A Holistic Framework for Supporting Maintenance and Asset Management Life Cycle Decisions for Power Systems

: The outburst of population as well as increasing industrialisation have triggered a very prominent imbalance between electricity demand and supply in emerging economies such as Indonesia. Based on this premise, electricity generation and distribution ﬁrms such as Perusahaan Listrik Negara (PLN) are faced with an urgent need to enhance availability and reliability through capacity expansion as well as the institutionalisation of cost-e ﬀ ective maintenance and asset management (MAM) principles. Some of the principles recommended here involve embedding customised overall health index (OHI) and total life cycle cost (LCC) estimation principles into engineering decisions that relate to asset renewal and / or replacement. While discussions about the fundamental theories and estimation approaches for OHI and LCC for power transformers (PTs) already exist in the current body of literature, however, they are mostly in a generic form which has somewhat limited proper implementation of these valuable principles in practice. This study is unique because it provides a very systematic framework towards achieving cost-e ﬀ ective MAM through a case study. Additionally, the proposed framework is all-encompassing, as it also assesses the impacts of human unreliability through the application or proven risk assessment techniques. The proposed framework commences with the evaluation of existing decision support system at PLN through a MAM audit, whereby the performance of the West Java arm of PLN with regards to critical MAM elements was examined.


Introduction
An aftermath of the mid-eighteenth century industrial revolution through to the twentieth century is the ability of humans to generate electricity by exploiting various energy sources [1,2]. The emergence of electricity generation resulted to what can be described as the causal loop of energy whereby advancements in electricity led to the development and operation of several heavy and complex industrial activities, which then contributed to the outburst of global economy. The availability of reliable, sufficient and affordable energy services are vital enablers for economic growth as well as averting most of the challenges currently facing the world, especially inequality, health, education and poverty. Within the past two decades, routine analyses conducted by regulatory agencies such as World Bank have continuously emphasized the correlation between economic growth and electricity consumption [3][4][5][6][7], especially among the non-Organization for Economic Cooperation and Development (non-OECD) countries [8]. In 2012, the non-OECD electricity generation represented more than 50% of the world's total electricity demand which is projected to further rise to 61% in 2040 (i.e., 11  As impressive as the tremendous growth in the recognition of industrial CBM seems, the guidelines of the recently launched asset management standards -ISO 55000 series (initially a publicly available specification published by the British Standards Institution in 2004) in 2014 makes it crystal clear that asset performance and condition data alone are no longer sufficient for making robust MAM engineering decisions in capital intensive sectors such as power [24]. This is based on the premise that the role of MAM is changing from the classical "problem-fixer" to a very important aspect of asset life cycle management through the incorporation of the following key themes [24]:  Clear alignment of organisational objectives (including asset design, operation, decommissioning, disposal and renewal) with MAM strategies and plans  Enhance overall asset value through complete asset life cycle MAM planning and cross-functional collaborations  Risk-based decision analyses  Emphasis on leadership as well as understanding the requirements of all stakeholders Unfortunately, despite widespread consensus that MAM is a necessity for the cost-effectiveness of any plant, some decision-makers within several organisations still view the maintenance function as a mere cost centre or necessary evil [23,24], which is perhaps why maintenance as a function has struggled to attain the same level of recognition attributed to other vital plant functions such as finance [25][26][27][28][29][30][31][32], production planning [33][34][35][36][37][38][39][40], marketing [41][42][43][44], etc. Searches within several top percentile energy-related journals clearly show a contrariety between the scanty number of academic publications advocating MAM optimisation and the abundant resources on topics such as energy policy and finance. It must be admitted that several researchers [45][46][47] and industry professionals in plant condition monitoring/industrial maintenance have over the years produced commendable studies on power systems. However, most of the currently available studies are usually specific to a particular approach or failure mode which in turn reduces the attractiveness of such individualized approaches to field experts that would most often prefer a systematic, practical and all-encompassing framework that is based on a case study.
The purpose of this paper is, therefore, to practically evaluate the robustness of MAM for power transformers and its potential to serve as a true business partner in the generation and distribution company of a selected non-OECD country, Indonesia. Power transformers within Perusahaan Listrik Negara (PLN) in West Java were chosen for this investigation because they are the single highest value assets installed in high-voltage substations and could account for well over 50% of the total investment [48]. Besides the aforementioned premise of this study, it is also worth noting that a fundamental value of the study lies in the development of a systematic process for assessing and managing critical industrial assets. Through such frameworks and processes, organisations would possess a platform that supports coherence and repeatability of analysis, irrespective of whom As impressive as the tremendous growth in the recognition of industrial CBM seems, the guidelines of the recently launched asset management standards -ISO 55000 series (initially a publicly available specification published by the British Standards Institution in 2004) in 2014 makes it crystal clear that asset performance and condition data alone are no longer sufficient for making robust MAM engineering decisions in capital intensive sectors such as power [24]. This is based on the premise that the role of MAM is changing from the classical "problem-fixer" to a very important aspect of asset life cycle management through the incorporation of the following key themes [24]: • Clear alignment of organisational objectives (including asset design, operation, decommissioning, disposal and renewal) with MAM strategies and plans • Enhance overall asset value through complete asset life cycle MAM planning and cross-functional collaborations • Risk-based decision analyses • Emphasis on leadership as well as understanding the requirements of all stakeholders Unfortunately, despite widespread consensus that MAM is a necessity for the cost-effectiveness of any plant, some decision-makers within several organisations still view the maintenance function as a mere cost centre or necessary evil [23,24], which is perhaps why maintenance as a function has struggled to attain the same level of recognition attributed to other vital plant functions such as finance [25][26][27][28][29][30][31][32], production planning [33][34][35][36][37][38][39][40], marketing [41][42][43][44], etc. Searches within several top percentile energy-related journals clearly show a contrariety between the scanty number of academic publications advocating MAM optimisation and the abundant resources on topics such as energy policy and finance. It must be admitted that several researchers [45][46][47] and industry professionals in plant condition monitoring/industrial maintenance have over the years produced commendable studies on power systems. However, most of the currently available studies are usually specific to a particular approach or failure mode which in turn reduces the attractiveness of such individualized approaches to field experts that would most often prefer a systematic, practical and all-encompassing framework that is based on a case study.
The purpose of this paper is, therefore, to practically evaluate the robustness of MAM for power transformers and its potential to serve as a true business partner in the generation and distribution company of a selected non-OECD country, Indonesia. Power transformers within Perusahaan Listrik Negara (PLN) in West Java were chosen for this investigation because they are the single highest value assets installed in high-voltage substations and could account for well over 50% of the total investment [48]. Besides the aforementioned premise of this study, it is also worth noting that a Energies 2020, 13,1937 4 of 32 fundamental value of the study lies in the development of a systematic process for assessing and managing critical industrial assets. Through such frameworks and processes, organisations would possess a platform that supports coherence and repeatability of analysis, irrespective of whom performs such or when it was performed. Therefore, the quantitative analysis incorporated here based on an extract of available data from the case study was done to test the applicability and practicality of the proposed framework, bearing in mind that similar analysis can be performed in the future (once new data sets become available). Additionally, the significant rise in consumer demand for enhanced performance from power utilities has triggered the need to base business and engineering investment decisions on a justifiable balance among capital investments, maintenance and operating costs [48][49][50]. The remainder of the paper is organized as follows; Sections 2 and 3 respectively provide a brief overview of energy scenarios in Indonesia and different maintenance regimes. A description of the methodology adopted and data employed for the study are presented in Section 4. The penultimate section describes a framework for estimating maintenance life cycle cost.

A Brief Overview of the Energy Scenarios in Indonesia and MAM Challenges
Projection results have indicated that Indonesia's electric power demand (EPD) will double from its current 219 trillion Watt-hours (TWh) to approximately 464 TWh in 2024, which corresponds to an electric power demand rate of 8.7% per annum [51,52]. Additionally, the national electrification ratio (NER) which is defined as the percentage of the total population with access to electricity was 87% in 2016 but targeted to reach 99.4% in 2024 [51,52]. Table 1 presents detailed projections of Indonesia's current and projected NERs over 11 years [51,52] where it can be seen that the government-owned Perusahaan Listrik Negara (PLN) Company dominates the production, transmission and distribution of electricity. The main sources of energy to PLN are shown in Figure 2, with a split of 87% and 13% for non-renewable and renewable sources respectively. Over the last eight years, the contribution of renewable energy sources has remained relatively constant (i.e., 11% in 2009, 15% in 2010, 12.2% in 2011, 11.35% in 2012, 12.31% in 2013, 11.25% in 2014, 10.47% in 2015 and 12.45% in 2016). However, crude oil as an energy source significantly dropped from 23.7% to 6.5% while that of coal rose to 54.6% from 43.6% within the same period. PLN process architecture as illustrated by Figure 3 consists of generators that generate power from the various energy sources, transmission system that transfers the generated power and distribution system that manages supplies to the consumers.   [51,52].
Owing to the fact that transformers represent the core of most planned capacity expansions within electricity utility processes, PLN has steadily upgraded the population as well as capacities of its transformers since 2011 as depicted by Table 2. However, despite this steady growth in capital expenditures (CAPEX) and acquisition of new equipment, the disparity between installed and actual outputs has been correspondingly plagued by incessant failures due to lapses in the current MAM strategies. It is thus reasonable to infer that in addition to expanding capacity through the installation of new equipment, improving the reliability of existing assets through enhanced MAM practices provides opportunities for sustainable operations. Table 2. Transformer population and capacities from 2011 and 2016 [51,52].   [51,52].
Owing to the fact that transformers represent the core of most planned capacity expansions within electricity utility processes, PLN has steadily upgraded the population as well as capacities of its transformers since 2011 as depicted by Table 2. However, despite this steady growth in capital expenditures (CAPEX) and acquisition of new equipment, the disparity between installed and actual outputs has been correspondingly plagued by incessant failures due to lapses in the current MAM strategies. It is thus reasonable to infer that in addition to expanding capacity through the installation of new equipment, improving the reliability of existing assets through enhanced MAM practices provides opportunities for sustainable operations. Owing to the fact that transformers represent the core of most planned capacity expansions within electricity utility processes, PLN has steadily upgraded the population as well as capacities of its transformers since 2011 as depicted by Table 2. However, despite this steady growth in capital expenditures (CAPEX) and acquisition of new equipment, the disparity between installed and actual outputs has been correspondingly plagued by incessant failures due to lapses in the current MAM strategies. It is thus reasonable to infer that in addition to expanding capacity through the installation of new equipment, improving the reliability of existing assets through enhanced MAM practices provides opportunities for sustainable operations.

Maintenance Regimes and Their Interdependence
A significant aspect of MAM is in-depth understanding of the various maintenance strategies deployed and how they influence each other. Figure 1 already provided a brief description of the main classes of maintenance strategies and their individual characteristics. While knowledge about the different types of maintenance philosophies (i.e., BM, PPM and CBM) is widely available within literature [16,[53][54][55], their relationships/influence on each other is often neglected. In this section, a very brief overview of each of the popular maintenance philosophies is revisited but with emphasis on the impacts they have on one another and the overall maintenance workload which is vital for MAM planning. Figure 4 shows that there are three main classes of maintenance (i.e., BM, PPM and CBM). CBM significantly relies on measured parameters and human senses for the determination of asset health. Important aspects of CBM implementation are the monitoring interval and lead time to failure. A well-implemented CBM program should only generate PPMs and non-urgent BMs (lines 1 and 2, respectively). Besides inflating maintenance man-hours, a poorly estimated CBM monitoring interval often leads to urgent BMs (line 3) because asset health would have deteriorated significantly before next measurement.

Maintenance Regimes and Their Interdependence
A significant aspect of MAM is in-depth understanding of the various maintenance strategies deployed and how they influence each other. Figure 1 already provided a brief description of the main classes of maintenance strategies and their individual characteristics. While knowledge about the different types of maintenance philosophies (i.e. BM, PPM and CBM) is widely available within literature [16,[53][54][55], their relationships/influence on each other is often neglected. In this section, a very brief overview of each of the popular maintenance philosophies is revisited but with emphasis on the impacts they have on one another and the overall maintenance workload which is vital for MAM planning. Figure 4 shows that there are three main classes of maintenance (i.e. BM, PPM and CBM). CBM significantly relies on measured parameters and human senses for the determination of asset health. Important aspects of CBM implementation are the monitoring interval and lead time to failure. A well-implemented CBM program should only generate PPMs and non-urgent BMs (lines 1 and 2, respectively). Besides inflating maintenance man-hours, a poorly estimated CBM monitoring interval often leads to urgent BMs (line 3) because asset health would have deteriorated significantly before next measurement. PPM is based on the premise that assets steadily deteriorate with time. The three main sources of PPMs are original equipment manufacturer (OEM) recommendations, legal requirements and operating experience. A significant number of PPM activities as well as the specific spare parts required for their execution are usually extracted from OEM manuals especially for assets that the  PPM is based on the premise that assets steadily deteriorate with time. The three main sources of PPMs are original equipment manufacturer (OEM) recommendations, legal requirements and operating experience. A significant number of PPM activities as well as the specific spare parts required for their execution are usually extracted from OEM manuals especially for assets that the plant team are unfamiliar with. Since OEMs are in the business of selling spare parts, asset owners should always explore the possibilities of re-validating the effectiveness and sustainability of initial OEM maintenance recommendations once the operating experience of the plant team increases. However, care must be taken so as not to violate the originally specified operating context. The third and arguably most crucial source of PPM activities is based on legal requirements. Owing to historical cases of industrial accidents, there is a class of PPM activities that are legally binding. For instance, companies are required to certify that the integrity of their pressure vessels is intact at all times through regular inspections. At best, delayed PPM activities increase the need for non-urgent BMs (line 4) and urgent BMs at worst (line 8). For example, a delay in the inspection of pressure vessels could lead to loss of wall thickness which then requires urgent replacement.
BM is the type of maintenance philosophy whereby no repair/replace actions are initiated until failure occurs. Depending on how much time is available for repairs and the criticality of the failure, BM could be further divided into urgent and non-urgent sub-classes. A typical example of a non-urgent BM action is the replacement of the electric motor of a standby cooling water pump that had been previously fitted onto the duty cooling water pump. Under this scenario, such a maintenance action may continue to be non-urgent until a failure occurs on the duty pump. Therefore, delays in non-urgent BMs increase the risks of generating several urgent BMs (line 6). Urgent BMs naturally lack planning due to the limited amount of time available for their implementation which in turn disorganise and delay the implementation of other non-urgent BMs and PPMs (lines 5 and 7).

Proposed MAM Framework
The proposed approach entails the fusion of several plant asset reliability enhancement tools into a holistic and practical framework ( Figure 5) that will sustainably address the issues identified from the MAM audit, so that engineering decision makers at PLN (West Java) region can have a better understanding of the usefulness of maintenance life cycle costs analysis of new assets from historical information. In this study, the proposed framework ( Figure 5) commences with the evaluation of the current state of MAM activities through a plant-based audit. In practice however, audits can also constitute the final stage of the framework whereby audit findings are used to improve the quality of system inputs. Once a reasonable understanding of the current state is gained, the next step involves identifying the relevant standards for PT health management, estimation of health index, failure analysis (including failure investigation using FTA, RBD and FMECA approaches) [51,[56][57][58][59][60][61][62], useful age and cost estimations. The final stages of the framework involve the harmonization of the acquired information to improve engineering decision-making as well as the routine evaluation of the suitability of such decisions.

Information Gathering and Triangulation
The authors of the current study decided on the application of a case study owing to the need to obtain an all-encompassing but yet in-depth practical understanding of MAM activities in PLN West Java, with particular emphasis on the power transformers through audit and benchmarking. The fundamental aim of a typical MAM audit is to generate and possibly institutionalise a systematic process that helps identify the areas of strengths and weaknesses of the existing system so as to easily identify where specific efforts need to be focused [63,64].  Data from various sources including plant documentation, questionnaires, interviews, direct observation and archival records were acquired. The selection of several information sources is based on the premise that no single data source is absolute; rather, the strengths of one source might complement the weaknesses of others. The questionnaire (see Appendix B) was divided into five main parts, called audit elements (AE). The first audit element (i.e. maintenance strategy and planning, AE1) sought information regarding general management of MAM activities, including; frequency and planning of maintenance, maintenance tasks criticality classifications, and the role of criticality ratings on strategies (i.e. BM, PPM and CBM) selection. The remaining audit elements (i.e. AE2-5) respectively sought information about critical failures and their investigation (AE2), staff competence and development (AE3), performance evaluation (AE4) and MAM life cycle cost evaluation (AE5).

AE1: Maintenance Strategy and Planning Activities
MAM activities are mainly managed by a computerised maintenance management system (CMMS) known as the Legacy System Application (LSA). The LSA comprises of 3 integrated applications, namely; Pekerjaan Instalasi Penyaluran (also known as JALUR), CBM and forced outage information system (FOIS). Though integrated, but each application handles a different aspect of maintenance. For instance, JALUR is only concerned with PPM (i.e. daily, weekly, monthly, 3-monthly, yearly and 2-yearly maintenance schedules) while CBM is a predictive maintenance application designed to acquire both visual inspection and measured transmission equipment data from operators. The FOIS and JALUR modules of the LSA are actively implemented but same cannot be said about the CBM module. Further examination of maintenance planning and their frequencies revealed that the so-called predictive maintenance activities as indicated by the LSA system were never done in advance but on a needs basis (usually when failures occur so as to obtain evidence for root cause failure analysis) which raised the question as to whether this is actually CBM or BM. According to the plant's most recent MAM records (i.e. 2016), the approximate annual split between Data from various sources including plant documentation, questionnaires, interviews, direct observation and archival records were acquired. The selection of several information sources is based on the premise that no single data source is absolute; rather, the strengths of one source might complement the weaknesses of others. The questionnaire (see Appendix A) was divided into five main parts, called audit elements (AE). The first audit element (i.e., maintenance strategy and planning, AE1) sought information regarding general management of MAM activities, including; frequency and planning of maintenance, maintenance tasks criticality classifications, and the role of criticality ratings on strategies (i.e., BM, PPM and CBM) selection. The remaining audit elements (i.e., AE2-5) respectively sought information about critical failures and their investigation (AE2), staff competence and development (AE3), performance evaluation (AE4) and MAM life cycle cost evaluation (AE5).

AE1: Maintenance Strategy and Planning Activities
MAM activities are mainly managed by a computerised maintenance management system (CMMS) known as the Legacy System Application (LSA). The LSA comprises of 3 integrated applications, namely; Pekerjaan Instalasi Penyaluran (also known as JALUR), CBM and forced outage information system (FOIS). Though integrated, but each application handles a different aspect of maintenance. For instance, JALUR is only concerned with PPM (i.e., daily, weekly, monthly, 3-monthly, yearly and 2-yearly maintenance schedules) while CBM is a predictive maintenance application designed to acquire both visual inspection and measured transmission equipment data from operators. The FOIS and JALUR modules of the LSA are actively implemented but same cannot be said about the CBM module. Further examination of maintenance planning and their frequencies revealed that the so-called predictive maintenance activities as indicated by the LSA system were never done in advance but on a needs basis (usually when failures occur so as to obtain evidence for root cause failure analysis) which raised the question as to whether this is actually CBM or BM. According to the plant's most recent Energies 2020, 13, 1937 9 of 32 MAM records (i.e., 2016), the approximate annual split between the different classes of maintenance philosophies is 1176 h of BM (45%), 1320 h of PPM (51%) and 96 h of CBM (4%). FOIS also revealed that as many as 1018 (of which 433 and 585 were classified outage and non-outage respectively) individual Java-Bali transmission system total failures were recorded within the last two years alone, which resulted in 14,846 MWh of energy not served (ENS). The transformer category of equipment accounted for 30% (305) of total failures and 97% of ENS (14,431 MWh). Table 3 provides a breakdown of the failures and the class of contributing equipment. Since the transformer category of equipment are the most critical based on their failure frequency and impact on ENS, a further review of 8-year (2008-2016) statistical data of transformer failures revealed that winding, bushing and OLTC respectively accounted for 83%, 13% and 4% of total failures. These failures and their corresponding periods are further illustrated in Table 4. It is quite clear from the failure records that winding and bushing failures are chronic in nature, which raises significant questions about the existing failure investigation approach within PLN.
To further confirm this assertion, a combination of two very popular risk assessments tools (fault tree analysis and reliability block diagram) was used to investigate one of the most recent power transformer bushing failures. Fault tree (FTA) [15,53,54,[65][66][67][68][69][70][71] and reliability block diagrams (RBD) [53,54,[72][73][74][75] are very illustrative performance evaluation tools that have been immensely used for investigating critical plant failures across a variety of industries within the last five decades.
The connections between the different events of a classical FTA is done using logic gates such as AND, OR, k-out-of-n, exclusive OR, inhibit, etc. However, since the relationships that exist between most real-life events can be comfortably represented by either AND or OR gates, the same approach is adopted here. The success of industry-based FTAs is often a function of the experience of the investigating team, which is why a brainstorming element is often recommended. Based on this premise and to foster practical knowledge transfer, a team-based FTA was employed at PLN. It is vital to note that besides visually representing the relationships between various causal factors of an FTA, it is also possible to estimate the probability of occurrence of the "unwanted" or "top event" using Equations (1) and (2) [53,54,[65][66][67][68][69][70][71]76]; OR gate: where n denotes the number of input fault events, P X OR gate is the probability of occurrence of OR gate's output fault event X OR gate and P(X k ) is the probability of occurrence of input fault event X k (for k = 1, 2, 3, . . . , n). AND gate: where P X AND gate is the probability of occurrence of AND gate's output fault event X AND gate . The FTA and RBD for the catastrophic failure of the power transformer 1 (PT 1) failure are respectively shown in Figures 6 and 7 where G1-G7 are the logic gates, IE1-IE6 are the intermediate events and b1-b10 are basic events. The results of the investigation shown in Figures 6 and 7 were then compared to the findings obtained from the RCFA earlier conducted in-house which only identified incompatible design as the cause of failure. Based on the RCFA recommendations, PT1 bushing was replaced but the replacement bushing only lasted four days. However, in addition to incompatible design (i.e., b1), the FTA also captured people and system lapses (i.e., b3-b10) which makes the current investigation more holistic despite similarities in team composition.
In addition to the FTA, an equivalent RBD (Figure 7) was generated so as to further expose the vulnerabilities of the entire system. An RBD is a collection of logical representations that either illustrates combinations of system elements that could lead to failure or success [53,54]. It is evident from both Figures 6 and 7 that people issues play a very significant role in the recurrent failures that have plagued the ability of PLN to realise its ENS targets. In addition to the FTA, an equivalent RBD ( Figure 7) was generated so as to further expose the vulnerabilities of the entire system. An RBD is a collection of logical representations that either illustrates combinations of system elements that could lead to failure or success [53][54]. It is evident from both Figures 6 and 7 that people issues play a very significant role in the recurrent failures that have plagued the ability of PLN to realise its ENS targets. The plant management team at PLN (West Java) recognizes the relevance of staff development, especially owing to the growing design and operational complexities associated with crucial industries such as power. The organisation has occasionally invested heavily in staff development programmes at different levels, including instances of maintenance staff attending master's level courses at some of the best institutions in the world. Despite these efforts, the general audit In addition to the FTA, an equivalent RBD (Figure 7) was generated so as to further expose the vulnerabilities of the entire system. An RBD is a collection of logical representations that either illustrates combinations of system elements that could lead to failure or success [53][54]. It is evident from both Figures 6 and 7 that people issues play a very significant role in the recurrent failures that have plagued the ability of PLN to realise its ENS targets. The plant management team at PLN (West Java) recognizes the relevance of staff development, especially owing to the growing design and operational complexities associated with crucial industries such as power. The organisation has occasionally invested heavily in staff development programmes at different levels, including instances of maintenance staff attending master's level courses at some of the best institutions in the world. Despite these efforts, the general audit responses and failure investigations still indicate that some of the core derelictions hinge on lack of adequate, systematic and up-to-date MAM training programmes. The fault tree in Figure 6 categorically attributed several causes of failure to staff skill levels. For instance, wrong installations, extended plant downtimes due to poor maintainability, poor maintenance procedures, etc. Some of the auditees further explained that the maintenance team made very negligible contributions to the The plant management team at PLN (West Java) recognizes the relevance of staff development, especially owing to the growing design and operational complexities associated with crucial industries such as power. The organisation has occasionally invested heavily in staff development programmes at different levels, including instances of maintenance staff attending master's level courses at some of the best institutions in the world. Despite these efforts, the general audit responses and failure investigations still indicate that some of the core derelictions hinge on lack of adequate, systematic and up-to-date MAM training programmes. The fault tree in Figure 6 categorically attributed several causes of failure to staff skill levels. For instance, wrong installations, extended plant downtimes due to poor maintainability, poor maintenance procedures, etc. Some of the auditees further explained that the maintenance team made very negligible contributions to the design and installation of new plant assets but rather inherit them along with their design flaws from the project team after commissioning. The incorporation of plant operators and maintainers into capital projects core teams could serve as: • A means of promoting asset ownership, since all parties would have contributed their respective ideas to the various stages of the design, installation and commission • An avenue for incorporating maintenance awareness into the very early stages of design and installation so as to avoid costly retrofitting. For instance, the audit and fault tree analysis revealed that accessibility issues were significant causes of poor maintainability.

•
An on-the-job training platform for plant operators and maintainers, whereby they can actively participate in the development of the standard operating procedures.

AE4: Maintenance Performance Evaluation
Performance evaluation is very vital to the sustainability of any MAM system, especially when it relates to assets within a capital intensive industry such as power. Routine audits and benchmarking are some of the most widely applied industrial performance evaluation tools. For an organisation like PLN with multiple plants across different regions in Indonesia, it would be expected that internal benchmarking activities are well-established since the different regional plants perform differently with regards to performance indicators such as ENS, MAM strategies split and maintenance workload allocation. According to historical data, a combination of CMMS records and response from auditees revealed that there is a significant sense of false economy at PLN with regards to maintenance workload tracking. The contributions of internal maintenance labour is not tracked and hence doesn't form part of the downtime cost estimation based on the premise that PLN maintenance staff are integral parts of the organisation and would always be available. Despite these limitations, the performance of PLN (West Java) with regards to AE4 was far better than it did in the other elements, owing to evidence of a recently concluded audit for ISO 55000 certification conducted by members of the Institute of Asset Management (IAM). This audit only focussed on establishing failure modes and effects analysis (FMEA) principles as a means of creating a criticality rating scheme that would help determine what assets to prioritise. Unlike the audit performed as a part of this study, that performed by IAM was a one-off exercise that did not cover all of the elements of a typical MAM system, but could provide a basis for future comparisons.

AE5: Maintenance and Asset Management Life Cycle Cost Evaluation
Despite the availability of relevant and sufficient data, there is no established framework for estimating maintenance life cycle cost of currently held assets which implies that this does not contribute significantly towards the engineering decision-making and budgeting process for plant assets.

Identification of Relevant Standards
There are various guidelines stipulated by well-known electrical standards organisations such as International Electro-technical Commission (IEC), Institute of Electrical and Electronics Engineers (IEEE) and American Society for Testing and Materials (ASTM) for individual parameters during in-service and shutdown measurements. For instance, ASTM D3612-02-2009/IEEE C57 104 2008/IEC 60599 2007 for dissolved gas analysis (DGA); IEC62021-1 for acidity level; IEC60814 for water content; IEC 60156-02 for dielectric strength; IEC 60247 for tan delta and metal in oil; etc. Table A1 in Appendix B provides a detailed summary of some commonly applied standards, which have also been consulted during this study.

Principles of PT Condition Assessment Using Overall Health Index (OHI) Approach
An accurately conducted OHI estimation can help quantify asset condition based on several criteria that provide reasonable indications of how close such an asset is to its end-of-life. OHI estimation is quite popular amongst academics and professionals in the power industry, with several academic publications [48,77] already stipulating their full details. However, our focus here is to develop a framework that can potentially help energy providers such as PLN to shift the paradigm from just performing OHI because it is a recommendation (which has not adequately promoted process ownership, based on the MAM audit results) to a true value addition tool that is adequately incorporated into engineering decision-making processes. The accurate estimation of OHI is quite critical and often necessitates the inclusion of two basic test classes; electrical and insulating oil tests [48]. The electrical tests are basically conducted to ascertain the insulation integrity of PT windings which also establishes the power factor (PF) for overall insulation of windings and bushings. The PF for a typical PT is estimated based on measured values of voltage (V), current (I) and power (P), using Equation (3) [77]: A chart of the commonly used classifications of PF and the corresponding PT health is provided in Table A2 in Appendix B.
Insulating oil tests on the other hand are conducted to determine the suitability of the insulating oils. This evaluation of oil integrity often entails the monitoring of condition indicators such as dissolved gas analysis (DGA), furfural and oil quality. The respective limit values of scoring and weighting for each of the parameters is often mathematically estimated using Equation (4) and then compared to the standard chart shown in Table A3 (Appendix B). For example, the score for DGA is divided into six grades, with one denoting good/fit-for-purpose and six denoting poor. For the weighting factor on the other hand, factor importance increases with the allocated number (i.e., lowest number indicates least important and vice versa). In practice, it is crucial to note that DGA information by itself may or may not be self-sufficient for accurately establishing the health status of a PT, owing to the fact that normal operation could generate some of the gases. It is therefore vital to integrate all other historical information such as previous faults, maintenance, OEM data and loading routine [48]: The oil quality factor (OQF) can be similarly estimated using the approach described for DGAF in Equation (4) but the scoring and weighting regimes differ as clearly depicted in Table A4 (Appendix B). Table A4 (Appendix B) provides the grading methods for estimating OQF based on IEEE C57.106-2006. Though not conducted on a periodic basis for PTs, furan tests can be very useful post-diagnostic estimators for the amount of polymerisation associated with the paper insulation within PT oils. Typical furan compounds that emerge from such polymerisations include 2-furaldehyde (2-FAL), 2-acetylfuran (2-ACF), 2-furfuryl alcohol (2-FOL), 5-methyl-2-furaldehyde (5-MEF) and 5-hydroxymethyl-2-furadehyde (5-HMF). Extensive information with regards to measurement and classifications of furanic compounds are available in an earlier study by Pahlavanpour and Martins [78]. Furan tests are often recommended for ageing PTs (typically those more than 25 years old) or if signs of overheating are observed. If reliable furan measurement data is available, then such data can be included in the OHI calculation of the monitored PT. However, if the PT oil has been changed or reclaimed, furan measurements will not provide any meaningful information about the insulation paper degradation [48].
The final stage of PT health assessment is the estimation of the OHI by harmonizing the values obtained from each of the condition assessment criteria. Despite the availability of ample information [48,77] with regards to the application of OHI for PT health monitoring, a significant number of electricity generation and distribution companies including the case study PLN (West Java), prefer to implement a more simplistic approach of failure probability estimation. This approach as currently implemented at PLN (West Java) is based on a (n SI × n CI ) matrix of susceptibility (SI) and condition indexes (CI), whereby SI and CI both vary from 1-3 respectively. CI parameters directly relate to the PT while SI parameters on the other hand relate to external factors such as load type, true fault current, etc. The SIs and CIs are classified according to known standards, whereby values ranging from 7-9, 4-6 and 1-3 respectively correspond to good, fair and poor. Equation (5) further provides a description of the matrix configuration for better clarity: The product of the indexes are then used to classify the PT into grades A (<10% probability of failure), B (10-30% probability of failure), C (30-70% probability of failure), D (70-90% probability of failure) and E (>90% probability of failure). While this approach is quick and simple, its proneness to high levels of subjectivity makes it unsuitable for critical engineering decision analysis, especially when such decisions involve huge capital expenditures (CAPEX). As an illustration, a PT with condition index of 1 (i.e., poor) that operates in a good environment (i.e., susceptibility index = 9) will have the same probability of failure as another PT with condition index of 9 (i.e., good) that operates in a poor environment (i.e., susceptibility index = 1). Such generalised classifications often lead to the wrongful allocation of maintenance actions and resources, which at best increases overall maintenance cost and at worst leads to catastrophic failures. In order to significantly minimise subjectivity that has contributed to some of the failures shown in Table 4, the current study explores practical implementation of OHI estimation model reported in Jahromi et al. [48] which considers many more factors relating to PT health. During OHI estimation, the total condition score of each component is divided by its maximum condition score and then multiplied by 100 so as to always maintain a band of scores that lies between 0 (i.e., totally deteriorated) and 100 (i.e., perfect state of health). The A-E condition ratings shown in Table A11 (Appendix C) are converted to a factor between 4 and 0, respectively, referred to as health indication factor (HIF). Equation (6) provides the mathematical relationship of the various condition assessment parameters: The usual practice is to directly obtain recommended values of Kj and HIFj from standard tables such as that shown in Table A11 (Appendix C). These values are solely based on a comprehensive international survey conducted by a working group of CIGRE on large PT failures, where it was adjudged that approximately 40% of failures were associated with OLTC and the remaining 60% were attributed to the PT [79]. Since these percentage allocations are based on broad and generalised surveys, they may or may not accurately represent the true situations within every plant. In order to generate OHI that accurately represents the PTs within the case study, plant failure records were used to modify the weighting factors shown in Equation (6). According to the 8-year failure records examined during the MAM plant audit (also shown in Table 4), PT and OLTC associated failures respectively accounted for approximately 80% and 20% of total failures within the studied period. Hence, Equation (7) has been modified accordingly to generate the proposed representative OHI shown in Table 5. For the purpose of practical illustration, the OHI results in Table 5 have been computed for just PT1 Kembangan that encountered the catastrophic failure investigated using the FTA and RBD in Figures 6 and 7. The OHIs for all three phases (R, S and T) were estimated to be 53, 44 and 45 which correspond to fair, poor and poor conditions respectively.

Systematic Determination of Remaining Useful Life Using OHI and Failure Distribution
While the MAM patterns and requirements may differ, it is generally understood that all plant assets (including PTs) obey the different stages of a typical life cycle framework. Based on this premise, asset owners aiming for cost-effect business operations must have good understanding of how to predict the end of useful life of their assets, so as to proactively plan for replacement or upgrade. The estimation of OHI in itself is just a means to an end when it comes to CAPEX decisions; however, it provides valuable indications as to when a capital asset such as PT is approaching the end of its useful life. PTs are characterised by a certain level of design strength which diminishes in proportion to the wear and tear associated with routine operation. It can therefore be assumed that the probability of PT failure is equivalent to the probability of the stress generated from routine operation exceeding the characteristic strength [48]. Figure 8 provides a graphical illustration of how OHI and failure probability of the Kembangan PT at PLN (West Java) can be used to estimate its effective age.
PT are 35 (phase R), 30 (phase S) and 30 (phase T) respectively. It should be noted that OHI computed here are based on actual heath indexes (HIs) for each of the PT condition assessment parameters provided in Tables D1-D7 and Figure D1 in Appendix D. Once the OHIs are known, the corresponding probability of failures for each PT phase can be easily obtained by reading-off the values from the standard curve as shown in Figure 9, which is equivalent to 0.125, 0.15 and 0.15 for R, S and T respectively.  Table 6 years (i.e. in-service age) and its effective age per phase based on OHI/failure rate relationship are 29.5, 39.6 and 39.6 years. Therefore, the ageing rates per phase can be obtained by dividing the latter by the former which is equivalent to 4.91, 6.6 and 6.6 respectively, as the relationship in Equation (8) shows: where represents the ageing rate for the studied PT phase (i.e. R, S or T), while , and are respectively the effective and operational ages. Critical plant assets are often a fusion of both maintainable and non-maintainable items. During the process of remaining useful life estimation, the maintainable items can be excluded (i.e., setting their OHIs to zero) based on the assumption that this class of items have the ability to return to "as new condition" through the initiation of appropriate maintenance interventions. Hence, by removing the maintainable items from the OHI list in Table 5, the resultant OHIs for the Kembangan PT are 35 (phase R), 30 (phase S) and 30 (phase T) respectively. It should be noted that OHI computed here are based on actual heath indexes (HIs) for each of the PT condition assessment parameters provided in Tables A5-A11 and Figure A1 in Appendix C. Once the OHIs are known, the corresponding probability of failures for each PT phase can be easily obtained by reading-off the values from the standard curve as shown in Figure 9, which is equivalent to 0.125, 0.15 and 0.15 for R, S and T respectively.  Figure D1 in Appendix D. Once the OHIs are known, the corresponding probability of failures for each PT phase can be easily obtained by reading-off the values from the standard curve as shown in Figure 9, which is equivalent to 0.125, 0.15 and 0.15 for R, S and T respectively.
Since the standard chart provided in Figure 8 was generated from a survey of PTs under different operating contexts, the results obtained from it are most suited for ballpark estimates. Therefore, by plotting the failure rates obtained from Figure 8 onto Figure 9a, the effective age for each phase was obtained as 29.5, 39.6 and 39.6 for R, S and T, respectively.  Table 6 years (i.e. in-service age) and its effective age per phase based on OHI/failure rate relationship are 29.5, 39.6 and 39.6 years. Therefore, the ageing rates per phase can be obtained by dividing the latter by the former which is equivalent to 4.91, 6.6 and 6.6 respectively, as the relationship in Equation (8) shows: where represents the ageing rate for the studied PT phase (i.e. R, S or T), while , and are respectively the effective and operational ages. Since the standard chart provided in Figure 8 was generated from a survey of PTs under different operating contexts, the results obtained from it are most suited for ballpark estimates. Therefore, by plotting the failure rates obtained from Figure 8 onto Figure 9a, the effective age for each phase was obtained as 29.5, 39.6 and 39.6 for R, S and T, respectively. Table 6 years (i.e., in-service age) and its effective age per phase based on OHI/failure rate relationship are 29.5, 39.6 and 39.6 years. Therefore, the ageing rates per phase can be obtained by dividing the latter by the former which is equivalent to 4.91, 6.6 and 6.6 respectively, as the relationship in Equation (8) shows: Energies 2020, 13,1937 17 of 32 where γ P represents the ageing rate for the studied PT phase (i.e., R, S or T), while A e f f ,P and A O are respectively the effective and operational ages. Once the ageing rate (γ P ), effective age (A e f f ,P ) and the age (A TF ) at which the probability of failure will equal 99% (i.e., approximately 56 years from Figure 9b) are known, the remaining useful life (µ Li f e ) per phase were estimated in accordance with Equation (9) and the corresponding results are summarised in Table 6: It is crucial to highlight that the remaining useful life estimated based on 99% probability of failure is very conservative and unlikely to be implemented indubitably in practice, as it may leave no room for reaction to catastrophic plant downtime. However, it provides good basis upon which asset owners can plan as well as manage their MAM budgets cost-effectively.

MAM Life Cycle Cost Mapping
The current body of literature holds substantial guidance on asset life cycle costing analysis (LCCA) [80][81][82][83][84]. However, the practical integration of LCCA approaches into routine plant management systems especially MAM cannot be described as widespread. One fundamental limitation of the conventional LCCA approaches is lack of full acknowledgement of the interdependence that exists between system reliability and cost [81][82][83][84]. The current study proposes a MAM life cycle cost (MAMLCC) for PTs, based on item structure and maintenance regimes (i.e., BM, PPM & CBM for which their respective intervals are shown in column 3 of Table 5). For easy identification of the materials and spares required, the PT system is broken down into electromagnetic circuit, current carrying circuit, dielectric, mechanical structure, protection/relay system, cooling system, bushing and tap changer.
The approach to the maintenance costing adopted here is based on the maintenance regimes namely BM, PPM and CBM [85][86][87]. However, the maintenance costing strategy at PLN (West Java) recognises two main maintenance regimes (i.e., preventive and BM). BM represents maintenance costs incurred post-failure while the preventive integrates both PPM and CBM [88][89][90] into a common class owing to the fact these are activities performed pre-failure. In addition to the cost components of the individual maintenance regimes (e.g., spare parts/materials, maintenance outage cost, major repairs cost, minor repairs cost and labour), a significant percentage of total MAM cost can be attributed to failure cost (i.e., extra fuel cost and cost of ENS). For clarity, Figure 10 provides a flowchart of the major MAM cost elements for a typical PT. It should be noted that other vital cost elements such as safety and logistics/supply chain costs are not standalone elements of the total MAM cost because they have been integrated into the materials and labour costs. Based on the cost elements mapped in Figure 10, the annual TMAMC of PLN's (West Java) PT can be estimated using Equation (10): where PMC, BMC and FC denote preventive maintenance, corrective maintenance and failure costs, respectively, as already shown in Figure 10, which were individually estimated for the case study according to Equations (11)- (14): In Equations (11)- (14), ( ), ( ), CEC and c respectively represent the equipment failure rate, probability of major repairs, critical equipment costs and critical equipment.
The historical and present values for each of the critical maintenance cost elements that constitute TMAMC were then mapped and estimated for the entire remaining useful life so as to predict potential asset renewal stage. In order to maintain the coherence of text within the study, complete details of the mapped PLN (West Java) cost data used for estimating the optimum replacement periods shown in Figure 11 are also provided in Appendix E. The optimum period (i.e. after 4 years) was determined based on the intersection between TMAMC and the net present value (NPV) of replacement costs over the entire remaining useful life. While the PT may still be capable of performing its specified activities over the remainder of its useful life, the maintenance cost associated with such an asset becomes enormous which then calls cost effectiveness into question. It Based on the cost elements mapped in Figure 10, the annual TMAMC of PLN's (West Java) PT can be estimated using Equation (10): where PMC, BMC and FC denote preventive maintenance, corrective maintenance and failure costs, respectively, as already shown in Figure 10, which were individually estimated for the case study according to Equations (11)- (14): In Equations (11)- (14), λ(t), ρ(t), CEC and c respectively represent the equipment failure rate, probability of major repairs, critical equipment costs and critical equipment.
The historical and present values for each of the critical maintenance cost elements that constitute TMAMC were then mapped and estimated for the entire remaining useful life so as to predict potential asset renewal stage. In order to maintain the coherence of text within the study, complete details of the mapped PLN (West Java) cost data used for estimating the optimum replacement periods shown in Figure 11 are also provided in Appendix D. The optimum period (i.e., after 4 years) was determined based on the intersection between TMAMC and the net present value (NPV) of replacement costs over the entire remaining useful life. While the PT may still be capable of performing its specified activities over the remainder of its useful life, the maintenance cost associated with such an asset becomes enormous which then calls cost effectiveness into question. It is well acknowledged that asset replacement decisions are far from easy, owing to the huge CAPEX associated, especially for critical assets such as PTs. However, such analysis allows decision-makers to adequately understand the implications of existing MAM strategies and plan for the future. With reference to the MAM audit results and Figures 6 and 7, immediate actions could include the following: • Reducing the dominance of BM activities through prudent enhancement of CBM activities so that unnecessary failure costs (i.e., EFC and ENSC) can be eliminated.

•
Thorough assessment of maintainability issues (i.e., events IE6, b1, b5, etc.) during equipment design and commissioning stages as these may significantly increase downtime, which negatively impact MAM cost-effectiveness.
Energies 2020, 13, x FOR PEER REVIEW 19 of 33 is well acknowledged that asset replacement decisions are far from easy, owing to the huge CAPEX associated, especially for critical assets such as PTs. However, such analysis allows decision-makers to adequately understand the implications of existing MAM strategies and plan for the future. With reference to the MAM audit results and Figures 6-7, immediate actions could include the following:  Reducing the dominance of BM activities through prudent enhancement of CBM activities so that unnecessary failure costs (i.e. EFC and ENSC) can be eliminated.  Thorough assessment of maintainability issues (i.e. events IE6, b1, b5, etc.) during equipment design and commissioning stages as these may significantly increase downtime, which negatively impact MAM cost-effectiveness. Figure 11. Illustration of optimum replacement period for PT Kembangan.

Implementation Action Plan and Concluding Remarks
The need to understand the cost implications of owning plant assets, particularly operation and maintenance, is often assumed to be common knowledge amongst academics and industry professionals. However, practical engagement with some of the most critical industries such as power and manufacturing has indicated that this philosophy is not as widespread as initially anticipated, which is perhaps due to the existence of numerous cost mapping tools and fragmentary information. The current body of literature contains various studies that individually describe the theories and implementation of asset management principles such as life cycle costing, reliability/maintainability analysis, failure modes & effects analysis, overall health index (OHI) analysis, fault tree analysis, etc. However, to the best understanding of the authors of the current study, very limited studies provide an avenue by which the collective strengths of these proven tools can be adequately synergized in practice. The uniqueness of the current study lies in the fact that it provides a very systematic and easy-to-implement framework towards achieving cost-effective MAM, using a case study. Owing to the fact that human reluctance to change is one of the main limiters to learning new principles, the fundamental rationale here is to significantly minimise the steepness of the learning curve for industry professionals in maintenance management by encouraging the optimisation of tools that are reasonably popular to them.
Besides simplifying but at the same time harmonising the cost mapping process for critical power generation and distribution plant assets, the proposed framework also provides a means of querying the existing practice through the use of proven risk assessment tools such as fault tree analysis (FTA) and reliability block diagrams (RBDs). The proposed framework commences with a plant-based audit of the case study (i.e. PLN West Java) so as to develop in-depth practical understanding of how MAM activities feed into overall company strategy for asset replacement.

Implementation Action Plan and Concluding Remarks
The need to understand the cost implications of owning plant assets, particularly operation and maintenance, is often assumed to be common knowledge amongst academics and industry professionals. However, practical engagement with some of the most critical industries such as power and manufacturing has indicated that this philosophy is not as widespread as initially anticipated, which is perhaps due to the existence of numerous cost mapping tools and fragmentary information. The current body of literature contains various studies that individually describe the theories and implementation of asset management principles such as life cycle costing, reliability/maintainability analysis, failure modes & effects analysis, overall health index (OHI) analysis, fault tree analysis, etc. However, to the best understanding of the authors of the current study, very limited studies provide an avenue by which the collective strengths of these proven tools can be adequately synergized in practice. The uniqueness of the current study lies in the fact that it provides a very systematic and easy-to-implement framework towards achieving cost-effective MAM, using a case study. Owing to the fact that human reluctance to change is one of the main limiters to learning new principles, the fundamental rationale here is to significantly minimise the steepness of the learning curve for industry professionals in maintenance management by encouraging the optimisation of tools that are reasonably popular to them.
Besides simplifying but at the same time harmonising the cost mapping process for critical power generation and distribution plant assets, the proposed framework also provides a means of querying Energies 2020, 13,1937 20 of 32 the existing practice through the use of proven risk assessment tools such as fault tree analysis (FTA) and reliability block diagrams (RBDs). The proposed framework commences with a plant-based audit of the case study (i.e., PLN West Java) so as to develop in-depth practical understanding of how MAM activities feed into overall company strategy for asset replacement. Particular focal points of the audit include failure investigation, maintenance policy, overall health assessment, maintenance systems, customer satisfaction (with regards to energy not served) and skills development. During our initial interactions with the auditees, our team was made to believe that all high impact plant failures are adequately investigated using standard root cause analysis (RCA) principles after which corrective action plans are generated and tracked along all phases of implementation. However, our investigation of a very recent catastrophic power transformer (PT) explosion using FTA and RBD principles revealed that the previous RCAs are too outward looking (i.e., mainly focusing on design, manufacturing and installation issues) and therefore misses crucial internal lapses, especially the people issues such as maintenance skills shortage, lack of proper understanding of new installations, poor operational maintainability due to internal process delays, poor maintenance procedures and poor assessment skills. This is perhaps why capital intensive failures of bushings and windings have continuously plagued PLN's (West Java) operations over the last decade.
Once the existing MAM standing of PLN (West Java) was understood, the remainder of the framework focused on determining the vital maintenance cost elements across the remaining useful life of the examined PT, so that this can inform asset owners of the adequacy of existing MAM initiatives or otherwise. The remaining useful life estimation was solely based on plant-specific OHI and failure rate information. It is worth noting that as opposed to the common practice of estimating OHI based on the universal notion that adopts a 60% and 40% allocation of failure causes to load tap changer (LTC) and PT, respectively (based on an international survey of large PT failures), the current study slightly modifies the standard equation to reflect actual PLN (West Java) failure data between 2008 to 2016 which reveals that 80% and 20% of failures are caused by PT and LTC respectively. Finally, the majority of the findings from this study are currently being incorporated into PLN's (West Java) asset management strategy especially with regards to estimating the potential operation and maintenance cost of new PTs, owing to the surging need to expand the Indonesian power distribution. As a part of continuous improvement, future research endeavours are planned towards reviewing the robustness of this framework, particularly with regards to maintenance costs optimisation, failure investigation, maintenance strategy allocation and systematic maintenance skills upgrade. Acknowledgments: The authors of this study are immensely grateful to management of PLN (West Java) and the maintenance team for the provision of unrestricted access to their operation and maintenance management data as well as permission to use such data for engineering-related education at the University of Manchester (United Kingdom). Special appreciation is also directed to our anonymous interviewees from the maintenance and reliability team of PLN (West Java) for agreeing to devote time from their extremely busy schedules.

Conflicts of Interest:
The authors declare no conflict of interest.

Appendix A. MAM Audit Questionnaire
Please rate the extent to which the following audit elements are established within PLN (West Java region). How often are BM tasks directed to PLN's (West Java) assets with the least impact of downtime?

Critical failures and their investigations (AE2)
How would you rate PLN's (West Java) failure reporting system?
What percentage of failures are investigated using reliability or risk assessment tools such as fault tree analysis and reliability block diagrams?
What percentage of corrective actions generated from failure investigations are implemented?

Staff competence and development (AE3)
How would you rate the frequency and regularity of reliability, maintenance and asset management trainings?
What percentage of your plant maintenance team has been trained on reliability-based failure investigation techniques such as fault tree analysis and reliability block diagrams?
What is the level of involvement of maintenance staff in major plat projects?

Performance evaluation (AE4)
How often is PLN's (West Java) maintenance strategy reviewed?
How would you rate maintenance performance benchmarking activities at PLN (West Java)?
How would you rate the frequency and adequacy of maintenance audits in PLN (West Java)?

Maintenance and asset management life cycle cost evaluation (AE5)
How

PART B: ADDITIONAL COMMENTS
Please comment on any other factor(s) that influence maintenance and asset management within PLN (West Java).

Appendix C: Standards
Energies 2020, 13, x FOR PEER REVIEW 22 How would you rate the level of PPM optimisation at PLN (West Java)?
How often are BM tasks directed to PLN's (West Java) assets with the least impact of downtime?

Critical failures and their investigations (AE2)
How would you rate PLN's (West Java) failure reporting system?
What percentage of failures are investigated using reliability or risk assessment tools such as fault tree analysis and reliability block diagrams?
What percentage of corrective actions generated from failure investigations are implemented?

Staff competence and development (AE3)
How would you rate the frequency and regularity of reliability, maintenance and asset management trainings?
What percentage of your plant maintenance team has been trained on reliability-based failure investigation techniques such as fault tree analysis and reliability block diagrams?
What is the level of involvement of maintenance staff in major plat projects?

Performance evaluation (AE4)
How often is PLN's (West Java) maintenance strategy reviewed?
How would you rate maintenance performance benchmarking activities at PLN (West Java)?
How would you rate the frequency and adequacy of maintenance audits in PLN (West Java)? How often are BM tasks directed to PLN's (West Java) assets with the least impact of downtime?

Critical failures and their investigations (AE2)
How would you rate PLN's (West Java) failure reporting system?
What percentage of failures are investigated using reliability or risk assessment tools such as fault tree analysis and reliability block diagrams?
What percentage of corrective actions generated from failure investigations are implemented?

Staff competence and development (AE3)
How would you rate the frequency and regularity of reliability, maintenance and asset management trainings?
What percentage of your plant maintenance team has been trained on reliability-based failure investigation techniques such as fault tree analysis and reliability block diagrams?
What is the level of involvement of maintenance staff in major plat projects?

Performance evaluation (AE4)
How often is PLN's (West Java) maintenance strategy reviewed?
How would you rate maintenance performance benchmarking activities at PLN (West Java)?
How would you rate the frequency and adequacy of maintenance audits in PLN (West Java)? How often are BM tasks directed to PLN's (West Java) assets with the least impact of downtime?

Critical failures and their investigations (AE2)
How would you rate PLN's (West Java) failure reporting system?
What percentage of failures are investigated using reliability or risk assessment tools such as fault tree analysis and reliability block diagrams?
What percentage of corrective actions generated from failure investigations are implemented?

Staff competence and development (AE3)
How would you rate the frequency and regularity of reliability, maintenance and asset management trainings?
What percentage of your plant maintenance team has been trained on reliability-based failure investigation techniques such as fault tree analysis and reliability block diagrams?
What is the level of involvement of maintenance staff in major plat projects?

Performance evaluation (AE4)
How often is PLN's (West Java) maintenance strategy reviewed?
How would you rate maintenance performance benchmarking activities at PLN (West Java)?
How would you rate the frequency and adequacy of maintenance audits in PLN (West Java)? How often are BM tasks directed to PLN's (West Java) assets with the least impact of downtime?

Critical failures and their investigations (AE2)
How would you rate PLN's (West Java) failure reporting system?
What percentage of failures are investigated using reliability or risk assessment tools such as fault tree analysis and reliability block diagrams?
What percentage of corrective actions generated from failure investigations are implemented?

Staff competence and development (AE3)
How would you rate the frequency and regularity of reliability, maintenance and asset management trainings?
What percentage of your plant maintenance team has been trained on reliability-based failure investigation techniques such as fault tree analysis and reliability block diagrams?
What is the level of involvement of maintenance staff in major plat projects?

Performance evaluation (AE4)
How often is PLN's (West Java) maintenance strategy reviewed?
How would you rate maintenance performance benchmarking activities at PLN (West Java)?
How would you rate the frequency and adequacy of maintenance audits in PLN (West Java)?

Staff competence and development (AE3)
How would you rate the frequency and regularity of reliability, maintenance and asset management trainings? How often are BM tasks directed to PLN's (West Java) assets with the least impact of downtime?

Critical failures and their investigations (AE2)
How would you rate PLN's (West Java) failure reporting system?
What percentage of failures are investigated using reliability or risk assessment tools such as fault tree analysis and reliability block diagrams?
What percentage of corrective actions generated from failure investigations are implemented?
Energies 2020, 13, x FOR PEER REVIEW 22 How would you rate the level of PPM optimisation at PLN (West Java)?
How often are BM tasks directed to PLN's (West Java) assets with the least impact of downtime?

Critical failures and their investigations (AE2)
How would you rate PLN's (West Java) failure reporting system?
What percentage of failures are investigated using reliability or risk assessment tools such as fault tree analysis and reliability block diagrams?
What percentage of corrective actions generated from failure investigations are implemented?

PART B: ADDITIONAL COMMENTS
Please comment on any other factor(s) that influence maintenance and asset management within PLN (West Java).  Table A3 for each of the gasses contained in the oil, while DGAF is the dissolved gas analysis factor.