A Static Voltage Security Region for Centralized Wind Power Integration—Part II: Applications
AbstractIn Part I of this work, a static voltage security region was introduced to guarantee the safety of wind farm reactive power outputs under both base conditions and N-1 contingency. In this paper, a mathematical representation of the approximate N-1 security region has further studied to provide better coordination among wind farms and help prevent cascading tripping following a single wind farm trip. Besides, the influence of active power on the security region is studied. The proposed methods are demonstrated for N-1 contingency cases in a nine-bus system. The simulations verify that the N-1 security region is a small subset of the security region under base conditions. They also illustrate the fact that if the system is simply operated below the reactive power limits, without coordination among the wind farms, the static voltage is likely to exceed its limit. A two-step optimal adjustment strategy is introduced to shift insecure operating points into the security region under N-1 contingency. Through extensive numerical studies, the effectiveness of the proposed technique is confirmed. View Full-Text
Scifeed alert for new publicationsNever miss any articles matching your research from any publisher
- Get alerts for new papers matching your research
- Find out the new papers from selected authors
- Updated daily for 49'000+ journals and 6000+ publishers
- Define your Scifeed now
Ding, T.; Guo, Q.; Bo, R.; Sun, H.; Zhang, B.; Huang, T.-E. A Static Voltage Security Region for Centralized Wind Power Integration—Part II: Applications. Energies 2014, 7, 444-461.
Ding T, Guo Q, Bo R, Sun H, Zhang B, Huang T-E. A Static Voltage Security Region for Centralized Wind Power Integration—Part II: Applications. Energies. 2014; 7(1):444-461.Chicago/Turabian Style
Ding, Tao; Guo, Qinglai; Bo, Rui; Sun, Hongbin; Zhang, Boming; Huang, Tian-en. 2014. "A Static Voltage Security Region for Centralized Wind Power Integration—Part II: Applications." Energies 7, no. 1: 444-461.