage of its multi-timescale characteristics has not been emphasized in many DR resource scheduling models.In the literature [28], one study proposes an optimal scheduling model for the integrated energy system within the park, incorporating multiple demand response models.To minimize the scheduling cost within the park, an enhanced particle swarm algorithm and a fuzzy chance-conditional constraint planning method were employed to formulate a rolling optimization model.
There are also many studies on the coordinated optimal dispatch of adjustable resources on the source-side and load-side to reduce the system's wind curtailment [29,30].The literature [29] proposes a low-carbon economic operation model with a source-load interaction.In [30], a multi-scenario optimization strategy for energy accumulation in heating networks considering source-load uncertainty was proposed to improve the operational performance of the integrated energy sources.
In recent years, energy storage systems have gained attention as potential solutions to mitigate the intermittent nature of renewable energy sources such as wind power and photovoltaics.Research on energy storage has also progressed considerably.Considering the different energy storage technologies, mechanical energy storage systems are among the various options considered to address the intermittency of renewable energy sources (e.g., flywheel energy storage [31,32] and compressed air [33]), electrical energy storage (e.g., energy storage batteries [34] and supercapacitors [35]), and other types of energy storage (e.g., hydrogen, biomass, and thermal energy storage [36]).Each type of energy storage is dependent on its own charging and discharging characteristics, as well as its primary role in the grid.Energy storage can also regulate loads through ancillary services with the aim of balancing the grid [37].Moreover, energy storage systems can also meet the reserves to cope with the uncertainty of wind power generation [38], thus improving the stable operation of the system, and can also improve power quality [39].
Energies 2024, 17, 1257 3 of 18 Among the theoretical studies on the optimal dispatching of source-grid load and storage, the literature [40][41][42][43][44][45] presents innovations in terms of the integrated energy management system, hierarchical optimization of the model, and fast capability of the solution algorithm to improve the new energy consumption capacity of the system by developing a scheduling scheme.However, these studies have also considered the inadequacies in their research, and most of these model studies only consider the dispatching situation of the grid the day before, which may cause the effects of inefficient grid dispatching, energy waste, and inability to cope with unexpected situations; these factors impede the safe, stable, and economically efficient operation of the grid.
To address the above-mentioned problems in the demand response and new energy development, this paper coordinates and optimizes the thermal power, wind power, energy storage devices, and demand response resources on two timescales: day-ahead and intraday.Through the demand response mechanism, the flexible load, as one of the dispatching resources, and the energy storage plant jointly participate in the dispatching plan, and establish an optimal dispatching model with the objective of minimizing the operating cost of the power system on both the day-ahead and intra-day-ahead timescales.The primary objective is to maximize wind power utilization while ensuring its optimal consumption.The method is also analyzed using arithmetic results to improve the system peaking flexibility and to improve the wind power consumption capacity.In response to the abovementioned demand response and issues in the development of new energy, the first part of this article analyzes the characteristics of wind power generation.The second part coordinates and optimizes the thermal power, wind power, energy storage equipment, and demand response resources in two stages: day-ahead and intra-day, forming a scheduling mode for coordinated and optimized operation of source load storage, and modeling and solving it.Finally, CPLEX was used as a solving method, and the results showed the economic feasibility of the model.

Analysis of Wind Power Forward/Reverse Peaking Characteristics
With the increasing scale of wind power, the range of fluctuations in the wind power output increases accordingly, and may even vary from near-zero output to rated output.Wind power exhibits a wide range of volatility, as well as a large day-to-day variability and uncertainty.By studying the typical curves of wind power, two distinct and regular types of wind power characteristic curves can be derived, as shown in the figure below.For power system dispatch, the grid-connected wind power counter-peaking scenario has a greater impact on the power system stability, and the frequency of counter-peaking scenarios is higher.Figure 1 is a schematic diagram of a wind power forward peaking curve and a daily load curve; there is no significant difference between the wind power output curve and the load curve trend.Figure 2 is a schematic diagram of a wind power reverse peaking curve and a daily load curve; there is a significant difference between the wind power output curve and the load curve trend.In both figures, the green curve is the wind power output curve and the red curve is the load curve.The left vertical axis is the load power unit and the right vertical axis is the wind power unit.

Analysis of Wind Power Consumption Mechanism under Forward/Reverse Peaking Scenarios
The grid-connected capacity of wind power is gradually increasing.The randomness, volatility, and reverse peaking regulation of wind power increase the equivalent load peakto-valley difference (difference between load power and wind power) of the system after large-scale grid-connected consumption, leading to a multiplication of peak regulation pressure on the thermal power units.When the regulation capacity of the thermal power units cannot meet the regulation demand of the wind power and the load, one solution is to introduce an energy storage system and flexible load regulation to ensure the balance of the system's supply and demand, thus enhancing the system's ability to accommodate the wind power.Figures 3 and 4 show the analysis of the wind power consumption mechanism based on the reverse regulation and forward peaking regulation characteristics, respectively.

Analysis of Wind Power Consumption Mechanism under Forward/Reverse Peaking Scenarios
The grid-connected capacity of wind power is gradually increasing.The rando volatility, and reverse peaking regulation of wind power increase the equivale peak-to-valley difference (difference between load power and wind power) of the after large-scale grid-connected consumption, leading to a multiplication of peak tion pressure on the thermal power units.When the regulation capacity of the t power units cannot meet the regulation demand of the wind power and the lo solution is to introduce an energy storage system and flexible load regulation to the balance of the system's supply and demand, thus enhancing the system's ab accommodate the wind power.Figures 3 and 4 show the analysis of the wind pow sumption mechanism based on the reverse regulation and forward peaking reg characteristics, respectively.

Analysis of Wind Power Consumption Mechanism under Forward/Reverse Peaking Scenarios
The grid-connected capacity of wind power is gradually increasing.The rando volatility, and reverse peaking regulation of wind power increase the equivale peak-to-valley difference (difference between load power and wind power) of the after large-scale grid-connected consumption, leading to a multiplication of peak tion pressure on the thermal power units.When the regulation capacity of the t power units cannot meet the regulation demand of the wind power and the lo solution is to introduce an energy storage system and flexible load regulation to the balance of the system's supply and demand, thus enhancing the system's ab accommodate the wind power.Figures 3 and 4 show the analysis of the wind pow sumption mechanism based on the reverse regulation and forward peaking reg characteristics, respectively.Under the traditional mode of dispatch, the net load of the power system is: where P l is the conventional load of the system and P W is the wind power output.The blocked wind power ( 1 ⃝ + 2 ⃝ + 3 ⃝) at this time is: where P Gmin is the minimum value of the peaking capacity of conventional units.
If the flexible load participates in system peaking, its blocked wind power ( 1 ⃝ + 2 ⃝) is: where P ′ l_eq is the net load after the participation of the flexible load in the peaking.It can be seen from the figure that the abandoned wind volume of the system is reduced due to the participation of the flexible load.
As can be seen from the figure below, the participation of the energy storage system can shift the peak hours in the demand-side management planning to off-peak hours on the basis of the flexible loads for peaking.Simply put, during the hours of low electricity prices, the energy storage system undergoes charging, and during the hours of high electricity prices, it discharges stored energy.The system wind curtailment ( 1⃝) is also further reduced, and the net load peak-to-valley difference is somewhat smaller for the forward peaking scenario compared with the anti-peaking scenario.Under the traditional mode of dispatch, the net load of the power system is:  Under the traditional mode of dispatch, the net load of the power system is: where Pl is the conventional load of the system and PW is the wind power output.The

Multi-Timescale Models
These new energy sources have characteristics such as volatility and uncertainty, which have important impacts on the power system.In the study of this paper, the wind power is divided into two scenarios; one type exhibits a positive correlation with the daily load curve, while the other type demonstrates a reverse correlation with the daily load curve.When data from these two different scenarios are brought into the model for calculation, firstly, the prediction accuracy of the wind power has some deviation; however, this improves as the prediction scale is reduced.Secondly, there is a problem of differentiation in the regulation characteristics of the dispatching resources in the system, so a level-by-level refinement of the dispatching model is needed to accommodate different timescales.It is difficult to satisfy the operational characteristics of the various types of resources by only performing optimal scheduling on a single timescale.Therefore, to address these problems, further research and optimization of scheduling strategies are necessary to effectively meet the challenges of new energy consumption.
The two-stage optimization problem established in this article belongs to the mixed integer linear programming (MILP) problem, which has many solving methods.This article uses CPLEX to solve this type of problem.The standard form of the MILP problem [46] is: In the formula, x is the variable to be optimized and includes the wind power, operating cost of the thermal power units, penalty cost for the wind curtailment, output of the thermal power units, etc. Y is the start-stop plan for the thermal power units.
Considering the above factors, for the purpose of better improving the new energy consumption capacity and system economy, this paper establishes a multi-timescale scheduling model for the wind power forward/reverse peaking scenarios, the framework of which is shown in Figure 5.
In the following sections, the day-ahead and intra-day scheduling models are explained separately from an economic perspective.

Objective Function
The day-ahead optimal dispatch model, incorporating thermal power, wind power, and flexible load, constructed in this paper aims to achieve the economic operation of the power systems containing wind power by coordinating and optimizing the generation-side and load-side resources.The model converts the wind curtailment and load shortage into penalty costs by incorporating them into the system operating costs to achieve economic optimization and improves the grid new energy consumption capacity and power supply reliability in an emergency mode.The objective function includes the operating costs of conventional units, start-up and shutdown costs, wind farm operating costs, wind curtailment penalty costs, incentive-based demand response resource call compensation costs, energy storage costs, and load outage costs, aiming to minimize the total operating costs of the system.The day-ahead scheduling plan is implemented on a daily basis, utilizing an hourly timescale.The objective function is expressed as follows:  In the following sections, the day-ahead and intra-day scheduling models are e plained separately from an economic perspective.

Objective Function
The day-ahead optimal dispatch model, incorporating thermal power, wind pow and flexible load, constructed in this paper aims to achieve the economic operation of t power systems containing wind power by coordinating and optimizing the generatio side and load-side resources.The model converts the wind curtailment and load shorta into penalty costs by incorporating them into the system operating costs to achieve ec In Formula (5), f TH,t is the cost of the conventional unit operation; f QT,t is the cost of the start-up and shutdown; f w,t is the cost of the wind farm operation; f qw,t is the cost of the wind curtailment penalty; f IDR,t is the cost of the IDR incentive-based demand response resource call compensation; f bat,t is the cost of the energy storage; and f loss,t is the cost of the load shortage.Formula ( 6) is the expansion of each cost in Formula (5).In Formula (6), Ns is the number of scenarios; N G is the conventional unit; P s is the probability coefficient of occurrence of s scenario; P Gi,s,t is the generation capacity of the i-th conventional unit in s scenario at time t; a i , b i , and c i are the generation cost coefficients of the i-th unit, respectively; S i is the start-stop cost coefficient of the i-th conventional unit; u Gi,t is the start-stop status of the i-th unit at time t, which is a decision variable, where 1 means start and 0 means stop; k W is the wind farm operation cost coefficient; P w,s,t is the wind farm output in scenario s at moment t; k qw is the wind curtailment penalty coefficient; P pre,rp w,s,t is the predicted wind power output of the previous day's wind farm in scenario s at moment t; k IDRA and k IDRB are the class A IDR load and class B IDR load invocation cost coefficients, respectively; ∆P IDRA,t and ∆P IDRB,t are the class A IDR and class B IDR invocations at moment t, respectively; µ + s and µ − s are the charging and discharging energy storage cost coefficients, respectively; P + s,t and P − s,t are the charging and discharging powers of the energy storage, respectively; λ loss is the cost coefficient of the load deficiency; and P loss,t is the amount of load deficiency.

Binding Conditions
Equation ( 7) is the active power balance constraint, where ∆P PDR,t is the PDR call at time t, P L0,t is the initial state load value of the system, and P w,t is the wind power output.

P min
Gi ≤ P Gi,s,t ≤ P max Gi (8) Equation ( 8) is the unit output constraint, where the regulating capacity of thermal power units is limited [47], and P min Gi and P max Gi are the upper and lower limits of the output, respectively.
Equation ( 9) is the unit climbing constraint, where R i is the climbing rate.
Equation ( 10) is the minimum start/stop time constraint for the unit, where T on,i and T off,i are the minimum continuous start time and the minimum continuous stop time, respectively.0 ≤ P w,t ≤ P pre w,t Equation ( 11) is a constraint on the upper and lower limits of the wind power output, where P pre w,t is the wind power forecast at time t.
−R w_down ≤ P w,t − P w,t−1 ≤ R w_up (12) Equation ( 12) is the climbing constraint of the wind power output, where R w_down and R w_up are the climbing rate limits of the increase and decrease in the wind power, respectively.
PDR mainly influences customers' electricity consumption plans through the electricity price, so its response amount is related to the electricity price.Equation ( 13) is the elasticity Energies 2024, 17, 1257 9 of 18 matrix, where ∆q t is the rate of change in the load at moment t; ∆p t is the rate of change in the electricity price at moment t; and E is the price-based elasticity coefficient.

P min
pdr ≤ P pdr,t ≤ P max pdr (14) Equation ( 14) provides the upper and lower bound constraints of the PDR resource invocation, where P min pdr and P max pdr are the lower and upper limits of the PDR load calls, respectively.
Equation ( 15) is the IDR constraint, where P + idra,t and P + idrb,t are the IDR increase load amounts of class A and B, respectively; and P − idra,t and P − idrb,t are the IDR decrease load amounts of class A and B, respectively.
Equation ( 16) is the SOC calculation formula, where E bat is the current battery storage capacity and C bat is the energy storage battery capacity.
Equation ( 17) shows the change in power during the charging and discharging of the battery.The prolonged use of a battery can cause its capacity to drop [48].∆P cha,t bat is the moment t energy storage device charging power, and similarly, ∆P dis,t bat is the moment t energy storage device discharging power.η cha and η dis are the energy storage charging and discharging efficiencies, respectively, and ∆t is the charging and discharging time interval.


In Equation (18), SOC max and SOC min are the maximum and minimum values of the charge state of the energy storage device, respectively; P cha b_min and P cha b_max are the minimum charge power and maximum charge power of the energy storage device, respectively; and similarly, P dis b_min and P dis b_max are the upper and lower limits of the discharge power of the energy storage device, respectively.
Equation ( 19) is the transmission line power constraint, where, P ex,t is the power of the grid transmission line and P max ex,t is the transmission line power limit.

Optimization Results
The model was analyzed by the optimal solution algorithm to obtain the regular unit start/stop schedule.The PDR callable resource calls and class A IDR resource calls were brought into the subsequent scheduling model as the deterministic quantities.

Objective Function
The intra-day optimal scheduling objective is still to minimize the system operation cost, and the scheduling plan for this subsection is to schedule every 15 min with a timescale of 15 min in the next 4 h.With the gradual improvement of the accuracy of the new energy and load forecasting, at this time, the class B IDR and energy storage can respond in a shorter period of time with the following objective function:

Binding Conditions
The constraints in these two phases are similar.Since the regular unit start/stop schedule, PDR resource calls, and class A IDR resource calls were determined in the scheduling optimization results a few days ago, these constraints do not exist in this subsection and will not be repeated here.

Optimization Results
Using the algorithm to solve the model, the conventional unit output plan, class B IDR dosage, and electrochemical energy storage power station charge and discharge amounts were obtained.

Example Overview
For the model in this paper, the IEEE 30-node system was used as the base system model for improvement.The improved system contains six conventional units; Table 1 shows the operating parameters of the conventional thermal units: one wind farm with an installed capacity of 300 MW, an energy storage plant, and two IDR demand resource dispatching stations, whose topology diagram is shown in Figure 6 below.It is assumed that the variation range of the PDR does not exceed 6% of the total load, the invocation of the class A IDR load does not exceed 3% of the total load, the invocation of the class B IDR load does not exceed 2% of the total load, and the compensation cost of both the class A IDR and class B IDR are fixed values of 50 and 60, respectively.Table 2 shows the demand response resources classified as incentive-based according to the dispatch response speed, and the model that can be found in the MATLAB 2018 platform of the YALMIP 2018 toolkit to call the solver for solving.The load and wind power forecasts are generated based on measured data plus white noise, where the day-ahead forecast curve is extended from the original 1-h interval (24 data points) to 96 data points at 15-min intervals (the four extended data points within each hour are taken to be the same value).The prediction errors are 4% and 1% for the day-ahead and intra-day loads, respectively, and 6% and 3% for the corresponding wind powers, respectively.With the objective of verifying the effect of the proposed scheduling The load and wind power forecasts are generated based on measured data plus white noise, where the day-ahead forecast curve is extended from the original 1-h interval (24 data points) to 96 data points at 15-min intervals (the four extended data points within each hour are taken to be the same value).The prediction errors are 4% and 1% for the day-ahead and intra-day loads, respectively, and 6% and 3% for the corresponding wind powers, respectively.With the objective of verifying the effect of the proposed scheduling strategy in different wind power output scenarios, two typical scenarios of forward and reverse peaking regulation of wind power are selected for analysis in the example part, and the ratio of forward and reverse peaking regulation probability is taken as 3:7.The measured and forecasted load and wind power curves are shown in the following figures: Figures 7-9 show the day-ahead and intra-day prediction curves of the load and the forward and reverse peaking regulation of the wind power, respectively.
Energies 2024, 17, x FOR PEER REVIEW 12 of 18 strategy in different wind power output scenarios, two typical scenarios of forward and reverse peaking regulation of wind power are selected for analysis in the example part, and the ratio of forward and reverse peaking regulation probability is taken as 3:7.The measured and forecasted load and wind power curves are shown in the following figures: Figures 7-9 show the day-ahead and intra-day prediction curves of the load and the forward and reverse peaking regulation of the wind power, respectively.

Analysis of Scheduling Results
In this paper, the results of the established scheduling model are analyzed under the two scenarios of forward and reverse peaking.Figures 10 and 11 below show the scheduling results of the two scenarios of forward and reverse peaking.Figures 12 and 13 show the demand response resource calling plans under the two scenarios, and Figure 14 shows the scheduling of the energy storage plants.

Analysis of Scheduling Results
In this paper, the results of the established scheduling model are analyzed under the two scenarios of forward and reverse peaking.Figures 10 and 11 below show the scheduling results of the two scenarios of forward and reverse peaking.Figures 12 and 13 show the demand response resource calling plans under the two scenarios, and Figure 14 shows the scheduling of the energy storage plants.This study examines the forward and reverse peaking regulation scenarios.The scheduling model's results were analyzed comprehensively.During the forward peaking scenario, the wind power exhibits peak periods from 1:15 to 3:00, 5:00 to 11:00, and 17:00 to 19:30.The wind power output aligns closely with the load curve during these periods, and can efficiently absorb the wind power without any extensive demand response resource adjustments.Consequently, the system has a high non-DR capacity, requiring less IDR resource allocation compared with the wind power reverse peaking scenario.In the wind power reverse peaking scenario, the wind power peaks from 3:00 to 8:00 and from 13:30 to 17:00, with a significantly different output curve trend from the load curve and a lower load demand.During these periods, positive adjustments in the demand response resources and energy storage charging improve the level of wind power consumption.This study examines the forward and reverse peaking regulation scenarios.The scheduling model's results were analyzed comprehensively.During the forward peaking scenario, the wind power exhibits peak periods from 1:15 to 3:00, 5:00 to 11:00, and 17:00 to 19:30.The wind power output aligns closely with the load curve during these periods, It can be seen, based on the integrated result scheduling diagrams in Figures 10 and 11, and the demand response resource regulation diagrams in Figures 12 and 13, that the system still primarily relies on the conventional units for power adjustment to fulfill the peaking plan.Although the total amount of the load that can be transferred by the class B IDR resources and energy storage plants is less, it is more flexible compared with the class A IDR resources, which can only respond over a short period of time and need to be called upon frequently to alleviate wind power fluctuations over a short period of time.The magnitude of the class B IDR resources fluctuation is smaller, but its changes are more dramatic; in the figure, this can be seen in the intra-day dispatch of the class B IDR resources with the changes reflected being more dramatic, and suitable for some sudden load fluctuations or to calm the wind power fluctuations in a shorter timescale.From Figure 14, it can be concluded that the amount of energy storage called during the forward peaking regulation is smaller than that during the reverse peaking regulation, so that it can respond to regulation more quickly in the face of changing wind power or sudden load changes.

Comparison Analysis of Different Scheduling Modes
To compare and analyze the roles of the different scheduling methods in promoting wind power consumption and reducing system costs, this paper also set up different scheduling schemes for comparison and analysis under the two scenarios of forward and reverse peaking of wind power: (1) No energy storage plants are involved, while no multi-timescale dispatch is considered and only the thermal power units are involved in peaking; (2) Add DR resources on the basis of scheme (1) and only perform the day-ahead scheduling; (3) Based on the scheduling method proposed in this paper.
Table 3 shows the comparison of the results.In the day-ahead dispatching in option 1, where both the energy storage and flexible loads are not involved in regulation, especially in the high wind power new energy time, a single thermal power unit cannot meet the large-scale wind power consumption after the new energy is connected to the grid, leading to a serious wind curtailment phenomenon.The forward and reverse peaking scenarios in option 1 have abandonment rates of 8.4% and 12.3%, respectively, and the total system cost in the first option is also the highest, reaching 647,216 CNY.In the same scenario, the wind power abandoned in the reverse peaking scenario is larger than the wind power abandoned in the forward peaking scenario.This reverse peaking characteristic of the wind power increases the net load peak-to-valley difference and further enhances the difficulty of peak regulation.Option 2 and option 3 increase the flexible load on the basis of option 1. Adding an energy storage power station in option 3 alleviates part of the peak load of thermal power, and the total cost is reduced by 156,584 CNY and 200,935 CNY compared with option 1.Compared with option 1, option 2 adds an adjustable flexible load, which can decrease the system's curtailment wind to a certain extent.Under the two scenarios of forward and reverse peaking regulation, the wind curtailment rate is reduced by 4.8% and 7.4%, respectively, and the total system cost is also significantly reduced due to the absorption of a large amount of wind power.The flexible load and the thermal power jointly participate in peaking regulation, so that the overall benefit of the system is improved, and the flexible load can adjust the load change according to the flexible fluctuation of the wind power, which better promotes the consumption of new energy.On the basis of option 2, option 3 makes full use of the multi-timescale characteristics of the energy storage and other demand response resources, and can adjust wind power fluctuations in a short timescale in a timely manner.The class B IDR and energy storage can be more accurately invoked in the intra-day optimal scheduling, further reducing the system's wind curtailment rate and improving the system's benefits.In option 3, under the two scenarios of forward and reverse peaking regulation, the wind curtailment rate is reduced by 2% and 2.4%, respectively.The total system cost of option 3 is also the smallest at 446,281 CNY.
In summary, the scheduling model designed in this paper can make full use of the more or less timescale characteristics of the demand response resources to develop a reasonable scheduling plan, which can play a role in alleviating the wind curtailment problem and improving the system's economy.

Conclusions
In order to improve the wind power consumption, reduce the loss caused by the wind power fluctuations, and reduce the peak load balancing pressure of the power system, this paper proposes a two-stage scheduling method under the scenario of positive and negative peak balancing of the wind power.In these two stages, the wind power utilizes energy storage devices and demand response resources to participate in grid optimization scheduling through a smaller timescale, flexibly reducing the impact of the wind power grid-connection on the power system.With the continuous reduction in the thermal power generation scale and the continuous increase in the grid-connected capacity of the wind power, the coordination of the various resources in the power system is a very important research direction.
The composition of the energy storage power station proposed in this paper only considers electrochemical energy storage.Different energy storage technologies have different characteristics, and future power systems will be connected with various types of large-scale energy storage systems.In the future, we can consider adding a real-time phase on the basis of the two phases (day-ahead and intra-day) used in this paper to assess the scheduling performance of the system at a deeper level.

Energies 2024 ,Figure 1 .
Figure 1.Diagram of wind power forward peaking and daily load curves.

Figure 2 .
Figure 2. Diagram of wind power reverse peaking and daily load curves.

Figure 1 .Figure 1 .
Figure 1.Diagram of wind power forward peaking and daily load curves.

Figure 2 .
Figure 2. Diagram of wind power reverse peaking and daily load curves.

Figure 2 .
Figure 2. Diagram of wind power reverse peaking and daily load curves.

Figure 3 .
Figure 3. Diagram of wind power consumption mechanism analysis based on reverse peaking characteristics.

Figure 4 .
Figure 4. Diagram of wind power consumption mechanism analysis based on forward peaking characteristics.

Figure 3 . 18 Figure 3 .
Figure 3. Diagram of wind power consumption mechanism analysis based on reverse peaking characteristics.

Figure 4 .
Figure 4. Diagram of wind power consumption mechanism analysis based on forward peaking characteristics.

Figure 4 .
Figure 4. Diagram of wind power consumption mechanism analysis based on forward peaking characteristics.

Figure 9 .
Figure 9. Day-ahead and intra-day forecast curves for wind power reverse peaking.Figure 9. Day-ahead and intra-day forecast curves for wind power reverse peaking.

Figure 13 .Figure 14 .
Figure 13.Graph of wind power reverse peaking demand response resource utilization.

Figure 14 .
Figure 14.Energy storage call diagram for wind power forward and reverse peaking scenarios.

Table 1 .
Some operating parameters of thermal power units.

Table 3 .
Comparison of system operating costs under different scheduling schemes.