Effect of low quality effluent from wastewater stabilization ponds to receiving bodies, case of Kilombero sugar ponds and Ruaha river, Tanzania.

A study was conducted in a sewage system at Kilombero Sugar Company to review its design, configuration, effectiveness and the quality of influent and effluent discharged into the Ruaha river (receiving body). The concern was that, the water in the river, after effluent has joined the river, is used as drinking water by villages located downstream of the river. Strategic sampling at the inlet of the oxidation pond, at the outlet and in the river before and after the effluent has joined the receiving body (river) was undertaken. Samples from each of these locations were taken three times, in the morning, noon and evening. The sample were then analysed in the laboratory using standard methods of water quality analysis. The results showed that the configuration and or the layout of the oxidation ponds (treatment plant) were not in accordance with the acceptable standards. Thus, the BOD5 of the effluent discharged into the receiving body (Ruaha River) was in the order of 41 mg/l and therefore not meeting several standards as set out both by Tanzanian and international water authorities. The Tanzanian water authorities, for example, requires that the BOD5 of the effluent discharged into receiving bodies be not more that 30 mg/l while the World Health Organization (WHO) requires that the effluent quality ranges between 10 – 30 mg/l. The paper concludes that proper design of treatment plants (oxidation ponds) is of outmost importance especially for factories, industries, camps etc located in rural developing countries where drinking water from receiving bodies like rivers and lakes is consumed without thorough treatment. The paper further pinpoint that both owners of treatment plants and water authorities should establish monitoring/management plan such that treatment plants (oxidation ponds) could be reviewed regarding the change on quantity of influent caused by population increase.


Introduction
Sewage can be defined as discharges from domestic and sanitary appliances or simply a complex mixture of materials from varied sources. This complex mixture contains both soluble and insoluble materials [1]. It is under these reasons that sewage from homestead has to be managed before is flushed away into receiving bodies like rivers, lakes and oceans as harmless stuff. Since the mixture is complex, it is usually treated by a mixture of settlement and biological processes. Settlement process permits materials which are suspended in a sewage to settle to the bottom of a container and therefore to be removed from the bulk of the liquid. The longer the materials are retained in the container, the greater the amount of suspended solids that will be able to settle out. Thus short retention times will only remove the largest particles, while long retention times provide greater solids removal. Biological processes convert materials in the sewage into biological cell materials which can usually be easily settled out from a solution by a settlement process.
Both settlement and biological process can only be achieved with a right design of treatment plants (wastewater stabilization ponds). However, the effectiveness of stabilization ponds will mainly depend among others the configuration and size of the ponds with respect to the sewage discharges [2].
The effectiveness referred here is the ability to treat the influent to a standard (allowable) effluent to be discharged into receiving bodies.
Based on this understanding of sewage systems and their complexity in management and design, the Kilombero Sugar Company recently launched a study to review their sewage system in terms of design, configuration, effectiveness and the quality of influent and effluent discharged into the Ruaha River (receiving body). The concern was that the population at the company is increasing and the water in the river, after effluent from oxidation pond has joined the river, is used as raw drinking water by villages located further downstream.

Review of Existing Pond Layout
Generally there exist two types of waste stabilization pond systems. The Facultative -Maturation System (FM system) and the Anaerobic-Facultative -Maturation System (AFM-System). In the absence of the grit chambers and screen, the most layout of the conventional Waste Stabilization Pond (WSP) is given in Figure 1 [2]. Given the waste water discharge, the two systems require different area and configuration for proper functioning. The sewerage of the Kilombero Sugar Company (K2 side) consists of a network which gravitate to the pumping station thereafter gravitate to the wastewater stabilization ponds (treatment plant) [2]. The plant consists of a very basic, single series of ponds, one large pond connected to a much smaller pond. Earlier studies by different consultants have referred the first pond as Anaerobic pond and the second one as facultative pond. However, according to the layout and depth requirements the first pond can be regarded as facultative pond and the smaller one to be maturation pond thus a need for the anaerobic pond.

Review of Waste Water Discharges
For the design and operation of all treatment plants, an accurate knowledge of the sewage flow and sewage characteristics is essential. The daily volume of sewage per capita can vary from less than 50 l for a relatively primitive camping site to more than 300 l for an affluent high amenity residential area [1,5].
In order to accurately determine the flow of a particular sewage system, the best method is to measure the flow over a representative time. If this procedure cannot be followed, some less rigorous method has to be adopted [1,2]. Comparison with a similar site is advantageous, modifying the data in the light of particular circumstances. Often designs are based almost entirely upon educated estimates of flows. Even for cases when estimates are used, it is important to critically assess these design parameters.
During this study, Sewage flow was estimated using two methods. The first method was through use of population data and consideration of peak period and then the average flows were estimated. The second method of estimation made use of electronic flow measuring equipment called Ultrasonic metre. The equipment is capable of measuring both pressurized and non pressurized sewage flows in different piped materials.

Review of Waste Water Quality
The strength of sewage in an area drained by a sewerage system which permits the inclusion of surface water can be low, with a BOD5 of less than 100 mg/I, while the wastes from chemical closets can have a BOD5 in excess of 1,000 mg/I. It therefore follows that before a waste water stabilization system is design, the influent and effluent standards need to be fixed to a certain level. In reviewing the Kilombero system it was necessary to investigate the level of quality of both influent and effluent. In addition, the quality of receiving body (the Ruaha river) before and after effluent has joined the river was investigated.

Pond Layout and Size
The existing layout and configuration of the Kilombero wastewater stabilization pond probably does not belong into any of the two types of system mentioned above (FMS and AFMS) [2,3]. The pond has only two chambers, one large (65 x 161 m) and another small (65 x 25 m). The existing pond calculates an area of 1.2ha. Figure 2 shows the layout of the existing pond.

Discharge Data
Three types of data were collected in order to be able to review the sewage system of the Kilombero sugar company (K2 side). The first key data collected was the waste water discharge from the whole system. The two approaches which were used included the use of the social and quantitative approach where by a population and an estimated waste water discharge of 80 litres per day per capita were used to calculate the discharge. The second approach where special equipment called Ultrasonic meter was used to estimate the flows in the main pipe. The results from the two methods did not differ significantly as P = 0.61 which is greater than 0.05 in the ANOVA analysis Table 1  When the results from the two approaches were compared, the result from the social method showed higher daily discharges (600.56m 3 /day) compared to the ultrasonic meter results which showed 598.46m 3 /day. As it is usual with all designs, the higher parameter was considered during the design stage.

Water Quality Data
Water samples were taken at the inlet and outlet of the water stabilization ponds in a repetitive ways three times a day (morning, afternoon and evening). In addition water samples were taken from the receiving body (Ruaha River) before and after the effluent joined the river. The sampling locations were as illustrated by Figure 3.
The collected samples were then analyzed in the laboratory using standard procedures [6] as illustrated in Table 2. The results from the analysis in the laboratory, for each of the sample, are presented in Tables 3 and 4.

Configuration Analysis of the Ponds
The analysis of pond configuration is an attempt to re-design the current wastewater stabilization pond in Kilombero Sugar Company so as the discharged effluent into receiving water bodies is of acceptable standard. In this study, two systems were considered. The FM and AFM systems as discussed in detail below

Facultative Pond Plus Maturation Pond System
(a) Facultative Pond The main purpose of facultative pond is the BOD reduction. It is assumed that the pond is a completely mixed reactor in which BOD 5 removal follows the first order kinetics [1]. It is recommended that a minimum retention time of 7days should be used for individual ponds because of short circuiting in ponds with shorter retention time [1,5]. Sufficiently long retention time of about 5-10 days should be allowed.

(b) Maturation pond
Maturation ponds are designed to achieve bacterial removal as a final step after BOD 5 has been reduced in the anaerobic and facultative ponds. Facultative can also remove the bacteria.

19) T-20 in all ponds
For the design purposes a value of 200mg/l BOD5 (average strength) inlet is assumed and an outlet to be fixed at 30mg/l. E-coli was established to be 2.0x10 6 per 100ml in the influent (normally influent can contain up to 10 9 E-coli per 100ml. For receiving stream it is required that the E-coli should be less than 1,000 per 100ml. K b is E-coli removal rate constant; t f is the retention time in the facultative pond; t m retention time in one maturation pond usually 5-7 days. Anaerobic ponds should be designed mainly on the basis of volumetric organic loading (g.BOD 5 /m 3 /d) but detention time should also be taken into account. Anaerobic ponds are designed to receive BOD loadings between 100 -400g.BOD 5 /m 3 /d. The actual loading will depend on climate, with higher loadings possibility at higher temperatures. The hydraulic detention time is usually between 2.5-5 days and the rate of BOD removal is between 50-80% [1,2,5]. Normally 60% volumetric loading is given by: Bacteria will be removed in all of the ponds. Anaerobic and facultative can also remove the bacteria though in the anaerobic pond the removal is about half way: (1.19) T-20 in all ponds; Where Ne and Ni are number of E-coli per 100ml in the influent and effluents respectively; K b is E-coli removal rate constant t a is the retention time in anaerobic pond t f is the retention time in the facultative pond t m retention time in one maturation pond usually 5-7 days.
The value obtained is above 1,000 thus providing TWO maturation ponds as above each with mid-pond area of 0.35ha.

Configuration and Sizes Required for Proper Function of the Pond
The result of the calculations in revealing the existing configuration, layout and design of the oxidation ponds in K2 shows that the ponds are neither Facultative Maturation system (FMS) nor Anaerobic Facultative Maturation system (AFMS). This has been illustrated by a review design calculation above. The review design calculation shows configuration indicated in Table 5 for the proper functioning of the ponds. The layout would be as shown in Figures 4 and 5.

Discussion of the Results
Before the design options was made for the waste water treatment, the water quality samples were analyzed first. The main parameters looked at were the bacterial quality, BOD loads and residual chlorine status. These could give pollution levels in the environment [7][8][9]. The Ruaha river was found to be polluted even before the ponds effluents thus there are more polluters upstream. The existing pond system was not functioning properly as the effluents were of poor quality when compared with the standards [10][11][12]14], requiring the need for new system design. The BOD load variation was quite remarkable for morning hours and evening hours. During the evening most of the workers are at home and thus produce more pollution during this time of the day. This paper provides five points which are supposed to discuss the results as fully as possible. These are given below: 1 The Ruaha River is not safe bacteriologically even before the influence of the effluent from the Sugar Company as some levels of bacteria are observed. For drinking water without disinfection or boiling, the recommended standard is ZERO/100ml.   (Tables 3 & 6). 4 The general trend has shown that there are more BODs during the evenings compared to the rest of time. This is an indication that the peak hour is in the evening. 5 Highest recorded residual chlorine is 0.47 mg/l in the evening but in other cases the residual chloride is quite low indicating a proper disinfectants management (Table 7). Group A: Water with an excellent quality; Group B: Water with good quality; Group C: Water with low health risk; Group D: Water with a higher health risk or water unsuitable for human consumption

Conclusion
The design of the waste water stabilization pond in K2 is not in accordance with specification standards defined in different design books and manuals and that is why it does not produce effluent of acceptable standards in receiving bodies. A review and its proposed re-design for proper functioning of the existing stabilization ponds have been conducted and design options suggested in this paper.
In most developing countries like Tanzania, the low effluent which is discharged into receiving bodies and their effect to the downstream communities will need more investigation particularly on ways in which the effect can be minimized. There exists a number of water quality models that can trace the fate and transport of pollutants once discharged into the receiving water bodies. The impact of pollution can then be established to know the distance down stream to which pollution is still experienced. Application of models such as these will allow the governing authorities to advise the communities of where they should collect water. Also this can even optimize the pond design in terms of size, which can save cost.
In addition, studies of relation between water levels in receiving bodies and their relative level of pollutant can help in decision making by governing authorities to advise the communities living in the downstream to treat the water before using them at critical levels of pollution. Alternatively, the water collection point can be defined according to the seasonal calendar and or flow levels in receiving bodies.