Evaluation of the Summer Overheating Phenomenon in Reinforced Concrete and Cross Laminated Timber Residential Buildings in the Cold and Severe Cold Regions of China

: As the climate changed in recent years, an increase in summer indoor temperatures in severe cold and cold regions of China has started to a ﬀ ect thermal comfort. However, the local design standard for energy e ﬃ ciency does not recognize this phenomenon. This paper reports the potential overheating phenomenon in residential buildings and examines the rationale for the current thermal designs adopted in severe cold and cold regions of China. In this study, the two most commonly used building materials, reinforced concrete (RC) and cross laminated timber (CLT), are used separately in the design of an 18-story residential building envelope located in six di ﬀ erent cities in the severe cold and cold regions. The energy consumption and indoor operative temperatures during the operation of these buildings are simulated using Integrated Environmental Solutions Virtual Environment (IES VE). The results demonstrate that both the RC and the CLT buildings experience varying degrees of overheating in any climate subregion. The CLT buildings have longer overheating hours compared to the RC buildings, especially in the cold regions. The results also indicate that for apartments on higher stories, the cooling energy consumption and indoor temperature also increase gradually. The research results suggest that the local design standard for energy e ﬃ ciency needs to be adjusted by adding thermal design methods for summer to reduce the periods of overheating.


Climate Change and Northeast China
Climate change is one of the great challenges the world is facing today. In 2019, the average temperature across global land and ocean surfaces was 14.85 • C, an increase of 0.95 • C over the twentieth century, making 2019 the second warmest year on record. It is estimated that the average temperature could increase by 1.1 to 5.4 • C in 2100 according to a report by the National Oceanic and Atmospheric Administration (NOAA) [1]. The Intergovernmental Panel on Climate Change (IPCC) also announced that land regions should experience more severe increases than the ocean regions, and indicated that the warming trend in the northern hemisphere was more significant from 2006-2015 temperature could increase by 1.1 to 5.4 °C in 2100 according to a report by the National Oceanic and Atmospheric Administration (NOAA) [1]. The Intergovernmental Panel on Climate Change (IPCC) also announced that land regions should experience more severe increases than the ocean regions, and indicated that the warming trend in the northern hemisphere was more significant from 2006-2015 than from , and this trend is more obvious at higher latitudes [2]. Climate change raises the temperature of the northern hemisphere in summer, and China is located in this hemisphere, thus facing the same challenge [3], especially in Northeast China (Figure 1). There is growing evidence of overheating risk in warm weather in buildings in temperate climate regions [4]. Overheating has been observed in many countries in the northern hemisphere [4][5][6][7][8][9]. Overheating affects the health of occupants, with a particular bearing on the quality of sleep that leads to reduced productivity [10][11][12]. In some extreme cases, heat stress caused by overheating can result in death, particularly in some vulnerable groups [4]. Over 2000 people died in the UK during the 10-day European heatwave in 2003 [13]. It is predicted that the number of deaths related to overheating could triple by 2050 [14].

Global Overheating Building Standards
At present, there is no internationally accepted definition of overheating, and different countries have developed their own criterion for the assessment of overheating. The Chartered Institution of Building Services Engineers (CIBSE) produced the CIBSE TM36 standard for climate change and the indoor environment. Here, the criterion for overheating in dwellings is of temperatures above 28 °C in living areas for more than 1% of occupied hours and above 25 °C in bedrooms for more than 1% of occupied hours [15]. In subsequent standards, CIBSE TM52 points out the operative temperature of predominantly mechanically ventilated rooms in summer should not exceed 26 °C, and higher temperatures should not occur for more than 3% of the occupied time [16]. CIBSE TM59 specifies that the operative temperature in bedrooms between 10:00 p.m. and 7:00 a.m. should not exceed 26 °C, and higher temperatures should not occur for more than 1% of the annual hours in predominantly naturally ventilated dwellings [17]. The ANSI/ASHRAE Standard

Global Overheating Building Standards
At present, there is no internationally accepted definition of overheating, and different countries have developed their own criterion for the assessment of overheating. The Chartered Institution of Building Services Engineers (CIBSE) produced the CIBSE TM36 standard for climate change and the indoor environment. Here, the criterion for overheating in dwellings is of temperatures above 28 • C in living areas for more than 1% of occupied hours and above 25 • C in bedrooms for more than 1% of occupied hours [15]. In subsequent standards, CIBSE TM52 points out the operative temperature of predominantly mechanically ventilated rooms in summer should not exceed 26 • C, and higher temperatures should not occur for more than 3% of the occupied time [16]. CIBSE TM59 specifies that the operative temperature in bedrooms between 10:00 p.m. and 7:00 a.m. should not exceed 26 • C, and higher temperatures should not occur for more than 1% of the annual hours in predominantly naturally ventilated dwellings [17]. The ANSI/ASHRAE Standard 55-2017 developed by the American Society of Heating, Refrigerating, and Air Conditioning Engineers (ASHRAE) indicates the acceptable operative temperature ranges for naturally conditioned spaces [18]. In European Standard EN 15251, the maximum indoor temperature for residential mechanically cooled buildings is 26 • C. The standard also regulates the operative temperature range for the comfort zone in residential buildings without mechanical cooling systems, and indicates that the use of fans can increase the upper limits by a few degrees depending on the air velocity generated by the fan [19]. A discussion paper titled "Next steps Energies 2020, 13, 6305 3 of 25 in defining overheating from zero carbon hub (ZCH)" recommends that bedrooms should not be designed to experience temperatures above 26 • C for more than a specified percentage (1%) of occupied hours [20]. The Passive House Planning Package (PHPP) software released by the Passive House Institute defines 25 • C is the limit for overheating, classifying the outcome as catastrophic if higher temperatures are experienced for over 15% of the time and as poor in the case of 10 to 15% of the time [21]. Indoor operative temperature has been adopted in many specifications as the criteria for assessment of the overheating risk. In addition, the operative temperature is obtained by combining both the air temperature and the mean radiant temperature, which is deemed to be an effective way to describe the actual experience of the people [20]. The thermal comfort and overheating criteria are summarized and presented in Figure 2.

National Standard for Energy Saving Design of Residential Buildings in Severe Cold and Cold Areas of China
China is divided into several distinct climate zones due to its vast territory. According to the Code for Thermal Design of Civil Buildings (GB 50176-2016), there are five climate regions in China: severe cold, cold, temperate, hot summer and cold winter, and hot summer and warm winter. According to the number of cooling degree days based on 26 • C and heating degree days based on 18 • C, the severe cold and cold regions can be subdivided into five regions: "severe cold region 1A," "severe cold region 1B," "severe cold region 1C," "cold region 2A," and "cold region 2B" [22]. In clause 4.1 of the general provisions in the Design Standard for Energy Efficiency of Residential Buildings in Severe Cold and Cold zones (JGJ 26-2018) [23], it clearly stipulates that windproof design should be considered for the entrance and exit to buildings in regions 1A, 1B, 1C, and 2A in winter, and ventilation in summer should be considered for region 2B. Furthermore, clause 4.2 for thermal design of the structural envelope specifies that windows on the south (including balcony glazing) of buildings in region 2B should be provided with horizontal shading, whilst windows on the east and west façade should be provided with movable sunshades. However, the code only specifies the heating insulation design for region Energies 2020, 13, 6305 4 of 25 2B in summer, and there are no clear criteria or design methods to mitigate the overheating problem in the summer, such as using shading designs for the solar gain prevention, phase change materials (PCM), or movable insulation layers for the other regions in the severe cold and cold regions.

Studies on Overheating in Biobased and RC Buildings
Biobased materials and reinforced concrete (RC) are the two main classifications of building materials used in China. RC is currently the most popular structural material, and the proportion of the urban and rural residential buildings using concrete and cement was 95.8% in 2018 [24]. However, as a biobased material, timber has thousands of years of application in China, and the importance of using timber has been recognized by the government [25]. In addition, there are abundant forest resources in the severe cold and cold regions, and woodland accounts for 40.9% of the land area [26]. CLT commonly consists of an uneven number of timber panel layers (3, 5, or 7). Each timber panel is placed side-by-side in a 90 • arrangement [27]. CLT has good physical and mechanical properties and the use of this building material can lower carbon emissions and save energy in cold climates [28,29]. Research has shown that RC and timber structures incur the risk of overheating due to the rising temperatures [30]. Willand et al. [8] tested the temperatures and energy efficiency rating of living rooms in the summer in 107 homes in Australia. They highlighted that 20% of the living rooms tested maximum indoor temperatures exceeding 33 • C. Mavrogianni et al. [31] investigated indoor overheating assessments of 101 London dwellings in summer 2009 using temperature monitoring, a questionnaire survey, and simulation. Results indicated overheating phenomenon occurred in the majority of the living rooms and bedrooms surveyed. Sharifi et al. [32] investigated the summer indoor operative temperatures of apartments built in Adelaide by the year 2010. They clarified the overheating period during the summer months and pointed out that the daily air temperature of the top floor was above 32 • C. Appropriately one-fifth of the total summer hours were overheated. Adekunle et al. [30] focused on summer overheating and occupant comfort in two prefabricated timber houses in southeast England and found that 67% of the rooms had extreme overheating in summer, according to the CIBSE comfort model during the monitoring period, stating that the risk of overheating with timber construction is higher than that of more heavyweight construction on account of the lack of thermal mass in prefabricated timber. Pajek et al. [33] compared the surface temperature of lightweight construction (timber-framed) (LWC) and heavyweight construction (reinforced concrete) (HWC), and found that it was 1.3 • C higher for lightweight buildings, with the main reason being the relatively low thermal mass of LWC, approximately 2.4 times lower than heavyweight construction. Hudobivnik et al. [34] investigated the nonstationary thermal performance of different multilayer external walls in LWC and HWC under typical summer conditions in Slovenia and found that LWC resulted in higher indoor air temperatures than RC, brick, and stone, on the order of 3.5 • C, 3 • C, and 3.3 • C respectively. Kuczynski et al. [35] compared the influence of lightweight and heavyweight wall construction on summer thermal performance in conditions of persistent and prolonged heat waves in temperate climates and measured occurrences of maximum internal air temperature above 28 • C for as many as 18.6 days in an exceptionally warm August. Nebia et al. [36] aimed to predict and assess the impact of floor level, thermal mass, ventilation strategy, and orientation on overheating risk and daylighting levels, and determined that the number of hours above the overheating benchmark increased from the bottom to the top floors. Research related to overheating phenomenon is tabulated in Table 1. The floor position is considered to be an important factor. The overheating hours increase with the height of the apartment. [36] Data source: summarized by the authors from the references.

of 25
There are few studies on the phenomenon of overheating in the severe cold and cold regions in China, since the focus has been on the thermal environment in winter. As shown in Table 2, in northern China, Su et al. [37] analyzed thermal comfort in old residential buildings in summer and found that the average temperatures in north-and south-facing bedrooms were 32.1 and 33.2 • C, respectively, and that discomfort was experienced without mechanical cooling in August. Yan et al. [38] investigated human thermal comfort in residential buildings in cold areas in summer in a study of 72 residential buildings in Yinchuan, and the results showed that the neutral temperature was 4.2 • C higher than the preferred temperature. The subjects in the cold region are poorly adapted to higher temperatures; the neutral temperature and the upper limit of acceptable temperature are lower than the indoor thermal comfort standards for free-running buildings in China. Yang et al. [39] studied the indoor environment and thermal comfort in residential buildings in Baotou, China, and indicated that the neutral temperature in summer was higher than the expected temperature, implying that residents preferred lower indoor temperatures. Mao et al. [40] studied the indoor thermal environment in residential buildings in cold regions in summer using a questionnaire survey and temperature monitoring, and suggested that residents were dissatisfied with the indoor thermal environment, although they were tolerant to higher temperatures due to the restriction of natural ventilation and economic conditions. Wang et al. [41] used an air temperature transducer to find that the frequency of indoor air temperatures above 26.5 • C exceeded 56%. Yang et al. [42] studied the thermal comfort of occupants in a mix of air conditioned (AC) and no air conditioned buildings and found that the mean operative temperature of residential buildings reached 29.3 • C in summer. Song [43] investigated 43 families in Tianjin and found that only 7% of the sample fell within the range of 22 • C to 26 • C specified in the design code for heating ventilation and air conditioning of civil buildings (2012), and most indoor temperatures were between 27 • C and 31 • C in summer. Data source: summarized by the authors from the references.

Study Objective
The aforementioned context raises several questions. The current national standard released in 2018 claims that it is unnecessary for residential buildings located in the severe cold and cold regions to mitigate overheating in the summer, such as using external shading devices. Hence, there are few studies on the potential summer overheating in residential buildings in the cold and severe cold regions of China. Furthermore, as a sustainable building material, CLT has already been proved to be effective for reducing energy consumption in the winter. The performance of this material in the summer remains unclear.
This paper considers the operative temperature in summer for RC and CLT residential buildings and addresses the following questions: (1) How serious is the potential overheating phenomenon in summer in the severe cold and cold regions in China? (2) Do the higher floors of residential buildings

Framework of the Study
The area of this work centered on building cooling energy consumption and indoor operative temperatures in summer during the operational phase. The study is divided into the following steps ( Figure 3). First, six representative cities were selected from the severe cold subregion (1A, 1B, 1C) and cold subregions (2A, 2B) as the simulation environment. Second, an 18-story reinforced concrete apartment with 72 apartments that had already been established in Harbin city was adopted as the case study building. Third, building energy consumption and the indoor operative temperature in summer was simulated with the commercial software IES VE. During the entire simulation process, the following factors were examined as keynotes: (1) Building materials. The energy efficiency of both RC and CLT buildings were simulated and compared during the simulation. (2) Cooling loads and indoor temperatures.
(3) Relationship between indoor temperature and height.
Energies 2020, 13, x FOR PEER REVIEW 7 of 24 residential buildings have lower energy efficiency than the floors below? (3) Do CLT buildings have lower cooling energy consumption than RC buildings in the summer season?

Framework of the Study
The area of this work centered on building cooling energy consumption and indoor operative temperatures in summer during the operational phase. The study is divided into the following steps ( Figure 3). First, six representative cities were selected from the severe cold subregion (1A, 1B, 1C) and cold subregions (2A, 2B) as the simulation environment. Second, an 18-story reinforced concrete apartment with 72 apartments that had already been established in Harbin city was adopted as the case study building. Third, building energy consumption and the indoor operative temperature in summer was simulated with the commercial software IES VE. During the entire simulation process, the following factors were examined as keynotes: (1) Building materials. The energy efficiency of both RC and CLT buildings were simulated and compared during the simulation.

Simulation Environment
In this study, the six climate representative major cities from the severe cold and cold regions selected are Hailar, Harbin, Changchun, Shenyang, Dalian, and Beijing. The U-value and R-value of the roof, walls, windows, and ground are strictly limited in design codes in order to ensure the

Simulation Environment
In this study, the six climate representative major cities from the severe cold and cold regions selected are Hailar, Harbin, Changchun, Shenyang, Dalian, and Beijing. The U-value and R-value of Energies 2020, 13, 6305 9 of 25 the roof, walls, windows, and ground are strictly limited in design codes in order to ensure the thermal insulation of these buildings at low temperatures. The locations and the thermal design details of the six cities are presented in Table 3 and Figure 4.  thermal insulation of these buildings at low temperatures. The locations and the thermal design details of the six cities are presented in Table 3 and Figure 4.

The RC Building
The 18-story RC building in Harbin chosen as the case study building is a typical design in the severe cold and the cold regions. There are two units with similar plans on each floor. Each unit is made up of two apartments, each with a living room and two bedrooms with different orientations. For the simulation in other cities, the specification of the building envelope was adjusted for the different thermal zones to meet the requirements of the local codes. The details of the architectural design are presented in Tables 4 and 5 and Figure 5.  Table 5. External wall and roof designs for the RC residential buildings in the six cities.

The CLT Building
At present, there are no CLT residential building design standards in China, so EN 15251 (European standard) and other related documents were adopted as the design standards for the CLT structure in this study. The thickness of the thermal insulation and the CLT panels were adjusted for the different thermal zones to meet the requirements of local thermal design and envelope design codes. The basic design parameters of the two simulated buildings remained the   At present, there are no CLT residential building design standards in China, so EN 15251 (European standard) and other related documents were adopted as the design standards for the CLT structure in this study. The thickness of the thermal insulation and the CLT panels were adjusted for the different thermal zones to meet the requirements of local thermal design and envelope design codes. The basic design parameters of the two simulated buildings remained the same. The stairs of the timber buildings were assumed to be built by using concrete. The detailed design parameters for the six-case study CLT scenarios are presented in Table 6. Table 6. External wall and roof designs for the CLT residential buildings in the six cities.

Hailar
Data source: Code for thermal design of civil buildings (GB 50176-2016); drawn by the authors.

The CLT Building
At present, there are no CLT residential building design standards in China, so EN 15251 (European standard) and other related documents were adopted as the design standards for the CLT structure in this study. The thickness of the thermal insulation and the CLT panels were adjusted for the different thermal zones to meet the requirements of local thermal design and envelope design codes. The basic design parameters of the two simulated buildings remained the same. The stairs of the timber buildings were assumed to be built by using concrete. The detailed design parameters for the six-case study CLT scenarios are presented in Table 6. Table 6. External wall and roof designs for the CLT residential buildings in the six cities.

Harbin
Data source: Code for thermal design of civil buildings (GB 50176-2016); drawn by the authors.

The CLT Building
At present, there are no CLT residential building design standards in China, so EN 15251 (European standard) and other related documents were adopted as the design standards for the CLT structure in this study. The thickness of the thermal insulation and the CLT panels were adjusted for the different thermal zones to meet the requirements of local thermal design and envelope design codes. The basic design parameters of the two simulated buildings remained the same. The stairs of the timber buildings were assumed to be built by using concrete. The detailed design parameters for the six-case study CLT scenarios are presented in Table 6.

Simulation Parameters
This study simulates the indoor operative temperature and cooling energy consumption during the summer with the software IES-VE. In the software platform, the reinforced concrete and

Simulation Parameters
This study simulates the indoor operative temperature and cooling energy consumption during the summer with the software IES-VE. In the software platform, the reinforced concrete and

Simulation Parameters
This study simulates the indoor operative temperature and cooling energy consumption during the summer with the software IES-VE. In the software platform, the reinforced concrete and Data source: Code for thermal design of civil buildings (GB 50176-2016); drawn by the authors.

Simulation Parameters
This study simulates the indoor operative temperature and cooling energy consumption during the summer with the software IES-VE. In the software platform, the reinforced concrete and timber buildings are established as separate simulation models. The following assumptions are made for simplification of the simulation.
(1) Simulation rooms. In order to study the temperature differences in the various rooms in a single apartment, the temperature of bedroom 1 (facing south), bedroom 2 (facing north) and the living room (facing south) are investigated separately ( Figure 6). In the simulation, the door of each room is taken to be open or closed depending on the operation of the cooling system. The basic settings are tabulated in Table 9.
(2) Space Cooling. Apache Systems (ApSys) in the IES VE, which is a simplified HVAC methodology, is adopted for the simulation. This paper focuses on the potential overheating phenomenon in residential buildings in summer. As a result, heating parameter settings are not considered. For the cooling settings, the energy efficiency ratio (EER) of the cooling system is set to be 2.5000 kW/kW. According to the Code for thermal design of civil buildings (GB 50176-2016), comfortable temperatures in summer should not exceed 26 • C. In the simulation, the cooling system is automatically put into operation if the indoor temperature exceeds 26 • C during occupied hours. The basic parameters for the cooling operation settings are shown in Table 7. (3) Ventilation. In the study, both natural ventilation and infiltration are considered in the simulation.
According to the rules from the design standard for heating ventilation and air conditioning of civil buildings (GB 50736-2012), the basic parameters for natural ventilation are shown in Table 8.
The natural ventilation and infiltration air change rates of bedroom 1, bedroom 2, and living room are set to be 1.0 h −1 and 0.3 h −1 in this study. The ventilation times is set based on the habits of the local residents. For example, the average daily temperature of winter in Harbin, which is located in a severe cold region, is lower than −20 • C. The local residents open the window for ventilation at a regular time in the morning or evening.

Results and Analysis
(1) Cooling loads and operative temperatures. The estimated cooling energy consumption for the RC and CLT buildings is presented in Table 10.
The results indicate that in summer, the average cooling energy consumption in CLT buildings is higher than that in the RC buildings. In the severe cold region, the CLT buildings consume from 20.97% to 42.93% of additional cooling energy when compared with the RC buildings. In the cold region, the figures drop to 2.2% to 19.3%. The difference in cooling energy consumption between CLT and RC buildings in Beijing is not significant; Beijing is located in cold region 2B.  Figure 7 presents the results for the operative temperature in bedroom 1 on the 11th floor (the middle floor) for both RC and CLT residential buildings in the six cities that are located in different climate regions. The results indicate that both the RC and the CLT buildings experience varying degrees of overheating in any climate subregion. The total overheating hours are closely related to the climate region. Table 11 presents an assessment of the overheating time in the case study buildings using the CIBSE TM59 criterion, namely that the operative temperature in the bedrooms should not exceed 26 • C from 10:00 p.m. to 7:00 a.m. for more than 1% of the annual hours in predominantly naturally ventilated dwellings [17]. CIBSE TM59 recommends occupied hours as 3672 h per year for bedrooms (24 h for the May-September dates covered) and 1989 h per year for living rooms (13 h per day for the May-September dates covered). This provides a useful check that profiles have been correctly applied. The estimated results show that operative temperature in bedrooms exceeding 26 • C in the summer increases gradually from north to south. None of the rooms meet the thermal comfort standards based on CIBSE 59. Energies 2020, 13, x FOR PEER REVIEW 4 of 5 The results also restate the research findings for other residential buildings that are located at the same latitude as the areas studied. The calculations results, tabulated in Table 12, showed that the degree of overheating problem in the severe cold region of China is similar to that in Austria, UK, and Canada. However, in the cold region of China, the overheating problem appears to be more serious than these other regions. In view of the thermal comfort in the summer, it is an imminent task for managers of residential buildings in the cold region of China to solve the overheating problem.
(2) Apartment level. The results from the building simulation presented in Figure 8 indicate that the level of the apartment is a major factor having a bearing on summer energy performance and indoor temperature. The simulation results for energy consumption and the operative temperatures indicate that apartments on higher floors experience an increase in energy consumption and overheating. The energy consumption on the ground floor of the building is lower than on all other floors. The total overheating hours on the ground floor are from 80.31% to 92.27% of the average for the building.

Discussion
(1) Suggestions for the revision of building design code. Figure 9 shows that in the severe cold region, there are two or three overheating periods which are not continuous in Hailar, Harbin, Changchun, and Shenyang. The duration of overheating in the RC case study buildings is 51, 59, 54, and 67 days per year, respectively. In the CLT case study building, this period is from 10 to 20 days longer. In the cold regions, the overheating period is longer and continuous, lasting from 69 to 110 days per year for the RC case study building. It should be noted that overheating days in Beijing account for over 71.8% of the summer period (from May to September), which indicates a serious indoor overheating problem due to the high thermal insulation.
The national design standard for energy efficiency of residential buildings in severe cold and cold zones of China (JGJ 26-2018) [23], issued by Ministry of Housing and Urban-Rural Development of the People's Republic of China (MOHURD), only recommends solar shading and additional natural ventilation for the cold 2B region in summer (clause 4.1). There are no definite design criteria to avoid overheating in the summer for any other subregion in the severe cold and cold region. However, the simulation results demonstrate that total hours above 26 • C are far in excess of the criterion for overheating in dwellings. It is suggested that policy makers should promote potential designs such as movable insulation layer, shading devices, and phase change materials for the summer period in the severe cold region (1A, 1B, 1C) and the cold region (2A, 2B).
The results indicate that CLT buildings may have more problems with overheating than RC structures; overheating in the RC case study building is of shorter duration in most of the studied cities. Biobased building materials such as timber, hemp, and straw bales may have overheating problems in summer due to their lower thermal mass. Keeping the indoor temperature above 18 • C for the residential buildings in the winter is the priority design task in the severe cold region and cold region. Thus, although more cooling energy is consumed in the summer, CLT buildings should be developed in such areas of China due to their excellent performance in saving heating energy. In view of saving cooling energy only, CLT may not be such a suitable building material in regions without considerable heating requirements.
(3) Potential ways to mitigate overheating. High thermal insulation of walls is a key factor that leads to summer overheating in the severe cold and cold regions of China. Since the principal aim is to maintain indoor temperatures above 18 • C in the winter in these regions, the high thermal insulation is deemed essential. Still, there are other ways to mitigate the overheating problem. Using light thermal insulation with the cavity wall technique is suggested to prevent summer overheating [47]. Exterior solar shading and additional natural ventilation are also effective in reducing cooling demand in the summer [48]. Makantasi et al. [49] studied the influence on thermal insulation and shading on overheating time and heating demand in a residential building, which was a 17-story tower block in Islington, London, in current and future climates. Meanwhile, they set different emission scenarios. In the high emissions scenario under 90th probability in 2050s, they found external vertical louvers reduced overheating hours by 28.4% compared to no shading; however, the demand for heating increased by 19.5% in the same situation. The movable external shading compared with the fixed reduced overheating time by 43.7% and increased the heating time by 8.3%, which was a better balance, and hence it can be recommended for residential buildings located in China's severe cold and cold regions.

Conclusions
This paper describes a simulation of the cooling energy consumption and indoor temperatures in concrete and timber residential buildings to identify the potential overheating phenomenon in the Energies 2020, 13, 6305 23 of 25 severe cold and cold regions of China. The research reveals that the residential buildings in such areas suffer overheating problems due to climate change. The local design standard for energy efficiency needs to be promoted by adding design methods to reduce the periods of overheating in the summer. The CLT buildings have longer overheating hours compared to the RC buildings, especially in the cold regions. The main findings are summarized below.
(1) Both RC and CLT buildings experience varying degrees of overheating in these climate subregions.
The extent of overheating hours depends on the climate region. Operative temperatures above 26 • C in bedrooms increase gradually from north to south. For the RC case study building, bedroom temperatures above 26 • C in summer in Hailar, Harbin, Shenyang, Changchun, Dalian, and Beijing occur for 7.95%, 7.82%, 7.65%, 18.44%, 18.38%, and 48.23% of the total occupied time, respectively. The corresponding figures for the CLT case study building in these cities are 9.50%, 9.23%, 9.07%, 18.68%, 18.63%, and 47.82%, respectively. (2) Apartments on higher floors experience an increase in energy consumption and overheating.
The energy consumption on the bottom floor of the building is lower than on the other floors.

Conflicts of Interest:
The authors declare no conflict of interest.