Verification of the Performance of a Vertical Ground Heat Exchanger Applied to a Test House in Melbourne, Australia
AbstractThe ground heat exchanger is traditionally used as a heat source or sink for the heat pump that raises the temperature of water to about 50 °C to heat houses. However, in winter, the heating thermostat (temperature at which heating begins) in the Australian Nationwide House Energy Rating Scheme (NatHERS) is only 20 °C during daytime and 15 °C at night. In South-East Melbourne, the temperature at the bottom of a 50-meter-deep borehole has been recorded with an Emerson™ recorder at 17 °C. Melbourne has an annual average temperature of 15 °C, so the ground temperature increases by 2 °C per 50-m depth. A linear projection gives 23 °C at 200-m of depth, and as the average undisturbed temperature of the ground for a 400-m-deep vertical ground heat exchanger (VGHE). This study, by simulation and experimentation, aims to verify that the circulation of water in the VGHE’s U-tube to low-temperature radiators (LTRs) could heat a house to thermal comfort. A literature review is included in the introduction. A simulation, using a model of a 60-m2 experimental house, shows that the daytime circulation of water in this VGHE/LTR-on-opposite-walls system during the 8-month cold half of the year, heats the indoors to NatHERS settings. Simulation for the cold half shows that this VGHE-LTR system could cool the indoors. Instead, a fan creating a cooling sensation of up to 4 °C is used so that the VGHE is available for the regeneration of heat extracted from the ground during the cold portion. Simulations for this hot portion show that a 3.4-m2 flat plate solar collector can collect more than twice the heat extracted from the ground in the cold portion. Thus, it can thus replenish the ground heat extracted for houses double the size of this 60-m2 experimental house. Therefore, ground heat is sustainable for family-size homes. Since no heat pump is used, the cost of VGHE-LTR systems could be comparable to systems using the ground source heat pump. Water circulation pumps and fans require low power that can be supplied by photovoltaic thermal (PVT). The EnergyPlus™ v8.7 object modeling the PVT requires user-defined efficiencies, so a PVT will be tested in the experimental house. View Full-Text
Scifeed alert for new publicationsNever miss any articles matching your research from any publisher
- Get alerts for new papers matching your research
- Find out the new papers from selected authors
- Updated daily for 49'000+ journals and 6000+ publishers
- Define your Scifeed now
Ooi, K.B.; Noguchi, M. Verification of the Performance of a Vertical Ground Heat Exchanger Applied to a Test House in Melbourne, Australia. Energies 2017, 10, 1558.
Ooi KB, Noguchi M. Verification of the Performance of a Vertical Ground Heat Exchanger Applied to a Test House in Melbourne, Australia. Energies. 2017; 10(10):1558.Chicago/Turabian Style
Ooi, Koon B.; Noguchi, Masa. 2017. "Verification of the Performance of a Vertical Ground Heat Exchanger Applied to a Test House in Melbourne, Australia." Energies 10, no. 10: 1558.
Note that from the first issue of 2016, MDPI journals use article numbers instead of page numbers. See further details here.