Coordinated LVRT Support for a PMSG-Based Wind Energy Conversion System Integrated into a Weak AC-Grid

: In a grid, the choice of the point of common coupling (PCC) does not solely rely on the voltage level alone but also conjointly depends on the grid strength for many explicit purposes. Nowadays, the afﬁnity of low SCR grid connections has become a crucial thought once it involves the integration of wind generation plants (WPPs). Since the quality of wind resources is a critical issue, these plants are usually placed in remote areas with a sophisticated potential of wind ﬂow. These remote areas are typically less inhabited, where the grid does not perpetually always have to be sturdy. Moreover, the exceeded power demand loading and higher wind penetration affect the generation, transmission, and distribution utilities by permitting the ﬂow of unbalanced voltages and currents in the power system. Therefore, the quality of transmitted power is becoming a crucial facet of distributed energy generation units. In this paper, a permanent-magnet synchronous generator (PMSG) based wind energy conversion system (WECS) is presented. It discusses a solution, which provides the low voltage ride through (LVRT) provision by the suppression of DC link overvoltage and active power limitation during an asymmetrical grid fault. With improved back-to-back converter control, the machine side converter (MSC) is employed to control the DC-link voltage. Furthermore, the grid side converter (GSC) is used to implement the active/reactive current injection according to the outlined limits. The need for external hardware is eventually avoided, which is typically required to dissipate the additional energy generated during a grid fault. Hence, it is proven to be an affordable solution.


Introduction
The greenhouse emission commencing from the ignition of fossil fuels to harvest electrical energy contributes as the foremost factor in global warming and climate change.
In the new era of consumers and power quality, there is a need to install renewable energy resources-based power plants. According to the Pakistan Economic Survey (PES) in 2019-2020, the approximation of installed capacity of power generation in Pakistan is 37,402 MW, the total consumer average demand is 25,000 MW, and the transmission and distribution capacity is 22,000 MW [1]. Pakistan is producing 62% of its energy requirements using conventional resources. To reduce the greenhouse emission effect, there is a need to invest in renewable energy resources, such as photovoltaic, biomass, fuel cells, and wind farms. Wind farms are becoming popular among other renewable energy resources. It is a pollution-free and ecologically pleasant solution, which requires Table 1. Comparison between past and proposed techniques.

Item Past Technique (Crowbar) Proposed Technique
Cost Cost-ineffective [4] Cost-effective [4] Design Complexity Design is complex as it includes additional devices [13] Design is moderate complex Controllability Less controllability [14] Controllable [14] Validity Valid only for asymmetrical faults [4] Valid for both symmetrical and asymmetrical faults Additional hardware Required, e.g., crowbar, SDBR, ESS, etc. [15,16] Does not require any additional hardware

Losses
Losses are comparatively high as the crowbar converts the surplus power into heat energy which could result in more losses [13] Losses are low compared to the conventional techniques Efficiency Moderate efficiency [4] High efficiency

Proposed Framework
In Figure 1, a conventional controller is shown, where MPPT is achieved with the help of MSC. However, in this paper, MSC is utilized for the suppression of DC-link over-voltage. The proposed control system is illustrated in Figure 2. In Figure 3, the GSC is shown performing the maximum power point tracking as well as compensating the unbalanced grid voltages.

Losses
Losses are comparatively high as the crowbar converts the surplus power into heat energy which could result in more losses [13] Losses are low compared to the conventional techniques Efficiency Moderate efficiency [4] High efficiency

Proposed Framework
In Figure 1, a conventional controller is shown, where MPPT is achieved with the help of MSC. However, in this paper, MSC is utilized for the suppression of DC-link overvoltage. The proposed control system is illustrated in Figure 2. In Figure 3, the GSC is shown performing the maximum power point tracking as well as compensating the unbalanced grid voltages.  Additional hardware Required, e.g., crowbar, SDBR, ESS, etc. [15,16] Does not require any additional hardware

Losses
Losses are comparatively high as the crowbar converts the surplus power into heat energy which could result in more losses [13] Losses are low compared to the conventional techniques Efficiency Moderate efficiency [4] High efficiency

Proposed Framework
In Figure 1, a conventional controller is shown, where MPPT is achieved with the help of MSC. However, in this paper, MSC is utilized for the suppression of DC-link overvoltage. The proposed control system is illustrated in Figure 2. In Figure 3, the GSC is shown performing the maximum power point tracking as well as compensating the unbalanced grid voltages.

Background Information
In Figure 4, a PMSG-based WECS is shown. The configuration has three major parts: a. Permanent magnet synchronous generator; b. Back to back converters; and c. AC grid.

Permanent Magnet Synchronous Generator
The mathematical modeling of voltages of a surface-mounted PMSG is considered in the synchronous d-q reference frame. In Figures 5 and 6, the d-axis and q-axis equivalent circuits are shown, respectively [17][18][19]. The expressions defining the cross-coupling effect in d-q axis voltages are expressed as (1) and (2)

Background Information
In Figure 4, a PMSG-based WECS is shown. The configuration has three major parts:

Background Information
In Figure 4, a PMSG-based WECS is shown. The configuration has three major parts: a. Permanent magnet synchronous generator; b. Back to back converters; and c. AC grid.

Permanent Magnet Synchronous Generator
The mathematical modeling of voltages of a surface-mounted PMSG is considered in the synchronous d-q reference frame. In Figures 5 and 6, the d-axis and q-axis equivalent circuits are shown, respectively [17][18][19]. The expressions defining the cross-coupling effect in d-q axis voltages are expressed as (1) and (2) where the PMSG stator winding resistance is denoted with Rs and inductance is donated with Ls.

Permanent Magnet Synchronous Generator
The mathematical modeling of voltages of a surface-mounted PMSG is considered in the synchronous d-q reference frame. In Figures 5 and 6, the d-axis and q-axis equivalent circuits are shown, respectively [17][18][19]. The expressions defining the cross-coupling effect in d-q axis voltages are expressed as (1) and (2): where the PMSG stator winding resistance is denoted with Rs and inductance is donated with Ls. V d s ,V q s ,i d s , and i d s are the d-q components of the stator direct and quadrature axis voltages and currents, respectively. The magnetic flux is donated with a symbol ω e and, θ d represents the electrical angular speed.

Back to Back Converters
In Figure 4, a block diagram of the deployed scheme is shown, where GSC (grid side converter) and MSC (machine side converter) are integrated to control the power flow within the system.

Grid Side Converter (GSC)
In the proposed control topology, wind power regulation is achieved with the help of GSC. The injection of reactive current during the asymmetrical fault is also provided by the GSC according to grid side control as shown in Figure 3. A comprehensive block diagram of the GSC control is depicted in Figure 7. In this research paper, a dual vector current control strategy for positive and negative sequences is used to eradicate secondorder component oscillations of the AC grid active power. Two components P 2 s and P 2 c are set to zero for the elimination of second-order component fluctuation of AC grid active power. The negative and positive d and q axis components can be identified by solving the matrix shown in (3) [4]. During grid faults, the grid side control will regulate the voltage by injecting reactive power:

Back to Back Converters
In Figure 4, a block diagram of the deployed scheme is shown, where GSC (grid side converter) and MSC (machine side converter) are integrated to control the power flow within the system.

Grid Side Converter (GSC)
In the proposed control topology, wind power regulation is achieved with the help of GSC. The injection of reactive current during the asymmetrical fault is also provided by the GSC according to grid side control as shown in Figure 3. A comprehensive block diagram of the GSC control is depicted in Figure 7. In this research paper, a dual vector current control strategy for positive and negative sequences is used to eradicate secondorder component oscillations of the AC grid active power. Two components P 2 s and P 2 c are set to zero for the elimination of second-order component fluctuation of AC grid active power. The negative and positive d and q axis components can be identified by solving the matrix shown in (3) [4]. During grid faults, the grid side control will regulate the voltage by injecting reactive power: Figure 6. q axis PMSG mathematical model.

Back to Back Converters
In Figure 4, a block diagram of the deployed scheme is shown, where GSC (grid side converter) and MSC (machine side converter) are integrated to control the power flow within the system.

Grid Side Converter (GSC)
In the proposed control topology, wind power regulation is achieved with the help of GSC. The injection of reactive current during the asymmetrical fault is also provided by the GSC according to grid side control as shown in Figure 3. A comprehensive block diagram of the GSC control is depicted in Figure 7. In this research paper, a dual vector current control strategy for positive and negative sequences is used to eradicate second-order component oscillations of the AC grid active power. Two components P 2 s and P 2 c are set to zero for the elimination of second-order component fluctuation of AC grid active power. The negative and positive d and q axis components can be identified by solving the matrix shown in (3) [4]. During grid faults, the grid side control will regulate the voltage by injecting reactive power:  The extraction of the maximum generated power from wind is achieved by activepower reference . The reactive-power reference is provided according to the grid code requirement. The expression (4) gives the active power reference as:

Machine Side Converter (MSC)
In the literature, the quadrature axis current (Iq) is used to obtain/extract maximum power using WECS to smoothen the power flow [13]. The proposed MSC control in this research paper has two control loops, as shown in Figure 2 [20]. In the discussed technique, actual DC-link voltage is compared with reference DC-link voltage. The comparative result difference is fed to a PI-controller to obtain the quadrature axis reference current ( ). The complete MSC grid control is depicted in Figure 8. The DC-link voltage is controlled in such a way that the DC-link voltage stays constant during the unbalanced condition. To avoid demagnetizing permanent magnets in PMSG and minimizing the stator winding losses, the direct-axis current (Id) is set to zero.  The extraction of the maximum generated power from wind is achieved by activepower reference P 0 re f . The reactive-power reference Q 0 re f is provided according to the grid code requirement. The expression (4) gives the active power reference P 0 re f as: where P 0 re f = 0.5ρπR 5 C p−max /λ 3 opt .

Machine Side Converter (MSC)
In the literature, the quadrature axis current (Iq) is used to obtain/extract maximum power using WECS to smoothen the power flow [13]. The proposed MSC control in this research paper has two control loops, as shown in Figure 2 [20]. In the discussed technique, actual DC-link voltage is compared with reference DC-link voltage. The comparative result difference is fed to a PI-controller to obtain the quadrature axis reference current (I re f qs ). The complete MSC grid control is depicted in Figure 8. The DC-link voltage is controlled in such a way that the DC-link voltage stays constant during the unbalanced condition. To avoid demagnetizing permanent magnets in PMSG and minimizing the stator winding losses, the direct-axis current (Id) is set to zero.  The extraction of the maximum generated power from wind is achieved by activepower reference . The reactive-power reference is provided according to the grid code requirement. The expression (4) gives the active power reference as:

Machine Side Converter (MSC)
In the literature, the quadrature axis current (Iq) is used to obtain/extract maximum power using WECS to smoothen the power flow [13]. The proposed MSC control in this research paper has two control loops, as shown in Figure 2 [20]. In the discussed technique, actual DC-link voltage is compared with reference DC-link voltage. The comparative result difference is fed to a PI-controller to obtain the quadrature axis reference current ( ). The complete MSC grid control is depicted in Figure 8. The DC-link voltage is controlled in such a way that the DC-link voltage stays constant during the unbalanced condition. To avoid demagnetizing permanent magnets in PMSG and minimizing the stator winding losses, the direct-axis current (Id) is set to zero.

Proposed Power (Active) Limiter
The currents of each phase Ia, Ib, and Ic are considered lesser than Imax, which is the rated current. The injection of reactive current during unbalanced conditions is achieved with the help of the technique mentioned in Figure 2. The extraction of positive and negative sequence direct axis and quadrature axis currents is done with the help of (5)-(8) [4,19]: where Q 0 re f and P lim are: where δ and K are: whereas the values of positive and negative sequences direct/quadrature axis currents and voltages are: V

Simulation Results
To demonstrate the capability of the proposed technique, an asymmetrical fault was introduced in the WECS during the period of 1.2 to 1.4 s using the Matlab Simulink platform.
First of all, the results were extracted by implementing the technique from [13], where a crowbar was utilized to dissipate surplus power for suppression of the DC-link voltage overshoot. The Matlab-based simulation results were achieved, where the compensated d-q voltages are shown in Figure 9a and the regulated DC-link voltage is displayed in Figure 9b.

Simulation Results
To demonstrate the capability of the proposed technique, an asymmetrical fault was introduced in the WECS during the period of 1.2 to 1.4 s using the Matlab Simulink platform.
First of all, the results were extracted by implementing the technique from [13], where a crowbar was utilized to dissipate surplus power for suppression of the DC-link voltage overshoot. The Matlab-based simulation results were achieved, where the compensated d-q voltages are shown in Figure 9a and the regulated DC-link voltage is displayed in Figure  9b. The grid current is presented in Figure 9c, where the current is decreasing during the fault period and has a long settling time. Using the technique discussed in [13], the system is fairly balancing the grid voltages, which can be observed in Figure 9d. Now, for the proposed technique, the simulation-based results are displayed in Figure  10. The modified control strategy was utilized to regulate the DC-link voltage. It can be seen from the comparison of Figures 9b and 10c that the DC-link voltages are more stable by implementing the proposed control with the aid of MSC, i.e., without using the additional hardware for dissipating the extra power. In Figure 10b, compensated grid dq voltages are shown. The grid current is presented in Figure 9c, where the current is decreasing during the fault period and has a long settling time. Using the technique discussed in [13], the system is fairly balancing the grid voltages, which can be observed in Figure 9d. Now, for the proposed technique, the simulation-based results are displayed in Figure 10. The modified control strategy was utilized to regulate the DC-link voltage. It can be seen from the comparison of Figures 9b and 10c that the DC-link voltages are more stable by implementing the proposed control with the aid of MSC, i.e., without using the additional hardware for dissipating the extra power. In Figure 10b, compensated grid dq voltages are shown. Direct and quadrature axis positive and negative axis currents are observed in Figure  10d,e respectively. It is observed that during unbalanced conditions with the support of Direct and quadrature axis positive and negative axis currents are observed in Figure 10d,e respectively. It is observed that during unbalanced conditions with the support of reactive current components, the active component is being regulated to balance the output supply as mathematically described in (13)- (16). Active/reactive power during unbalanced conditions is observed in Figure 10f.

Experiments and Results
In Figure 11, the experimental lab setup is shown, where the control panel includes the FPGA-based real time controller, back-to-back converters, filter, and protection circuitry. The complete rig with a grid emulator and a variable speed prime-mover (being used as a wind turbine emulator) is also depicted here.
Energies 2021, 14, x FOR PEER REVIEW 10 of 14 reactive current components, the active component is being regulated to balance the output supply as mathematically described in (13)- (16). Active/reactive power during unbalanced conditions is observed in Figure 10f. Figure 10g is related to grid compensated voltages, and with comparison to the conventional technique, the output voltages are more balanced with fewer harmonics than Figure 9d.

Experiments and Results
In Figure 11, the experimental lab setup is shown, where the control panel includes the FPGA-based real time controller, back-to-back converters, filter, and protection circuitry. The complete rig with a grid emulator and a variable speed prime-mover (being used as a wind turbine emulator) is also depicted here. Figure 11. Experimental setup: control panel, grid emulator, PMSG, and its drive. Figure 11. Experimental setup: control panel, grid emulator, PMSG, and its drive.
The hardware results with the implementation of the proposed technique are shown in Figure 12. These results were acquired by introducing an asymmetrical fault (single line to ground) with the help of a grid emulator for 10 s (140 to 150 s). The direct and quadrature axis positive and negative sequence currents are illustrated in Figure 12d,e respectively. The compensated grid three-phase voltages are also shown in Figure 12g.
There are some variations, but a slight difference is observed in both Idq+ waveforms in Figures 12d and 10d during the asymmetrical fault whereas balanced output three-phase voltages can be observed in Figure 12g, which is similar to the result achieved in Figure 10h.
The results were evaluated based on the simulation and hardware tests. In Figure 9, the simulation results were acquired for the conventional technique presented in [13]. The results were observed while introducing a single line to ground fault (asymmetrical fault) on a weak AC grid for 500 ms. During this unbalanced situation, an overshoot was observed in the DC-link voltage, which was suppressed with the help of a crowbar. It can be seen during the fault period that the per-unit current drops to 0.6 pu and takes more time to reach its nominal value. Although this technique is commonly used in WECS, it gives poor results during asymmetrical faults. The hardware results with the implementation of the proposed technique are shown in Figure 12. These results were acquired by introducing an asymmetrical fault (single line to ground) with the help of a grid emulator for 10 s (140 to 150 s). The direct and quadrature axis positive and negative sequence currents are illustrated in Figure 12d,e respectively. The compensated grid three-phase voltages are also shown in Figure 12g. There are some variations, but a slight difference is observed in both Idq+ waveforms in Figures 12d and 10d during the asymmetrical fault whereas balanced output threephase voltages can be observed in Figure 12g, which is similar to the result achieved in Figure 10h.
The results were evaluated based on the simulation and hardware tests. In Figure 9, the simulation results were acquired for the conventional technique presented in [13]. The results were observed while introducing a single line to ground fault (asymmetrical fault) on a weak AC grid for 500 ms. During this unbalanced situation, an overshoot was observed in the DC-link voltage, which was suppressed with the help of a crowbar. It can be seen during the fault period that the per-unit current drops to 0.6 pu and takes more time to reach its nominal value. Although this technique is commonly used in WECS, it gives poor results during asymmetrical faults.
On the other hand, in Figure 10, simulation results were obtained by implementing the proposed technique. A similar fault was introduced in a weak AC grid and suppression of DC-link overshoot was achieved in Figure 10b with the help of MSC dual vector control. With this control technique, the requirement of any additional devices can be avoided to dissipate additional power. The compensated dq voltages are seen in Figure  10c, which are comparatively better than the conventional technique. The direct axis voltage is compensated to 0.9 pu. Moreover, the Idq + and Idqvalues are observed to be within safety limits. To experimentally validate the proposed technique, a hardware-based setup was deployed and similar results are shown in Figure 12.

Conclusions
In this research, a new technique was implemented to enrich the competence of low voltage ride through for a PMSG-based WECS integrated into a weak AC grid. The majority of the control techniques discussed in the literature used the conventional way of controlling the DC-link voltage with the GSC and MPPT with the MSC. On the other hand, in Figure 10, simulation results were obtained by implementing the proposed technique. A similar fault was introduced in a weak AC grid and suppression of DC-link overshoot was achieved in Figure 10b with the help of MSC dual vector control. With this control technique, the requirement of any additional devices can be avoided to dissipate additional power. The compensated dq voltages are seen in Figure 10c, which are comparatively better than the conventional technique. The direct axis voltage is compensated to 0.9 pu. Moreover, the Idq + and Idqvalues are observed to be within safety limits. To experimentally validate the proposed technique, a hardware-based setup was deployed and similar results are shown in Figure 12.

Conclusions
In this research, a new technique was implemented to enrich the competence of low voltage ride through for a PMSG-based WECS integrated into a weak AC grid. The majority of the control techniques discussed in the literature used the conventional way of controlling the DC-link voltage with the GSC and MPPT with the MSC.
There are also many challenges related to these conventional techniques. However, by swapping the control functions of the converters, DC link over-voltages can be regulated by the MSC and the GSC can assist with the balancing of the power supply to a weak AC grid.
The three major contributions of this paper are: DC-link overshoot was regulated without any additional hardware and active/reactive power limitations were implemented during grid faults. During the DC-link regulation, grid current magnitudes were also kept within the safety limits.

Future Work
In this paper, the wind speed was considered to be constant. In the future, the proposed control technique could also be applied to nonlinear wind curves. The same Energies 2021, 14, 6588 13 of 14 method could also be applied by having information of weak AC grid impedances, which will allow the currents to be injected with certain angles for increased efficiency.